q = 6.74x1 = mg/l x 3.78x10 L/d = 3.4x10 mg / day a) Single CMFR mg/g C Organic Load = Carbon requirement = 6.74 mg 1000 g C inf = 10 mg/l


 Alfred Lane
 1 years ago
 Views:
Transcription
1 Example An industrial wastewater contains 10 mg/l chlorophenol, and is going to be treated by carbon adsorption. 90% removal is desired. The wastewater is discharged at a rate of 0.1 MGD. Calculate the carbon requirement for a) a single, mixed contactor (CMFR) b) two mixed (CMFR) contactors in series c) a column contactor. Freundlich isoherm 0.41 q = 6.74xC mg/g C mg/l
2 a) Single CMFR C inf = 10 mg/l Organic Load = Carbon requirement = 0.41 q = 6.74x1 =6.74 mg/g C mg/l x.78x10 L/d =.4x10 mg / day 6 g C 1 kg.4x10 mg/day x x = 505 kg/day 6.74 mg 1000 g C eff = 1 mg/l
3 b) Two CSTRs connected in series 10 mg/l 5 mg/l 1 mg/l We assume it. It is not given in the question. If you change it, you will calculate a different value.
4 Contactor 1 C inf = 10 mg/l C eff = 5 mg/l 0.41 q = 6.74x5 =1.0 mg/g C Organic Load = mg/l x.78x10 L/d = 1.89x10 mg/day Carbon requirement = 6 g C 1 kg 1.89x10 mg/day x x = 145 kg / day 1.0 mg 1000 g
5 Contactor 2 C inf = 5 mg/l C eff = 1 mg/l 0.41 q = 6.74x1 =6.74 Organic Load = Carbon requirement = mg/g C mg/l x.78x10 L/d = 1.51x10 mg/day 6 g C 1 kg 1.51x10 mg/day x x = 224 kg/day 6.74 mg 1000 g
6 qe C e of 1 CMFR and 2 nd Contactor Ce C e of 1 st Contactor C o
7 Total C requirement = =69 kg/day a) a single, mixed contactor (CMFR) b) two mixed (CMFR) contactors in series C requirement decreased because, in the 1 st contactor, we are able to put more on the surface of the carbon.
8
9 Column Height Flow Direction 0 C o Everything happens in the primary adsorption zone (or mass transfer zone, MTZ). This layer is in contact with the solution at its highest concentration level, C o. As time passes, this layer will start saturating. Whatever escapes this zone will than be trapped in the next zones. As the polluted feed water continues to flow into the column, the top layers of carbon become, practically, saturated with solute and less effective for further adsorption. Thus the primary adsorption zone moves downward through the column to regions of fresher adsorbent. Concentration (mg/l) Here you start observing your breakthrough curve when the last layer starts getting saturated.
10 0 C o Flow Direction Last primary adsorption zone. It is called primary because the upper layers are not doing any removal job. They are saturated. When breakthrough occurs there is some amount of carbon in the column still not used. Generally, this is accepted to be 1015%.
11 Primary adsorption zone Region where the solute is most effectively and rapidly adsorbed. This zone moves downward with a constant velocity as the upper regions become saturated.
12 Active zones at various times during adsorption and the breakthrough curve.. Ref:
13 Column Contactor C inf = 10 mg/l C eff = 1 mg/l 0.41 q = 6.74x10 =17. mg/g C Organic Load = mg/l x.78x10 L/d =.4x10 mg/day Assume that the breakthrough occurs while 10% of the carbon in the column is still not used. Carbon requirement = 6 g C 1 kg 100%.4x10 mg/day x x x = kg/day 17. mg 1000 g 90%
14 Packed Column Design It is not possible to design a column accurately without a test column breakthrough curve for the liquid of interest and the adsorbent solid to be used.
15 Theoretical Breakthrough Curve
16 i. Scale up procedure ii. and Kinetic approach Packed Column Design are available to design adsorption columns. In both of the approaches a breakthrough curve from a test column, either laboratory or pilot scale, is required, and the column should be as large as possible to minimize side wall effects. Neither of the procedures requires the adsorption to be represented by an isotherm such as the Freundlich equation.
17 Packed Column Design Scale up Procedure for Packed Columns Use a pilot test column filled with the carbon to be used in full scale application. Apply a filtration rate and contact time (EBCT) which will be the same for full scale application (to obtain similar mass transfer characteristics). Obtain the breakthrough curve. Work on the curve for scale up.
18 Example An industrial wastewater having a TOC of 200 mg/l will be treated by GAC for a flowrate of 150 m /day. Allowable TOC in the effluent is 10 mg/l. Pilot Plant Data Q = 50 L/hr Column diameter = 9.5 cm Column depth (packed bed) = 175 cm Packed bed carbon density = 400 kg/m V breakthrough = 8400 L V exhaustion = 9500 L
19 Breakthrough Curve of the Pilot Plant
20 a) Filtration rate of the pilot plant FR = Q L cm = 50 x x = 2 A hr π d 1L 2 cm 705 hr.cm 2 d = 9.5 cm The same FR applies to Packed Column.
21 b) Area of the Packed Column FR = Q A Q A = FR 2 6 m 1 h.cm 1 d 10 cm A = 150 x. x x = d 705 cm 24 h 1 m 8865cm 2 4 x 8865 d= = π 106cm
22 c) Empty Bed Contact Time of the Pilot Plant τ = Q 2 2 d 9.5 = A x Height = π x H =.14 x x175 = 12,404 cm = L 12.4 L τ = = hr = L/hr 15 min 15 mins.is the EBCT of the Packed Column.
23 d) Height of the Packed Column Q cm 1 hr τ x = 15 min x 705 x = 2 A hr.cm 60 min 176 cm The same as the height of the Pilot Plant. Because height τ Q/A is set by and, and these are the same for Pilot Plant and the Packed Column.
24 e) Mass of Carbon required in the Packed Column π 4 2 = 1.76 m x x 1.06 = 1.55 m Packed bed carbon density is given by the supplier. density = 400 kg/m kg m 1.55 m x 400 = 621 kg
25 f) Determination of q e Mass of carbon in the pilot column = Volume of the pilot column = 12.4 L x density kg = m x 400 = 4.96 m TOC removed by 5 kg of carbon = 5 kg 200 mg/l x 9500 L = 6 1.9x10 mg 6 1.9x10 mg TOC q e = = 5 kg C mg 80 C g
26 g) Fraction of Capacity Left Unused (Pilot Plant) mg Total capacity = 9500 L x 200 = L 6 1.9x10 mg TOC removed before breakthrough = mg 8400 L x 200 = L x10 mg Fraction of capacity left unused = f = x10 6 x x10 12% This fraction of capacity left unused will apply to the Packed Column also.
27 h) Breakthrough time of the Packed Column Organic Loading = mg m 1000 L 200 x 150 x = L d 1 m 6 0x10 mg/d 6 mg 1 Carbon consumption rate = 0x10 x = d 80 mg/g C 78.9 kg/d Amount of carbon consumed = 621 kg x = kg Breakthrough time = kg 78.9 kg/d 7 days The same as the Packed Column : 1 hr 1 d 8400 L x x = 50 L 24 hr 7 days
28
29 i) Volume Treated Before Breakthrough treated m = 150 x 7 days = d 1050 m
30 Kinetic Approach Packed Column Design This method utilizes the following kinetic equation. C 1 C k o 1 + e Q 1 q M  C V o o
31 where C = effluent solute concentration C o = influent solute concentration k 1 = rate constant q o = maximum solid phase concentration of the sorbed solute, e.g. g/g M = mass of the adsorbent. For example, g V = throughput volume. For example, liters Q = flow rate. For example, liters per hour
32 Kinetic Approach Packed Column Design The principal experimental information required is a breakthrough curve from a test column, either laboratory or pilot scale. One advantage of the kinetic approach is that the breakthrough volume, V, may be selected in the design of a column.
33 Packed Column Design Assuming the left side equals the rigth side, cross multiplying gives k t Q q M  C V o 1 + e = C o Co Rearranging and taking the natural logarithms of both sides yield the design equation
34 Packed Column Design Rearranging and taking the natural logarithms of both sides yield the design equation. C k q M k C V ln o 1 = 1 o  1 o C Q Q y = b  mx
35 Example A phenolic wastewater having a TOC of 200 mg/l is to be treated by a fixed bed granular carbon adsorption column for a wastewater flow of 150 m /d, and the allowable effluent concentration, C a, is 10 mg/l as TOC. A breakthrough curve has been obtained from an experimental pilot column operated at 1.67 BV/h. Other data concerning the pilot column are as follows: inside diameter = 9.5 cm, length = 1.04 m, mass of carbon = 2.98 kg, liquid flowrate = 12.9 L/h, unit liquid flowrate = L/s.m 2, and the packed carbon density = 400 kg/m. The design column is to have a unit liquid flowrate of 2.04 L/s.m 2, and the allowable breakthrough volume is 1060 m.
36 Example Using the kinetic approach for design, determine : The design reaction constant, k 1, L/skg. The design maximum solid  phase concentration, q o, kg/kg. The carbon required for the design column, kg. The diameter and height of the design column, m. The kilograms of carbon required per cubic meter of waste treated.
37 V (L) C(mg/L) C/Co Co/C Co/C1 ln(co/c1) 0 0 0,000 78,0 9 0,045 22,222 21,222,06 984,0 11 0,055 18,182 17,182 2,84 124,0 8 0,040 25,000 24,000,18 190,0 9 0,045 22,222 21,222, ,0 0 0,150 6,667 5,667 1,7 2520, ,500 2,000 1,000 0, , ,825 1,212 0,2121,55 290,0 19 0,965 1,06 0,06 ,2 126, ,000 1,000 0,000
38 C, mg/l V, Liters
39 ln(co/c  1) V (L) Plot of Complete Data Set
40 ln(co/c  1) 15 y = 0,0064x + 15, Volume treated (L) Take the linear range only!
41 q k M = 0 1 Q k 1 C L = 1 0 Q (0.0064L1) (12.9 L) a)k = h = L 1 mg 200 mg h L L 1h 10 mg =0.11 L mg h 600s 1kg kg s 4 6
42 q 0.11 L 2.98kg b)15.787= 0 kg s 12.9 L h 600s 1h L h 600s 1h q = L 2.98kg kg s q =0.166 kg 0 kg
43 k = mg h q = kg kg 4 L Q = 6250 L / h V = L C 0 = 200 mg / L Using Co k1qom k1cov ln 1 =  C Q Q L kg L mg 200 mg h kg mg h L ln 1 =  10 L L h h M L M= mg =1545 kg
44 M =1545 kg Packet carbon density = 400 kg / m Then, design bed volume is; 1545 kg V.86 m kg 400 m Q = 6250 L / h = 1.76 L / s (given) Unit liquid flowrate = 2.04 L / s m 2 (given) 1.76 L / s Cross section area = 0.85m d = 1.04 m Breakthrough time is; L / s m.86 m m Column height = 1050 m T B = 7 d 150 m / d 4.54 m
45 Scaleup approach: 1. The design bed volume (BV) is found as; 150 m / d 1.67 BV / h = = 6.25 m / h BV =.74 m 24 h/ d 2. The mass of carbon required is; M = BV =.74 m 400 kg / m =1500 kg From the breakthrough curve the volume treated at the allowable breakthrough (10 mg/l TOC) is 2080 L. So, the solution treated per kilogram of carbon is 2080 L/2.98 kg or 698 L/kg (pilot scale). The same applies to the design column; for a flow rate of 150 m /d.. The weight of carbon exhausted per hour (M t ) is 150 m / d kg 1000 L t M = 24 h 698 L m kg/h
46 C, mg/l V, Liters
47 4. The breakthrough time is; 1500 kg T = =168 h = 7 d kg / h 5. The breakthrough volume of the design column is; V = Q T =150 m / d 7 d = 1050 m B Comparing the results of two approaches: Kinetic approach M=1545 kg V = 1050 m B T B = 7 d V =.86 m Design Scaleup approach M = 1500 kg V = 1050 m B T B = 7 d V =.74 m Design
48 Example A phenolic wastewater that has phenol concentration of 400 mg/l as TOC is to be treated by a fixed bed granular carbon adsorption column for a wastewater flow of L/d, and the allowable effluent concentration, C a, is 5 mg/l as TOC. A breakthrough curve has been obtained from an experimental pilot column operated at 1.67 BV/h. Other data concerning the pilot column are as follows: inside diameter = 9.5 cm, length = 1.04 m, mass of carbon = 2.98 kg, liquid flowrate = L/h, unit liquid flowrate = L/s.m 2, and the packed carbon density = 401 kg/m. The design column is to have a unit liquid flowrate of 2.8 L/s.m 2, and the allowable breakthrough volume is 850 m.
49 V (L) C (mg/l) C/Co Co/C Co/C  1 ln(co/c  1)
50 C, mg/l V, Liters
51 ln(co/c  1) V (L)
52 ln(co/c  1) 2 1 y = 0,0146x + 18,657 R² = 0, V (L)
53 q k M = 0 1 Q k C L 1= 1 0 Q ( L 1) (17.42 L) h L L mg mg h kg s L k = = L h 600s 1h q = L 2.98kg kg s q =0.171 kg 0 kg
54 k = mg h q = kg kg 4 L Q = L / h V = L C 0 = 400 mg / L Using Co k1qom k1cov ln 1 =  C Q Q L kg L mg 400 mg h kg mg h L ln 1 =  5 L L h h M L M=2190 kg
55 M =2190 kg Packet carbon density = 401 kg / m Then, design bed volume is; 2190 kg V 5.46 m kg 401 m Q = L / h = 2.6 L / s (given) Unit liquid flowrate = 2.8 L / s m 2 (given) 5.46 L / s Cross section area = 2.29m d = 1.71 m Breakthrough time is; L / s m 5.46 m m Column height = T = 850 m.74 d m / d B 2.8 m
56 Scaleup approach: The design bed volume (BV) is found as; L/ d 1.67 BV / h = = L / h 24 h/ d BV = L = 5.67 m The mass of carbon required is; M = BV = 5.67 m 401 kg / m = 2272 kg From the breakthrough curve the volume treated at the allowable breakthrough (5 mg/l TOC) is 1110 L. So, the solution treated per kilogram of carbon is 1110 L/2.98 kg or 72.5 L/kg (pilot scale). The same applies to the design column; for a flow rate of L/d, the weight of carbon exhausted per hour (M t ) is M = t L / d kg 24 h /d 72.5 L 25.4 kg/h
57 C, mg/l V, Liters
58 The breakthrough time is; 2272 kg T = = 89.5 h =.7 d 25.4 kg / h The breakthrough volume of the design column is; V = Q T = m / d.7 d = m B Comparing the results of two approaches: Kinetic approach Scaleup approach M=2190 kg M = 2272 kg V = 850 m B T B =.74 d V = 5.46 m Design V = m B T B =.7 d V = 5.67 m Design
GRANULAR ACTIVATED CARBON FOR WATER & WASTEWATER TREATMENT
GRANULAR ACTIVATED CARBON FOR WATER & WASTEWATER TREATMENT CARBTROL Corporation September 1992 Rev. 10/92 TP3 INTRODUCTION Carbon has been used as an adsorbent for centuries. Early uses of carbon were
More informationTHE DESIGN OF ION EXCHANGE COLUMN JIALI WANG
THE DESIGN OF ION EXCHANGE COLUMN JIALI WANG 01042015 CONTENTS Introduction and research question Theoretical background Methods and material Results Discussion Ion exchange column design Conclusion
More informationPowdered and Granular Activated Carbon Treatment for TOC Reduction and Stage 2 D/DBPR Compliance
Powdered and Granular Treatment for TOC Reduction and Stage 2 D/DBPR Compliance NC AWWAWEA Spring Conference, Wilmington, NC April 15, 2013 Pete D Adamo, PhD, PE pdadamo@hdrinc.com Basics Learning Objectives
More informationAnion Exchange and GAC Demonstration for TOC Removal and THM Control
Anion Exchange and GAC Demonstration for TOC Removal and THM Control Rick Schantz, Retired Village of Archbold Marvin Gnagy, P.E., President PMG Consulting, Inc. Project by URS Corporation Ohio Section
More informationConversions between the common units of length used in the Imperial system are listed below 12 in = 1 ft 3 ft = 1 yard 1760 yards = 1 mile
THE METRIC SYSTEM The metric system or SI (International System) is the most common system of measurements in the world, and the easiest to use. The base units for the metric system are the units of: length,
More informationPractice Tests Answer Keys
Practice Tests Answer Keys COURSE OUTLINE: Module # Name Practice Test included Module 1: Basic Math Refresher Module 2: Fractions, Decimals and Percents Module 3: Measurement Conversions Module 4: Linear,
More information1.85 WATER AND WASTEWATER TREATMENT ENGINEERING HOMEWORK 5
1.85 WATER AND WASTEWATER TREATMENT ENGINEERING HOMEWORK 5 Question 1 (4 points) The water defined by the analysis given below is to be softened by excesslime (and soda ash) treatment. a. Sketch an meq/l
More informationAdsorption WATER TREATMENT
WATER TREATMENT WATER TREATMENT Adsorption micro pores pump macro pores meso pores 2 micro pores atrazine (mg/l) 1.5 1 > 25 nm 125 nm < 1 nm pesticides macro pore meso pore pump.5 1, 2, 3, bed volumes
More informationRemoval of Sulfate from Waste Water by Activated Carbon. Mohammed Sadeq Salman Computer Centre/ University of Baghdad
AlKhwarizmi Engineering Journal, Vol. 5, No. 3, PP 7276 (29) AlKhwarizmi Engineering Journal Removal of Sulfate from Waste Water by Activated Carbon Mohammed Sadeq Salman Computer Centre/ University
More informationFE REVIEW: ENVIRONMENTAL ENGINEERING
FE REVIEW: ENVIRONMENTAL ENGINEERING Y. T. Wang Chemical Equilibrium and Stoichiometry 1. The chloride (C1  ) concentration in a lake is found to be 102 M. The HgC1 2 (aq) concentration is found to be
More informationOxygenTransfer Measurement in Clean Water
OxygenTransfer Measurement in Clean Water Zhen He*, Anurak Petiraksakul** and Warawitya Meesapya** Abstract This paper presents the experiments on measurement of oxygen transfer capacity in clean water
More informationLafayette College Department of Civil and Environmental Engineering
Lafayette College Department of Civil and Environmental Engineering CE 321: Introduction to Environmental Engineering Fall 2010 Homework #4 SOLUTIONS Due: Monday, 9/27/10 SOLUTIONS 1. A completely mixed
More informationREMOVAL OF PHOSPHATE FROM WASTEWATER USING LOWCOST ADSORBENTS
International Journal of Engineering Inventions ISSN: 22787461, www.ijeijournal.com Volume 1, Issue 7 (October2012) PP: 4450 REMOVAL OF PHOSPHATE FROM WASTEWATER USING LOWCOST ADSORBENTS Dr. C.R.Ramakrishnaiah
More informationIon Exchange Design Hand calculation. Brian Windsor (Purolite International Ltd)
Ion Exchange Design Hand calculation Brian Windsor (Purolite International Ltd) Introduction Before design programmes were introduced, every engineer had to calculate the design by hand using resin manufacturers
More informationFLORIDA DEPARTMENT OF ENVIRONMENTAL PROTECTION Wastewater Treatment Formulas/Conversion Table
Revised February 2014 FLORIDA DEPARTMENT OF ENVIRONMENTAL PROTECTION Wastewater Treatment Formulas/Conversion Table Measurement Conversion Measurement Conversion Measurement Conversion 12 in= 1 ft 27 cu.
More informationEnhanced Organic Precursor Removals Using Aged Filter Media Page 1. Enhanced Organic Precursor Removals Using Aged Filter Media
Enhanced Organic Precursor Removals Using Aged Media Page 1 Enhanced Organic Precursor Removals Using Aged Media O b j e c t i v e s The main goals of this project was to evaluate the dissolved organic
More informationHomework #9 Wastewater Treatment
5 points total for CEE 371 entire homework Fall 2009 Homework #9 Wastewater Treatment Consider the design of a wastewater treatment plant (WWTP) for a community with average daily and peak hourly wastewater
More informationConversion Table Provincial Programs
Conversion Table Provincial Programs Canadian ABC Formula/Conversion Table for Water Treatment, Distribution and Laboratory Exams Alkalinity, as mg CaC0 3 /L = Amps = Volts 0hms Area of Circle = (0.785)
More informationCost assessment of Produced Water Treatment
Cost assessment of Produced Water Treatment John Hackney and Mark R. Wiesner May 996 INTRODUCTION This work investigates treatment of waste or "produced" waters generated during the exploration for and
More information(Refer Slide Time: 05:33)
Water and Wastewater Engineering Dr. Ligy Philip Department of Civil Engineering Indian Institute of Technology, Madras Sedimentation (Continued) Lecture # 9 Last class we were discussing about sedimentation.
More informationDisinfection Byproducts Control with Ion Exchange. Francis Boodoo a DJ Shannahan b Edward Begg a Joe D Alessandro a
Disinfection Byproducts Control with Ion Exchange Francis Boodoo a DJ Shannahan b Edward Begg a Joe D Alessandro a a The Purolite Company b Sharpe Water Abstract Reduction of TOC prior to chlorination
More informationDistribution through a Permeable Medium
PlumeStop Technical Bulletin 1.1 Distribution through a Permeable Medium Quick Reference: PlumeStop distribution through > 16 (5 m) packed medium readily achieved Even coating of sand matrix with PlumeStop
More informationRemediation of VOC Contaminated Groundwater
Remediation of VOC Contaminated Groundwater Background Contaminated groundwater has become an everincreasing problem in the United States and around the world. Treatment and disposal of waste is a serious
More information(a) Calculate the voidage (volume fraction occupied by voids) of the bed.
SOLUTIONS TO CAPTER 6: FLOW TROUG A PACKED BED OF PARTICLES EXERCISE 6.1: A packed bed of solid particles of density 500 kg/m 3, occupies a depth of 1 m in a vessel of crosssectional area 0.04 m. The
More informationPOLLUTED EMISSION TREATMENTS FROM INCINERATOR GASES
POLLUTED EMISSION TREATMENTS FROM INCINERATOR GASES Ecole Nationale Supérieure de Chimie Avenue du Général Leclerc, Campus de Beaulieu 35700 Rennes, France Tel 33 (0)2 23 23 80 02 Fax 33 (0)2 23 23 81
More informationEnhanced Organic Precursor Removals Using Aged Filter Media Page 1
Enhanced Organic Precursor Removals Using Aged Filter Media Page 1 Assessing Innovative Arsenic Adsorbents O b j e c t i v e s According to a 1999 study by the National Academy of Sciences, arsenic in
More information20 m neon m propane 20
Problems with solutions:. A m 3 tank is filled with a gas at room temperature 0 C and pressure 00 Kpa. How much mass is there if the gas is a) Air b) Neon, or c) Propane? Given: T73K; P00KPa; M air 9;
More informationTreatment Strategies for DBP Reduction. Module 10
Treatment Strategies for DBP Reduction Module 10 DBP Control Options Optimize existing facilities Treatment plant Distribution system Make the most of what you ve got! Implement new facilities Treatment
More informationFeasibility study of crystallization process for water softening in a pellet reactor
International A. H. Mahvi, Journal et al. of Environmental Science & Technology Feasibility study of crystallization... Vol. 1, No. 4, pp. 14, Winter 5 Feasibility study of crystallization process for
More informationPALM BEACH COUNTY WATER UTILITIES DEPARTMENT WATER TREATMENT PLANT 2 MAGNETIC ION EXCHANGE
PALM BEACH COUNTY WATER UTILITIES DEPARTMENT WATER TREATMENT PLANT 2 MAGNETIC ION EXCHANGE By: Monica Pazahanick and Chris Reinbold, P.E.  Carollo Engineers, Inc. CoAuthors: Stephen McGrew, P.E. and
More informationDepartment of Civil EngineeringI.I.T. Delhi CEL 212: Environmental Engineering
Department of Civil EngineeringI.I.T. Delhi CEL 212: Environmental Engineering Q1. An anaerobic reactor, operated at 35 o C, treats wastewater with a flow of 2000m 3 /d and a biological soluble COD (bscod)
More informationBASIC MATH FORMULAS  CLASS I. A. Rectangle [clarifiers, ponds] I = length; w = width; A = area; area in square ft [sq ft]
WASTEWATER MATH CONVERSION FACTORS 1. 1 acre =43,560 sq ft 2. 1 acre =2.47 hectares 3. 1 cu ft [of water] = 7.48 gallons 4. 1 cu ft [of water] = 62.4 Ibs/ft 3 5. Diameter =radius plus radius, D =r + r
More information( ) ABC Formula/Conversion Table for Wastewater Treatment, Industrial, Collection and Laboratory Exams. Alkalinity, as mg CaCO 3 /L =
ABC Formula/Conversion Table for Wastewater Treatment, Industrial, Collection and Laboratory Exams Alkalinity, as mg CaCO 3 /L = (Titrant Volume, ml) (Acid Normality)(50,000) Volts Amps = Ohms Area of
More informationFLOW EQUALIZATION [ ] water in the system the system by flow by reaction
FLOW EQUALIZATION Flow equalization is the process of mitigating changes in flow rate through a portion of a system by providing storage to hold water when it is arriving too rapidly, and to supply additional
More informationThe atomic packing factor is defined as the ratio of sphere volume to the total unit cell volume, or APF = V S V C. = 2(sphere volume) = 2 = V C = 4R
3.5 Show that the atomic packing factor for BCC is 0.68. The atomic packing factor is defined as the ratio of sphere volume to the total unit cell volume, or APF = V S V C Since there are two spheres associated
More informationChemistry 3012 Foundational Chemistry Laboratory Manual
Chemistry 3012 Foundational Chemistry Laboratory Manual Table of Contents Page Experiment 1. Experiment 2. Experiment 3. Experiment 4. Experiment 5. Experiment 6. Experiment 7. Experiment 8. Determining
More informationLecture # 13 Filtration
Water and Wastewater Engineering Dr. Ligy Philip Department of Civil Engineering Indian Institute of Technology, Madras Water and Wastewater Engineering Lecture # 13 Filtration Last class we were discussing
More informationABC & C 2 EP Formula/Conversion Table for Water Treatment, Distribution, & Laboratory Exams
ABC & C EP Formula/Conversion Table for Water Treatment, Distribution, & Laboratory Exams Alkalinity, as mg CaCO 3 /L = (Titrant, ml) (Acid Normality)(50,000) Sample, ml Volts Amps = Ohms * of Circle =
More informationLecture 7 Gaseous emission control by adsorption
Lecture 7 Gaseous emission control by adsorption GASEOUS EMISSION CONTROL BY ABSORPTION AND ADSORPTION INTRODUCTION Combustion processes generate various primary and secondary air pollutants such as carbon
More informationTransient Mass Transfer
Lecture T1 Transient Mass Transfer Up to now, we have considered either processes applied to closed systems or processes involving steadystate flows. In this lecture we turn our attention to transient
More informationA Low Cost Chemical Remediation Technology for Heavy Metals in Shipyard Stormwater. SBIR Topic N06 133
A Low Cost Chemical Remediation Technology for Heavy Metals in Shipyard Stormwater SBIR Topic N06 133 1 Normal Ave, CSAM RI 121A Montclair, NJ 07043 973 655 7385 SIROM TECHNOLOGY SIROM has developed a
More informationDesigning a Flow Through Raceway System for Salmonids  Westers Design
Designing a Flow Through Raceway System for Salmonids  Westers Design North Central Aquaculture Conference Toledo, Ohio February 2223, 2014 Chris Weeks Intensive FlowThrough Systems Salmon and trout
More informationTexture characteristic of membrane materials ASAP, BET
Texture characteristic of membrane materials ASAP, BET Theory Specific surface (surface area) is used for the characterization of many materials. There are various techniques how measure the specific surface
More informationMathematics For Wastewater Operators
Mathematics For Wastewater Operators Chapter 17: Mathematics The understanding of the mathematics of wastewater treatment is an important tool for all wastewater system operators. This chapter covers most
More informationFLOW MEASUREMENT 2001 INTERNATIONAL CONFERENCE DERIVATION OF AN EXPANSIBILITY FACTOR FOR THE VCONE METER
FLOW MEASUREMENT 200 INTERNATIONAL CONFERENCE DERIVATION OF AN EXPANSIBILITY FACTOR FOR THE VCONE METER Dr D G Stewart, NEL Dr M ReaderHarris, NEL Dr R J W Peters, McCrometer Inc INTRODUCTION The VCone
More information土 壤 物 理 題 庫 1. Prove the following relation of porosity to particle density and to bulk density: ƒ=(ρ s  ρ b )/ρ s = 1  ρ b /ρ s
土 壤 物 理 題 庫 1. Prove the following relation of porosity to particle density and to bulk density: ƒ=(ρ s  ρ b )/ρ s = 1  ρ b /ρ s 2. Prove the following relation between volume wetness, mass wetness,
More informationChapter 6  Solute Transport
SSC 107, Fall 00 Chapter 6 Page 61 Chapter 6  Solute Transport fertilizer movement leaching of salt (reclamation) pollutant movement Transport depends on H O flow velocity Water content Soil characteristics
More informationCompletely Mixed Activated Sludge (CMAS) Bioreactor Design Equations
ompletely Mixed Activated Sludge (MAS) Bioreactor Design Equations Secondary larifier (QQ W ), S, X e Q, S O (Q+Q r ), S, X X, S, V Aeration Tank Q r, X r, S Return Activated Sludge (RAS) Q W, X r, S
More informationINTEGRATED ANAEROBIC  AEROBIC MBBR: A NOVEL APPROACH TO HIGH STRENGTH WASTEWATER TREATMENT
INTEGRATED ANAEROBIC  AEROBIC MBBR: A NOVEL APPROACH TO HIGH STRENGTH Gali Stamper 1, Tamar Arbel 1, Nir Assulin 1, Antoine Engelaar 2, Alje Haan 2 and Sanne Steenbrink 2 1 Aqwise Wise Water Technologies,
More informationThe design for ion exchange column
The design for ion exchange column Jiali Wang + Kenchouw Wu March 2015 ii The design for ion exchange column (Internship report) Submitted to: Mr. Harmen van der Laan (Oasen Drinking water company) Ms.
More informationDepartment of Chemical and Environmental Process Engineering. Extraction. Chemical Unit Operations II. Béla Simándi, Edit Székely
Department of Chemical and Environmental Process Engineering Extraction Chemical Unit Operations II. Béla Simándi, Edit Székely Extraction I. Liquidliquid extraction (Solvent extraction) II. Solidliquid
More informationCHAPTER 15 FORCE, MASS AND ACCELERATION
CHAPTER 5 FORCE, MASS AND ACCELERATION EXERCISE 83, Page 9. A car initially at rest accelerates uniformly to a speed of 55 km/h in 4 s. Determine the accelerating force required if the mass of the car
More informationMath. The top number (numerator) represents how many parts you have and the bottom number (denominator) represents the number in the whole.
Math This chapter is intended to be an aid to the operator in solving everyday operating problems in the operation of a water system. It deals with basic math that would be required for an operator to
More informationExample Calculations Evaluation for Fine Bubble Aeration System. Red Valve Company, Inc. 700 NORTH BELL AVENUE CARNEGIE, PA 151060548
Revision Date 6/10/02 9:52 Red Valve Company, Inc. 700 NORTH BELL AVENUE CARNEGIE, PA 151060548 PHONE (412) 2790044 FAX (412) 2795410 Red Valve Representative Sample Air Diffuser Calcs.xls Input Data
More informationThe Next Generation of Activated Carbon Adsorbents for the Pre Combustion Capture of Carbon Dioxide.
The Next Generation of Activated Carbon Adsorbents for the Pre Combustion Capture of Carbon Dioxide. Power Plant Modelling Workshop at University of Warwick Dr. Joe Wood,Prof. Jihong Wang, Simon Caldwell,
More informationHeterogeneous Catalysis and Catalytic Processes Prof. K. K. Pant Department of Chemical Engineering Indian Institute of Technology, Delhi
Heterogeneous Catalysis and Catalytic Processes Prof. K. K. Pant Department of Chemical Engineering Indian Institute of Technology, Delhi Module  03 Lecture 10 Good morning. In my last lecture, I was
More informationNew technological root for regenerating demineralized water plants for safe environment
International Journal of Water Resources and Environmental Engineering Vol. 3(2), pp. 5256, February 2011 Available online at http://www.academicjournals.org/ijwree ISSN 21416613 2011 Academic Journals
More informationHeterogeneous Catalysis and Catalytic Processes Prof. K. K. Pant Department of Chemical Engineering Indian Institute of Technology, Delhi
Heterogeneous Catalysis and Catalytic Processes Prof. K. K. Pant Department of Chemical Engineering Indian Institute of Technology, Delhi Module No. #03 Lecture  08 So, last time we were talking about
More informationI SOIL WATER POTENTIAL
I SOIL WATER POTENTIAL 1.1. Introduction Soil water content is not sufficient to specify the entire status of water in soil. For example, if soils with a same water content but with different particle
More informationModule 25: Introduction to Flowmeters Answer Key
Module 25: Introduction to Flowmeters wer Key 1. If you have a channel that is 1 foot wide, the flow is 6 inches deep, and the velocity is 2.5 feet per second (fps), what is the volume in cubic feet per
More informationChE 182 Major #1 Acrylic Acid Process
ChE 182 Major #1 Acrylic Acid Process Background The plant at which you are employed currently manufactures acrylic acid in Unit 300 by the catalytic oxidation of propylene. Plant capacity is on the order
More informationColumn Design. Gavin Duffy School of Electrical Engineering Systems DIT, Kevin Street
Column Design Gavin Duffy School of Electrical Engineering Systems DIT, Kevin Street Learning Outcomes After this lecture you should be able to. Explain why the ratio of vapour and liquid velocities is
More informationIllinois Environmental Protection Agency Division of Water Pollution Control Class K Study Guide Industrial Wastewater Operator Certification
Illinois Environmental Protection Agency Division of Water Pollution Control Class K Study Guide Industrial Wastewater Operator Certification Revised March 2003 The purpose of this study guide is to help
More informationExample: 2. Solution. Provide depth D = 1.5 m. Sewage flow = 10000 x 170 x 0.80 x 103 = 1360 m 3 /d. Now, 0.182(1+. = 1.562. Q L = 2.
Example: 2 Design low rate trickling filter for secondary treatment of sewage generated from 10000 persons with rate of water supply 170 LPCD. The BOD 5 after primary treatment is 110 mg/l and BOD 5 of
More informationPump Formulas Imperial and SI Units
Pump Formulas Imperial and Pressure to Head H = head, ft P = pressure, psi H = head, m P = pressure, bar Mass Flow to Volumetric Flow ṁ = mass flow, lbm/h ρ = fluid density, lbm/ft 3 ṁ = mass flow, kg/h
More informationColdwater Biofilter Design Examples
Coldwater Biofilter Design Examples M.B. Timmons, Ph.D. Biological & Environmental Engineering Cornell University Ithaca, NY Coldwater Design Example Production Goal: 1.0 million lb/yr (454 mton/yr) Arctic
More informationHeat transfer in Rotating Fluidized Beds in a Static Geometry: A CFD study
Heat transfer in Rotating Fluidized Beds in a Static Geometry: A CFD study Nicolas Staudt, Juray De Wilde* * Université catholique de Louvain MAPR / IMAP Réaumur, Place Sainte Barbe 2 1348 LouvainlaNeuve
More informationCOMPARISON OF PROCESS FLOWS: FLUID BED COMBUSTOR AND GLASSPACK
COMPARISON OF PROCESS FLOWS: FLUID BED COMBUSTOR AND GLASSPACK PURPOSE The purpose of this document is to present the assumptions and calculations used to prepare Minergy Drawing 1000204PP00 (attached).
More informationTechnical Bulletin // UpFlo Filter
Technical Bulletin // UpFlo Filter Evaluation of SilCosil 106 Removal Performance using cpz mix tm media 2006 Hydro International 94 Hutchins Drive Portland, ME 04102 Tel: 207.756.6200 Fax: 207.756.6212
More informationProduction Scale Briquetting of Torrefied Biomass
Production Scale Briquetting of Torrefied Biomass Wolfgang Stelte Danish Technological Institute DTI European Biomass Conference 2013 Copenhagen, 7 th June 2013 Danish Technological Institute Center for
More informationThe Treatment of Cupric Chloride Solution after the Etching Process by Ion Exchange Membrane Electrodialysis*
Desalination, 62 (1987) 251257 Elsevier Science Publishers B.V., Amsterdam  Printed in The Netherlands The Treatment of Cupric Chloride Solution after the Etching Process by Ion Exchange Membrane Electrodialysis*
More informationDevelopment of a Model for Wet Scrubbing of Carbon Dioxide by Chilled Ammonia
Development of a Model for Wet Scrubbing of Carbon Dioxide by Chilled Ammonia John Nilsson Department of Chemical Engineering, Lund University, P. O. Box 124, SE221 00 Lund, Sweden In this paper, the
More informationChapter 2. Preview. Section 1 What Is Matter? Section 2 Physical Properties. Section 3 Chemical Properties. The Properties of Matter.
The Properties of Matter Preview Section 1 What Is Matter? Section 2 Physical Properties Section 3 Chemical Properties Concept Mapping Section 1 What Is Matter? Bellringer What do you think some of the
More informationPalmdale. Palmdale, CA Water District Chooses GAC Treatment to Meet TTHM Guidelines for Today and Tomorrow
Palmdale, CA Water District Chooses GAC Treatment to Meet TTHM Guidelines for Today and Tomorrow Palmdale By Palmdale Water District, Palmdale, California Named one of the fastestgrowing cities in America
More informationA novel filtration configuration for targeted humic acid removal from drinking water
A novel filtration configuration for targeted humic acid removal from drinking water M. A. Grace, E. Clifford,2, and M.G. Healy,2 Civil Engineering, College of Engineering and Informatics, National University
More informationModule 9: Basics of Pumps and Hydraulics Instructor Guide
Module 9: Basics of Pumps and Hydraulics Instructor Guide Activities for Unit 1 Basic Hydraulics Activity 1.1: Convert 45 psi to feet of head. 45 psis x 1 ft. = 103.8 ft 0.433 psi Activity 1.2: Determine
More informationFluid Mechanics Prof. T.I. Eldho Department of Civil Engineering Indian Institute of Technology, Bombay. Lecture  22 Laminar and Turbulent flows
Fluid Mechanics Prof. T.I. Eldho Department of Civil Engineering Indian Institute of Technology, Bombay Lecture  22 Laminar and Turbulent flows Welcome back to the video course on fluid mechanics. So
More informationPhysics Internal Assessment: Experiment Report. An Increasing Flow of Knowledge: Investigating Torricelli s Law, or the Effect of Height on Flow Rate
0008440029 Ding 1 Physics Internal Assessment: Experiment Report An Increasing Flow of Knowledge: Investigating Torricelli s Law, or the Effect of Height on Flow Rate Candidate Name: Chunyang Ding Candidate
More informationDESIGN OF A COMMON EFFLUENT TREATMENT PLANT FOR AN INDUSTRIAL ESTATE
DESIGN OF A COMMON EFFLUENT TREATMENT PLANT FOR AN INDUSTRIAL ESTATE S. RAMPAIR1, C. VENKOBACHAR2, R. CHEVANNES3, F. GRANT1, & D. THORNHILL4 1. Undergraduate Students Department of Civil Engineering, UWI,
More informationUnit Operations in Mineral Processing Prof. Rodrigo Serna Aalto University
Unit Operations in Mineral Processing Prof. Rodrigo Serna Aalto University Operations after enrichment After enrichment, slurries will require further handling Concentrate will be transported to smelters
More informationABC & C 2 EP Formula/Conversion Table for Wastewater Treatment, Industrial, Collection, & Laboratory Exams
ABC & C EP Formula/Conversion Table for Wastewater Treatment, Industrial, Collection, & Laboratory Exams Alkalinity, as mg CaCO /L (Titrant, ml) (Acid Normality)(50,000) Sample, ml Volts Amps Ohms * of
More informationVALIDATION, MODELING, AND SCALEUP OF CHEMICAL LOOPING COMBUSTION WITH OXYGEN UNCOUPLING
VALIDATION, MODELING, AND SCALEUP OF CHEMICAL LOOPING COMBUSTION WITH OXYGEN UNCOUPLING A research program funded by the University of Wyoming School of Energy Resources Executive Summary Principal Investigator:
More informationA NEW SPIN ON LIQUID CHLORINATION
A NEW SPIN ON LIQUID CHLORINATION Michael Braden 1 and James W. Weishuhn 2 Abstract Liquid chlorination has historically utilized excess energy of an effluent pump to power a venturi to introduce sodium
More informationWorking Math Formulas, Units, Conversions
Working Math Formulas, Units, Conversions This presentation has been adapted from Math for Subsurface Operators given at the North Carolina Subsurface Operator School Math will be used to Determine a flow
More informationChapter 12  Chemical Kinetics
Chapter 1  Chemical Kinetics 1.1 Reaction Rates A. Chemical kinetics 1. Study of the speed with which reactants are converted to products B. Reaction Rate 1. The change in concentration of a reactant
More informationAnalysis of Experimental Uncertainties: Density Measurement Physics Lab II
Analysis of Experimental Uncertainties: Density Measurement Physics Lab II Objective This laboratory exercise allows students to estimate and analyze experimental uncertainties. Students will calculate
More informationFederico Patti and Francisco Sanchez Carelli FLARGENT
H 2 S REMOVAL FROM CO2 VENT STREAM OF AMINE PLANTS Federico Patti and Francisco Sanchez Carelli FLARGENT ABSTRACT In amines plants, venting CO2 into the atmosphere is a problem which demands hard work
More informationFILTRATION. Introduction. Batch Filtration (Small Scale) Controlling parameters: Pressure drop, time for filtration, concentration of slurry
FILTRATION Introduction Separation of solids from liquids is a common operation that requires empirical data to make predictions of performance. These data are usually obtained from experiments performed
More informationSaudi Aramco Project Development
Saudi Aramco Project Development Wastewater Treatment Facilities Jeddah Refinery And Marine Area December 2007 Facilities Planning Dept. OBJECTIVE: Provide an overview of the complexities of developing
More informationLecture 5: Filtration
Islamic University of Gaza Environmental Engineering Department Water Treatment EENV 4331 Lecture 5: Filtration Dr. Fahid Rabah 1 5. Filtration in water Treatment 5.1 Definition of Sedimentation: Filtration
More informationPHYS 1405 Conceptual Physics I Laboratory # 8 Density and Buoyancy. Investigation: How can we identify a substance by figuring out its density?
PHYS 1405 Conceptual Physics I Laboratory # 8 Density and Buoyancy Investigation: How can we identify a substance by figuring out its density? What to measure: Volume, mass. Measuring devices: Calipers,
More informationToday. Career Services and Fundamental Concepts in Environmental Engineering. Density. Example. Concentration
Career Services and Fundamental Concepts in Environmental Engineering CIEG 125 Introduction to Civil Engineering Fall 2005 Today Career Services Ethics Groups 10, 11 and 12 Fundamental Concepts in Environmental
More informationChapter 5. Name: Class: Date: Multiple Choice Identify the choice that best completes the statement or answers the question.
Class: Date: Chapter 5 Multiple Choice Identify the choice that best completes the statement or answers the question. 1. What is the pressure of the sample of gas trapped in the opentube mercury manometer
More informationFILTRATION. Introduction
FILTRATION Introduction Separation of solids from liquids is a common operation that requires empirical data to make predictions of performance. These data are usually obtained from experiments performed
More informationCHEM 1411, chapter 5 exercises
CHEM 1411, chapter 5 exercises 1. A gasfilled balloon with a volume of 12.5 L at 0.90 atm and 21 C is allowed to rise to the stratosphere where the temperature is 5 C and the pressure is 1.0 millibar.
More informationThe value of the wastewater flow used for sewer design is the daily peak flow. This can be estimated as follows:
This Section presents the theory of simplified sewer design. Firstly, in Section 2.1, the peak daily wastewater flow in the length of sewer being designed is described. Section 2.2 presents the trigonometric
More informationFor Water to Move a driving force is needed
RECALL FIRST CLASS: Q K Head Difference Area Distance between Heads Q 0.01 cm 0.19 m 6cm 0.75cm 1 liter 86400sec 1.17 liter ~ 1 liter sec 0.63 m 1000cm 3 day day day constant head 0.4 m 0.1 m FINE SAND
More information8. Pore analysis by adsorption
8. Pore analysis by adsorption 1 8.1. Kelvin equation Adsorption data pore size or pore size distribution θ P : equilibrium P in pores with a radius r. P 0 : equilibrium P 0 on planar surface. r : pore
More informationComparison of commercial and new developed adsorbent materials for precombustion CO 2 capture by pressure swing adsorption
Comparison of commercial and new developed adsorbent materials for precombustion CO 2 capture by pressure swing adsorption Johanna Schell, Nathalie Casas, Lisa Joss, Marco Mazzotti  ETH Zurich, Switzerland
More information
Unit Conversions. Ben Logan Feb 10, 2005
Unit Conversions Ben Logan Feb 0, 2005 Abstract Conversion between different units of measurement is one of the first concepts covered at the start of a course in chemistry or physics.
More information