1 Installation Instructions MicroLogix 1762-IF4 Analog Input Module Catalog Number 1762-IF4 Table of Contents Topic Page Important User Information 2 North American Hazardous Location Approval 4 Additional Resources 5 Overview 6 Module Description 7 Mount the Module 8 Field Wiring Connections 11 Input Type Selection 12 Wiring the Finger-Safe Terminal Block 15 Wire Size and Terminal Screw Torque 15 Specifications 20
2 2 MicroLogix 1762-IF4 Analog Input Module Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety Guidelines for the Application, Installation and Maintenance of Solid State Controls (Publication SGI-1.1 available from your local Rockwell Automation sales office or online at describes some important differences between solid state equipment and hard-wired electromechanical devices. Because of this difference, and also because of the wide variety of uses for solid state equipment, all persons responsible for applying this equipment must satisfy themselves that each intended application of this equipment is acceptable. In no event will Rockwell Automation, Inc. be responsible or liable for indirect or consequential damages resulting from the use or application of this equipment. The examples and diagrams in this manual are included solely for illustrative purposes. Because of the many variables and requirements associated with any particular installation, Rockwell Automation, Inc. cannot assume responsibility or liability for actual use based on the examples and diagrams. No patent liability is assumed by Rockwell Automation, Inc. with respect to use of information, circuits, equipment, or software described in this manual. Reproduction of the contents of this manual, in whole or in part, without written permission of Rockwell Automation, Inc., is prohibited. Throughout this manual, when necessary, we use notes to make you aware of safety considerations. WARNING Identifies information about practices or circumstances that can cause an explosion in a hazardous environment, which may lead to personal injury or death, property damage, or economic loss. IMPORTANT ATTENTION Identifies information that is critical for successful application and understanding of the product. Identifies information about practices or circumstances that can lead to personal injury or death, property damage, or economic loss. Attentions help you identify a hazard, avoid a hazard and recognize the consequences. SHOCK HAZARD Labels may be on or inside the equipment (for example, drive or motor) to alert people that dangerous voltage may be present. BURN HAZARD Labels may be on or inside the equipment (for example, drive or motor) to alert people that surfaces may reach dangerous temperatures.
3 MicroLogix 1762-IF4 Analog Input Module 3 Environment and Enclosure ATTENTION This equipment is intended for use in a Pollution Degree 2 industrial environment, in overvoltage Category II applications (as defined in IEC ), at altitudes up to 2000 m (6562 ft) without derating.this equipment is considered Group 1, Class A industrial equipment according to IEC/CISPR 11. Without appropriate precautions, there may be difficulties with electromagnetic compatibility in residential and other environments due to conducted and radiated disturbances. This equipment is supplied as open-type equipment. It must be mounted within an enclosure that is suitably designed for those specific environmental conditions that will be present and appropriately designed to prevent personal injury resulting from accessibility to live parts. The enclosure must have suitable flame-retardant properties to prevent or minimize the spread of flame, complying with a flame spread rating of 5VA, V2, V1, V0 (or equivalent) if non-metallic. The interior of the enclosure must be accessible only by the use of a tool. Subsequent sections of this publication may contain additional information regarding specific enclosure type ratings that are required to comply with certain product safety certifications. In addition to this publication, see: Industrial Automation Wiring and Grounding Guidelines, for additional installation requirements, Allen-Bradley publication NEMA Standards 250 and IEC 60529, as applicable, for explanations of the degrees of protection provided by different types of enclosure. Preventing Electrostatic Discharge ATTENTION This equipment is sensitive to electrostatic discharge, which can cause internal damage and affect normal operation. Follow these guidelines when you handle this equipment: Touch a grounded object to discharge potential static. Wear an approved grounding wriststrap. Do not touch connectors or pins on component boards. Do not touch circuit components inside the equipment. Use a static-safe workstation, if available. Store the equipment in appropriate static-safe packaging when not in use.
4 4 MicroLogix 1762-IF4 Analog Input Module North American Hazardous Location Approval The following modules are North American Hazardous Location approved: 1762-IF4 The following information applies when operating this equipment in hazardous locations: Products marked "CL I, DIV 2, GP A, B, C, D" are suitable for use in Class I Division 2 Groups A, B, C, D, Hazardous Locations and nonhazardous locations only. Each product is supplied with markings on the rating nameplate indicating the hazardous location temperature code. When combining products within a system, the most adverse temperature code (lowest "T" number) may be used to help determine the overall temperature code of the system. Combinations of equipment in your system are subject to investigation by the local Authority Having Jurisdiction at the time of installation. WARNING EXPLOSION HAZARD Do not disconnect equipment unless power has been removed or the area is known to be nonhazardous. Do not disconnect connections to this equipment unless power has been removed or the area is known to be nonhazardous. Secure any external connections that mate to this equipment by using screws, sliding latches, threaded connectors, or other means provided with this product. Substitution of components may impair suitability for Class I, Division 2. If this product contains batteries, they must only be changed in an area known to be nonhazardous. All wiring must comply with N.E.C. article 501-4(b). The interior of the enclosure must be accessible only by the use of a tool. For applicable equipment (relay modules, etc.), exposure to some chemicals may degrade the sealing properties of materials used in the following devices: Relays, Epoxy. It is recommended that the User periodically inspect these devices for any degradation of properties and replace the module if degradation is found. Informations sur l utilisation de cet équipement en environnements dangereux: Les produits marqués "CL I, DIV 2, GP A, B, C, D" ne conviennent qu'à une utilisation en environnements de Classe I Division 2 Groupes A, B, C, D dangereux et non dangereux. Chaque produit est livré avec des marquages sur sa plaque d'identification qui indiquent le code de température pour les environnements dangereux. Lorsque plusieurs produits sont combinés dans un système, le code de température le plus défavorable (code de température le plus faible) peut être utilisé pour déterminer le code de température global du système. Les combinaisons d'équipements dans le système sont sujettes à inspection par les autorités locales qualifiées au moment de l'installation. AVERTISSEMENT RISQUE D EXPLOSION Couper le courant ou s assurer que l environnement est classé non dangereux avant de débrancher l'équipement. Couper le courant ou s'assurer que l'environnement est classé non dangereux avant de débrancher les connecteurs. Fixer tous les connecteurs externes reliés à cet équipement à l'aide de vis, loquets coulissants, connecteurs filetés ou autres moyens fournis avec ce produit. La substitution de composants peut rendre cet équipement inadapté à une utilisation en environnement de Classe I, Division 2. S assurer que l environnement est classé non dangereux avant de changer les piles.
5 MicroLogix 1762-IF4 Analog Input Module 5 Additional Resources Resource MicroLogix 1100 Programmable Controllers User Manual, publication 1763-UM001. MicroLogix 1200 Programmable Controllers User Manual, publication 1762-UM001. MicroLogix 1400 Programmable Controllers User Manual, publication 1766-UM001. MicroLogix 1100 Programmable Controllers Installation Instructions, publication 1763-IN001. MicroLogix 1200 Programmable Controllers Installation Instructions, publication 1762-IN006. MicroLogix 1400 Programmable Controllers Installation Instructions, publication 1766-IN001. Industrial Automation Wiring and Grounding Guidelines, publication Description A more detailed description of how to install and use your MicroLogix 1100 programmable controller and expansion I/O system. A more detailed description of how to install and use your MicroLogix 1200 programmable controller and expansion I/O system. A more detailed description of how to install and use your MicroLogix 1400 programmable controller and expansion I/O system. Information on installing and using the MicroLogix 1100 programmable controller. Information on installing and using the MicroLogix 1200 programmable controller. Information on installing and using the MicroLogix 1400 programmable controller. More information on proper wiring and grounding techniques. If you would like a manual, you can: download a free electronic version from the Internet: purchase a printed manual by contacting your local Allen-Bradley distributor or Rockwell Automation representative
6 6 MicroLogix 1762-IF4 Analog Input Module Overview The 1762 input module is suitable for use in an industrial environment when installed in accordance with these instructions. Specifically, this equipment is intended for use in clean, dry environments (Pollution degree 2 (1) ) and to circuits not exceeding Over Voltage Category II (2) (IEC ) (3). Install your module using these installation instructions Input Module Debris strip ATTENTION Do not remove the protective debris strip until after the module and all other equipment in the panel near the module are mounted and wiring is complete. Once wiring is complete, remove protective debris strip. Failure to remove strip before operating can cause overheating. ATTENTION Electrostatic discharge can damage semiconductor devices inside the module. Do not touch the connector pins or other sensitive areas. (1) (2) (3) Pollution Degree 2 is an environment where, normally, only non-conductive pollution occurs except that occasionally a temporary conductivity caused by condensation shall be expected. Over Voltage Category II is the load level section of the electrical distribution system. At this level transient voltages are controlled and do not exceed the impulse voltage capability of the product s insulation. Pollution Degree 2 and Over Voltage Category II are International Electrotechnical Commission (IEC) designations.
7 MicroLogix 1762-IF4 Analog Input Module 7 Module Description 1a 1a Front view b Left side view This equipment is sensitive to electrostatic discharge (ESD). Follow ESD prevention guidelines when handling this equipment. Description Description 1a upper panel mounting tab 6 pull loop 1b lower panel mounting tab 7 module door with terminal identification label 2 power diagnostic LED 8 bus connector cover 3 flat ribbon cable with bus connector (female) 9 bus connector with male pins 4 DIN rail latch 10 terminal block 5 input type selector switch ATTENTION To comply with UL restrictions, this equipment must be powered from a source compliant with Class 2 or Limited Voltage/Current.
8 8 MicroLogix 1762-IF4 Analog Input Module Mount the Module General Considerations Most applications require installation in an industrial enclosure to reduce the effects of electrical interference and environmental exposure. Locate your controller as far as possible from power lines, load lines, and other sources of electrical noise such as hard-contact switches, relays, and AC motor drives. For more information on proper grounding guidelines, see the Industrial Automation Wiring and Grounding Guidelines, publication ATTENTION This product is intended to be mounted to a well-grounded mounting surface such as a metal panel. Additional grounding connections from the power supply's mounting tabs or DIN rail (if used) are not required unless the mounting surface cannot be grounded. Refer to Industrial Automation Wiring and Grounding Guidelines, Allen-Bradley publication , for additional information. Mounting Dimensions 90 mm (3.5 in.) 40.4 mm (1.59 in.) 87 mm (3.43 in.) Measurements do not include mounting feet or DIN rail latches.
9 MicroLogix 1762-IF4 Analog Input Module 9 Module Spacing Maintain spacing from objects such as enclosure walls, wireways and adjacent equipment. Allow 50.8 mm (2 in.) of space on all sides for adequate ventilation, as shown: Top Side MicroLogix 1100/1200/ I/O 1762 I/O 1762 I/O Side Bottom DIN Rail Mounting The module can be mounted using the following DIN rails: 35 x 7.5 mm (EN x 7.5) or 35 x 15 mm (EN x 15). Before mounting the module on a DIN rail, close the DIN rail latch. Press the DIN rail mounting area of the module against the DIN rail. The latch will momentarily open and lock into place. Use DIN rail end anchors (Allen-Bradley part number 1492-EA35 or 1492-EAH35) for vibration or shock environments. End anchor End anchor TIP For environments with greater vibration and shock concerns, use the panel mounting method described below, instead of DIN rail mounting.
10 10 MicroLogix 1762-IF4 Analog Input Module Panel Mounting Use the dimensional template shown below to mount the module. The preferred mounting method is to use two M4 (#8) panhead screws per module. M3.5 (#6) panhead screws may also be used, but a washer may be needed to ensure a good mechanical contact. Mounting screws are required on every module. For more than two I/O modules: measure (number of modules - 1) x 40 mm (1.59 in.) 14.2 (0.568) 40.4 (1.59) (3.939) (3.54) MicroLogix 1100/1200/ I/O 1762 I/O 1762 I/O 95 (3.74) 40.4 (1.59) NOTE: All dimensions are in mm (in.). Hole spacing tolerance: ±0.4 mm (0.016 in.). System Assembly The expansion I/O module is attached to the controller or another I/O module by means of a flat ribbon cable after mounting as shown below expansion bus connector cover Bus connector covers TIP Use the pull loop on the connector to disconnect modules. Do not pull on the ribbon cable.
11 MicroLogix 1762-IF4 Analog Input Module 11 Field Wiring Connections Grounding the Module In solid-state control systems, grounding and wire routing helps limit the effects of noise due to electromagnetic interference (EMI). Run the ground connection from the ground screw of the controller to the ground bus prior to connecting any devices. Use AWG #14 wire. For AC-powered controllers, this connection must be made for safety purposes. You must also provide an acceptable grounding path for each device in your application. For more information on proper grounding guidelines, refer to the Industrial Automation Wiring and Grounding Guidelines, publication WARNING EXPLOSION HAZARD In Class I, Division 2 applications, the bus connector must be fully seated and the bus connector cover must be snapped in place. In Class I, Division 2 applications, all modules must be mounted in direct contact with each other as shown on page 10. If DIN rail mounting is used, an end anchor must be installed ahead of the controller and after the last 1762 I/O module. ATTENTION To comply with the CE Low Voltage Directive (LVD), all connected I/O must be powered from a source compliant with the Safety Extra Low Voltage (SELV) or Protected Extra Low Voltage (PELV). WARNING If you connect or disconnect wiring while the field-side power is on, an electrical arc can occur. This could cause an explosion in hazardous location installations. Be sure that power is removed or the area is nonhazardous before proceeding.
12 12 MicroLogix 1762-IF4 Analog Input Module Input Type Selection Select the input type, current or voltage, using the switch located on the module s circuit board and the input type/range selection bits in the Configuration Data File (see page 17). You can access the switch through the ventilation slots on the top of the module. The factory default setting for all switches is Current. Switch positions are shown below. Switch Location Ch0 Ch1 Ch2 Ch3 Voltage (OFF) ON 1 ON Current (ON) Default Input Wiring Basic wiring of input devices to the 1762-IF4 is shown below. Terminal Block Layout IN0 - IN1 - IN2 - IN3 - IN0 + IN1 + IN2 + IN3 + COM COM Commons connected internally
13 MicroLogix 1762-IF4 Analog Input Module 13 Basic Input Wiring to the 1762-IF4 Module Differential Sensor Transmitter Types Analog Sensor IN 0 (+) IN 0 (-) IN 1 (+) IN 1 (-) IN 2 (+) IN 2 (-) IN 3 (+) IN 3 (-) COM COM TIP Grounding the cable shield at the module end only usually provides sufficient noise immunity. However, for best cable shield performance, earth ground the shield at both ends, using a 0.01µF capacitor at one end to block AC power ground currents, if necessary.
14 14 MicroLogix 1762-IF4 Analog Input Module Sensor/Transmitter Types 2-Wire Transmitter Power Supply (1) + - Transmitter + - Module IN + IN - COM 3-Wire Transmitter Power Supply (1) + - Supply Transmitter Signal Module IN + IN - COM 4-Wire Transmitter Power Supply (1) + - Transmitter Supply Signal Module IN + IN - COM (1) All power supplies rated N.E.C. Class 2.
15 MicroLogix 1762-IF4 Analog Input Module 15 Wiring the Finger-Safe Terminal Block ATTENTION Be careful when stripping wires. Wire fragments that fall into a module could cause damage when power is applied. Once wiring is complete, ensure the module is free of all metal fragments. When wiring the terminal block, keep the finger-safe cover in place. 1. Route the wire under the terminal pressure plate. You can use the stripped end of the wire or a spade lug. The terminals will accept a 6.35 mm (0.25 in.) spade lug. 2. Tighten the terminal screw making sure the pressure plate secures the wire. Recommended torque when tightening terminal screws is Nm (8 lb-in.). 3. After wiring is complete, remove the debris shield. TIP If you need to remove the finger-safe cover, insert a screw driver into one of the square wiring holes and gently pry the cover off. If you wire the terminal block with the finger-safe cover removed, you will not be able to put it back on the terminal block because the wires will be in the way. Wire Size and Terminal Screw Torque Each terminal accepts up to two wires with the following restrictions: Wire Type Wire Size Terminal Screw Torque Solid Cu-90 C (194 F) #14 22 AWG Nm (8 lb-in.) Stranded Cu-90 C (194 F) #16 22 AWG Nm (8 lb-in.)
16 16 MicroLogix 1762-IF4 Analog Input Module Labeling the Terminals A write-on label is provided with the module. Mark the identification of each terminal with permanent ink, and slide the label back into the door Expansion I/O Addressing The addressing scheme for 1762 Expansion I/O is represented in the following figure. Data file Slot number (1) Word I1:x.0/0 Bit (0...15) Bit delimiter Input Word delimiter Slot delimiter (1) I/O located on the controller (embedded I/O) is slot 0. I/O added to the controller (expansion I/O) begins with slot 1. Input Data File For each module, slot x, words 0 3 contain the analog values of the inputs. The module can be configured to use either raw/proportional data or scaled-for-pid data. The input data file for either configuration is shown below. Word Bit Position SGN0 Channel 0 Data 1 SGN1 Channel 1 Data 2 SGN2 Channel 2 Data 3 SGN3 Channel 3 Data 4 reserved S3 S2 S1 S0 5 U0 O0 U1 O1 U2 O2 U3 O3 reserved 6 reserved
17 MicroLogix 1762-IF4 Analog Input Module 17 The bits are defined as follows: Sx = General status bits for channels 0 3. This bit is set when an error (over- or under-range) exists for that channel, or there is a general module hardware error. Ox = Over-range flag bits for channels 0 3. These bits are set when the input signal is above the user-specified range. The module continues to convert data to the maximum full range value during an over-range condition. The bits reset when the over-range condition clears. Ux = Under-range flag bits for input channels 0 3. These bits are set when the input signal is below the user-specified range. The module continues to convert data to the maximum full range value during an under-range condition. The bits reset when the under-range condition clears. SGNx = The sign bit for channels 0 3. Configuration Data File The configuration of the format for analog inputs is made at going to run (GTR). Changes made to the configuration file while in run mode have no effect. The configuration table is shown below. Word Bit Position Data Format Channel 0 1 Data Format Channel 1 2 Data Format Channel 2 3 Data Format Channel 3 4 reserved 5 reserved 6 reserved 7 reserved reserved Type/Range Select Channel 0 Type/Range Select Channel 1 Type/Range Select Channel 2 Type/Range Select Channel 3 reserved reserved reserved reserved Filter Select Channel 0 Filter Select Channel 1 Filter Select Channel 2 Filter Select Channel 3 Bit 15 and Bits Reserved These bits are reserved and are not checked by the module.
18 18 MicroLogix 1762-IF4 Analog Input Module Data Format (Bits 14 12) These bits indicate the format of the data as shown in the following table. Other combinations of these bits are not supported and result in an error. Bit Settings Data Format Raw/Proportional Scaled for PID other Not Supported Type/Range Select (Bits 11 8) These bits indicate the type and range as in the following table. Other combinations of these bits are not supported and result in an error. Bit Settings Data Format Voltage Mode V DC Current Mode 4 20 ma other Not Supported Filter Select (Bits 3 0) These bits indicate the filter (for desired normal mode rejection) as shown in the table below. Other combinations of these bits are not supported and result in an error. Bit Settings Filter Frequency 4-Channel Attenuation at Filter Conversion Time Frequency Hz 450 ms >55dB Hz 530 ms >55dB Hz 250 ms >20dB Hz 290 ms >20dB No filter 130 ms
19 MicroLogix 1762-IF4 Analog Input Module 19 Error Codes The 1762-IF4 module notifies the controller of critical and non-critical errors. The module condition array word 0 contains the error codes that are generated by the module, as shown below. Don t Care Bits Module Error Extended Error Information Hex Digit 4 Hex Digit 3 Hex Digit 2 Hex Digit 1 The table below describes the module error codes. Error Type Hex Equivalent (1) Module Error Code Binary Extended Error Information Code Binary No Error X No error General Common Hardware Error Error Description X General hardware error; no additional information X Power-up reset state Hardware- Specific Error Configuration Error X Reserved X General configuration error; no additional information X Invalid range select (Channel 0) X Invalid range select (Channel 1) X Invalid range select (Channel 2) X Invalid range select (Channel 3) X Invalid filter select (Channel 0) X Invalid filter select (Channel 1) X Invalid filter select (Channel 2) X Invalid filter select (Channel 3) X Invalid format select (Channel 0) X40A Invalid format select (Channel 1) X40B Invalid format select (Channel 2) X40C Invalid format select (Channel 3) (1) X represents Don t Care.
20 20 MicroLogix 1762-IF4 Analog Input Module Specifications Input Attribute Value Number of inputs 4 differential (bipolar) A/D converter type Sigma-Delta Common mode voltage range (1) ±27V Common mode rejection (2) > and 60 Hz Non-linearity (in percent full scale) ±0.12% Typical overall accuracy (3) ±0.32% full C (-4 F 149 F) ±0.24% full 25 C (77 F) Input impedance Voltage terminal: 200KΩ Current terminal: 275Ω Current input protection ±32 ma Voltage input protection ±30V Channel diagnostics Over or under range or open circuit condition by bit reporting for analog inputs. (1) (2) For proper operation, both the plus and minus input terminals must be within ±27V of analog common. V cm = 1 V pk-pk AC (3) V cm = 0 (includes offset, gain, non-linearity and repeatability error terms)
21 MicroLogix 1762-IF4 Analog Input Module 21 General Attribute Dimensions, HxWxD Approximate shipping weight (with carton) Bus current draw, max Analog normal operating range Full scale (1) analog ranges Resolution Repeatability (2) Value 90 x 40.4 x 87 mm (3.54 x 1.59 x 3.43 in.) 235 g (8.28 oz) 40 5V DC 50 24V DC Voltage: V DC Current: 4 20 ma Voltage: V DC Current: ma 15 bits (bipolar) ±0.12% Input group to system isolation 30V AC/30V DC rated working voltage (4) (IEC Class 2 reinforced insulation) type test: 500V AC or 707V DC for 1 min Module power LED On: indicates power is applied. Recommended cable Belden 8761 (shielded) Vendor ID code 1 Product type code 10 Product code 67 Wire size See Wire Size and Terminal Screw Torque on page 15 Wiring category (3) Pilot duty rating Enclosure type rating North American temp code 2 - on signal ports Not rated IP20 T3C (1) The over- or under-range flag comes on when the normal operating range (over/under) is exceeded. The module continues to convert the analog input up to the maximum full scale range. (2) Repeatability is the ability of the input module to register the same reading in successive measurements for the same input signal. (3) (4) Use this Conductor Category information for planning conductor routing. Refer to Industrial Automation Wiring and Grounding Guidelines, publication Rated working voltage is the maximum continuous voltage that can be applied at the terminals with respect to earth ground.
22 22 MicroLogix 1762-IF4 Analog Input Module Environmental Attribute Temperature, operating Temperature, storage Relative humidity Vibration Altitude, operating, max Shock, operating Shock, nonoperating Value IEC (Test Ad, Operating Cold), IEC (Test Bd, Operating Dry Heat), IEC (Test Nb, Operating Thermal Shock): C ( F) IEC (Test Ab, Unpackaged Non-operating Cold), IEC (Test Bb, Unpackaged Non-operating Dry Heat), IEC (Test Na, Unpackaged Non-operating Thermal Shock): C ( F) IEC (Test Db, Unpackaged Damp Heat): % non-condensing IEC (Test Fc, Operating): Hz 2000 m (6562 ft) IEC (Test Ea, Unpackaged Shock): 30 g IEC (Test Ea, Unpackaged Shock): Panel mount - 50 g DIN mount - 40 g Emissions CISPR 11 Group 1, Class A ESD immunity IEC : 4 kv contact discharges 8 kv air discharges 4 kv indirect Radiated RF immunity IEC : 10V/m with 1 khz sine-wave 80% AM from MHz EFT/B immunity IEC : ±2 kv at 5 khz on signal ports Surge transient immunity IEC : ±1 kv shielded line-earth (CM) on signal ports Conducted RF immunity IEC : 10V rms with 1 khz sine-wave 80% AM from 150 khz...80 MHz
23 MicroLogix 1762-IF4 Analog Input Module 23 Certifications Certification (when product is marked) (1) c-ul-us Value UL Listed Industrial Control Equipment, certified for US and Canada. See UL File E UL Listed for Class I, Division 2 Group A,B,C,D Hazardous Locations, certified for U.S. and Canada. See UL File E CE C-Tick KC European Union 2004/108/EC EMC Directive, compliant with: EN ; Meas./Control/Lab., Industrial Requirements EN ; Industrial Immunity EN ; Industrial Emissions EN ; Programmable Controllers (Clause 8, Zone A & B) Australian Radiocommunications Act, compliant with: AS/NZS CISPR 11; Industrial Emissions Korean Registration of Broadcasting and Communications Equipment, compliant with: Article 58-2 of Radio Waves Act, Clause 3 (1) See the Product Certification link at for Declaration of Conformity, Certificates, and other certification details.
24 Rockwell Automation Support Rockwell Automation provides technical information on the Web to assist you in using its products. At you can find technical manuals, a knowledge base of FAQs, technical and application notes, sample code and links to software service packs, and a MySupport feature that you can customize to make the best use of these tools. For an additional level of technical phone support for installation, configuration and troubleshooting, we offer TechConnect support programs. For more information, contact your local distributor or Rockwell Automation representative, or visit Installation Assistance If you experience a problem within the first 24 hours of installation, please review the information that's contained in this manual. You can also contact a special Customer Support number for initial help in getting your product up and running. United States or Canada Outside United States or Canada Use the Worldwide Locator at or contact your local Rockwell Automation representative. New Product Satisfaction Return Rockwell Automation tests all of its products to ensure that they are fully operational when shipped from the manufacturing facility. However, if your product is not functioning and needs to be returned, follow these procedures. United States Outside United States Contact your distributor. You must provide a Customer Support case number (call the phone number above to obtain one) to your distributor to complete the return process. Please contact your local Rockwell Automation representative for the return procedure. Documentation Feedback Your comments will help us serve your documentation needs better. If you have any suggestions on how to improve this document, complete this form, publication RA-DU002, available at Allen-Bradley, Rockwell Automation, MicroLogix, and TechConnect are trademarks of Rockwell Automation, Inc. Trademarks not belonging to Rockwell Automation are property of their respective companies. Supersedes Publication 1762-IN012B-EN-P - April 2011 Copyright 2013 Rockwell Automation, Inc. All rights reserved.
Installation Instructions Compact I/O End Caps/Terminators Catalog Numbers 1769-ECL, 1769-ECR Topic Page Important User Information 2 Environment and Enclosure 3 North American Hazardous Location Approval
Wiring Diagrams Micro800 1.5" LCD Display and Keypad Module Catalog Number 2080-LCD http://literature.rockwellautomation.com Cette publication est disponible en français sous forme électronique (fichier
FLEX I/O DeviceNet Adapter Module 1794-ADN Series C and 1794-ADNK Series C (Modules with a K in the last position of the catalog number are conformally coated to meet noxious gas requirements of ISA/ANSI-71.040
Installation Instructions DeviceNet Modules Catalog Numbers 1756-DNB, 1769-ADN, 1769-SDN Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical
Installation Instructions POINT I/O Input Modules Catalog numbers 734-IB, 734-IB4, 734-IB8, Series C Table of Contents Topic Page Important User Information Environment and Enclosure 3 Preventing Electrostatic
Installation Instructions USB-to-Data Highway Plus Cable Catalog Number 1784-U2DHP Topic Page Important User Information 2 Environment and Enclosure 3 Install the Cable 5 Configure the DH+ Node Address
Installation Instructions POINT I/O 8 Channel High Density Current Input Module Catalog Number 1734-IE8C Topic Page Important User Information 2 Environment and Enclosure 3 Prevent Electrostatic Discharge
Installation Instructions SLC 500 Analog Input Module (Catalog Number 1746NI8) Inside Important User Information... 2 For More Information... 3 Hazardous Location Considerations... 4 Environnements dangereux...
Installation Instructions POINT I/O EtherNet/IP Adapter Catalog Number 1734-AENT LED Indicators Safety End Cap Node Address Thumbwheel EtherNet Network RJ45 Connector DIN Rail Locking Screw (orange) RTB
nstallation nstructions FLEX /O solated nput Analog Module Cat. No. 1794-F4 mportant User nformation Solid state equipment has operational characteristics differing from those of electromechanical equipment.
Backup Scanner Module Catalog Number 1747-BSN Installation Instructions 2 Backup Scanner Module Important User Information Because of the variety of uses for the products described in this publication,
Technical Data 1756 ControlLogix Power Supplies Specifications Standard Power Supplies Catalog Numbers 1756-PA72, 1756-PA75, 1756-PB72, 1756-PB75, 1756-PC75, 1756-PH75 Standard Slim Power Supplies Catalog
Installation Instructions Hard Disk Drive (HDD) Catalog Number 6189V-35HDDST80, 6189V-35HDDST160 Topic Page About This Publication 1 Important User Information 2 Electrostatic Discharge (ESD) Precautions
nstallation nstructions PONT /O 4V dc xpansion Supply atalog Number 1734-P4D, Series nside... For See Page mportant User nformation Preventing lectrostatic Discharge 3 nvironment and nclosure 4 North American
Installation Instructions Universal Serial Bus (USB) to DH-485 Interface Converter Catalog Number 1747-UIC Contents Overview..................................................3 Computer and Operating System
Installation Instructions 1769-L35E CompactLogix Controller (Catalog Numbers 1769-L35E) Inside... Before You Begin... 3 How to Handle CompactLogix Components... 3 Make Sure that You Have All the Components...
Installation Instructions LEX I/O Input, and Input/ Analog odules at. Nos. 9-IE8, -IE8K, -OE, -OEK, and -IEXOE Series B (odules with a K in the last position of the catalog number are conformally coated
Product datasheet Characteristics TM7BDM8B expansion block - TM7 - IP67-8 DI/DO - 24V DC - 0.5 A - M8 connector Main Range of product Product or component type Range compatibility Enclosure material Bus
Installation Instructions Micro830 10 Point Programmable Controllers Catalog Numbers 2080-LC30-10QWB, 2080-LC30-10QVB http://rockwellautomation.com/literature Cette publication est disponible en français
ata sheet Analog signal converters CC-E I/I Current / current isolators The CC-E I/I is an isolator for the electrical isolation of current signals without auxiliary supply. It allows the isolation between
Micro800 Programmable Controllers Bulletin 2080 Selection Guide Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety
Micro800 Programmable Controller Family Bulletin 2080 Selection Guide Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment.
Characteristics multifunction control relay RM17-TE - range 183..528 V AC Complementary Reset time Maximum switching voltage Minimum switching current Maximum switching current [Us] rated supply voltage
Highlights & Features Protection Class II, Double Isolation (No Earth connection is required) Universal AC input voltage and full power up to 55 C Power will not de-rate for the entire input voltage range
XM-160/161/162 Direct Vibration Module User Guide Firmware Revision 5 1440-VDRS06-00RH, 1440-VDRS06-06RH, 1440-VDRP06-00RH Important User Information Solid state equipment has operational characteristics
Highlights & Features Protection Class II, Double Isolation (No Earth connection is required) Universal AC input voltage without power de-rating Efficiency > 87.0% @ 115Vac & 230Vac NEC Class 2 / Limited
Power Supply Unit, Primary Switched, Narrow Design MINI POWER provides: Extra narrow design with widths of 22.5 mm, 45 mm, and 67.5 mm (0.886, 1.772, and 2.657 in.) Global use due to a wide-range input
Square D Clipsal DIN-Rail Four-Channel Auxiliary Input Unit SLCLE5504AUX for Use with Wired C-Bus Networks Instruction Bulletin Retain for future use. Square D Clipsal DIN-Rail Four-Channel Auxiliary Input
T7560A,B,C Digital Wall Module HONEYWELL EXCEL 5000 OPEN SYSTEM BEFORE INSTALLATION All wiring must comply with local electrical codes and ordinances or as specified on installation wiring diagrams. Digital
Installation Instructions Ethernet PLC-5 Programmable Controllers Catalog Numbers 1785-L20E, 1785-L40E, 1785-L80E, Series F Contents For This Topic See Page About This Publication 1 Related User Manual
User Manual Micro820 Programmable Controllers Catalog Numbers 2080-LC20-20QWB, 2080-LC20-20QBB, 2080-LC20-20AWB, 2080-LC20-20QWBR, 2080- LC20-20QBBR, 2080-LC20-20AWBR Important User Information Solid-state
PowerFlex 700S and 700H Frame 12 DC Bus Connector Kit Installation Instructions This document provides instructions for the installation of a DC bus connector kit for PowerFlex 700S and 700H frame 12 drives
Telephone- and leased line modem for industrial applications TD-36 Modem for industrial PSTN- and leased line applications The TD-36 is an analogue V.34 PSTN modem as well as an industrial 2-wire leased
MILLENIUM Table of contents 1. INTRODUCTION 1 2. HARDWARE DESCRIPTION 2 3. INSTALLATION 5 4. CONNECTION 6 5. USER SAFETY AND PROTECTION OF EQUIPMENT 8 1. Introduction The MILLENIUM series has been designed
8 172 TX-I/O Digital input modules TXM1.8D TXM1.16D Two fully compatible versions: TXM1.8D: 8 inputs, each with a three-color LED (green, yellow or red) TXM1.16D: As TXM1.8X, but 16 inputs, each with a
Characteristics multifunction voltage control relay RM35-U - range 15..600 V Complementary Reset time Maximum switching voltage [Us] rated supply voltage Supply voltage limits Power consumption in W Main
Features STRATO switch mode driver technology is designed to generate one constant current output from a wide range AC input. The size and performance of these products make them the ideal choice for LED
SDC-H Duct Humidity Transmitter Features Replaceable sensor element Humidity measurement for air ducts Minimum and maximum value memory 0 0V, 0 0mA or 0V, 4 0mA measuring signals selectable with jumpers
User Manual 1769 CompactLogix Controllers User Manual Catalog Numbers 1769-L31, 1769-L32C, 1769-L32E, 1769-L35CR, 1769-L35E Important User Information Solid-state equipment has operational characteristics
Data sheet Electronic timer CT-AHD.12 OFF-delayed with 1 c/o (SPDT) contact The CT-AHD.12 is an electronic time relay with OFF-delay. It is from the CT-D range. With their MDRC profile and a width of only
MCR1900 Media Converter 19-Slot Chassis Installation Guide Part #5500304-11 Copyright Statement This document must not be reproduced in any way whatsoever, either printed or electronically, without the
Type: EASY719 DC RC Article.: 274119 Ordering information Relay outputs Quantity 6 Power supply V DC 24 V DC Description 12 digital inputs (4 inputs available as analog inputs) 6 relay outputs LCD display
ABB Drives User s Manual Pulse Encoder Interface Module RTAC-0 Pulse Encoder Interface Module RTAC-0 User s Manual 3AFE 64486853 REV A EN EFFECTIVE:.5.00 00 ABB Oy. All Rights Reserved. Safety instructions
Data sheet Three-phase monitoring relay CM-PFE The CM-PFE is a three-phase monitoring relay that monitors the phase parameter phase sequence and phase failure in three-phase mains. 2CDC 251 005 S0012 Characteristics
User Manual EtherNet/IP and ControlNet to PROFIBUS PA Linking Devices Catalog Numbers 1788-EN2PAR, 1788-CN2PAR Important User Information Read this document and the documents listed in the additional resources
C13 C13 Document ID: 2CMC486004M0201 2013-06-19 Disclaimer Copyrights Trademarks Contact The information in this document is subject to change without notice and should not be construed as a commitment
Specifications Specifications Standard Features Optional Features Installation Setup Communications Power Wiring Control Wiring Keypad Software Starting and Stopping Modes Protection and Diagnostics Metering
Quick Guide Fiber Optic Cable Installation Introduction Fiber optic cables can be easily damaged if they are improperly handled or installed. It is imperative that certain procedures be followed in the
Data sheet Voltage monitoring relays CM-ESS.2 For single-phase AC/DC voltages The CM-ESS.2 is an electronic voltage monitoring relay that provides reliable monitoring of voltages as well as detection of
UniStream CPU-for-Panel Installation Guide USC-P-B10 Unitronics UniStream platform comprises control devices that provide robust, flexible solutions for industrial automation. This guide provides basic
Installation Instructions ControlNet PCI Communication Interface Card Catalog Number 9904-PCIC This document describes how to install the 9904-PCIC ControlNet TM communication interface card. Topic: Page:
Extract from the online catalog STEP-PS/1AC/12DC/1.5 Order No.: 2868567 DIN rail power supply unit 12 V DC/1.5 A, primary switched-mode, 1- phase Commercial data EAN 4046356292924 Pack 1 pcs. Customs tariff
Power Supply Guide Version 1.0 for D-Show Digidesign 2001 Junipero Serra Boulevard Daly City, CA 94014-3886 USA tel: 650 731 6300 fax: 650 731 6399 Technical Support (USA) tel: 650 731 6100 fax: 650 731
AC 800M EtherNet/IP DeviceNet Linking Device LD 800DN SP1134 Power and productivity for a better world TM AC 800M EtherNet/IP DeviceNet Linking Device LD 800DN NOTICE This document contains information
Redundancy Module QUT DIODE provides: 00% decoupling of power supplies connected in parallel Can be installed in potentially explosive areas Load currents up to 60 A supported Easy assembly by snapping
1769-SDN DeviceNet Scanner Module Catalog Numbers 1769-SDN User Manual Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment.
Characteristics three-phase network control relay RM4-T - range 200..500 V Complementary [Us] rated supply voltage Output contacts Setting accuracy of time delay Delay at power up Measuring cycle Marking
Product and Applications Description The power supply units N 125/x2 can supply DC 24 V power from an additional pair of terminals (yellowwhite). This DC 24 V output voltage can be used to power e.g. an
33.6W Power over Ethernet Waterproof Adapter PoE Plus Single Port Injector for Outdoor Application Features Compliant with the IEEE802.3at Standard -40 to +60 C Temperature Range Diagnostic LEDs Full Protection
LIEBERT VNSA Installation Sheet Description The Liebert vnsa network switch is designed for connecting multiple Ethernet-ready devices and comes in various models. The unit may have: A Liebert icom display
User Manual MicroLogix 1100 Embedded Web Server Bulletin 1763 Controllers Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical equipment.
Owner s Manual Manual Ranging MultiMeter Model 82345 CAUTION: Read, understand and follow Safety Rules and Operating Instructions in this manual before using this product.! Safety! Operation! Maintenance!
Data sheet Electronic overload relay EF65, EF96 and EF146 Electronic overload relays offer reliable protection in case of overload and phase-failure. They are the alternative to thermal overload relays.
Resistance/potiposition transducer INTERFACE Data Sheet 0807_en_05 Description PHOENIX CONTACT - 0/008 Features The slim MINI MCR-SL-R-UI... potiposition transducer has a width of only 6. mm and converts
Data sheet Electronic overload relay EF19 and EF45 Electronic overload relays offer reliable protection in case of overload and phase-failure. They are the alternative to thermal overload relays. Motor
HP UPS R1500 Generation 3 Installation Instructions Part Number 650952-001 NOTE: The rating label on the device provides the class (A or B) of the equipment. Class B devices have a Federal Communications
Perle Protocol Transparent Media Converter Modules Installation Guide C-4GPT-DSFP CM-4GPT-DSFP Part# 5500335-10 Overview This document contains instructions necessary for the installation and operation
Overview/Modes of Operation Bulletin 150 Smart Motor Controller The SMC-3 is a compact, simple to use, solid-state motor controller designed to operate 3-phase motors. It features a built-in overload relay
Installation Instructions Chassis Interface Module for 1746 Local I/O (Catalog Number 1747-PCIL) Use this document to install the Chassis Interface module for 1746 Local I/O and connect it to a PCI Bus