1 Installation Instructions MicroLogix 1100 Programmable Controllers Catalog Numbers 1763-L16AWA, 1763-L16BWA, 1763-L16BBB, 1763-L16DWD Topic Page Important User Information 4 Additional Resources 5 Overview 6 Controller Description 7 Hazardous Location Considerations 8 Mounting the Controller 10 Connecting 1762 I/O Expansion Modules 16 Wiring the Controller 17 Specifications 23
2 4 Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety Guidelines for the Application, Installation and Maintenance of Solid State Controls (Publication SGI-1.1 available from your local Rockwell Automation sales office or online at describes some important differences between solid state equipment and hard-wired electromechanical devices. Because of this difference, and also because of the wide variety of uses for solid state equipment, all persons responsible for applying this equipment must satisfy themselves that each intended application of this equipment is acceptable. In no event will Rockwell Automation, Inc. be responsible or liable for indirect or consequential damages resulting from the use or application of this equipment. The examples and diagrams in this manual are included solely for illustrative purposes. Because of the many variables and requirements associated with any particular installation, Rockwell Automation, Inc. cannot assume responsibility or liability for actual use based on the examples and diagrams. No patent liability is assumed by Rockwell Automation, Inc. with respect to use of information, circuits, equipment, or software described in this manual. Reproduction of the contents of this manual, in whole or in part, without written permission of Rockwell Automation, Inc., is prohibited. Throughout this manual, when necessary, we use notes to make you aware of safety considerations. WARNING Identifies information about practices or circumstances that can cause an explosion in a hazardous environment, which may lead to personal injury or death, property damage, or economic loss. IMPORTANT ATTENTION Identifies information that is critical for successful application and understanding of the product. Identifies information about practices or circumstances that can lead to personal injury or death, property damage, or economic loss. Attentions help you identify a hazard, avoid a hazard and recognize the consequences. SHOCK HAZARD Labels may be on or inside the equipment (for example, drive or motor) to alert people that dangerous voltage may be present. BURN HAZARD Labels may be on or inside the equipment (for example, drive or motor) to alert people that surfaces may reach dangerous temperatures.
3 5 Additional Resources Resource MicroLogix 1100 Programmable Controllers User Manual 1763-UM001 MicroLogix 1100 Instruction Set Reference Manual1763-RM001 Installation Instructions 1762-INxxx Industrial Automation Wiring and Grounding Guidelines Description A more detailed description of how to install and use your MicroLogix 1100 programmable controller and expansion I/O system. A reference manual that contains data and function files, instruction set, and troubleshooting information for MicroLogix Information on installing and using 1762 expansion I/O modules. More information on proper wiring and grounding techniques. If you would like a manual, you can: download a free electronic version from the internet: purchase a printed manual by contacting your local Allen-Bradley distributor or Rockwell Automation representative
4 6 Overview MicroLogix 1100 controllers are suitable for use in an industrial environment when installed in accordance with these instructions. Specifically, this equipment is intended for use in clean, dry environments (Pollution degree 2 (1) ) and with circuits not exceeding Over Voltage Category II (2) (IEC ). (3) Install your controller using these installation instructions. debris strip ATTENTION Do not remove the protective debris strip until after the controller and all other equipment in the panel near the controller are mounted and wiring is complete. Once wiring is complete, remove protective debris strip. Failure to remove strip before operating can cause overheating. ATTENTION Electrostatic discharge can damage semiconductor devices inside the controller. Do not touch the connector pins or other sensitive areas. (1) (2) (3) Pollution Degree 2 is an environment where, normally, only non-conductive pollution occurs except that occasionally a temporary conductivity caused by condensation shall be expected. Over Voltage Category II is the load level section of the electrical distribution system. At this level transient voltages are controlled and do not exceed the impulse voltage capability of the product s insulation. Pollution Degree 2 and Over Voltage Category II are International Electrotechnical Commission (IEC) designations.
5 7 Controller Description ESC OK Item Description 1 Output Terminal Block 2 Battery Connector 3 Bus Connector Interface to Expansion I/O 4 Battery 5 Input Terminal Block 6 LCD Display 7 LCD Display Keypad (ESC, OK, Up, Down, Left, Right) 8 Status LEDs 9 Memory Module Port Cover (1) -or- Memory Module (2) 10 DIN Rail Latches 11 RS-232/485 Communication Port (Channel 0, isolated) 12 Ethernet Port (Channel 1) (1) Shipped with controller. (2) Optional equipment.
6 8 Catalog Number Description Input Power Digital Inputs Analog Inputs 1763-L16AWA 120/240V ac (10) 120V ac (2) voltage input 1763-L16BWA 120/240V ac (6) 24V dc (4) high-speed 24V dc (1) 1763-L16BBB 24V dc (6) 24V dc (4) high-speed 24V dc (1) 1763-L16DWD 12/24V dc (6) 12/24V dc (4) high-speed 12/24V dc (1) V dc (2) voltage input V dc (2) voltage input V dc (2) voltage input V dc Digital Outputs (6) relay All individually isolated (6) relay All individually isolated (2) relay (isolated) (2) 24V dc FET (2) high-speed 24V dc FET (6) relay All individually isolated Comm. Ports (1) RS-232/485 combo (isolated) (1) Ethernet (1) RS-232/485 combo (isolated) (1) Ethernet (1) RS-232/485 combo (isolated) (1) Ethernet (1) RS-232/485 combo (isolated) (1) Ethernet (1) The 4 high-speed inputs (inputs 0 through 3) can be used for pulse latching or higher speed counting. Refer to Input Specifications on page 25 and the MicroLogix 1100 Instruction Set Reference Manual, publication 1763-RM001, for more information. Hazardous Location Considerations This equipment is suitable for use in Class I, Division 2, Groups A, B, C, D or non-hazardous locations only. The following WARNING statement applies to use in hazardous locations.
7 9 WARNING EXPLOSION HAZARD Substitution of components may impair suitability for Class I, Division 2. Do not replace components or disconnect equipment unless power has been switched off. Do not connect or disconnect components unless power has been switched off. This product must be installed in an enclosure. All cables connected to the product must remain in the enclosure or be protected by conduit or other means. All wiring must comply with N.E.C. article (b). The interior of the enclosure must be accessible only by the use of a tool. For applicable equipment (for example, relay modules), exposure to some chemicals may degrade the sealing properties of the materials used in these devices: Relays, epoxy It is recommended that you periodically inspect these devices for any degradation of properties and replace the module if degradation is found.
8 10 Use only the following communication cables in Class I, Division 2 hazardous locations. Environment Classification Class I, Division 2 Hazardous Environment Communication Cables 1761-CBL-AC00 Series C or later 1761-CBL-AM00 Series C or later 1761-CBL-AP00 Series C or later 1761-CBL-PM02 Series C or later 1761-CBL-HM02 Series C or later 1761-CBL-PH02 Series A or later 1761-CBL-AH02 Series A or later 2707-NC9 Series C or later 1763-NC01 Series A or later ATTENTION UNSUPPORTED CONNECTION Do not connect a MicroLogix 1100 controller to another MicroLogix family controller such as MicroLogix 1000, MicroLogix 1200, or MicroLogix 1500 using a 1761-CBL-AM00 (8-pin mini-din to 8-pin mini-din) cable or equivalent. This type of connection will cause damage to the RS-232/485 communication port (Channel 0) of the MicroLogix 1100 and/or the controller itself. Communication pins used for RS-485 communications are alternately used for 24V power on the other MicroLogix controllers. Mounting the Controller General Considerations Most applications require installation in an industrial enclosure to reduce the effects of electrical interference and environmental exposure. Locate your controller as far as possible from power lines, load lines, and other sources of electrical noise such as hard-contact switches, relays, and ac motor drives. For more information on proper grounding guidelines, see the Industrial Automation Wiring and Grounding Guidelines, publication
9 11 ATTENTION Vertical mounting is not supported due to thermal considerations. ATTENTION Be careful of metal chips when drilling mounting holes for your controller or other equipment within the enclosure or panel. Drilled fragments that fall into the controller could cause damage. Do not drill holes above a mounted controller if the protective debris strips have been removed. Mounting Dimensions C A B 1763-L16AWA, 1763-L16BWA, 1763-L16BBB, 1763-L16DWD Dimension L16AWA L16BWA L16BBB L16DWD A B C 90 mm (3.5 in.) 110 mm (4.33 in.) 87 mm (3.43 in.)
10 12 Controller Spacing The controller mounts horizontally, with the expansion I/O extending to the right of the controller. Allow 50 mm (2 in.) of space on all but the right side for adequate ventilation, as shown below. Top Side ESC OK Bottom DIN Rail Mounting The maximum extension of the latch is 14 mm (0.55 in.) in the open position. A flat-blade screwdriver is required for removal of the controller. The controller can be mounted to EN x7.5 or EN x15 DIN rails. DIN rail mounting dimensions are shown below. B A C Dimension A B C Height 90 mm (3.5 in.) 27.5 mm (1.08 in.) 27.5 mm (1.08 in.)
11 13 Follow these steps to install your controller on the DIN rail. 1. Mount your DIN rail. (Make sure that the placement of the controller on the DIN rail meets the recommended spacing requirements. See Controller Spacing on page 12. Refer to the mounting template inside the back cover of this document.) 2. If it is open, close the DIN latch. 3. Hook the top slot over the DIN rail. 4. While pressing the controller down against the top of the rail, snap the bottom of the controller into position. 5. Leave the protective debris strip attached until you are finished wiring the controller and any other devices. Follow these steps to remove your controller from the DIN rail. 1. Place a flat-blade screwdriver in the DIN rail latch at the bottom of the controller. 2. Holding the controller, pry downward on the latch until the latch locks in the open position. 3. Repeat steps 1 and 2 for the second DIN rail latch. 4. Unhook the top of the DIN rail slot from the rail. ESC OK open closed
12 14 Panel Mounting Mount to panel using #8 or M4 screws. Follow these steps to install your controller using mounting screws. 1. Remove the mounting template from inside the back cover of this document. 2. Secure the template to the mounting surface. (Make sure your controller is spaced properly. See Controller Spacing on page 12.) 3. Drill holes through the template. 4. Remove the mounting template. 5. Mount the controller. Mounting Template 6. Leave the protective debris strip in place until you are finished wiring the controller and any other devices Using the Battery The MicroLogix 1100 controller is equipped with a replaceable battery. The Battery Low indicator on the LCD display of the controller shows the status of the replaceable battery. When the battery is low, the indicator is set (displayed as a solid rectangle). This means that either the battery wire connector is disconnected, or the battery may fail within 2 days if it is connected. IMPORTANT The MicroLogix 1100 controller ships with the battery wire connector connected. Ensure that the battery wire connector is inserted into the connector port if your application needs battery power. For example, when using a real-time clock (RTC), or to store the program in the controller s memory for an extended period of time while the power is removed. Refer to the MicroLogix 1100 Programmable Controller User Manual, publication 1763-UM001, for more information on installation, handling, usage, storage, and disposal of the battery.
13 15 Follow these steps to connect the replaceable battery. 1. Insert the replaceable battery wire connector into the battery connector. 2. Secure the battery connector wires along the wire guide as shown below. Replaceable Battery Pocket Replaceable Battery Wire Guide Battery Connector Wires ESC OK Battery Wire Connector Battery Connector
14 16 Connecting 1762 I/O Expansion Modules ATTENTION Remove power to the system before installing or removing expansion I/O or damage to the controller may result. Connect 1762 I/O after mounting the controller. 1. Remove the expansion port cover to install expansion I/O modules. 2. Plug the ribbon cable connector into the bus connector. 3. Replace the cover as shown below. The MicroLogix 1100 controller is designed to support up to any four 1762 expansion I/O modules. For detailed information on using expansion I/O, refer to the installation instructions for your expansion module.
15 17 Wiring the Controller Terminal Block Layouts TIP The shading in the following terminal block illustrations indicates which terminals are tied to which commons L16AWA Input Terminal Block NOT NOT AC USED USED COM I/0 I/1 I/2 I/3 AC COM I/4 I/5 I/6 I/7 I/8 I/9 IA COM IV1(+) IV2(+) L1 L2/N VAC NOT USED VAC O/0 VAC O/1 VAC O/2 VAC O/3 VAC O/4 VAC O/5 NOT USED Output Terminal Block 1763-L16BWA Input Terminal Block DC OUT DC + 24V - COM I/0 I/1 I/2 I/3 DC COM I/4 I/5 I/6 I/7 I/8 I/9 IA COM IV1(+) IV2(+) L1 L2/N VAC NOT USED VAC O/0 VAC O/1 VAC O/2 VAC O/3 VAC O/4 VAC O/5 NOT USED Output Terminal Block 1763-L16BBB Input Terminal Block NOT NOT DC USED USED COM I/0 I/1 I/2 I/3 DC COM I/4 I/5 I/6 I/7 I/8 I/9 IA COM IV1(+) IV2(+) + 24V - DC IN NOT USED VAC O/0 VAC O/1 NOT USED NOT USED DC O/2 O/3 24V+ O/4 O/5 DC 24V- NOT USED Output Terminal Block
16 L16DWD Input Terminal Block NOT NOT DC USED USED COM I/0 I/1 I/2 I/3 DC COM I/4 I/5 I/6 I/7 I/8 I/9 IA COM IV1(+) IV2(+) + 12/24V - DC IN NOT USED VAC O/0 VAC O/1 VAC O/2 VAC O/3 VAC O/4 VAC O/5 NOT USED Output Terminal Block Wire Requirements Wire Type Wire Size (2 wire maximum per terminal) 1 wire per terminal 2 wire per terminal Solid Cu-90 C (194 F) AWG AWG Stranded Cu-90 C (194 F) AWG AWG Wiring torque = 0.56 Nm (5.0 in-lb) rated. ATTENTION Be careful when stripping wires. Wire fragments that fall into the controller could cause damage. Once wiring is complete, be sure the controller is free of all metal fragments before removing the protective debris strip. Failure to remove the strip before operating can cause overheating. Wiring Recommendation The MicroLogix 1100 controllers have screw-cage clamps on the input and output terminal blocks. With screw-cage clamp terminal blocks, there is no need to attach additional hardware such as a spade lug to the wire, or use a finger-safe cover. Follow these steps to wire the terminal block. 1. Strip the end of the wire. The recommended length for the stripped end of the wire is 11.0 mm (0.440 in.).
17 19 2. Insert it into an open clamp. 3. Using a small, flat-blade screwdriver, tighten the terminal screw. To ensure that the wire conductor is secured inside the clamp, tighten it to the rated torque, 0.56 Nm (5.0 in-lb). The diameter of the terminal screw head is 5.5 mm (0.220 in.). Screw-cage clamp terminal block Surge Suppression ATTENTION Inductive load devices such as motor starters and solenoids require the use of some type of surge suppression to protect the controller output. Switching inductive loads without surge suppression can significantly reduce the life of relay contacts or damage transistor outputs. By using suppression, you also reduce the effects of voltage transients caused by interrupting the current to that inductive device, and prevent electrical noise from radiating into system wiring. Refer to the MicroLogix 1100 Programmable Controller User Manual, publication 1763-UM001, for more information on surge suppression.
18 20 Grounding the Controller In solid-state control systems, grounding and wire routing helps limit the effects of noise due to electromagnetic interference (EMI). Run the ground connection from the ground screw of the controller to the ground bus prior to connecting any devices. Use AWG #14 wire. For ac-powered controllers, this connection must be made for safety purposes. ATTENTION All devices connected to the RS-232/485 communication port must be referenced to controller ground, or be floating (not referenced to a potential other than ground). Failure to follow this procedure may result in property damage or personal injury. For the 1763-L16BWA controller: The COM of the sensor supply is also connected to chassis ground internally. The 24V dc sensor power source should not be used to power output circuits. It should only be used to power input devices. For 1763-L16BBB and 1763-L16DWD controllers: The NEUT or common terminal of the power supply is also connected to chassis ground internally. You must also provide an acceptable grounding path for each device in your application. For more information on proper grounding guidelines, refer to the Industrial Automation Wiring and Grounding Guidelines, publication
19 21 Wiring Your Analog Channels Analog input circuits can monitor voltage signals and convert them to serial digital data. Sensor 2 (V) Voltage Sensor 1 (V) Voltage IA COM IV1(+) IV2(+) The controller does not provide loop power for analog inputs. Use a power supply that matches the transmitter specifications as shown below. 2-Wire Transmitter Power Supply Wire Transmitter Power Supply + - Transmitter + - Transmitter Supply Signal GND Controller IV1(+) or IV2(+) IA COM Controller IV1(+) or IV2(+) IA COM 4-Wire Transmitter Power Supply + - Transmitter Supply Signal Controller IV1(+) or IV2(+) IA COM Minimizing Electrical Noise on Analog Channels Inputs on analog channels employ digital high-frequency filters that significantly reduce the effects of electrical noise on input signals. However, because of the variety of applications and environments where analog controllers are installed and operated, it is impossible to ensure that all environmental noise will be removed by the input filters. Several specific steps can be taken to help reduce the effects of environmental noise on analog signals:
20 22 install the MicroLogix 1100 system in a properly rated (NEMA) enclosure. Make sure that the MicroLogix 1100 system is properly grounded. use Belden cable #8761 for wiring the analog channels, making sure that the drain wire and foil shield are properly earth grounded. route the Belden cable separately from any ac wiring. Additional noise immunity can be obtained by routing the cables in grounded conduit. Grounding Your Analog Cable Use shielded communication cable (Belden #8761). The Belden cable has two signal wires (black and clear), one drain wire, and a foil shield. The drain wire and foil shield must be grounded at one end of the cable. Insulation Foil Shield Black Wire Clear Wire Drain Wire IMPORTANT Do not ground the drain wire and foil shield at both ends of the cable.
21 23 Specifications General Specifications Description L16AWA L16BWA L16BBB L16DWD Dimensions Shipping Weight Number of I/O Power Supply Voltage Heat Dissipation Power Supply Inrush Current Power Consumption 24V dc Sensor Power Input Circuit Type Output Circuit Type Pilot Duty Rating Temperature, Operating Temperature, Storage Relative Humidity Vibration Shock, Operating Height: 90 mm (3.5 in.), 104 mm (4.09 in.) (with DIN latch open) Width: 110 mm (4.33 in.), Depth: 87 mm (3.43 in.) 0.9 kg (2.0 lbs) 12 inputs (10 digital and 2 analog) and 6 outputs V ac (-15%, +10%) at Hz 24V dc (-15%, +10%) Class 2 SELV 12V to 24V dc ( -15%, +10%) Class 2 SELV Refer to the MicroLogix 1100 Programmable Controllers User Manual, Publication 1763-UM V ac: 25 A for 8 ms 240V ac: 40 A for 4 ms 46 VA 52 VA 35W none Digital: 120V ac Analog: V dc 250 ma at 24V DC 400 µf max. Digital: 24V dc sink/source (standard and high-speed) Analog: V dc 24V dc: 15 A for 20 ms none Digital: 24V dc sink/source (standard and high-speed) Analog: V dc Relay Relay Relay/FET Relay Ordinary location B300, R150 Hazardous location C300, R C ( F) C ( F) % non-condensing Operating: Hz, 5 g, in. max. peak-to-peak, 2 hours each axis Relay Operation: 1.5 g 30 g; 3 pulses each direction, each axis Relay Operation: 10 g Digital: 12/24V dc sink/source (standard and high-speed) Analog: V dc
22 24 General Specifications Description L16AWA L16BWA L16BBB L16DWD Shock, Nonoperating Terminal Screw Torque 50 g panel mounted (40 g DIN Rail mounted); 3 pulses each direction, each axis 0.56 Nm (5.0 in-lb) rated Certifications UL Listed Industrial Control Equipment for use in Class 1, Division 2, Hazardous Locations, Groups A, B, C, D C-UL Listed Industrial Control Equipment for use in Canada CE marked for all applicable directives RCM marked for all applicable acts EAC certified for: Russian Customs Union TR CU 020/2011 EMC Technical Regulation, Russian Customs Union TR CU 004/2011 LV Technical Regulation ESD Immunity EN kv contact, 8 kv air, 4 kv indirect Radiated RF Immunity Fast Transient Immunity Surge Transient Immunity Conducted RF Immunity EN V/m, 26 to 1000 MHz (alternatively, 80 to 1000 MHz), 80% amplitude modulation, +900 MHz keyed carrier EN kv, 5 khz communications cable such as EtherNet, RS-232, and RS-485: 1 kv, 5 khz EN Unshielded communications cable: 2 kv CM (common mode), 1 kv DM (differential mode) Shielded communications cable: 1 kv galvanic gun I/O: 2 kv CM (common mode), 1 kv DM (differential mode) ac Power Supply Input: 4 kv CM (common mode), 2 kv DM (differential mode) dc Power Supply Input: 500V CM (common mode), 500V DM (differential mode) ac/dc Auxiliary Output: 500V CM (common mode), 500V DM (differential mode) EN V, 150 khz...80 MHz
23 25 General Specifications Description L16AWA L16BWA L16BBB L16DWD Conducted Emissions Radiated Emissions EN ac Power Supply Input: 150 khz...30 MHz EN MHz Line Related Tests EN ac Power Supply Input: voltage drop: -30% for 10 ms, -60% for 100 ms voltage interrupt: at voltage greater than -95% for 5 secs. voltage fluctuation: +10% for 15 minutes, -10% for 15 minutes dc Power Supply Input: voltage fluctuation: +20% for 15 minutes, -20% for 15 minutes Input Specifications Digital Inputs Description 1763-L16AWA 1763-L16BWA, -L16BBB On-State Voltage Range Off-State Voltage Range Operating Frequency On-State Current: V ac V dc V ac Inputs 0 through 3 (4 high-speed dc inputs) ( V dc (+10%) at 65 C/149 F) ( V dc (+25%) at 30 C/86 F) 0...5V dc Inputs 4 and higher (6 standard dc inputs) V dc ( V dc (+10%) at 65 C/149 F) ( V dc (+25%) at 30 C/86 F) Hz 0 Hz...20 khz 0 Hz...40 khz (1) 0 Hz...1 khz (scan time dependent) minimum nominal maximum 5.0 ma at 79V ac 12 ma at 120V ac 2.5 ma at 14V dc 8.8 ma at 24V dc 12.0 ma at 30V dc 2.0 ma at 10V dc 8.5 ma at 24V dc 12.0 ma at 30V dc 16.0 ma at 132V ac
24 26 Digital Inputs Description 1763-L16AWA 1763-L16BWA, -L16BBB Off-State Leakage Current Nominal Impedance Inrush Current (max.) at 120V ac 2.5 ma max. 1.5 ma max. 12 kω at 50 Hz 10 kω at 60 Hz Inputs 0 through 3 (4 high-speed dc inputs) 250 ma Not Applicable 3.1 kω 3.1 kω Inputs 4 and higher (6 standard dc inputs) (1) OS Series B FRN 4 or later Digital Input Specifications for 1763-L16DWD Description 1763-L16DWD Inputs 0 through 3 (4 high-speed dc inputs) On-State Voltage Range V dc at 65 C/149 F) ( V dc at 30 C/86 F) Off-State Voltage Range 0...5V dc Operating Frequency 0 Hz...40 khz (1) Inputs 4 and higher (6 standard dc inputs) 0 Hz...1 khz On-State Current: minimum 2.0 ma at 10V dc nominal 8.5 ma at 24V dc maximum 12.0 ma at 30V dc Off-State Leakage Current 1.5 ma max. Nominal Impedance 2.61 kω 3.1 kω Maximum Inrush Current Not Applicable (1) OS Series B FRN 4 or later.
25 27 Analog Inputs Description 1763-L16AWA, -L16BWA, -L16BBB, -L16DWD Voltage Input Range V dc - 1 LSB Type of Data 10-bit unsigned integer Input Coding (0 to 10.0V dc - 1 LSB) ,023 Voltage Input Impedance 210 kω Input Resolution 10 bit Non-linearity ±0.5% of full scale Overall Accurarcy ±0.5% of full scale C ( F) Voltage Input Overvoltage Protection Field Wiring to Logic Isolation 10.5V dc Non-isolated with logic Output Specifications For Hazardous Locations Applications (Class I, Division 2, Groups A, B, C, D) General Description L16AWA, -L16BWA, -L16DWD -L16BBB Relay and FET Outputs Maximum Controlled Load 1080 VA 360 VA Maximum Continuous Current: Current per Group Common 3A 3A Current per Controller at 150V max 18 A or total of per-point loads, whichever is less Relay Outputs at 240V max 18 A or total of per-point loads, whichever is less Turn On Time/Turn Off Time 10 msec (maximum) (1) Relay life - Electrical (Resistive Load) Relay life - Mechanical Load Current Refer to Relay Life Chart 10,000,000 cycles 10 ma (minimum) (1) Scan time dependent.
26 28 Relay Contact Ratings (1) Maximum Volts Amperes Amperes Volt-Amperes Make Break Continuous Make Break 240V AC (2) 7.5 A 0.75 A 2.5 A 1800 VA 180 VA 120V AC (3) 15.0 A 1.5 A 2.5 A 1800 VA 180 VA 125V DC (4) 0.22 A 1.0 A 28 VA (1) Pilot Duty Rating: (ordinary location) B300, R150. (hazardous location) C300, R150. (2) For AC voltage applications lower than 240V AC but higher than 120V AC, the maximum make and break ratings are to be obtained by dividing the volt-amperes rating by the application voltage. (3) For AC voltage applications lower than 120V AC, the maximum make current is to be the same as for 120V AC, and the maximum break current is to be obtained by dividing the break volt-amperes rating by the application voltage, but the currents are not to exceed the thermal continuous current. (4) For DC voltage applications lower than 125V DC, the make/break ampere rating for relay contacts can be determined by dividing the volt-ampere rating by the applied DC voltage but the current values are not to exceed the thermal continuous current. ATTENTION Do not exceed the Current per group common specification. Output Specifications For Ordinary (Non-Hazardous) Locations only General Description L16AWA, -L16BWA, -L16DWD -L16BBB Relay and FET Outputs Maximum Controlled Load 1440 VA 720 VA Maximum Continuous Current: Current per Group Common 5A (1) 5A Current per Controller at 150V max 30 A or total of per-point loads, whichever is less at 240V max 20 A or total of per-point loads, whichever is less
27 29 General Description L16AWA, -L16BWA, -L16DWD -L16BBB Relay Outputs Turn On Time/Turn Off Time 10 msec (maximum) (2) Relay life - Electrical (Resistive Load) Relay life - Mechanical Load Current Refer to Relay Life Chart 10,000,000 cycles 10 ma (minimum) (1) (2) 3.0 A above 40 C. Scan time dependent. Relay Contact Ratings (1) Maximum Volts Amperes Amperes Volt-Amperes Make Break Continuous Make Break 240V AC (2) 15.0 A 1.5 A 5.0 A (5) 3600 VA 360 VA 120V AC (3) 30.0 A 3.0 A 3600 VA 360 VA 125V DC (4) 0.22 A 1.0 A 28 VA (1) (2) Pilot Duty Rating: (ordinary location) B300, R150. (hazardous location) C300, R150. For AC voltage applications lower than 240V AC but higher than 120V AC, the maximum make and break ratings are to be obtained by dividing the volt-amperes rating by the application voltage. (3) For AC voltage applications lower than 120V AC, the maximum make current is to be the same as for 120V AC, and the maximum break current is to be obtained by dividing the break volt-amperes rating by the application voltage, but the currents are not to exceed the thermal continuous current. (4) For DC voltage applications lower than 125V DC, the make/break ampere rating for relay contacts can be determined by dividing the volt-ampere rating by the applied DC voltage but the current values are not to exceed the thermal continuous current. (5) 3.0 A above 40 C. ATTENTION Do not exceed the Current per group common specification.
28 30 Relay Life Chart 1000 Number of operations (x 10 3 ) resistive load 250 VAC resistive load 250 VAC induction load (cosφ=0.4) Switching capacity(a) BBB FET Output Specifications Description General Operationl High Speed Operation (1) (Output 2 and 3 Only) Power Supply Voltage 24V dc (-15%, +10%) On-State Voltage Drop: at maximum load current at maximum surge current Current Rating per Point maximum load minimum load maximum leakage 1V dc 2.5V dc See graphs below 1.0 ma 1.0 ma Not Applicable Not Applicable 100 ma 10 ma 1.0 ma
29 BBB FET Output Specifications Description General Operationl High Speed Operation (1) (Output 2 and 3 Only) Maximum Output Current (temperature dependent): FET Current per Point (1763-L16BBB) FET Total Current (1763-L16BBB) A, 30 C (86 F) Current (Amps) Valid Range 0.75A, 65 C (149 F) Current (Amps) Valid Range 3.0A, 30 C (86 F) 1.5A, 65 C (149 F) 10 C (50 F) 30 C (86 F) 50 C (122 F) 70 C (158 F) 80 C (176 F) 10 C (50 F) 30 C (86 F) 50 C (122 F) 70 C (158 F) 80 C (176 F) Temperature Temperature Surge Current per Point: peak current maximum surge duration maximum rate of repetition at 30 C (86 F) maximum rate of repetition at 65 C (149 F) 4.0 A 10 ms once every second once every 2 seconds Not Applicable Not Applicable Not Applicable Not Applicable Turn-On Time (maximum) 0.1 ms 6 µs Turn-Off Time (maximum) 1.0 ms 18 µs Repeatability (maximum) Not Applicable 2 µs Drift (maximum) Not Applicable 1 µs per 5 C (9 F) (1) Output 2 and 3 are designed to provide increased functionality over the other FET outputs. Output 2 and 3 may be used like the other FET transistor outputs, but in addition, within a limited current range, they may be operated at a higher speed. Output 2 and 3 also provide a pulse train output (PTO) or pulse width modulation output (PWM) function.
30 32 Working Voltage Working Voltage (1763-L16AWA) Description Power Supply Input to Backplane Isolation Input Group to Backplane Isolation Input Group to Input Group Isolation Output Group to Backplane Isolation Output Group to Output Group Isolation 1763-L16AWA Verified by one of the following dielectric tests: 1836V ac for 1 second or 2596V dc for 1 second 265V ac Working Voltage (IEC Class 2 reinforced insulation) Verified by one of the following dielectric tests:1517v ac for 1 second or 2145V dc for 1 second 132V ac Working Voltage (IEC Class 2 reinforced insulation) Verified by one of the following dielectric tests:1517v ac for 1 second or 2145V dc for 1 second 132V ac Working Voltage (basic insulation) Verified by one of the following dielectric tests: 1836V ac for 1 second or 2596V dc for 1 second 265V ac Working Voltage (IEC Class 2 reinforced insulation) Verified by one of the following dielectric tests: 1836V ac for 1 second or 2596V dc for 1second 265V ac Working Voltage (basic insulation), 150V ac Working Voltage (IEC Class 2 reinforced insulation) Working Voltage (1763-L16DWD) Description Input Group to Backplane Isolation and Input Group to Input Group Isolation Output Group to Backplane Isolation Output Group to Output Group Isolation 1763-L16DWD Verified by one of the following dielectric tests: 1200V ac for 1 second or 1697V dc for 1 second 75V dc Working Voltage (IEC Class 2 reinforced insulation) Verified by one of the following dielectric tests: 1836V ac for 1 second or 2596V dc for 1 second 265V ac Working Voltage (IEC Class 2 reinforced insulation). Verified by one of the following dielectric tests: 1836V ac for 1 second or 2596V dc for 1 second 265V ac Working Voltage (basic insulation) 150V Working Voltage (IEC Class 2 reinforced insulation)
32 mm (4.295 in.) mm (1.016 in.) 4.6 mm (0.181 in.) mm (3.740 in.) DIN rail center line. Ligne médiane du rail DIN. Mittellinie der DIN-Schiene. Línea central del riel DIN. Linea centrale della guida DIN. linha de centro do trilho DIN. Expansion I/O d'extension d'e/s E/A - Erweiterungsmodule l'espansione dei moduli I/O mm (3.937 in.) de expansión de E/S de expa nsão de E/S 1763-L16AWA 1763-L16BWA 1763-L16BBB
34 Rockwell Automation Support Rockwell Automation provides technical information on the Web to assist you in using its products. At you can find technical manuals, a knowledge base of FAQs, technical and application notes, sample code and links to software service packs, and a MySupport feature that you can customize to make the best use of these tools. For an additional level of technical phone support for installation, configuration and troubleshooting, we offer TechConnect support programs. For more information, contact your local distributor or Rockwell Automation representative, or visit Installation Assistance If you experience a problem with a hardware module within the first 24 hours of installation, please review the information that's contained in this manual. You can also contact a special Customer Support number for initial help in getting your module up and running: United States Monday Friday, 8am 5pm EST Outside United States Please contact your local Rockwell Automation representative for any technical support issues. New Product Satisfaction Return Rockwell Automation tests all of its products to ensure that they are fully operational when shipped from the manufacturing facility. However, if your product is not functioning and needs to be returned, follow these procedures. United States Outside United States Contact your distributor. You must provide a Customer Support case number (see phone number above to obtain one) to your distributor in order to complete the return process. Please contact your local Rockwell Automation representative for return procedure. Allen-Bradley, Rockwell Automation, MicroLogix and TechConnect are trademarks of Rockwell Automation, Inc. Trademarks not belonging to Rockwell Automation are property of their respective companies. Supersedes Publication 1763-IN001B-EN-P - September 2007 Copyright 2015 Rockwell Automation, Inc. All rights reserved.
Installation Instructions Universal Serial Bus (USB) to DH-485 Interface Converter Catalog Number 1747-UIC Contents Overview..................................................3 Computer and Operating System
Installation Instructions USB-to-Data Highway Plus Cable Catalog Number 1784-U2DHP Topic Page Important User Information 2 Environment and Enclosure 3 Install the Cable 5 Configure the DH+ Node Address
MicroLogix 1100 Programmable Controllers Bulletin 1763 Controllers and 1762 Expansion I/O User Manual Important User Information Solid state equipment has operational characteristics differing from those
Micro800 Programmable Controllers Bulletin 2080 Selection Guide Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety
MicroLogix 1200 Programmable Controllers Bulletin 1762 Controllers and Expansion I/O User Manual Important User Information Solid state equipment has operational characteristics differing from those of
MILLENIUM Table of contents 1. INTRODUCTION 1 2. HARDWARE DESCRIPTION 2 3. INSTALLATION 5 4. CONNECTION 6 5. USER SAFETY AND PROTECTION OF EQUIPMENT 8 1. Introduction The MILLENIUM series has been designed
Type: EASY719 DC RC Article.: 274119 Ordering information Relay outputs Quantity 6 Power supply V DC 24 V DC Description 12 digital inputs (4 inputs available as analog inputs) 6 relay outputs LCD display
Installation Instructions SLC 500 Analog Input Module (Catalog Number 1746NI8) Inside Important User Information... 2 For More Information... 3 Hazardous Location Considerations... 4 Environnements dangereux...
Overview/Modes of Operation Bulletin 150 Smart Motor Controller The SMC-3 is a compact, simple to use, solid-state motor controller designed to operate 3-phase motors. It features a built-in overload relay
Specifications Specifications Standard Features Optional Features Installation Setup Communications Power Wiring Control Wiring Keypad Software Starting and Stopping Modes Protection and Diagnostics Metering
Installation Instructions Hard Disk Drive (HDD) Catalog Number 6189V-35HDDST80, 6189V-35HDDST160 Topic Page About This Publication 1 Important User Information 2 Electrostatic Discharge (ESD) Precautions
Backup Scanner Module Catalog Number 1747-BSN Installation Instructions 2 Backup Scanner Module Important User Information Because of the variety of uses for the products described in this publication,
38 Relay interface modules 0.1-2 - 3-5 - 6-8 - 16 A 38 Common features Instant ejection of relay by plastic retaining clip Integral coil indication and protection circuit 6.2 mm wide EMR - DC, AC or AC/DC
Technical Data 1756 ControlLogix Power Supplies Specifications Standard Power Supplies Catalog Numbers 1756-PA72, 1756-PA75, 1756-PB72, 1756-PB75, 1756-PC75, 1756-PH75 Standard Slim Power Supplies Catalog
Micro800 Programmable Controller Family Bulletin 2080 Selection Guide Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment.
E031026 000823 Process modules Digital input PMI for inputs for 120 V AC inputs PMI Input E4, E5, GND L- PMI 120 V AC Input E4, E5, Common C E6, E7, GND L- E6, E7, Common C LEDs for the inputs operation
Highlights & Features Protection Class II, Double Isolation (No Earth connection is required) Universal AC input voltage without power de-rating Efficiency > 87.0% @ 115Vac & 230Vac NEC Class 2 / Limited
38 Series - Relay interface modules 0.1-2 - 3-5 - 6-8 - 16 A 38 SERIES Common features Instant ejection of relay by plastic retaining clip Integral coil indication and protection circuit EMR Electromechanical
Power Supply Unit, Primary Switched, Narrow Design MINI POWER provides: Extra narrow design with widths of 22.5 mm, 45 mm, and 67.5 mm (0.886, 1.772, and 2.657 in.) Global use due to a wide-range input
Data sheet Electronic timer CT-AHD.12 OFF-delayed with 1 c/o (SPDT) contact The CT-AHD.12 is an electronic time relay with OFF-delay. It is from the CT-D range. With their MDRC profile and a width of only
MasterINTERFACE 39 Series - Relay interface modules Common features Space saving 6.2 mm wide Connections for 16-way jumper link Integral coil indication and protection circuit Secure retention and easy
Telephone- and leased line modem for industrial applications TD-36 Modem for industrial PSTN- and leased line applications The TD-36 is an analogue V.34 PSTN modem as well as an industrial 2-wire leased
Product datasheet Characteristics TM7BDM8B expansion block - TM7 - IP67-8 DI/DO - 24V DC - 0.5 A - M8 connector Main Range of product Product or component type Range compatibility Enclosure material Bus
Highlights & Features Protection Class II, Double Isolation (No Earth connection is required) Universal AC input voltage and full power up to 55 C Power will not de-rate for the entire input voltage range
SDC-H Duct Humidity Transmitter Features Replaceable sensor element Humidity measurement for air ducts Minimum and maximum value memory 0 0V, 0 0mA or 0V, 4 0mA measuring signals selectable with jumpers
8 172 TX-I/O Digital input modules TXM1.8D TXM1.16D Two fully compatible versions: TXM1.8D: 8 inputs, each with a three-color LED (green, yellow or red) TXM1.16D: As TXM1.8X, but 16 inputs, each with a
Safety Technique SAFEMASTER Emergency Stop Module BG 5924, IP 5924 Your Advantages For safety application up to PL e / Cat. 4 e.g. SIL 3 Manual or automatic start 0225592 BG 5924 IP 5924 Product Description
ata sheet Analog signal converters CC-E I/I Current / current isolators The CC-E I/I is an isolator for the electrical isolation of current signals without auxiliary supply. It allows the isolation between
SDN-P DIN Rail Series The SDN DIN Rail power supplies provide industry leading performance. Sag Immunity, transient suppression and noise tolerant, the SDN series ensures compatibility in demanding applications.
MCR1900 Media Converter 19-Slot Chassis Installation Guide Part #5500304-11 Copyright Statement This document must not be reproduced in any way whatsoever, either printed or electronically, without the
Square D Clipsal DIN-Rail Four-Channel Auxiliary Input Unit SLCLE5504AUX for Use with Wired C-Bus Networks Instruction Bulletin Retain for future use. Square D Clipsal DIN-Rail Four-Channel Auxiliary Input
Samba OPLC SM35-J-R20 Installation Guide The Unitronics SM35-J-R20 offers the following onboard I/Os: 12 Digital Inputs, configurable via wiring to include: 1 HSC/Shaft-encoder Input, 2 Analog inputs (only
Extract from the online catalog STEP-PS/1AC/12DC/1.5 Order No.: 2868567 DIN rail power supply unit 12 V DC/1.5 A, primary switched-mode, 1- phase Commercial data EAN 4046356292924 Pack 1 pcs. Customs tariff
, 2CDG 110 084 R0011 2CDC 071 112 F0008 The Fan Coil Actuator is a modular installation device (MDRC) in pro M design. It is intended for installation in the distribution board on 35 mm mounting rails.
Photoelectrics, Background Suppression reflective with IR light Main features Description The PD30ET... stainless steel sensors are built with high-quality materials and designed for harsh environments.
LIEBERT VNSA Installation Sheet Description The Liebert vnsa network switch is designed for connecting multiple Ethernet-ready devices and comes in various models. The unit may have: A Liebert icom display
Safety Relay Unit ( I/O Unit Type) CQM1-SF200/CS1W-SF200 CSM_CQM1-SF200_CS1W-SF200_DS_E_2_1 A Safety Relay Unit That Functions as a I/O Unit. Less Installation Space and Wiring Required. Safety Relay Unit
80 Series - Modular timers 16 A Features 80.11 Multi-function and mono-function timer range - Multi-function & multi-voltage 80.11 - On-delay, multi-voltage 17.5 mm wide Six time scales from 0.1s to 24h
Owner's Manual AutoRanging Digital MultiMeter Model No. 82139 CAUTION: Read, understand and follow Safety Rules and Operating Instructions in this manual before using this product. Safety Operation Maintenance
C13 C13 Document ID: 2CMC486004M0201 2013-06-19 Disclaimer Copyrights Trademarks Contact The information in this document is subject to change without notice and should not be construed as a commitment
LIGHTING CONTROL PANELS 4 AND 8 RELAYS INSTALLATION INSTRUCTIONS INSTALLATION OVERVIEW The installation instructions contained in this document are provided as a guide for proper and reliable installation.
Outdoor 33.6W Dual Port Passive Power-over-Ethernet Midspan For External Security Cameras and Wireless Access Points Features SELV Compliant No Detection Passive Injector Gigabit Compatible Full Protection
User Manual MicroLogix 1400 Programmable Controllers Bulletin 1766 Controllers and 1762 Expansion I/O Important User Information Solid-state equipment has operational characteristics differing from those
Data sheet Three-phase monitoring relay CM-PFE The CM-PFE is a three-phase monitoring relay that monitors the phase parameter phase sequence and phase failure in three-phase mains. 2CDC 251 005 S0012 Characteristics
T7560A,B,C Digital Wall Module HONEYWELL EXCEL 5000 OPEN SYSTEM BEFORE INSTALLATION All wiring must comply with local electrical codes and ordinances or as specified on installation wiring diagrams. Digital
33.6W Power over Ethernet Waterproof Adapter PoE Plus Single Port Injector for Outdoor Application Features Compliant with the IEEE802.3at Standard -40 to +60 C Temperature Range Diagnostic LEDs Full Protection
Data sheet Voltage monitoring relays CM-ESS.2 For single-phase AC/DC voltages The CM-ESS.2 is an electronic voltage monitoring relay that provides reliable monitoring of voltages as well as detection of
Characteristics three-phase network control relay RM4-T - range 200..500 V Complementary [Us] rated supply voltage Output contacts Setting accuracy of time delay Delay at power up Measuring cycle Marking
Samba OPLC SM43-J-T20/ SM35-J-T20 OPLC Installation Guide 12 Digital Inputs, include 1 HSC/Shaft-encoder Input, 2 Analog inputs (only when the digital inputs are set to pnp), 8 Relay Outputs 12 Digital
Characteristics multifunction control relay RM17-TE - range 183..528 V AC Complementary Reset time Maximum switching voltage Minimum switching current Maximum switching current [Us] rated supply voltage
Relés e Contatores de Estado Sólido SIRIUS Coletânea de dados técnicos ( product data sheet ) Agosto/212 SSR - 3RF21 22,5 mm Ponto Zero SSR - 3RF2 45 mm Ponto Zero SSR - 3RF22 45 mm Ponto Zero Trifásico
Foxboro Evo Process Automation System Product Specifications PSS 31H-2Z32 FBM232 Field Device System Integrator Module, 10/100 Mbps Ethernet, Single The FBM232 Field Device System Integrator (FDSI) module
Redundancy Module QUT DIODE provides: 00% decoupling of power supplies connected in parallel Can be installed in potentially explosive areas Load currents up to 60 A supported Easy assembly by snapping
Rack mounted telephone- and leased line modem for industrial applications TR-6 Rack modem for industrial PSTNand /-wire leased line applications The TR-6 is an analogue V. 9 -rack PSTN modem as well as
Electrical Specification for: CPCI-3U-AC-300W-R Rugged 300W AC Input 3U CompactPCI Power Supply Telkoor Part Number: 900-4602-0000 GENERAL SCALE RELEASE DATE 12/9/06 SHEET 1 OF 6 REVISION HISTORY Rev Level
MANUFACTURER DATA SHEET Analog I/O Module Manufacturer: Allen-Bradley/Rockwell Model Number: 1746-NI4 See www.geomartin.com for additional PDF datasheets Martin Part Number: E-014624-18 VendorPartNumber:
Data sheet Electronic overload relay EF19 and EF45 Electronic overload relays offer reliable protection in case of overload and phase-failure. They are the alternative to thermal overload relays. Motor
UniStream CPU-for-Panel Installation Guide USC-P-B10 Unitronics UniStream platform comprises control devices that provide robust, flexible solutions for industrial automation. This guide provides basic
Quick Guide Fiber Optic Cable Installation Introduction Fiber optic cables can be easily damaged if they are improperly handled or installed. It is imperative that certain procedures be followed in the
s 8 185 8185P01 TX-I/O ; DESIGO OPEN TX OPEN RS/485 module for integrating third-party systems and devices to DESIGO (V4 or higher) TXI1.OPEN Platform to integrate third-party systems and devices to the
MTE SERIES RLW World REACTORS USER MANUAL PART NO. INSTR 030 REL. 090930 2009 MTE Corporation IMPORTANT USER INFORMATION NOTICE MTE Series RLW reactors are components designed to improve the reliability
Technical Data 2CDC505051D0205 ABB i-bus KNX Product description Switch Actuators SA/S x.16.2.1, 16 A are modular installation devices in ProM design for installation in the distribution board. They are
ABB Drives User s Manual Pulse Encoder Interface Module RTAC-0 Pulse Encoder Interface Module RTAC-0 User s Manual 3AFE 64486853 REV A EN EFFECTIVE:.5.00 00 ABB Oy. All Rights Reserved. Safety instructions
48 Series - Relay interface modules 8 A Features 48.12 2 Pole Safety relay interface modules, 15.8 mm wide 48.12-2 Pole 8 A (screw terminal) DC sensitive coils Relay with forcibly guided contacts according
2CDC 251 014 F0t09 Features Monitoring of three-phase mains for grid feeding Type-tested in accordance with DIN V VDE V 0126-1-1: February 2006 Neutral conductor connection configurable Can also be used
PowerFlex 700S and 700H Frame 12 DC Bus Connector Kit Installation Instructions This document provides instructions for the installation of a DC bus connector kit for PowerFlex 700S and 700H frame 12 drives
Owner s Manual Manual Ranging MultiMeter Model 82345 CAUTION: Read, understand and follow Safety Rules and Operating Instructions in this manual before using this product.! Safety! Operation! Maintenance!