1 Code Requirements for Existing Buildings Kevin S. Hastings, P.E., LEED AP R. W. Sullivan, Inc. 529 Main St., Suite 203 Charlestown, MA (617)
2 R.W. Sullivan Engineering (RWS) was established in 1945 and currently has 90 employees. RWS is a full service engineering firm offering integrated services in the following disciplines:
3 Sullivan Code Group Comprehensive Code Services Building, Fire, Life Safety, Accessibility Plan Review Existing Building Surveys (Statement of Conditions) Variances and Appeals National and International Experience
4 R.W. Sullivan Engineering Code Group Beyond the Code Revit Sustainability and LEED Atrium Fire/Smoke and Egress Modeling Hazardous Materials
5 Agenda Existing Buildings Building Code: Introduction to IEBC Compliance Options Prescriptive Work Area Performance Energy Code Accessibility Codes: Massachusetts Architectural Access Board Regulations American s with Disabilities Act
6 Applicable Codes in New England State Building Fire Energy Existing Connecticut Maine Massachusetts New Hampshire Rhode Island 2003 IBC 2009 IBC 2009 IBC 2009 IBC 2009 IBC 2003 IFC 2003 NFPA 101 NFPA 1 & CMR MA Fire Prevention 2009 NFPA 1 & NFPA 1 & IECC 2009 IECC 2003 IEBC 2003 NFPA IEBC 2009 NFPA IECC 2009 IEBC 2009 IECC 2009 IECC 2006 NFPA Vermont 2006 IBC 2006 IECC 1 & 101 Based on population and previous code adoptions 2009 IBC - C NFPA IBC - C.34 or Rehab. Code 2009 NFPA IBC - C NFPA 101
7 Existing Buildings Applicability to Existing Buildings (IBC Section 102.6) The legal occupancy of any structure existing on the date of adoption of this code shall be permitted to continue without change, except as is specifically covered in this code or, as deemed necessary by the building official for the general safety and welfare of the occupants and the public. MA Amendment: Any existing building or structure shall meet and shall be presumed to meet the provisions of the applicable laws, codes, rules or regulations, bylaws or ordinances in effect at the time such building or structure was constructed or altered
8 Int. Existing Building Code Three ways to comply with the code: Prescriptive Compliance Method (IBC Chapter 34): Additions, alterations or repairs, unless otherwise noted, follow that of new construction. Work Area Compliance Method: Requirements are based on level of work and generally applies to work area only. Performance Compliance Method (IBC Chapter 34): Utilizes a point system to ensure the level of public safety, health & welfare is maintained or exceeded after a renovation.
9 Prescriptive Compliance Method Chapter 3
10 Prescriptive Compliance Method Chapter 3 Building Must comply with IFC (IEBC ) General. Except as provided by Section or this section, alterations to any building or structure shall comply with the requirements of the International Building Code for new construction. Alterations shall be such that the existing building or structure is no less conforming to the provisions of the International Building Code than the existing building or structure was prior to the alteration.
11 Prescriptive Compliance Method Chapter 3 Additions (302): Additions to the building or structure must comply with 780 CMR (2009 IBC) for new construction. Combined height and area must conform to IBC.
12 Prescriptive Compliance Method Chapter 3 Fire Escapes (305) Existing fire escapes are allowed to be counted as means of egress on existing buildings if tested and certified. New fire escapes on existing buildings are only permitted if exterior stairs are infeasible. Restrictions on location Cannot access through a window or use ladders.
13 Prescriptive Compliance Method Chapter 3 Change of Occupancy (307) Cannot change use/occupancy unless the building meets the requirements of IBC for the proposed occupancy. Building official may permit change in use without full IBC compliance if the new use is less hazardous than the existing use based on life and fire risk.
14 Work Area Method Chapters 4 12
15 Work Area Compliance Chapters 4-12 Provisions are based on the type of work as defined in Chapter 4 Repairs (402): Patching, restoration, or replacement of damaged elements to good or sound condition for maintenance purposes. Level 1 Alteration (403): Alterations to elements to serve the same purpose. No reconfiguration of spaces. Level 2 Alteration (404): Reconfiguration of spaces Addition or elimination of windows or doors Installation of any additional equipment Renovation area 50% of the aggregate building area. Level 3 Alteration (405): Renovation area > 50% of the aggregate building area. Change of Occupancy (406) Additions (407) Historic Buildings (408) Relocated Structures (409)
16 Repairs Chapter 5 Nonstructural repair work other than routine maintenance / ordinary repairs requires a permit and can be made with same or like materials. Work shall not make the building less conforming that it was before the repair was undertaken.
17 Level 1 Alteration Chapter 6 New finishes must comply with the IBC for new construction ( ). All new work must comply with the materials and methods of the applicable code (602.4).
18 Level 2 Alteration Chapter 7 Compliance with Level 1 work required (701.2). All new construction and elements must comply with the code for new construction except as noted in Chapter 7 (701.3). For example dead end corridors and ceiling heights have slightly less stringent requirements.
19 Level 2 Alteration Floor Openings (703.2) All floor openings must be enclosed with 1-hour fire resistance rated construction except: Where permitted by the code for new construction Mini-Atrium 3 story atrium at grade Use Group specific allowances for rating reductions or allowed floor openings Existing open stairs up to 3 stories are permitted in fully sprinklered buildings of Use Group B, E, F, M, R-1, R-2, S
20 Level 2 Alteration Floor Openings (703.2) Additional Requirements ( ): If work area exceeds 50% of the floor area, then all vertical openings other than stairways must be enclosed (applies outside work area) Does not include vertical openings in tenant spaces completely outside the scope of work. Stairway Enclosure Requirements ( ): If work area exceeds 50% of the floor area, then all egress stairways must be enclosed with smoke-tight construction (at a minimum) from the highest work area floor and all floors below. Unless enclosure is not required by the IBC
21 Level 2 Alteration Chapter 7 Existing interior finishes in exits and corridors within work area must comply with IBC requirements (703.4) If the work area is > 50% of the floor area, entire floor must use IBC approved finishes Automatic sprinkler systems must be installed in the work area if: (704.2) The work area has exits or corridors shared by more than one tenant or they serve more than 30 occupants The work area exceeds 50% of the floor area The water supply is sufficient The IBC requires it Fire alarm systems are required in the work area for Use Group E, I, and R occupancies (704.4) Required throughout the floor if the work area exceeds 50% of that floor
22 Level 2 Alteration Chapter 7 Means of egress provisions only apply to work areas that include exits or corridors shared by more than one tenant. In general, egress requirements for doorways or corridors in work areas follow that of new construction ( ) Existing dead end corridors up to 35 ft are allowed (705.6) In other than A and H occupancies, dead end corridors up to 70 ft are allowed if fully sprinklered
23 Level 3 Alteration Chapter 8 Compliance with Level 1 and 2 work required (801.2) Existing shafts and vertical openings must be protected by a 1 hour wall from the floor of the work area to the level of exit discharge (803.1) Fire alarm and detection systems must be provided throughout the building where required by Section (Level 2). All Level 2 means of egress provisions apply regardless of number of tenants.
24 Change of Occupancy Chapter 9
25 Change of Occupancy Chapter 9 Definition - A change in the purpose or level of activity within a building that involves a change in application of the requirements of this code Can apply even when the occupancy classification is not changed.
26 Change of Occupancy Chapter 9 Hazard Categories determine what needs to be updated to new construction standards when changing occupancies.
27 Hazard Categories Chapter 9 Means of Egress (912.4) Height and Area (912.5) Exterior Wall Fire-Resistance (912.6) Enclosure of Vertical Shafts (912.7)
28 Hazard Categories Chapter 9 TABLE MEANS OF EGRESS HAZARD CATEGORIES RELATIVE HAZARD OCCUPANCY CLASSIFICATIONS 1 (Highest Hazard) H 2 I-2, I-3, I-4 3 A, E, I-1, M, R-1, R-2, R-4 4 B, F-1, R-3, S-1 5 (Lowest Hazard) F-2, S-2, U
29 Additions Chapter 10
30 Additions Chapter 10 All additions to existing structures, including areas impacted by an addition, must meet the new construction requirements unless otherwise noted (1001.1) Additions must meet height and area limitations of the code for new construction (1002.1) Existing fire areas increased by the addition must be provided with fire protection systems per the code for new construction (1002.3)
31 Performance Compliance Methods Chapter 13
32 Performance Compliance Methods Chapter 13 Applies to alterations, repairs, additions and change of occupancies in existing buildings including historic and moved. Cannot be used for Use Group H or I occupancies (1301.2).
33 Performance Compliance Methods Chapter 13 Change in Occupancy Provisions of this chapter must be that of the new occupancy Partial Change in Occupancy If separated by a fire barrier then only the section changed needs to comply If not, then the more stringent of the provisions between the two occupancies shall apply to the entire building Additions Must meet IBC requirements for new construction. Height and area limitations of IBC can not be exceeded If a fire wall is provided between existing building and addition, then the addition can be considered a separate building. Alterations and Repairs If the existing building does not comply with the code for new construction, any alterations or repairs cannot result in the buildings being less safe.
34 Performance Compliance Methods Chapter 13 The design evaluation is comprised of three main categories: Fire Safety Structural Fire Resistance Automatic Fire Detection Fire Alarm Fire-Suppression System Means of Egress Configuration Characteristics Support Features General Safety Fire Safety Parameters Means of Egress Parameters
35 Evaluation Example Chapter 13 Example Automatic Sprinklers Occupancy A-1, A-3, F, M, R, S-1 Categories a b c d e f A A-4, B, E, S Category a Sprinklers are required throughout; sprinkler protection is not provided or the sprinkler system design is not adequate for the hazard protected. 2. Category b Sprinklers are required in a portion of the building; sprinkler protection is not provided or the sprinkler system design is not adequate for the hazard protected. 3. Category c Sprinklers are not required; none are provided. 4. Category d Sprinklers are required in a portion of the building; sprinklers are provided in such portion; the system is one that complied with the code at the time of installation. 5. Category e Sprinklers are required throughout; sprinklers are provided throughout in accordance with Chapter 9 of the International Building Code. 6. Category f Sprinklers are not required throughout; sprinklers are provided throughout in accordance with Chapter 9 of the International Building Code.
36 Evaluation Building Score Section Insert points from evaluation of building elements
37 Mandatory Safety Scores Option for building official to require a peer review by a registered design professional prior to issuing a building permit
38 Structural Work Int. Existing Building Code Any work impacting existing structural systems must be evaluated by a structural engineer. Seismic Upgrades For both the Prescriptive Method and Work Area Method generally required when lateral load increased more than 10% due to alteration. However required compliance varies (Prescriptive Method generally preferred). MA Amendment for Masonry Walls (101.10): requires compliance with IEBC Appendix A1. Costly and scheduled for deletion.
39 Energy Code International Energy Conservation Code
40 Energy Code Additions, renovations, and repairs to an existing building system or portion thereof must conform to the code for new construction, without requiring the unaltered portion of the building to comply If the energy use of the building is not increased the following need not comply: Storm windows Glass only replacements in existing sash and frame (unless required elsewhere in IEBC) Existing ceiling, wall, and floor cavities exposed during construction if filled with insulation Construction where existing roof, wall or floor cavity is not exposed
41 Accessibility 521 CMR
42 ADA & Int. Codes Existing Buildings: Alterations Altered portions of a facility are required to comply with the accessibility regulations to the maximum extent feasible. The accessibility of the path of travel and facilities (toilet rooms, drinking fountains, etc.) serving an altered area must also be improved, unless the cost and scope of the overall alteration is disproportionate to the cost of the overall alteration. Disproportionate = cost exceeds 20% of the cost of primary alteration If the cost of alterations to the path of travel or facilities is disproportionate, these areas must still be improved up to 20% of the cost of the primary alteration.
43 ADA Existing Buildings: Removal of Barriers Existing Public Accommodation: architectural barriers must be removed where such removal is able to be carried out without much difficulty or expense. Priorities: Accessible route and entrance to facility. Access to areas within the facility where goods and services are made available to the public. Accessible restroom facilities. Take any other measures necessary to provide access to accommodations, privileges, advantages, goods, or services of a place of public accommodation
44 521 CMR: Massachusetts Architectural Access Board Existing Buildings: Renovations (3.3) The level of compliance for existing buildings is based on the following thresholds: Work costs less than $100,000: only the work being performed is required to comply. Work costs $100,000 or more but less than 30% of assessed value of existing building: in addition to work being performed, an accessible public entrance and an accessible toilet room, telephone and drinking fountain must comply with 521 CMR (if public toilets, telephones and drinking fountains are provided). Exempt Work: Curb cuts, MEP without architectural alterations, roof repair or replacement, window repair or replacement, repointing and masonry repair, septic systems, site utilities, and landscaping.
45 521 CMR: Massachusetts Architectural Access Board Existing Buildings: Renovations (3.3), con t Cost of work is equal to 30% or more of the assessed value of the existing building: entire building is required to comply with 521 CMR. Exempt Work: None In determining applicability of 521 CMR, the cost of all work performed within a 3 year period must be added together.
46 Questions? Kevin Hastings 46 R.W. Sullivan, Inc. (617) , Fax (617)
Massachusetts State Building Code 8 th Edition A. Vernon Woodworth, AIA, LEED AP Kevin S. Hastings, P.E., LEED AP R. W. Sullivan, Inc. 529 Main St., Suite 203 Charlestown, MA (617) 523-8227 www.rwsullivan.com
August 3, 2012 Existing Building Code 2012 versus the Rhode Island State By: Structural Engineers Association of Rhode Island, Building Code Committee Introduction At the request of the Building Code Standards
KBC Chapter 34 : Applying the Kentucky Building Code to Existing and Historic Buildings Presented by: Kentucky Department of Housing, Buildings, and Construction Kentucky Heritage Council Louisville Metro
! Building Codes Update: The 2009 International Fire Code and the Apartment Industry Apartment operators and developers should be aware of organizational changes in the 2009 edition of the International
9770 CULVER BOULEVARD CULVER CITY, CA 90232-0507 www.culvercity.org Construction Permitting Guidelines for Businesses Moving into Existing Buildings in Culver City If your business is moving into an existing
City of Dover Public Services http://www.cityofdover.com/ 302-736-7010, 7011, 4457 Commercial Plans General information for: New Construction, Renovations and Tenant Fit Outs. o Construction documents:
February 2014 Code Requirements and Inspections in Educational Occupancies Presented By: Barry W. Rickert Douglas M. Schanne Fire Marshal Training Program Supervisor Office of Education & Data Management
SWAN POINT YACHT & COUNTRY CLUB PROJECT INFORMATION: SCOPE OF WORK: INTERIOR ALTERATIONS ABBREVIATIONS: VICINITY MAP 33 East Charles Street PO Box 598 30-934-8078 PROPERTY MANAGER: DOTTIE HARPER BROOKFIELD
780 CMR: MASSACHUSETTS AMENDMENTS TO THE INTERNATIONAL EXISTING BUILDING CODE 2009 CHAPTER 34: EXISTING STRUCTURES 3401.1 Replace as follows: 3401.1 Scope. Chapter 34 of the International Building Code
Design Guidelines, Historic Districts and Codes as Downtown Development Tools The NC Rehab Code and Its Benefits for Older Buildings North Carolina Main Street Conference January 25-27, 2012 History of
Ch. 58 DIVISION D-O 34 CHAPTER 58. DIVISION D-O ORDINARY COMMERCIAL, INDUSTRIAL, OFFICE Sec. 58.1. Division D-O occupancies. 58.2. Separation and mixed occupancy. OCCUPANCY GROUP CONSTRUCTION TYPE MAXIMUM
City of Riverside Building & Safety Division Phone: (951) 826-5697 www.riversideca.gov BUILDING CODE REQUIREMENTS FOR CHILD DAY CARE The purpose of this document is to provide the user with a basic level
Rule 8. Indiana Building Rehabilitation Standard 675 IAC 12-8-1 Definitions Sec. 1. The following definitions apply throughout this rule: (1) "Building code" means the Indiana Building Code under 675 IAC
Home NJ Department of Community Affairs Governor Chris Christie Lt.Governor Kim Guadagno NJ Home Services A to Z Departments/Agencies FAQs Search All of NJ Announcements Upcoming Events FAQs Select Language
New Ontario Building Code Requirements for Mid-rise Wood Frame Buildings Note: This information addresses complex issues in a summary fashion. Consideration should be given to the official version of the
TOWN OF SIDNEY Multi-Family, Commercial, Industrial and Institutional Building Permit Guide The information provided is intended as a guide only and does not replace current bylaws and regulations. Complete
MAJOR 2015 MN RESIDENTIAL CODE CHANGES Effective Date: January 24 th, 2015 **Disclaimer: This document is to serve as informational purposes only. This is not a code book or a final interpretation of the
The New NYC Building Code Chapter 10 Means of Egress New York City Department of Buildings Technical Affairs Fatma M. Amer, P.E. Copyright Materials This presentation is protected by US and International
Vestibule Case Study [2003 IECC, 2006 IECC, 2003 IBC, 2006 IBC, 90.1-2001, 90.1-2004] Vestibule Requirement Intent Page 1 of 14 The primary intent behind the requirement for a vestibule is to reduce infiltration
Guidance on loft conversions in two-storey houses Technical guidance for building control surveyors, designers and installers 01 Guidance on loft conversions in two-storey houses Technical guidance for
City of La Habra Heights Building Division 1245 N. Hacienda Road La Habra Heights, CA 90631 Office: (562) 694-6302 ext. 228 Fax: (562) 690-5010 WINDOW REPLACEMENT 2010 CALIFORNIA RESIDENTIAL CODE (CRC)
Issued 01/01/13 Rev Page 1 of 5 If you intend to convert an existing loft space into additional rooms you will need to apply for Building Regulation Approval. You may also need Planning Permission if you
DCD-0304 Identification # Rev. 9/08 County Date of Inspection NAME OF OPERATION BUILDING INSPECTORS INSPECTION FORM FOR CHILD CARE CENTERS ADDRESS TELEPHONE: CITY STATE ZIP BUILDING INSPECTORS CERTIFICATE
Overview of Hotel Fire Safety Requirements in the Fire Code Susan Clarke, P.Eng. Office of the Fire Marshal - January 10, 2012 1 Agenda Regulation History - Hotels Fire Code Overview (Parts 1 to 8) Defined
The New NYC Building Code Chapter 11 Accessibility New York City Department of Buildings Technical Affairs Keith Wen, R.A. Copyright Materials This presentation is protected by US and International Copyright
Page 25 ABOUT CODE CORNER CCFS would like to remind you to check with your local Authority Having Jurisdiction (AHJ) for questions and opinions concerning your local Fire and Building Codes. The information
COMPLIANCE CHECKLIST Page 1 of 6 > Long Term Care Facility - Nursing Unit The following checklist is for plan review of new long-term care facilities and new additions to existing long-term care facilities.
Page 1 of 17 Page 2 of 17 Committee Input NFPA 101 Coordinate Smoke detector versus smoke alarm terminology. CODE PARAGRAPH WITH SUGGESTED CHANGES: 220.127.116.11.2 Residents should be rated as response probable
2012 Michigan Rehabilitation Code for Existing Buildings First Printing: June 2014 ISBN: 978-1-60983-208-7 COPYRIGHT 2014 by INTERNATIONAL CODE COUNCIL, INC. ALL RIGHTS RESERVED. This 2012 Michigan Rehabilitation
ADDENDUM NO. 2 TO REQUEST FOR QUALIFICATIONS FOR NEW DEVELOPMENT OF OAKLAND UNIFIED SCHOOL DISTRICT PROPERTIES, INCLUDING THE PARCELS HOUSING THE PAUL ROBESON ADMINISTRATION BUILDING AND DEWEY HIGH SCHOOL
SPECIAL RESIDENCE (ASSISTED SELF-PRESERVATION) OCCUPANCIES (Adopted by the State of Oregon) SECTION SR101 GENERAL SR101.1 General. Group SR occupancies shall comply with the provisions of this appendix
2009 IFC Performing Commercial Fire Inspections Inventory Number: 1424S09 Second Printing; July 2014 Changes HAVE been made- Third Printing: September 2014 Errata has been identified as follows: 1. Page
COMMONWEALTH OF MASSACHUSETTS STATE BUILDING CODE 780 CMR, 6 th Edition FIRE PROTECTION SYSTEMS CHAPTER 9 GUIDELINES FOR THE PREPARATION OF FIRE PROTECTION SYSTEM NARRATIVE REPORTS 780 CMR 903.1.1 State
Executive Summary Inclusion of Current Firewall Requirements in NBCC This background paper has been prepared on behalf of the Gypsum Manufacturers of Canada by Standing Committee on Fire Safety & Occupancy
Why does the renovation and expansion of an EXISTING SCHOOL sometimes cost about the SAME or MORE than the construction of a NEW SCHOOL? 1. BASIC FACTS: The current Abington High School building is 111,831
Area of Rescue Assistance Communication System ADA Code Applicable excerpts: CONTENTS (Guidelines and Definitions) Page 1 Area of Rescue Assistance Requirements Page 2 Emergency Communication Equipment
Excerpts from the Canadian National Building Code (NBC) Reproduced here with Permission of the Copyright Owner, the National Research Council of Canada, Institute for Research in Construction. For more
WINDOW AND DOOR REPLACEMENT REQUIREMENTS Should you have any questions after reading the following information, please call the Building Inspection Department at 651-439-4439 to discuss the topics of concern.
White Paper: Energy Efficiency Provisions in Building Rehabilitation Codes for Commercial Buildings - Pennsylvania & New Jersey January 2014 Citation: Rutgers Center for Green Building, David B. Hattis,
BUILDING REGULATIONS Newbury, New Hampshire Building Regulations last revised: March 11, 2008 Important Notice last revised: January 28, 2015 IMPORTANT NOTICE Please be advised that the following are suggestions
DESIGN EQUIEMENTS POJECT DELIVEABLES CHECKLISTS GENEAL INFOMATION 1.1 The following is a checklist to be used as a guide for the required deliverables for the Schematic Design phase. 1.2 Schematic Design
WALT WHITE Fire Chief 5770 Freeport Blvd., Suite 200 Sacramento, CA 95822-3516 Ph: (916) 808-1300 Fax: (916) 808-1629 www.sacfire.org Fire Alarm Systems Requirements by Occupancy Type 2013 California Building
MITT ROMNEY GOVERNOR KERRY HEALEY LT. GOVERNOR EDWARD A. FLYNN SECRETARY The Commonwealth of Massachusetts Executive Office of Public Safety Department of Fire Services P.O. Box 1025 State Road Stow, Massachusetts
EXISTING BUILDINGS AND STRUCTURES There are no margin bars shown in this chapter due to its substantial revision. SECTION AJ1 ADMINISTRATION SECTION AJ101 PURPOSE AND INTENT AJ101.1 Scope. The provisions
Classroom Door Security & Locking Hardware The ability to protect students and teachers while in the classroom is a high priority in all educational institutions. Many schools and school districts have
NFPA 101 Life Safety Code Section 5-8 Illumination of Means of Egress 5-8.1 General. 5-8.1* Illumination of means of egress shall be provided in accordance with this section for every building and structure
U. S. A CCESS B O A R D T E C H N I C A L G U I D E This guide explains requirements in the ADA Standards and referenced sections of the International Building Code (IBC) and was developed in cooperation
ARCHITECTURAL SAFETY FEATURES Exit Separations Continuation of Exit Stairs from lower to upper floors Discharge from Exits FIRE PROTECTION FEATURES Fire Command Centre FB Breeching Inlets ACMV EXIT SEPARATION
FIRE SAFETY INSPECTION REPORT SINCERE KNIT GARMENTS LTD UNIT-1 EAST ISDAIR, CHANDMARI, FATULLAH OTHER FACTORIES: FAKIR KNIT LTD. July 20, 2014 Page 2 SUMMARY was surveyed for fire safety on 7/20/2014 by
MINNESOTA DEPARTMENT OF PUBLIC SAFETY State Fire Marshal Division STATEMENT OF POLICY Policy #: Subject of Policy: INS-04 (2007) Escape Windows Revised and Approved By: Title: Jerry Rosendahl State Fire
2.02 DESIGN DEVELOPMENT PHASE GENERAL The Architect shall prepare the Design Development Documents from the approved Schematic Design. The Design Development Documents shall consist of drawings and other
General Safety & Health Standards Published by the Division of Building Safety In Cooperation with the Idaho Industrial Commission Local Fire Alarm 064. FIRE ALARM SYSTEMS 01. Scope 02. Definitions 03.
2010 FLORIDA BUILDNG CODE, FIRE AND LIFE SAFETY i Changes between the 2006 and 2009 Editions of the International Codes account for the vast majority of changes to the 2010 Florida Building Code. In many
CHAPTER 46 FIRE AND LIFE SAFETY REQUIREMENTS FOR EXISTING BUILDINGS SECTION 4601 GENERAL 4601.1 Scope. The provisions of this chapter shall apply to existing buildings constructed prior to a state building
CITY PLAN REVIEW AND INSPECTION Lisa Fleming Brown, CPM Houston Commercial Energy Conservation Code (2011) A choice of 2009 IECC or ASHRAE 90.1-2007 with amendments. Effective September 2, 2011. Complete
Appendix B 2010 Florida Building Code Building Section 423.25 Public Shelter Design Criteria 423.25 Public shelter design criteria. 423.25.1 New facilities. New educational facilities for school boards
AT THE STRATOSPHERE TOWER, LAS VEGAS NEVADA By: James R. Quiter, P.E., Senior Vice President Rolf Jensen & Associates, Inc. INTRODUCTION This paper discusses the performance based approach to fire protection
Sam Docknevich, PSP, Security Service Portfolio Manager Are You Prepared? The impending impact of Code on Servicing Security Systems usa.siemens.com/infrastructure-cities Share current and upcoming standards
CHAPTER 7 FIRE-RESISTANCE-RATED CONSTRUCTION SECTION 70 GENERAL 70. Scope. The provisions of this chapter shall govern the materials and assemblies used for structural fire resistance and fire-resistance-rated
Floor Area Calculation Floor area shall: Part A Fees Payable for Permits (Effective January 1, 2015) a) be calculated by measuring to the outer face of exterior walls and to the centre of party walls or
INITIAL YEAR BUILT 1968 BUILDING AREA 187,700 SF CURRENT PROGRAM CAPACITY N/A ENROLLMENT 2008 129 WARD 5 PROPOSED PROGRAM CAPACITY N/A Site Plan HAMILTON - 1 PROPOSED PROGRAM PROFILE GRADE CONFIGURATION
A Conversation on Energy Codes in Existing Buildings Webinar April 10, 2013 Agenda Overview / Historic Buildings Sean Denniston - NBI 15 minutes + QA Current I-Codes / Reorganization IECC Proposals Proposals
MINNESOTA STATE DEPARTMENT OF PUBLIC SAFETY State Fire Marshal Division 444 Cedar Street, Suite 145, St. Paul, Minnesota 55101-5145 Phone: 651/201-7200 FAX: 651/215-0525 TTY: 651/282/6555 Internet: http://www.fire.state.mn.us
CHAPTER 160 BUILDING CODE 160.01 International Building Code Adopted 160.27 Automatic Fire Sprinkler Systems 160.02 Amendments to the Building Code 160.28 Smoke Alarms 160.03 Name of Jurisdiction 160.29
APPENDIX M.O. 57/2012 Minimum Housing and Health Standards Original version July 20, 1999. Revisions to Part lll, Housing Premises, sections 3 and 4, June 30, 2012 (all revisions are bolded and underlined).
IECC Compliance Guide for Homes in Virginia Amended Version of 2012 International Energy Conservation Code July 14, 2014 Climate Zone Since the entire state of Virginia falls in the IECC Climate Zone 4,
IBCI CONFERENCE 22 nd MARCH 2007 Recent Trends in Fire Safety Design of Houses and Apartments COLIN BARDEN & PARTNERS LTD 11 Parnell Street Waterford TEL: 051-876545 FAX: 051-876534 EMAIL: email@example.com
Does Concord have its own Building codes? No, we utilize the 8th Edition of the Massachusetts State Building code for one and two family dwellings, multi-family dwellings, and Commercial Buildings. When
Amended by By-law 8-2016 Note: This consolidation is prepared for convenience only. For accurate reference the original by-laws should be reviewed. Floor Area Calculation Floor area shall: Schedule B to
A ROAD MAP FOR YOUR CODE, SMOKE BARRIER & SMOKE PARTITION REQUIREMENTS International Code Council National Fire Protection Association Underwriters Laboratories Inc. 5203 Leesburg Pike, Suite 600 1 Batterymarch
Date: 06/09/99 Ref: 45/1/166 Note: The following letter was issued by our former department, the Department for Environment, Transport and the Regions (DETR). DETR is now Communities and Local Government
- 5 - Part II - SPECIFIC REQUIREMENTS 5. Compartmentation 5.1 Every building should be divided into compartments by walls and floors to inhibit the spread of fire. 5.2 Compartment walls, compartment floors,
UCL Fire Technical Note - TN006 Fire Safety Technical Guide GENERAL FIRE SAFETY TERMS & DEFINITIONS Reference: BS4422-2005 Fire Safety Vocabulary - for further information and definitions BS EN ISO 13943-2000:
2010 ADA Standards for Accessible Design Department of Justice September 15, 2010 Reproduction of this document is encouraged. This publication may be viewed or downloaded from the ADA website (www.ada.gov).
Exterior Elevated Elements Inspection Guidelines Planning and Development 1. Guideline Purpose These guidelines are intended to assist practicing professionals in complying with Berkeley Municipal Code
th Edition i One- and Two-Family 8 th Dwelling Code: What s New? Presented by: Mike Guigli DPS, Technical Director firstname.lastname@example.org 617-826- 5215 Housekeeping Items Class Times Breaks/Lunch Cell
THE REQUIREMENTS This section of this Complying Document/Complimentary Guide? deals ways of meeting the following requirements in Part B of Schedule 1 to the Building Regulations 2000 (as amended) when
CHAPTER 9 FIRE PROTECTION SYSTEMS SECTION 901 GENERAL 901.1 Scope. Provisions of this chapter shall govern the application, design, installation, testing and maintenance of automatic sprinklers, standpipes
APPLYING MIXED USE, ACCESSORY USE AND INCIDENTAL PROVIONS OF THE 2006 INTERNAITONAL BUILDING CODE By: Carroll Lee Pruitt, FAIA, NCARB, ICC William Rakatansky, AIA, CSI, LEED AP Just when you thought that
FIRE LOSS STATISTICAL CONSIDERATIONS IN RELATING FAILURE AND BUILDING DAMAGE TO THE BUILDING CODE OBJECTIVES P.L. Senez*, K.D. Calder, Hsing H (Isabella) Li Sereca Fire Consulting Ltd., Canada INTRODUCTION