1 Installation Instructions POINT I/O Input Modules Catalog numbers 734-IB, 734-IB4, 734-IB8, Series C Table of Contents Topic Page Important User Information Environment and Enclosure 3 Preventing Electrostatic Discharge 3 North American Hazardous Location Approval 4 European Hazardous Location Approval 5 Before You Begin 6 About the Module 7 Install the Mounting Base 7 Install the Module 8 Install the Removable Terminal Block 9 Remove a Mounting Base Communicate with Your Module Wire the Module Interpret Indicators 8 Specifications
2 POINT I/O Input Modules Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical equipment. Safety Guidelines for the Application, Installation, and Maintenance of Solid-State Controls (Publication SGI-. available from your local Rockwell Automation Sales Office or online at describes some important differences between solid-state equipment and hard-wired electromechanical devices. Because of this difference, and also because of the wide variety of uses for solid-state equipment, all persons responsible for applying this equipment must satisfy themselves that each intended application of this equipment is acceptable. In no event will Rockwell Automation, Inc. be responsible or liable for indirect or consequential damages resulting from the use or application of this equipment. The examples and diagrams in this manual are included solely for illustrative purposes. Because of the many variables and requirements associated with any particular installation, Rockwell Automation, Inc. cannot assume responsibility or liability for actual use based on the examples and diagrams. No patent liability is assumed by Rockwell Automation, Inc. with respect to use of information, circuits, equipment, or software described in this manual. Reproduction of the contents of this manual, in whole or in part, without written permission of Rockwell Automation, Inc., is prohibited. Throughout this manual, when necessary, we use notes to make you aware of safety considerations. WARNING: Identifies information about practices or circumstances that can cause an explosion in a hazardous environment, which may lead to personal injury or death, property damage, or economic loss. ATTENTION: Identifies information about practices or circumstances that can lead to personal injury or death, property damage, or economic loss. Attentions help you identify a hazard, avoid a hazard, and recognize the consequences. SHOCK HAZARD: Labels may be on or inside the equipment (for example, drive or motor) to alert people that dangerous voltage may be present. BURN HAZARD: Labels may be on or inside the equipment (for example, drive or motor) to alert people that surfaces may reach dangerous temperatures. IMPORTANT Identifies information that is critical for successful application and understanding of the product.
3 POINT I/O Input Modules 3 Environment and Enclosure ATTENTION: This equipment is intended for use in a Pollution Degree industrial environment, in overvoltage Category II applications (as defined in IEC 6664-), at altitudes up to m (656 ft) without derating. This equipment is considered Group, Class A industrial equipment according to IEC/CISPR. Without appropriate precautions, there may be difficulties with electromagnetic compatibility in residential and other environments due to conducted and radiated disturbances. This equipment is supplied as open-type equipment. It must be mounted within an enclosure that is suitably designed for those specific environmental conditions that will be present and appropriately designed to prevent personal injury resulting from accessibility to live parts. The enclosure must have suitable flame-retardant properties to prevent or minimize the spread of flame, complying with a flame spread rating of 5VA, V, V, V (or equivalent) if nonmetallic. The interior of the enclosure must be accessible only by the use of a tool. Subsequent sections of this publication may contain additional information regarding specific enclosure type ratings that are required to comply with certain product safety certifications. In addition to this publication, see: Industrial Automation Wiring and Grounding Guidelines, publication 77-IN4, for additional installation requirements. NEMA Standard 5 and IEC 659, as applicable, for explanations of the degrees of protection provided by enclosures. Preventing Electrostatic Discharge ATTENTION: This equipment is sensitive to electrostatic discharge, which can cause internal damage and affect normal operation. Follow these guidelines when you handle this equipment: Touch a grounded object to discharge potential static. Wear an approved grounding wriststrap. Do not touch connectors or pins on component boards. Do not touch circuit components inside the equipment. Use a static-safe workstation, if available. Store the equipment in appropriate static-safe packaging when not in use.
4 4 POINT I/O Input Modules North American Hazardous Location Approval The following information applies when operating this equipment in hazardous locations: Informations sur l utilisation de cet équipement en environnements dangereux: Products marked "CL I, DIV, GP A, B, C, D" are suitable for use in Class I Division Groups A, B, C, D, Hazardous Locations and nonhazardous locations only. Each product is supplied with markings on the rating nameplate indicating the hazardous location temperature code. When combining products within a system, the most adverse temperature code (lowest "T" number) may be used to help determine the overall temperature code of the system. Combinations of equipment in your system are subject to investigation by the local Authority Having Jurisdiction at the time of installation. Les produits marqués "CL I, DIV, GP A, B, C, D" ne conviennent qu'à une utilisation en environnements de Classe I Division Groupes A, B, C, D dangereux et non dangereux. Chaque produit est livré avec des marquages sur sa plaque d'identification qui indiquent le code de température pour les environnements dangereux. Lorsque plusieurs produits sont combinés dans un système, le code de température le plus défavorable (code de température le plus faible) peut être utilisé pour déterminer le code de température global du système. Les combinaisons d'équipements dans le système sont sujettes à inspection par les autorités locales qualifiées au moment de l'installation. EXPLOSION HAZARD Do not disconnect equipment unless power has been removed or the area is known to be nonhazardous. Do not disconnect connections to this equipment unless power has been removed or the area is known to be nonhazardous. Secure any external connections that mate to this equipment by using screws, sliding latches, threaded connectors, or other means provided with this product. Substitution of components may impair suitability for Class I, Division. If this product contains batteries, they must only be changed in an area known to be nonhazardous. RISQUE D EXPLOSION Couper le courant ou s'assurer que l'environnement est classé non dangereux avant de débrancher l'équipement. Couper le courant ou s'assurer que l'environnement est classé non dangereux avant de débrancher les connecteurs. Fixer tous les connecteurs externes reliés à cet équipement à l'aide de vis, loquets coulissants, connecteurs filetés ou autres moyens fournis avec ce produit. La substitution de composants peut rendre cet équipement inadapté à une utilisation en environnement de Classe I, Division. S'assurer que l'environnement est classé non dangereux avant de changer les piles.
5 POINT I/O Input Modules 5 European Hazardous Location Approval The following applies when the product bears the Ex Marking This equipment is intended for use in potentially explosive atmospheres as defined by European Union Directive 94/9/EC. DEMKO certifies that this equipment has been found to comply with the Essential Health and Safety Requirements relating to the design and construction of Category 3 equipment intended for use in Zone potentially explosive atmospheres, given in Annex II to this Directive. Compliance with the Essential Health and Safety Requirements has been assured by compliance with EN 679-:+A:3, EN 679-5:, reference certificate number DEMKO 4ATEX33347X. ATTENTION: This equipment is not resistant to sunlight or other sources of UV radiation. WARNING: This equipment shall be mounted in an ATEX certified enclosure with a minimum ingress protection rating of at least IP54 (as defined in IEC659) and used in an environment of not more than Pollution Degree (as defined in IEC 6664-) when applied in Zone environments. The enclosure must utilize a tool removable cover or door. WARNING: This equipment shall be used within its specified ratings defined by Rockwell Automation. WARNING: Provision shall be made to prevent the rated voltage from being exceeded by transient disturbances of more than 4% of the rated voltage when applied in Zone environments. WARNING: Secure any external connections that mate to this equipment by using screws, sliding latches, threaded connectors, or other means provided with this product. WARNING: Do not disconnect equipment unless power has been removed or the area is known to be nonhazardous.
6 3 6 POINT I/O Input Modules Before You Begin You can use these Series C POINT I/O Input Modules with DeviceNet and PROFIBUS adapters. If you are using RSLogix 5 software, version or higher, you can also use the modules with ControlNet and Ethernet adapters. Use this diagram to identify the external features of the module. POINT I/O Input Module Module Network NODE: Description Description Module locking mechanism 6 Mounting base Slide-in writable label 7 Interlocking side pieces 3 Insertable I/O module 8 Mechanical keying 4 Removable Terminal Block handle 9 DIN rail locking screw 5 Removable Terminal Block (RTB) Module wiring diagram
7 About the Module POINT I/O Input Modules 7 The POINT I/O sink input modules are available in two-input, four-input, and eight-input options. They install on mounting bases that mount on a DIN rail. All wiring is made to a Removable Terminal Block (RTB) mounted on the mounting base. Install the Mounting Base To install the mounting base on the DIN rail, proceed as follows: ATTENTION: This product is grounded through the DIN rail to chassis ground. Use zinc plated yellow-chromate steel DIN rail to assure proper grounding. The use of other DIN rail materials (for example, aluminum or plastic) that can corrode, oxidize, or are poor conductors, can result in improper or intermittent grounding. Secure DIN rail to mounting surface approximately every mm (7.8 in.) and use end-anchors appropriately.. Position the mounting base vertically above the installed units (adapter, power supply, or existing module).. Slide the mounting base down allowing the interlocking side pieces to engage the adjacent module or adapter. 3. Press firmly to seat the mounting base on the DIN rail. The mounting base snaps into place.
8 8 POINT I/O Input Modules Install the Module The module can be installed before or after base installation. Make sure that the mounting base is correctly keyed before installing the module into the mounting base. In addition, make sure that the mounting base locking screw is positioned horizontal referenced to the base. WARNING: When you insert or remove the module while backplane power is on, an electrical arc can occur. This could cause an explosion in hazardous location installations. Be sure that power is removed or the area is nonhazardous before proceeding. Repeated electrical arcing causes excessive wear to contacts on both the module and its mating connector. Worn contacts may create electrical resistance that can affect module operation. ATTENTION: Do not remove or replace an Adapter Module while power is applied. Interruption of the backplane can result in unintentional operation or machine motion.. Using a bladed screwdriver, rotate the keyswitch on the mounting base clockwise until the number required for the type of module being installed aligns with the notch in the base.. Verify the DIN rail locking screw is in the horizontal position. You cannot insert the module if the locking mechanism is unlocked. 3. Insert the module straight down into the mounting base and press to secure. The module locks into place. ATTENTION: Do not discard the end cap. Use this end cap to cover the exposed interconnections on the last mounting base on the DIN rail. Failure to do so could result in equipment damage or injury from electric shock.
9 POINT I/O Input Modules 9 Install the Removable Terminal Block A Removable Terminal Block (RTB) is supplied with your wiring base assembly. This allows the mounting base to be removed and replaced as necessary without removing any of the wirings. To insert the Removable Terminal Block, proceed as follows:. Insert the end opposite the handle into the base unit. This end has a curved section that engages with the wiring base.. Rotate the terminal block into the wiring base until it locks itself in place. 3. If an I/O module is installed, snap the RTB handle into place on the module. WARNING: When you connect or disconnect the Removable Terminal Block (RTB) with field side power applied, an electrical arc can occur. This could cause an explosion in hazardous location installations. Be sure that power is removed or the area is nonhazardous before proceeding. WARNING: When used in a Class I, Division, hazardous location, this equipment must be mounted in a suitable enclosure with proper wiring method that complies with the governing electrical codes.
10 POINT I/O Input Modules Remove a Mounting Base To remove a mounting base, you must remove any installed module, and the module that is installed in the base to the right. Remove the Removable Terminal Block, if wired.. Unlatch the RTB handle on the I/O module.. Pull on the RTB handle to remove the Removable Terminal Block. 3. Press the module lock on the top of the module. 4. Pull on the I/O module to remove from the base. 5. Repeat steps,, 3 and 4 for the module to the right. 6. Use a small bladed screwdriver to rotate the orange base locking screw to a vertical position. This releases the locking mechanism. 7. Lift straight up to remove.
11 Communicate with Your Module POINT I/O Input Modules I/O messages are sent to (consumed) and received from (produced) the POINT I/O modules. These messages are mapped into the processor s memory. This POINT I/O input module produces Byte of input data (scanner Rx). It does not consume I/O data (scanner Tx). Default Data Map for 734-IB Message size: Byte Produces (Rx) I I Consumes (Tx) No consumed data Where: I = Channel, I = Channel, = Off, = On Default Data Map for 734-IB4 Message size: Byte Produces (Rx) I3 I I I Consumes (Tx) No consumed data Where: I3 = Channel 3, I = Channel, I = Channel, I = Channel, = Off, = On Default Data Map for 734-IB8 Message size: Byte Produces (Rx) I7 I6 I5 I4 I3 I I I Consumes (Tx) No consumed data Where: I7 = Channel 7, I6 = Channel 6, I5 = Channel 5, I4 = Channel 4, I3 = Channel 3, I = Channel, I = Channel, I = Channel, = Off, = On
12 POINT I/O Input Modules Wire the Module 734-IB 734-IB4 734-IB8 Module Module status Module Module Network NODE: Network status Network NODE: Network NODE: of input of input 4VDC Sink Input 734 IB of input of input of input of input 3 3 4VDC Sink Input 734 IB4 of inputs & 4 of inputs & 5 of inputs & 6 of inputs 3 & 7 3 4VDC Sink Input 734 IB Input Input Input Input Input Input NC NC Input Input 3 Input Input 3 C C C C Input 4 Input 5 V V V V Input 6 Input Input =, NC = No connection (, 3) C = Common (4, 5) V = Supply (6, 7) Input =,,, 3 C = Common (4, 5) V = Supply (6, 7) Input =,,, 3, 4, 5, 6, 7 V and C are daisy-chained from either the adapter, 734-FPD, 734-EP4DC, or from a user-supplied auxiliary terminal block.
13 POINT I/O Input Modules 3 WARNING: If you connect or disconnect wiring while the field-side power is on, an electrical arc can occur. This could cause an explosion in hazardous location installations. Be sure that power is removed or the area is nonhazardous before proceeding. WARNING: To comply with the CE Low Voltage Directive (LVD), this equipment must be powered from a source compliant with the following: Safety Extra Low Voltage (SELV) or Protected Extra Low Voltage (PELV). Wiring for 734-IB Sink Input In In -wire NC 4 C 3 NC 5 C 3-wire V = /4V DC C = Common 6 V 7 V Channel Input Common Voltage Connect common on 3-wire proximity switches. /4V DC is supplied through the internal power bus.
14 4 POINT I/O Input Modules Wiring for 734-IB4 Sink Input In In -wire 3-wire In 4 C 3 In 3 5 C V = /4V DC C = Common 6 V 7 V Channel Input Common Voltage Connect common on 3-wire proximity switches. /4V DC is supplied through the internal power bus.
15 POINT I/O Input Modules 5 Wiring for 734-IB8 Sink Input V = /4V DC C = Common 3-wire -wire 3-wire -wire In In In 4 In 4 6 In 6 3 In 3 5 In 5 7 In 7 3-wire -wire 3-wire -wire V C C V Channel Input Channel Input Daisychain common and power connections from 734 adapter, 734-FPD, 734-EP4DC, or from user-supplied external auxiliary terminal block. Note: When connecting more than one wire in a termination point, make sure that both wires are the same gauge and type.
16 6 POINT I/O Input Modules Wiring Example for 734-IB8 Using -Wire imity Switches DeviceNet Module Network Module Network System Power 6 6 DeviceNet Power OB8E IB8 4V DC return 4V DC Terminal block with bus connector strip 4574
17 POINT I/O Input Modules 7 Wiring Example for 734-IB8 Using 3-Wire imity Switches DeviceNet Module Network Module Network System Power 6 6 DeviceNet Power OB8E IB8 4V DC return 4V DC Terminal block with bus connector strip Terminal block with bus connector strip 4575
18 8 POINT I/O Input Modules Interpret Indicators Refer to the following diagram and table for information on how to interpret the status indicators. 734-IB 734-IB4 734-IB8 Module Module status Module Module Network NODE: Network status Network NODE: Network NODE: of input of input 4VDC Sink Input 734 IB of input of input of input of input 3 3 4VDC Sink Input 734 IB4 of inputs & 4 of inputs & 5 of inputs & 6 of inputs 3 & 7 3 4VDC Sink Input 734 IB
19 POINT I/O Input Modules 9 Indicator for Modules Description Module status Off No power applied to device. Green Device operating normally. Flashing green Device needs commissioning due to missing, incomplete, or incorrect configuration. Flashing red Recoverable fault. Red Unrecoverable fault may require device replacement. Flashing red/green Device is in self-test mode. Network status Off Device is not online: - Device has not completed dup_mac-id test. - Device not powered check module status indicator. Flashing green Device is online but has no connections in the established state. Green Device is online and has connections in the established state. Flashing red One or more I/O connections are in timed-out state. Red Critical link failure failed communication device. Device detected error that prevents it from communicating on the network. Flashing red/green Communication faulted device the device has detected a network access error and is in communication faulted state. Device has received and accepted an Identity Communication Faulted Request long protocol message. I/O status Off Input is in the off state. Yellow Input is in the on state.
20 POINT I/O Input Modules Specifications POINT I/O Input Module 734-IB, 734-IB4, 734-IB8 Attribute Inputs per module Voltage, on-state, min Voltage, on-state, nom Voltage, on-state, max Current, on-state, min Current, on-state, nom Current, on-state, max Voltage, off-state, max Current, off-state, min Impedance, input, nom Impedance, input, max Input filter time () OFF to ON ON to OFF Field wiring terminations Value 734-IB ( group of ), sinking 734-IB4 4 ( group of 4), sinking 734-IB8 8 ( group of 8), sinking V DC 4V DC 8.8V DC ma 4 4V DC 5 ma 5V DC.5 ma 3.6 kω 4.7 kω.5 ms hardware plus...63 ms (user-selectable).5 ms hardware plus...63 ms (user-selectable) 734-IB Input Input No connection 3 No connection 4 Common 5 Common 6 User supply 7 User supply 734-IB4 Input Input Input 3 Input 3 4 Common 5 Common 6 User supply 7 User supply 734-IB8 Input Input Input 3 Input 3 4 Input 4 5 Input 5 6 Input 6 7 Input 7 () Input off-to-on filter time is the time from a valid input signal to recognition by the module. Input on-to-off time is the time from a valid input signal to recognition by the module. General Specifications () Attribute Terminal base screw torque Module location Indicators, network status Value.8 Nm (7 lb-in.) 734-TB or 734-TBS wiring base assembly green/red, logic side
21 POINT I/O Input Modules General Specifications () Attribute Indicators, module status Indicators, input status POINTBus current, max Power 8.8V DC, max Thermal 8.8V DC, max Isolation voltage Field power supply voltage, nom Field power voltage range Dimensions, HxWxD, approx. Wiring category () Wire size Weight, approx. Value Enclosure type rating Keyswitch position North American Temp Code T4A IEC Temp Code T4 green/red, logic side 734-IB yellow, logic side 734-IB4 4 yellow, logic side 734-IB8 8 yellow, logic side 75 5V DC 734-IB.7 W 734-IB4. W 734-IB8.6 W 734-IB.4 BTU/hr 734-IB4 3.4 BTU/hr 734-IB8 5.5 BTU/hr 5V (continuous), Reinforced Insulation Type 5V DC for 6 s, field-side to system 4V DC...8.8V DC 56 x x 75.5 mm (. x.47 x.97 in.) on signal ports Determined by installed terminal block. 734-IB 3.9 g (.9 oz) 734-IB4 3.8 g (. oz) 734-IB8 3.3 g (.4 oz) None (open-style) () IEC 3 4V DC input compliant. () Use this conductor category information for planning conductor routing as described in Industrial Automation Wiring and Grounding Guidelines, publication 77-IN4.
22 POINT I/O Input Modules Environmental Specifications Attribute Temperature, operating Temperature, surrounding air, max. Temperature, nonoperating Relative humidity Vibration Shock, operating Shock, nonoperating Value IEC (Test Ad, Operating Cold), IEC (Test Bd, Operating Dry Heat), IEC (Test Nb, Operating Thermal Shock): C ( F) 55 C (3 F) IEC (Test Ab, Unpackaged Nonoperating Cold), IEC (Test Bb, Unpackaged Nonoperating Dry Heat), IEC (Test Na, Unpackaged Nonoperating Thermal Shock): C ( F) IEC (Test Db, Unpackaged Nonoperating Damp Heat): % noncondensing IEC (Test Fc, Operating): 5 Hz IEC (Test Ea, Unpackaged Shock): 3 g IEC (Test Ea, Unpackaged Shock): 5 g Emissions CISPR : Group, Class A ESD immunity IEC 6-4-: 6 kv contact discharges 8 kv air discharges Radiated RF immunity IEC 6-4-3: V/m with khz sine-wave 8% AM from 8... MHz V/m with Hz 5% Pulse % 9 MHz V/m with Hz 5% Pulse % 89 MHz V/m with khz sine-wave 8% AM from...7 MHz EFT/B immunity IEC 6-4-4: ±4 5 khz on signal ports Surge transient immunity ± kv line-line (DM) and ± kv line-earth (CM) on signal ports Conducted RF immunity IEC 6-4-6: V rms with khz sine-wave 8% AM from 5 khz...8 MHz
23 POINT I/O Input Modules 3 Certifications Certification (when product is marked) () c-ul-us Value UL Listed Industrial Control Equipment, certified for US and Canada. See UL File E UL Listed for Class I, Division Group A,B,C,D Hazardous Locations, certified for U.S. and Canada. See UL File E948. CE C-Tick Ex KC European Union 4/8/EC EMC Directive, compliant with: EN 636-; Meas./Control/Lab., Industrial Requirements EN 6-6-; Industrial Immunity EN 6-6-4; Industrial Emissions EN 63-; Programmable Controllers (Clause 8, Zone A and B) Australian Radiocommunications Act, compliant with: AS/NZS CISPR ; Industrial Emissions European Union 94/9/EC ATEX Directive, compliant with: EN 679-: + A:3; General Requirements EN 679-5:; Potentially Explosive Atmospheres, Protection "n" II 3 G Ex na IIC T4 Gc DEMKO 4 ATEX 33347X Korean Registration of Broadcasting and Communications Equipment, compliant with: Article 58- of Radio Waves Act, Clause 3 () See the Product Certification link at for Declaration of Conformity, Certificates, and other certification details.
24 Rockwell Automation Support Rockwell Automation provides technical information on the Web to assist you in using its products. At you can find technical manuals, a knowledge base of FAQs, technical and application notes, sample code and links to software service packs, and a MySupport feature that you can customize to make the best use of these tools. For an additional level of technical phone support for installation, configuration and troubleshooting, we offer TechConnect support programs. For more information, contact your local distributor or Rockwell Automation representative, or visit Installation Assistance If you experience a problem within the first 4 hours of installation, please review the information that's contained in this manual. You can also contact a special Customer Support number for initial help in getting your product up and running. United States or Canada Outside United States or Canada Use the Worldwide Locator at or contact your local Rockwell Automation representative. New Product Satisfaction Return Rockwell Automation tests all of its products to ensure that they are fully operational when shipped from the manufacturing facility. However, if your product is not functioning and needs to be returned, follow these procedures. United States Outside United States Contact your distributor. You must provide a Customer Support case number (call the phone number above to obtain one) to your distributor to complete the return process. Please contact your local Rockwell Automation representative for the return procedure. Documentation Feedback Your comments will help us serve your documentation needs better. If you have any suggestions on how to improve this document, complete this form, publication RA-DU, available at Allen-Bradley, Rockwell Automation, POINT I/O, and TechConnect are trademarks of Rockwell Automation, Inc. Trademarks not belonging to Rockwell Automation are property of their respective companies. Supersedes Publication 734-IN5H-EN-E - April 3 Copyright 5 Rockwell Automation, Inc. All rights reserved.
Installation Instructions Compact I/O End Caps/Terminators Catalog Numbers 1769-ECL, 1769-ECR Topic Page Important User Information 2 Environment and Enclosure 3 North American Hazardous Location Approval
Installation Instructions POINT I/O 8 Channel High Density Current Input Module Catalog Number 1734-IE8C Topic Page Important User Information 2 Environment and Enclosure 3 Prevent Electrostatic Discharge
FLEX I/O DeviceNet Adapter Module 1794-ADN Series C and 1794-ADNK Series C (Modules with a K in the last position of the catalog number are conformally coated to meet noxious gas requirements of ISA/ANSI-71.040
Wiring Diagrams Micro800 1.5" LCD Display and Keypad Module Catalog Number 2080-LCD http://literature.rockwellautomation.com Cette publication est disponible en français sous forme électronique (fichier
Installation Instructions POINT I/O EtherNet/IP Adapter Catalog Number 1734-AENT LED Indicators Safety End Cap Node Address Thumbwheel EtherNet Network RJ45 Connector DIN Rail Locking Screw (orange) RTB
Installation Instructions DeviceNet Modules Catalog Numbers 1756-DNB, 1769-ADN, 1769-SDN Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical
Installation Instructions USB-to-Data Highway Plus Cable Catalog Number 1784-U2DHP Topic Page Important User Information 2 Environment and Enclosure 3 Install the Cable 5 Configure the DH+ Node Address
Installation Instructions MicroLogix 1762-IF4 Analog Input Module Catalog Number 1762-IF4 Table of Contents Topic Page Important User Information 2 North American Hazardous Location Approval 4 Additional
nstallation nstructions FLEX /O solated nput Analog Module Cat. No. 1794-F4 mportant User nformation Solid state equipment has operational characteristics differing from those of electromechanical equipment.
Technical Data 1756 ControlLogix Power Supplies Specifications Standard Power Supplies Catalog Numbers 1756-PA72, 1756-PA75, 1756-PB72, 1756-PB75, 1756-PC75, 1756-PH75 Standard Slim Power Supplies Catalog
nstallation nstructions PONT /O 4V dc xpansion Supply atalog Number 1734-P4D, Series nside... For See Page mportant User nformation Preventing lectrostatic Discharge 3 nvironment and nclosure 4 North American
Backup Scanner Module Catalog Number 1747-BSN Installation Instructions 2 Backup Scanner Module Important User Information Because of the variety of uses for the products described in this publication,
Installation Instructions 1769-L35E CompactLogix Controller (Catalog Numbers 1769-L35E) Inside... Before You Begin... 3 How to Handle CompactLogix Components... 3 Make Sure that You Have All the Components...
Installation Instructions SLC 500 Analog Input Module (Catalog Number 1746NI8) Inside Important User Information... 2 For More Information... 3 Hazardous Location Considerations... 4 Environnements dangereux...
Installation Instructions Universal Serial Bus (USB) to DH-485 Interface Converter Catalog Number 1747-UIC Contents Overview..................................................3 Computer and Operating System
Installation Instructions Micro830 10 Point Programmable Controllers Catalog Numbers 2080-LC30-10QWB, 2080-LC30-10QVB http://rockwellautomation.com/literature Cette publication est disponible en français
Micro800 Programmable Controller Family Bulletin 2080 Selection Guide Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment.
Installation Instructions LEX I/O Input, and Input/ Analog odules at. Nos. 9-IE8, -IE8K, -OE, -OEK, and -IEXOE Series B (odules with a K in the last position of the catalog number are conformally coated
Installation Instructions Hard Disk Drive (HDD) Catalog Number 6189V-35HDDST80, 6189V-35HDDST160 Topic Page About This Publication 1 Important User Information 2 Electrostatic Discharge (ESD) Precautions
Installation Instructions Ethernet PLC-5 Programmable Controllers Catalog Numbers 1785-L20E, 1785-L40E, 1785-L80E, Series F Contents For This Topic See Page About This Publication 1 Related User Manual
Product datasheet Characteristics TM7BDM8B expansion block - TM7 - IP67-8 DI/DO - 24V DC - 0.5 A - M8 connector Main Range of product Product or component type Range compatibility Enclosure material Bus
User Manual 1769 CompactLogix Controllers User Manual Catalog Numbers 1769-L31, 1769-L32C, 1769-L32E, 1769-L35CR, 1769-L35E Important User Information Solid-state equipment has operational characteristics
Square D Clipsal DIN-Rail Four-Channel Auxiliary Input Unit SLCLE5504AUX for Use with Wired C-Bus Networks Instruction Bulletin Retain for future use. Square D Clipsal DIN-Rail Four-Channel Auxiliary Input
Installation Instructions ControlNet PCI Communication Interface Card Catalog Number 9904-PCIC This document describes how to install the 9904-PCIC ControlNet TM communication interface card. Topic: Page:
XM-160/161/162 Direct Vibration Module User Guide Firmware Revision 5 1440-VDRS06-00RH, 1440-VDRS06-06RH, 1440-VDRP06-00RH Important User Information Solid state equipment has operational characteristics
Highlights & Features Protection Class II, Double Isolation (No Earth connection is required) Universal AC input voltage without power de-rating Efficiency > 87.0% @ 115Vac & 230Vac NEC Class 2 / Limited
8 172 TX-I/O Digital input modules TXM1.8D TXM1.16D Two fully compatible versions: TXM1.8D: 8 inputs, each with a three-color LED (green, yellow or red) TXM1.16D: As TXM1.8X, but 16 inputs, each with a
User Manual Micro820 Programmable Controllers Catalog Numbers 2080-LC20-20QWB, 2080-LC20-20QBB, 2080-LC20-20AWB, 2080-LC20-20QWBR, 2080- LC20-20QBBR, 2080-LC20-20AWBR Important User Information Solid-state
Redundancy Module QUT DIODE provides: 00% decoupling of power supplies connected in parallel Can be installed in potentially explosive areas Load currents up to 60 A supported Easy assembly by snapping
Micro800 Programmable Controllers Bulletin 2080 Selection Guide Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety
Overview/Modes of Operation Bulletin 150 Smart Motor Controller The SMC-3 is a compact, simple to use, solid-state motor controller designed to operate 3-phase motors. It features a built-in overload relay
Data sheet Electronic timer CT-AHD.12 OFF-delayed with 1 c/o (SPDT) contact The CT-AHD.12 is an electronic time relay with OFF-delay. It is from the CT-D range. With their MDRC profile and a width of only
Power Supply Unit, Primary Switched, Narrow Design MINI POWER provides: Extra narrow design with widths of 22.5 mm, 45 mm, and 67.5 mm (0.886, 1.772, and 2.657 in.) Global use due to a wide-range input
Highlights & Features Protection Class II, Double Isolation (No Earth connection is required) Universal AC input voltage and full power up to 55 C Power will not de-rate for the entire input voltage range
Foxboro Evo Process Automation System Product Specifications PSS 31H-2Z32 FBM232 Field Device System Integrator Module, 10/100 Mbps Ethernet, Single The FBM232 Field Device System Integrator (FDSI) module
User Manual EtherNet/IP and ControlNet to PROFIBUS PA Linking Devices Catalog Numbers 1788-EN2PAR, 1788-CN2PAR Important User Information Read this document and the documents listed in the additional resources
Installation Instructions Chassis Interface Module for 1746 Local I/O (Catalog Number 1747-PCIL) Use this document to install the Chassis Interface module for 1746 Local I/O and connect it to a PCI Bus
Application Technique Safety Function: Magnetic Door Switch Monitoring Products: MC1 Magnetically-coded Door Switch, Guardmaster Dual-input Safety Relay Safety Rating: CAT. 3, PLd to EN ISO 13849-1: 2008
Characteristics multifunction control relay RM17-TE - range 183..528 V AC Complementary Reset time Maximum switching voltage Minimum switching current Maximum switching current [Us] rated supply voltage
Installation Instructions NetLinx ControlNet 1784-PCIC Communication Card Catalog Number 1784-PCIC This document describes how to install and use the NetLinx 1784-PCIC ControlNet TM communication interface
PowerFlex 700S and 700H Frame 12 DC Bus Connector Kit Installation Instructions This document provides instructions for the installation of a DC bus connector kit for PowerFlex 700S and 700H frame 12 drives
OPERATING INSTRUCTIONS CompactRIO crio-9052 CompactRIO StarFabric Interface 1 POWER BACKUP STATUS FPGA V1 C V2 2 C Rx INPUT 9 35 V 17 W MAX 3 Tx NI crio-9052 CompactRIO StarFabric Interface 1 LEDs 2 Power
Stratix 5700 Network Address Translation Quick Start Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety Guidelines
Characteristics multifunction voltage control relay RM35-U - range 15..600 V Complementary Reset time Maximum switching voltage [Us] rated supply voltage Supply voltage limits Power consumption in W Main
Data sheet Voltage monitoring relays CM-ESS.2 For single-phase AC/DC voltages The CM-ESS.2 is an electronic voltage monitoring relay that provides reliable monitoring of voltages as well as detection of
31007950 7/2009 ConneXium Ethernet Switches TCSESU0 F N0 Quick Reference Guide 7/2009 31007950.02 www.schneider-electric.com NOTICE Read these instructions carefully, and look at the equipment to become
AC 800M EtherNet/IP DeviceNet Linking Device LD 800DN SP1134 Power and productivity for a better world TM AC 800M EtherNet/IP DeviceNet Linking Device LD 800DN NOTICE This document contains information
MasterINTERFACE 39 Series - Relay interface modules Common features Space saving 6.2 mm wide Connections for 16-way jumper link Integral coil indication and protection circuit Secure retention and easy
Features STRATO switch mode driver technology is designed to generate one constant current output from a wide range AC input. The size and performance of these products make them the ideal choice for LED
Data sheet Three-phase monitoring relay CM-PFE The CM-PFE is a three-phase monitoring relay that monitors the phase parameter phase sequence and phase failure in three-phase mains. 2CDC 251 005 S0012 Characteristics
Extract from the online catalog STEP-PS/1AC/12DC/1.5 Order No.: 2868567 DIN rail power supply unit 12 V DC/1.5 A, primary switched-mode, 1- phase Commercial data EAN 4046356292924 Pack 1 pcs. Customs tariff
ABB Drives User s Manual Pulse Encoder Interface Module RTAC-0 Pulse Encoder Interface Module RTAC-0 User s Manual 3AFE 64486853 REV A EN EFFECTIVE:.5.00 00 ABB Oy. All Rights Reserved. Safety instructions
FLEX I/O Isolated Analog Modules 1794-IF4I, -OF4I, IF2XOF2I, -IF4IXT, -IF4ICFXT, -OF4IXT, IF2XOF2IXT User Manual Important User Information Solid state equipment has operational characteristics differing
T7560A,B,C Digital Wall Module HONEYWELL EXCEL 5000 OPEN SYSTEM BEFORE INSTALLATION All wiring must comply with local electrical codes and ordinances or as specified on installation wiring diagrams. Digital
Product and Applications Description The power supply units N 125/x2 can supply DC 24 V power from an additional pair of terminals (yellowwhite). This DC 24 V output voltage can be used to power e.g. an
Specifications Specifications Standard Features Optional Features Installation Setup Communications Power Wiring Control Wiring Keypad Software Starting and Stopping Modes Protection and Diagnostics Metering
Data sheet Voltage monitoring relays CM-ESS.M For single-phase AC/DC voltages The CM-ESS.M is an electronic voltage monitoring relay that provides reliable monitoring of voltages as well as detection of
Perle Protocol Transparent Media Converter Modules Installation Guide C-4GPT-DSFP CM-4GPT-DSFP Part# 5500335-10 Overview This document contains instructions necessary for the installation and operation
DeltaV Distributed Control System Product Data Sheet December 2015 S-series SQ Controller Scalable controllers Quick assembly Easy-to-use Field proven architecture Designed for Electonic Marshalling Advanced
ata sheet Analog signal converters CC-E I/I Current / current isolators The CC-E I/I is an isolator for the electrical isolation of current signals without auxiliary supply. It allows the isolation between
Characteristics Single-function OFF-delay timer for DC contactors, without auxiliary voltage Width.5 mm CDC 5 6 F3 Approvals A culus E CCC CT-VBS a Circuit diagram b Marker label Marks a CE b C-Tick Order
LIGHTING CONTROL PANELS 4 AND 8 RELAYS INSTALLATION INSTRUCTIONS INSTALLATION OVERVIEW The installation instructions contained in this document are provided as a guide for proper and reliable installation.
1SR 430 824 F9300 Features Monitoring of three-phase mains for phase sequence and failure Powered by the measuring circuit 2 c/o (SPDT) contacts 1 LED for status indication Approvals R: yellow LED - relay
Relés e Contatores de Estado Sólido SIRIUS Coletânea de dados técnicos ( product data sheet ) Agosto/212 SSR - 3RF21 22,5 mm Ponto Zero SSR - 3RF2 45 mm Ponto Zero SSR - 3RF22 45 mm Ponto Zero Trifásico
Data sheet Temperature monitoring relays CM-TCS Monitoring relays for monitoring temperatures with a PT100 sensor (2- or 3-wire connection) The temperature monitoring relays CM-TCS monitor overtemperature,
2CDC 251 014 F0t09 Features Monitoring of three-phase mains for grid feeding Type-tested in accordance with DIN V VDE V 0126-1-1: February 2006 Neutral conductor connection configurable Can also be used
Application Technique Safety Function: Door Monitoring Products: Trojan 5 Switch, GuardLogix Controller Safety Rating: CAT. 3, PLd to ISO 13849-1: 2008 Topic Page Important User Information 2 General Safety
SDN-P DIN Rail Series The SDN DIN Rail power supplies provide industry leading performance. Sag Immunity, transient suppression and noise tolerant, the SDN series ensures compatibility in demanding applications.
MTE SERIES RLW World REACTORS USER MANUAL PART NO. INSTR 030 REL. 090930 2009 MTE Corporation IMPORTANT USER INFORMATION NOTICE MTE Series RLW reactors are components designed to improve the reliability
MCR1900 Media Converter 19-Slot Chassis Installation Guide Part #5500304-11 Copyright Statement This document must not be reproduced in any way whatsoever, either printed or electronically, without the
Telephone- and leased line modem for industrial applications TD-36 Modem for industrial PSTN- and leased line applications The TD-36 is an analogue V.34 PSTN modem as well as an industrial 2-wire leased