SteadyState Power System Security Analysis with PowerWorld Simulator


 Lorena Porter
 3 years ago
 Views:
Transcription
1 SteadyState Power System Security Analysis with PowerWorld Simulator S: Power System Modeling Methods and Equations 00 South First Street Champaign, Illinois (7)
2 Topics in the Section Nominal Voltage Levels Per Unit Values Admittance and Impedance YBus Matri Buses Transmission Branches Loads Switched Shunts Generators Power Flow Equations PV, PQ, Slack buses Newton's Method Multiple Solutions Bus Power Flow PV and QV Curves Maimum Loadability S: Power System Modeling 04 PowerWorld Corporation
3 Transmission System: Nominal Voltage Levels Why do transmission systems operate at many different voltage levels? Power Voltage * Current Thus for a given power, if you use a higher voltage, then the current will be lower Why do we care? Transmission Losses Losses Resistance * (Current) Eample: What if we want to transmit 460 MW? At 30 kv, that means,000 Amps At 5 kv, that means 4,000 Amps Because current is Twice as high for 5 kv, that means the losses would be 4 times higher Thus Higher Voltage is better, but more epensive, thus there is a tradeoff Means voltages vary depending on the situation S: Power System Modeling 04 PowerWorld Corporation 3
4 Transmission System: Nominal Voltage Levels Varying Nominal Voltage Harder for a human to compare the voltage levels Harder to handle in the equations used in power systems You d have to include turnsratio multipliers all over the place This leads the industry to use a normalization method 38 kv 345 kv 38 kv 69 kv 345 kv 345 kv 38 kv 69 kv S: Power System Modeling 04 PowerWorld Corporation 4
5 Transmission Voltage Normalization using PerUnit Values Per unit values are used in power systems to avoid worrying about various voltage level transitions created by transformers They also allow us to compare voltages using a percentagelike number All buses in the power system are assigned a Nominal Voltage. Normally this is corresponds the physical voltage rating of devices connected to this bus and voltages are epected to be close to this This means.00 per unit voltage is usually normal But strictly speaking it doesn t have to be. It s just a number used to normalize the various parameters in the power system model. Eample: In Western United States, there is a lot of 500 kv transmission, but it generally operates at about 55 kv S: Power System Modeling 04 PowerWorld Corporation 5
6 Base Values Define a Power Base (SBase ) for the entire system Transmission system SBase 00 MVA The Voltage Base (VBase) for each part of the system is equal to the nominal voltage From these determine the Impedance Base (ZBase) and Current Base (IBase) ZBase (VBase) SBase IBase SBase 3 VBase S: Power System Modeling 04 PowerWorld Corporation 6
7 Current Base Calculation: Line to Line Voltage Nominal Voltages are specified as the Line to Line voltage by tradition This is the voltage magnitude difference between the AB phase, BC phase, and CA phase V linetoground V linetoline 38 kv 80 kv LineGround Current applies to only one phase, but the Power is the sum across all three phases, thus S 3I V S 3IV linetoground linetoline 3 S MVARating I I Rating 3 3NomVoltage V line toline A B Ground C S: Power System Modeling 04 PowerWorld Corporation 7
8 Voltage Base Zones 345 kv 345 kv VBase 345 kv 38 kv 345 kv 38 kv VBase 38 kv 38 kv 69 kv 69 kv VBase 69 kv NOTE: Zones are separated by transformers S: Power System Modeling 04 PowerWorld Corporation 8
9 Determining a PerUnit Value To determine a perunit value, simply divide the actual number by the base For eample Z 0 + j50 ohms SBase 00 MVA ZBase S: Power System Modeling (38,000) 00,000, PowerWorld Corporation 38 kv Base Ohms Z 0 + j50 Ohms Zpu ZBase Ohms j0.65 9
10 The Transmission System  Model of the Wires YBus (Admittance Matri ) Will review the various parts of the transmission system How we model transmission system How these models are entered into software S: Power System Modeling 04 PowerWorld Corporation 0
11 Impedance (Z) and Admittance (Y) and related terms R, X, B, and G The comple number for Impedance is represented by the letter Z Z R + jx R Resistance X Reactance Admittance is the numeric inverse of Impedance and represented by the letter Y Y G + jb G Conductance B Susceptance S: Power System Modeling 04 PowerWorld Corporation
12 Conversion Between Impedance (Z) and Admittance (Y) Impedance and Admittance are comple numbers and are inverses of each other y z r + j r + r + g  j r + b g r r + b r + S: Power System Modeling 04 PowerWorld Corporation
13 YBus Matri (the Admittance Matri) Used to model ALL of the transmission lines, transformers, capacitors, etc. These are all the passive elements This part of the model does not change for different solution states Represents only constant impedances The YBus is an N X N matri N is the number of buses in the system A software package will calculate the YBus from the data provided by the user regarding the passive elements of the system Transmission Lines Line Shunts Switched Shunts (Capacitors/Reactors) Bus Shunts S: Power System Modeling 04 PowerWorld Corporation 3
14 Power System Bus (or node) Nominal Voltage (in kv) B Shunt, G Shunt (in Nominal Mvar) Voltage Magnitude in per unit (calculated) Used as initial guess in power flow solution Voltage Angle in degrees (calculated) Used as initial guess in power flow solution S: Power System Modeling 04 PowerWorld Corporation 4
15 Converting Nominal MW/Mvar into a per unit admittance G Shunt and B Shunt are given as MW or Mvar at Nominal Voltage ( GShuntMW and BShuntMVar ) They represent constant admittance G + jb Writing this in actual units Converting to Per Unit Values B pu + BShunt SBase MVar Similar derivation for G BShunt B MVar V nom BShunt SBase V nom V nom B MVar pu BShunt SBase MVar S: Power System Modeling 04 PowerWorld Corporation 5
16 Bus Shunts (B and G) Values epressed in MW/Mvar at nominal voltage Represent a constant impedance/admittance at bus B Shunt : represents an impedance Mvar injection G Shunt : represents an impedance MW absorption S: Power System Modeling Sign of B and G are opposite for historical reasons G represented a load term B represented a capacitor term YBus is affected only on diagonal On Bus Dialog Bus K Bus K 04 PowerWorld Corporation GShunt SBase MW BShunt + j SBase MVar 6
17 Transmission Branch (Line or Transformer) Impedance Parameters Series Resistance (R) in per unit Series Reactance (X) in per unit Shunt Charging (B) in per unit Shunt Conductance (G) in per unit On Branch Dialog Bus K R + jx Bus M jb G jb G S: Power System Modeling Note: This model is modified when including tapratios or phaseshifts for variable transformers 04 PowerWorld Corporation 7
18 Transmission Branch affect on the YBus To make the YBus, we epress all the impedances of the model as an admittance g series r r + b series + Then add several terms to the YBus as a result of the transmission line (or transformer) BusK BusM g BusK series + G jbseries + + ( g jb ) series series B j BusM g series r ( g jb ) + series series G jbseries + + B j S: Power System Modeling 04 PowerWorld Corporation 8
19 Switched Shunts (Capacitor and Reactor Banks) Input the nominal MVAR, the MVAR supplied by the capacitor at nominal voltage It represents a constant impedance Use same conversion as with the Bus Shunts YBus is thus affected only on diagonal terms Bus K On Switched Shunt Dialog Bus K + j QMVar SBase Bus K jb S: Power System Modeling 04 PowerWorld Corporation 9
20 What does YBus look like? Graphic represents a 8 Bus System Sparse or Mostly Zeros Incident Symmetric Each dot represents a nonzero entry in the YBus S: Power System Modeling 04 PowerWorld Corporation 0
21 Loads (ZIP model) Loads are modeled as constant impedance (Z), current (I), power (P), or a combination of the three For each of these values you specify a real power and a reactive power (P spec + jq spec ) Constant Power  the most commonly used On Load Dialog S Lk P + spec jq spec S: Power System Modeling 04 PowerWorld Corporation
22 Constant Current Load P+jQ specified are what the load would be at nominal voltage of.0 per unit Go back to the equations for comple power and derive epression for S S VI * I * S V P + jqspec Pspec + jq S V θ v.0 θv. 0 θv spec Load becomes a linear function of voltage magnitude On Load Dialog spec S V + Lk ( P jq spec spec ) S: Power System Modeling 04 PowerWorld Corporation
23 Constant Impedance Load P+jQ specified are what the load would be at nominal voltage of.0 per unit Go back to the equations for comple power load * spec * (.0) + jq spec * V Load becomes a quadratic function of voltage magnitude S S S VI P V V Z V Lk V + V Z Z * (P spec ( Pspec jqspec V S + ) jq P spec spec ) (.0) + jq On Load Dialog spec S: Power System Modeling 04 PowerWorld Corporation 3
24 Generators Model them as a source of Real and Reactive Power  MW, MVAR output Control features of generators AVR (Automatic Voltage Regulation) Controls the reactive power output (Q) to maintain a specified voltage level at a regulated bus (doesn t have to be the bus to which it is connected) AGC (Automatic Generation Control) Modifies the real power output (P) S: Power System Modeling 04 PowerWorld Corporation 4
25 Generator MW Power Control Input MW Output Minimum and Maimum MW Output Available for AGC Enforce Limits Participation Factor Used when on participation factor control On Generator Dialog S: Power System Modeling 04 PowerWorld Corporation 5
26 Generator Voltage Control Features Mvar Output Minimum and Maimum MVAR output Or can Use Capability Curve More detailed, but more data Voltage Setpoint in per unit Available for AVR Remote Regulation % Used when more than one generator is controlling the same bus voltage S: Power System Modeling On Generator Dialog (AVR) 04 PowerWorld Corporation Q out Must Stay inside shaded region during operation P out 6
27 The Power Flow Equations This is the heart of all power system analysis Kirchoff s Laws for a power system: Sum of the Currents at every Node Equals Zero S: Power System Modeling 04 PowerWorld Corporation 7
28 Why the Power Flow? Many loads (like heaters) are just big resistors which should be just an impedance, so why solve the power flow? Because our input data is MW and MVAR values. This is because The eperience of utilities for more than 00 years shows that consumers behave similar to constant power over the longrun If the voltage drops on a heater, the power consumption also decreases, but eventually some people get cold and turn up the heat Actually the built in thermostat and control system probably do this automatically S: Power System Modeling 04 PowerWorld Corporation 8
29 Deriving the Power Flow Equations Using the YBus, write Kirchoff s Current Law at every bus as a matri equation YV I I 0 generators + loads We are studying POWER systems, so we like to talk about power not current, so S VI * * [V](V Y * [V](V Y * ) S * generators ) [V]I + S loads * generators etc. These are N comple number equations (where N the number of buses in the system) 0 + [V]I * loads 0 S: Power System Modeling 04 PowerWorld Corporation 9
30 The Power Flow Equations These N comple number equations can then be written as *(N) real number equations as below P k 0 V N k m [ V [ g cos( δ δ ) + b sin( δ δ ) ] m km k m km k m P Gk + P Lk Transmission lines, transformers, capacitors Generators Loads Q k 0 V N k m [ Vm[ gkm sin( δ k δ m ) bkm cos( δ k δ m ) ] QGk + QLk S: Power System Modeling Elements of the YBus Note: The variables g km and b km are the real and imaginary parts of the YBus. ( Y G + jb or y km g km + jb km ) 04 PowerWorld Corporation 30
31 The Power Flow Equation Variables Four parameters describe the bus Voltage magnitude (V) Voltage angle (δ or θ) Real Power Injection (P P gen  P load ) Reactive Power Injection (Q Q gen  Q load ) The objective of the Power Flow algorithm is to determine all four of these values S: Power System Modeling 04 PowerWorld Corporation 3
32 Three Types of Buses In the Power Flow we are given two of these values at each bus and then solve for the other two Generally, there are three types of buses in a Power Flow Type of Bus Slack Bus (VδBus) (only one of these) PVBus (generator on AVR control) PQBus (load or generator not on AVR control) Voltage Mag. (V) Voltage Angle (δ) Power Injection (P P gen P load ) Reactive Power Injection (Q Q gen Q load ) GIVEN GIVEN SOLVE FOR SOLVE FOR GIVEN SOLVE GIVEN SOLVE FOR FOR SOLVE SOLVE GIVEN GIVEN FOR FOR S: Power System Modeling 04 PowerWorld Corporation 3
33 How does the Power Flow work? The power flow equations are nonlinear, which means they can not be directly solved Linear: , so 7 Nonlinear: 5 sin(), so??? To solve nonlinear equations, an iterative technique must be used To solve the Power Flow, Newton s Method is normally the best technique Simulator uses this by default. S: Power System Modeling 04 PowerWorld Corporation 33
34 Solving NonLinear Equations Power Flow Equations are NONLINEAR equations. There are cos(*) and sin(*) terms which make the equations nonlinear This means that finding a direct solution to them is impossible Thus we must use iterative numerical schemes to determine their solution For power flow equations, variations on Newton s Method has been found to be the best technique S: Power System Modeling 04 PowerWorld Corporation 34
35 35 04 PowerWorld Corporation S: Power System Modeling Discussed in Calculus courses Consider a simple scalar equation f() You can write f() as a Taylor Series Newton s Method... ) ( ) ( ) ( ) ( h o t f f f f + + +
36 36 04 PowerWorld Corporation S: Power System Modeling Now, approimate this Taylor Series by ignoring all but the first two terms We are trying to find where f() 0 (the power flow equations sum to zero), therefore we can approimate and estimate Newton s Method for Scalar Functions ) ( ) ( ) ( f f f + [ ] [ ] ) ( ) ( f f f [ ] ( 0 ) 0 0 f f
37 Newton s Method This is called an iterative method because you take a guess at 0 and use the Newtonstep to a new guess called. Then you use to find, etc. Consider f() . We find Thus f S: Power System Modeling k k ( ) k k k and + + ( k + k k k k k 04 PowerWorld Corporation ) 37
38 Newton s Method Now take and initial guess, say 0, and iterate the previous equation k k f( k ) k Done Error decreases quite quickly Quadratic convergence f( k ) is known as the mismatch The problem is solved when the mismatch is zero S: Power System Modeling 04 PowerWorld Corporation 38
39 NonLinear Equations can have Multiple Solutions Consider the previous eample. There are two solutions. and In an iterative scheme, the initial guess determines which solutions you converge to. Consider starting at 0 . k k f( k ) k Done S: Power System Modeling 04 PowerWorld Corporation S39 39
40 NonLinear Equations can have No Real Solution Consider the equation  λ 0, where λ is an independent parameter The number of real solutions depends on the value of λ. For λ > 0, there are two real solutions For λ 0, there is one real solution at 0 For λ <0, there are NO real solutions Parameter variation can change the number of solutions of nonlinear systems S: Power System Modeling 04 PowerWorld Corporation 40
41 NewtonRhapson Convergence Characteristics Global convergence characteristics of the NR algorithm are not easy to characterize The NR algorithm converges quite quickly provided the initial guess is close enough to the solution However the algorithm doesn t always converge to the closest solution Some initial guesses are just plain bad. For eample, if f is near zero ( illconditioned ), the process may diverge S: Power System Modeling 04 PowerWorld Corporation 4
42 Etending Scalar to Vectors and Matrices Newton s method may also be used when you are trying to find a solution where many functions are equal to zero Let f() be a ndimensional function and let be an ndimensional vector f ( ) f f n ( ) ( ) n S: Power System Modeling 04 PowerWorld Corporation 4
43 43 04 PowerWorld Corporation S: Power System Modeling Now, the Newtonstep is still defined as But is now a matri, called the Jacobian Newton s Method for Multiple Equations ) ( k k k k f f k + n n n n f f f f f f f f f
44 Solving the Power Flow Equations Power Flow Equations are NONLINEAR equations The cos(*) and sin(*) terms make them nonlinear This means we have to use an iterative technique to solve them Define f to be the real and reactive power balance equations at every bus Define to be the vector of voltages and angles at every bus (ecept the slack bus) S: Power System Modeling 04 PowerWorld Corporation 44
45 45 04 PowerWorld Corporation S: Power System Modeling Recall Thus, Setting up the Power Flow Solution ( ) ( ) [ ] [ ] ( ) ( ) [ ] [ ] Lk Gk N m m k km m k km m k Lk Gk N m m k km m k km m k Q Q b g V V Q P P b g V V P k k cos sin sin cos δ δ δ δ δ δ δ δ and ) ( n n n n V V V Q P Q P Q P δ δ δ f n n n n n n n n n n n n n n n n V Q Q V Q Q V P P V P P V Q Q V P P V Q Q V Q Q V Q Q V P P V P P V P P δ δ δ δ δ δ δ δ δ δ δ δ f Note: There are n buses, with bus n being the slack bus
46 Power Flow Solutions The power flow equations ehibit the same behavior as other nonlinear equations In theory there are up to n  solutions to the power flow equations Of these, ALL or NONE may be real number solutions In power system analysis, we are normally interested only in the solution that is the high voltage solution for every bus S: Power System Modeling 04 PowerWorld Corporation S46 46
47 Eample TwoBus Power System Consider this lossless (R0) eample system Bus (Slack) R+jX j0.00 Bus P + j Q L L Variable Definitions Power balance equations : θ Voltage Angle at Bus V Voltage Magnitude at Bus 0. B 0 r PMismatch P QMismatch Q L L BV sin( θ ) + BV cos( θ ) BV S: Power System Modeling 04 PowerWorld Corporation 47
48 How do power flow solutions vary as load is changed? Solution: Calculate a series of power flow solutions for various load levels First determine the following f J( θ, V ) BV BV cos( θ ) sin( θ ) Bsin( θ ) B cos( θ ) BV k θ V ; f ( ) Q L L + P BV sin( θ ) BV cos( θ ) BV S: Power System Modeling 04 PowerWorld Corporation 48
49 Eample Power Flow Solution Now for each load level, iterate from an initial guess until the solution (hopefully) converges [ f ( 0 )] Consider a per unit load of P L pu and Q L 0 pu A 00 MW load since SBase 00 MVA 0 f Then consider a flat start for the initial guess: V 0 ; θ 0 0. Also consider a start of V ; θ S: Power System Modeling 04 PowerWorld Corporation S49 49
50 Power Flow Two Bus.ls Simple Bus Power Flow in Ecel Open Microsoft Ecel \S0_SystemModeling\Power Flow Two Bus.ls Gray Shaded cells are user inputs (initial guess, load and network parameters) S: Power System Modeling 04 PowerWorld Corporation 50
51 Iteration Results for Power Flow Solution Power Flow Two Bus.ls Change Initial Voltage to V 0 ; θ 0 0 Cell B5.0 Cell C5 0.0 Change Initial Voltage to V ; θ 0  Cell B5 0.5 Cell C5 .0 S: Power System Modeling k V k θ k (radians) High Voltage Solution k V k θ k (radians) Low Voltage Solution 04 PowerWorld Corporation 5
52 Region of Convergence Initial guess of Bus angle is plotted on ais, voltage magnitude on yais, for load 00 MW, 00 Mvar; 0. pu Initial guesses in the red region converge to the high voltage solution, while those in the yellow region converge to the low voltage solution S: Power System Modeling 04 PowerWorld Corporation 5
53 PVCurves A PVCurve is generated by plotting these two solutions as the real power load is varied with the reactive load and impedance constant Eperiment with parameters in cells OO4 Higher transmission impedance usually decreases the system capacity (maimum load) Per unit voltage magnitude High voltage solutions Low voltage solutions Real power load (MW) S: Power System Modeling 04 PowerWorld Corporation Note: load values below 500 have two solutions, those above 500 have no solution For a critical value (i.e. the nose point ) there is only one solution 53
54 QVCurves A QVCurve is generated by plotting these two solutions as the reactive power load is varied with the real load and impedance constant Per unit voltage magnitude High voltage solutions 0. Low voltage solutions Reactive power load (Mvar) S: Power System Modeling 04 PowerWorld Corporation Again: load values below 50 have two solutions, while those above 50 have no solution For a critical value (i.e. the nose point ) there is only one solution 54
55 Maimum Loadability The nose points on the PV and QV curves are critical values They correspond to points of maimum loadability from a static point of view Note: this only considers the static equations. Other problems can occur long before the power system reaches this points: lines overheating or system dynamic problems The critical values depend on the relative allocation between real and reactive power S: Power System Modeling 04 PowerWorld Corporation 55
56 Mathematical Characteristics of the Critical Value At the critical value, the power flow Jacobian will be singular A singular matri is one that has a zero determinant (a generalization of scalar case when df/d 0) A singular matri CANNOT be inverted Thus the Newton power flow does not work well near this point because it requires us to invert the Jacobian matri S: Power System Modeling k f + k 04 PowerWorld Corporation f ( k k k ) 56
Power System Analysis Prof. A. K. Sinha Department of Electrical Engineering Indian Institute of Technology, Kharagpur. Lecture  19 Power Flow IV
Power System Analysis Prof. A. K. Sinha Department of Electrical Engineering Indian Institute of Technology, Kharagpur Lecture  19 Power Flow IV Welcome to lesson 19 on Power System Analysis. In this
More informationWeightedLeastSquare(WLS) State Estimation
WeightedLeastSquare(WLS) State Estimation Yousu Chen PNNL December 18, 2015 This document is a description of how to formulate the weightedleast squares (WLS) state estimation problem. Most of the formulation
More informationIntroduction to PowerWorld Simulator: Interface and Common Tools
Introduction to PowerWorld Simulator: Interface and Common Tools 2001 South First Street Champaign, Illinois 61820 +1 (217) 384.6330 support@powerworld.com http://www.powerworld.com Fault Analysis Analysis
More informationECE 740. Optimal Power Flow
ECE 740 Optimal Power Flow 1 Economic Dispatch A B C L Objective: minimize the cost of generation Constraints Equality constraint: load generation balance Inequality constraints: upper and lower limits
More informationSAMPLE OF THE STUDY MATERIAL PART OF CHAPTER 3. Symmetrical Components & Faults Calculations
SAMPLE OF THE STUDY MATERIAL PART OF CHAPTER 3 3.0 Introduction Fortescue's work proves that an unbalanced system of 'n' related phasors can be resolved into 'n' systems of balanced phasors called the
More informationPower System Simulation for Engineers (PSS/E version 33)
Power System Simulation for Engineers (PSS/E version 33) Here are instructions for accessing and using the PSS/E33 software. Oncampus students should access this software at any of the computers in the
More informationSymmetrical short circuit on Synchronous Machine
Introduction Short circuit study is one of the basic power system analysis problems. It is also known as fault analysis. When a fault occurs in a power system, bus voltages reduces and large current flows
More informationA Direct Numerical Method for Observability Analysis
IEEE TRANSACTIONS ON POWER SYSTEMS, VOL 15, NO 2, MAY 2000 625 A Direct Numerical Method for Observability Analysis Bei Gou and Ali Abur, Senior Member, IEEE Abstract This paper presents an algebraic method
More informationRoots of equation fx are the values of x which satisfy the above expression. Also referred to as the zeros of an equation
LECTURE 20 SOLVING FOR ROOTS OF NONLINEAR EQUATIONS Consider the equation f = 0 Roots of equation f are the values of which satisfy the above epression. Also referred to as the zeros of an equation f()
More informationFault Analysis I131. 2008 PowerWorld Corporation
Fault Analysis Analysis of power system parameters resulting from a ground or line to line fault somewhere in the system Simulator contains a tool for analyzing faults in an automatic fashion Can perform
More informationLAB1 INTRODUCTION TO PSS/E EE 461 Power Systems Colorado State University
LAB1 INTRODUCTION TO PSS/E EE 461 Power Systems Colorado State University PURPOSE: The purpose of this lab is to introduce PSS/E. This lab will introduce the following aspects of PSS/E: Introduction to
More informationPower System Simulation for Engineers (PSS/E): Fault Analysis
Power System Simulation for Engineers (PSS/E): Fault Analysis Table of contents: A. GENERAL INSTRUCTIONS 1 B. REQUIRED DATA 2 C. READING AN EXISTING CASE 2 D. SAVING A CASE 4 E. CREATING A NEW CASE 4 F.
More informationOPTIMAL DISPATCH OF POWER GENERATION SOFTWARE PACKAGE USING MATLAB
OPTIMAL DISPATCH OF POWER GENERATION SOFTWARE PACKAGE USING MATLAB MUHAMAD FIRDAUS BIN RAMLI UNIVERSITI MALAYSIA PAHANG v ABSTRACT In the reality practical power system, power plants are not at the same
More informationChapter 12. RL Circuits. Objectives
Chapter 12 RL Circuits Objectives Describe the relationship between current and voltage in an RL circuit Determine impedance and phase angle in a series RL circuit Analyze a series RL circuit Determine
More informationChapter 10. RC Circuits. Objectives
Chapter 10 RC Circuits Objectives Describe the relationship between current and voltage in an RC circuit Determine impedance and phase angle in a series RC circuit Analyze a series RC circuit Determine
More informationStatic Analysis of Power Systems. Lennart Söder and Mehrdad Ghandhari
Static Analysis of Power Systems Lennart Söder and Mehrdad Ghandhari Electric Power Systems Royal Institute of Technology August 200 ii Contents Introduction 2 Power system design 3 2. The development
More informationA New Method for Estimating Maximum Power Transfer and Voltage Stability Margins to Mitigate the Risk of Voltage Collapse
A New Method for Estimating Maximum Power Transfer and Voltage Stability Margins to Mitigate the Risk of Voltage Collapse Bernie Lesieutre Dan Molzahn University of WisconsinMadison PSERC Webinar, October
More informationShift Factors: Methodology and Example
Shift Factors: Methodology and Example CRR Educational Class #5 CAISO Market Operations Why are Shift Factors Important to the Allocation Process? The shift factors are derived directly from the DC version
More informationIMPROVED NETWORK PARAMETER ERROR IDENTIFICATION USING MULTIPLE MEASUREMENT SCANS
IMPROVED NETWORK PARAMETER ERROR IDENTIFICATION USING MULTIPLE MEASUREMENT SCANS Liuxi Zhang and Ali Abur Department of Electrical and Computer Engineering Northeastern University Boston, MA, USA lzhang@ece.neu.edu
More informationPowerWorld Simulator
PowerWorld Simulator Quick Start Guide 2001 South First Street Champaign, Illinois 61820 +1 (217) 384.6330 support@powerworld.com http://www.powerworld.com Purpose This quick start guide is intended to
More informationPower System review W I L L I A M V. T O R R E A P R I L 1 0, 2 0 1 3
Power System review W I L L I A M V. T O R R E A P R I L 1 0, 2 0 1 3 Basics of Power systems Network topology Transmission and Distribution Load and Resource Balance Economic Dispatch Steady State System
More informationRadial Distribution Test Feeders
Radial Distribution Test Feeders Distribution System Analysis Subcommittee Report Abstract: Many computer programs are available for the analysis of radial distribution feeders. In 1992 a paper was published
More informationVoltage Regulation by Distributed Generation
Voltage Regulation by Distributed Generation Supported by the NSW Government Energy Efficiency Training Program Kashem Muttaqi Overview Understanding the concept of voltage regulation by a DG system Method
More informationContouring and Advanced Visualization
Contouring and Advanced Visualization Contouring Underlay your oneline with an image Geographic Data Views Autocreated geographic data visualization Emphasis of Display Objects Make specific objects standout
More informationPower Technology Issue 104. Modeling of TwoWinding Voltage Regulating Transformers for Positive Sequence Load Flow Analysis in PSS E
SIEMENS Siemens Energy, Inc. Power Technology Issue 104 Modeling of TwoWinding Voltage Regulating Transformers for Positive Sequence Load Flow Analysis in PSS E Carlos GrandeMoran, Ph.D. Principal Consultant
More informationChapter 9 Balanced Faults
Chapter 9 alanced Faults 9.1 Introduction The most common types of fault are (in order) singlelinetoground fault, linetoline fault, and doublelinetoground fault. All of these are unbalanced faults.
More informationReactance and Impedance
Reactance and Impedance Capacitance in AC Circuits Professor Andrew H. Andersen 1 Objectives Describe capacitive ac circuits Analyze inductive ac circuits Describe the relationship between current and
More informationTransient Stability Analysis with PowerWorld Simulator
Transient Stability Analysis with PowerWorld Simulator T6: Storage of Transient Stability Results 2001 South First Street Champaign, Illinois 61820 +1 (217) 384.6330 support@powerworld.com http://www.powerworld.com
More informationKeysight Technologies Understanding the Fundamental Principles of Vector Network Analysis. Application Note
Keysight Technologies Understanding the Fundamental Principles of Vector Network Analysis Application Note Introduction Network analysis is the process by which designers and manufacturers measure the
More informationVoltage Stability Improvement using Static Var Compensator in Power Systems
Leonardo Journal of Sciences ISSN 15830233 Issue 14, JanuaryJune 2009 p. 167172 Voltage Stability Improvement using Static Var Compensator in Power Systems Department of Electrical/Computer Engineering,
More informationTransmission Lines. Smith Chart
Smith Chart The Smith chart is one of the most useful graphical tools for high frequency circuit applications. The chart provides a clever way to visualize complex functions and it continues to endure
More informationDistributed Flexible AC Transmission System (D FACTS) Jamie Weber. weber@powerworld.com, 217 384 6330 ext. 13
Distributed Flexible AC Transmission System (D FACTS) Jamie Weber weber@powerworld.com, 217 384 6330 ext. 13 Slide Preparation: Kate Rogers Davis kate@powerworld.com, 217 384 6330, Ext 14 2001 South First
More informationTransmission Lines. Smith Chart
Smith Chart The Smith chart is one of the most useful graphical tools for high frequency circuit applications. The chart provides a clever way to visualize complex functions and it continues to endure
More informationEstimating LineFlow Limits
Estimating LineFlow Limits University of WisconsinMadison May 1, 2013 Specifying reasonable lineflow limits requires two quantities: the surge impedance loading for the line and an estimate of the line
More informationLecture Notes ELE A6
ecture Notes EE A6 Ramadan ElShatshat Three Phase circuits 9/12/2006 EE A6 Threephase Circuits 1 Threephase Circuits 9/12/2006 EE A6 Threephase Circuits 2 Advantages of Threephase Circuits Smooth
More informationVoltage regulation in distribution systems  Tap changer and Wind Power
CODEN:LUTEDX/(TEIE5270)/159/(2010) Industrial Electrical Engineering and Automation Voltage regulation in distribution systems  Tap changer and Wind Power David Sáez Romero D of Industrial Electrical
More informationNUMERICAL OPTIMIZATION AND MODELING TECHNIQUES FOR POWER SYSTEM OPERATIONS AND PLANNING
NUMERICAL OPTIMIZATION AND MODELING TECHNIQUES FOR POWER SYSTEM OPERATIONS AND PLANNING A DISSERTATION SUBMITTED TO THE DEPARTMENT OF ELECTRICAL ENGINEERING AND THE COMMITTEE ON GRADUATE STUDIES OF STANFORD
More informationGenerator and Area Real Power Control
Generator and Area Real Power Control Scaling Case Load and Generation Control of generator real power Generator cost models Area interchange control Modeling MW transactions Areas the belong to multiple
More informationBasic AC Reactive Components IMPEDANCE
Basic AC Reactive Components Whenever inductive and capacitive components are used in an AC circuit, the calculation of their effects on the flow of current is important. EO 1.9 EO 1.10 EO 1.11 EO 1.12
More informationEquipment: Power Supply, DAI, Variable resistance (8311), Variable inductance (8321)
Lab 4: 3phase circuits. Objective: to study voltagecurrent relationships in 3phase circuits; to learn to make delta and Y connections; to calculate and measure real, apparent, and reactive powers. Equipment:
More informationChapter 24. ThreePhase Voltage Generation
Chapter 24 ThreePhase Systems ThreePhase Voltage Generation Threephase generators Three sets of windings and produce three ac voltages Windings are placed 120 apart Voltages are three identical sinusoidal
More informationFrequency response of a general purpose singlesided OpAmp amplifier
Frequency response of a general purpose singlesided OpAmp amplifier One configuration for a general purpose amplifier using an operational amplifier is the following. The circuit is characterized by:
More information2.1 Introduction. 2.2 Terms and definitions
.1 Introduction An important step in the procedure for solving any circuit problem consists first in selecting a number of independent branch currents as (known as loop currents or mesh currents) variables,
More informationPower Technology Issue 106. Modeling of ThreeWinding Voltage Regulating Transformers for Positive Sequence Load Flow Analysis in PSS E
SIEMENS Siemens Energy, Inc. Power Technology Issue 106 Modeling of ThreeWinding Voltage Regulating Transformers for Positive Sequence Load Flow Analysis in PSS E Carlos GrandeMoran, Ph.D. Principal
More information4.2 Impedance and Admittance Matrices
/0/009 _ mpedance and Admittance Matricies.doc /. mpedance and Admittance Matrices Reading Assignment: pp. 707 A passive load is an example of a port device only one transmission line is connected to
More informationUsing Microsoft Excel Builtin Functions and Matrix Operations. EGN 1006 Introduction to the Engineering Profession
Using Microsoft Ecel Builtin Functions and Matri Operations EGN 006 Introduction to the Engineering Profession Ecel Embedded Functions Ecel has a wide variety of Builtin Functions: Mathematical Financial
More informationSystem Analysis with the MVA Method for Symmetrical ThreePhase Faults
System Analysis with the Method for Symmetrical ThreePhase Faults Adnan Kakilli 1 1 Marmara University Technical Education Faculty, Istanbul, Turkey Abstract Electric energy is one of the fundamental
More informationUnderstanding Power Factor and How it Affects Your Electric Bill. Presented by Scott Peele PE
Understanding Power Factor and How it Affects Your Electric Bill Presented by Scott Peele PE Understanding Power Factor Definitions kva, kvar, kw, Apparent Power vs. True Power Calculations Measurements
More informationSParameters and Related Quantities Sam Wetterlin 10/20/09
SParameters and Related Quantities Sam Wetterlin 10/20/09 Basic Concept of SParameters SParameters are a type of network parameter, based on the concept of scattering. The more familiar network parameters
More informationApril 8. Physics 272. Spring Prof. Philip von Doetinchem
Physics 272 April 8 Spring 2014 http://www.phys.hawaii.edu/~philipvd/pvd_14_spring_272_uhm.html Prof. Philip von Doetinchem philipvd@hawaii.edu Phys272  Spring 14  von Doetinchem  218 LC in parallel
More informationPower transformers in parallel which share a neutral resistance: how to manage the circulating current between the secondary windings
Power transformers in parallel which share a neutral resistance: how to manage the circulating current between the secondary windings M.Sc. Eng. G.Calzolari, Member, IEEE, M.Sc. Eng. C.Saldaña, Member,
More informationCHAPTER 4. APPLICATION AND COMPARISON OF MOEAs TO MORPP PROBLEM
68 CHAPTER 4 APPLICATION AND COMPARISON OF MOEAs TO MORPP PROBLEM 4.1 INTRODUCTION This chapter describes about the application and comparison of MOEAs viz. NSGAII, MNSGAII and IGDE3 to solve MORPP
More informationDC power flow in unit commitment models
WP EN201412 DC power flow in unit commitment models Kenneth Van den Bergh, Erik Delarue and William D haeseleer TME Working Paper  Energy and Environment Last update: May 2014 An electronic version of
More informationImpact of untransposed 66kV subtransmission lines on voltage unbalance
University of Wollongong Research Online Faculty of Engineering  Papers (Archive) Faculty of Engineering and Information Sciences 2006 Impact of untransposed 66kV subtransmission lines on voltage unbalance
More informationштш User Manual 1.2.7 beta www.inorxl.com
штш User Manual 1.2.7 beta www.inorxl.com 2 TABLE OF CONTENTS What is InorXL?... 3 How to quickstart?... 3 What can you do with InorXL?... 3 What integration with Excel gives?... 4 What is system requirements?...
More informationRegular paper. Power Market Analysis Tool for Congestion Management. JES Proof
Silpa PARNANDI Karl SCHODER Ali FELIACHI Regular paper Power Maret Analysis Tool for Congestion Management In this paper a Power Maret Analysis Tool (PMAT) is designed for congestion management. The tool
More informationChapter 15 10/14/2014
Chapter 15 Analyze series and parallel ac circuits to find Voltage Current Power Total impedance, admittance Apply known circuit theories Kirchhoff s current, voltage laws Voltage or current divider rule
More informationA progressive method to solve largescale AC Optimal Power Flow with discrete variables and control of the feasibility
A progressive method to solve largescale AC Optimal Power Flow with discrete variables and control of the feasibility Manuel Ruiz, Jean Maeght, Alexandre Marié, Patrick Panciatici and Arnaud Renaud manuel.ruiz@artelys.com
More informationRecord Specification and File Format for Specifying Contingency Definitions and Remedial Actions Schemes
Record Specification and File Format for Specifying Contingency Definitions and Remedial Actions Schemes Date : October 22, 2013 December 6, 2013 January 21, 2015 August 28, 2015 November 6, 2015, November
More informationDirect versus Alternating Current Things We Can Measure
Phil Sherrod W4PHS Direct versus Alternating Current Things We Can Measure Direct Current (DC) Alternating Current (AC) Voltage Voltage (peak, RMS) Current Current (peak, effective) Power True power, Apparent
More informationCOMPREHENSIVE DISTRIBUTION POWER FLOW: MODELING, FORMULATION, SOLUTION ALGORITHMS AND ANALYSIS
COMPREHENSIVE DISTRIBUTION POWER FLOW: MODELING, FORMULATION, SOLUTION ALGORITHMS AND ANALYSIS A Dissertation Presented to the Faculty of the Graduate School of Cornell University in Partial Fulfillment
More informationThree phase circuits
Three phase circuits THREE PHASE CIRCUITS THREEPHASE ADVANTAGES 1. The horsepower rating of threephase motors and the kva rating of threephase transformers are 150% greater than singlephase motors
More informationPowerWorld Simulator for Market Analysis
Quick Start for Using PowerWorld Simulator for Market nalysis Overview This is a quick tutorial of PowerWorld Simulator s Optimal Power Flow (OPF) tool for analyzing power markets. The examples may be
More informationBasic Laws Circuit Theorems Methods of Network Analysis NonLinear Devices and Simulation Models
EE Modul 1: Electric Circuits Theory Basic Laws Circuit Theorems Methods of Network Analysis NonLinear Devices and Simulation Models EE Modul 1: Electric Circuits Theory Current, Voltage, Impedance Ohm
More informationLaboratory #2: AC Circuits, Impedance and Phasors Electrical and Computer Engineering EE University of Saskatchewan
Authors: Denard Lynch Date: Aug 30  Sep 28, 2012 Sep 23, 2013: revisionsdjl Description: This laboratory explores the behaviour of resistive, capacitive and inductive elements in alternating current
More informationThreephase analysis of unbalanced systems
Exercises of course ELEC0029  Electric power systems analysis and operation Threephase analysis of unbalanced systems Thierry Van Cutsem t.vancutsem@ulg.ac.be www.montefiore.ulg.ac.be/~vct March 205
More informationBasic Electrical Technology Dr. L. Umanand Department of Electrical Engineering Indian Institute of Science, Bangalore. Lecture  33 3 phase System 4
Basic Electrical Technology Dr. L. Umanand Department of Electrical Engineering Indian Institute of Science, Bangalore Lecture  33 3 phase System 4 Hello everybody. So, in the last class we have been
More informationImpact of increased penetration of wind and PV solar resources on the bulk power system
Impact of increased penetration of wind and PV solar resources on the bulk power system Vijay Vittal Ira A. Fulton Chair Professor School of Electrical, Computer and Energy Engineering Arizona State University
More informationChapter 08. Methods of Analysis
Chapter 08 Methods of Analysis Source: Circuit Analysis: Theory and Practice Delmar Cengage Learning CC Tsai Outline Source Conversion Mesh Analysis Nodal Analysis DeltaWye ( Y) Conversion Bridge Networks
More informationPower Factor Correction for Power Systems First Semester Report Spring Semester 2007
Power Factor Correction for Power Systems First Semester Report Spring Semester 2007 by Pamela Ackerman Prepared to partially fulfill the requirements for EE401 Department of Electrical and Computer Engineering
More informationBasics of Electricity
Basics of Electricity Power Flow on AC Transmission Lines PJM State & Member Training Dept. Objectives Describe the basic makeup and theory of an AC transmission line Given the formula for real power
More informationApplication of GA for Optimal Location of FACTS Devices for Steady State Voltage Stability Enhancement of Power System
I.J. Intelligent Systems and Applications, 2014, 03, 6975 Published Online February 2014 in MECS (http://www.mecspress.org/) DOI: 10.5815/ijisa.2014.03.07 Application of GA for Optimal Location of Devices
More informationELG4125: Power Transmission Lines The most common methods for transfer of electric power are: Overhead AC; Underground AC; Overhead DC; Underground
ELG4125: Power Transmission Lines The most common methods for transfer of electric power are: Overhead AC; Underground AC; Overhead DC; Underground DC Distribution Lines Distribution Lines and Transformers
More informationChapt ha e pt r e r 12 RL Circuits
Chapter 12 RL Circuits Sinusoidal Response of RL Circuits The inductor voltage leads the source voltage Inductance causes a phase shift between voltage and current that depends on the relative values of
More informationAn Introduction to the Mofied Nodal Analysis
An Introduction to the Mofied Nodal Analysis Michael Hanke May 30, 2006 1 Introduction Gilbert Strang provides an introduction to the analysis of electrical circuits in his book Introduction to Applied
More informationChapter 12: Three Phase Circuits
Chapter 12: Three Phase Circuits 12.1 What Is a Three Phase Circuit? 12.2 Balance Three Phase Voltages 12.3 Balance Three Phase Y to Y Connection 12.4 Other Balance Three Phase Connections 12.5 Power in
More informationCircuits with inductors and alternating currents. Chapter 20 #45, 46, 47, 49
Circuits with inductors and alternating currents Chapter 20 #45, 46, 47, 49 RL circuits Ch. 20 (last section) Symbol for inductor looks like a spring. An inductor is a circuit element that has a large
More informationMATH 304 Linear Algebra Lecture 4: Matrix multiplication. Diagonal matrices. Inverse matrix.
MATH 304 Linear Algebra Lecture 4: Matrix multiplication. Diagonal matrices. Inverse matrix. Matrices Definition. An mbyn matrix is a rectangular array of numbers that has m rows and n columns: a 11
More informationLecture 2 Linear functions and examples
EE263 Autumn 200708 Stephen Boyd Lecture 2 Linear functions and examples linear equations and functions engineering examples interpretations 2 1 Linear equations consider system of linear equations y
More informationChapter 5. The Inverse; Numerical Methods
Vector Spaces in Physics 8/6/ Chapter. The nverse Numerical Methods n the Chapter we discussed the solution of systems of simultaneous linear algebraic equations which could be written in the form C 
More informationPolynomial Degree and Finite Differences
CONDENSED LESSON 7.1 Polynomial Degree and Finite Differences In this lesson you will learn the terminology associated with polynomials use the finite differences method to determine the degree of a polynomial
More informationChapter 12. RL Circuits ISU EE. C.Y. Lee
Chapter 12 RL Circuits Objectives Describe the relationship between current and voltage in an RL circuit Determine impedance and phase angle in a series RL circuit Analyze a series RL circuit Determine
More information1 Introduction. 2 Power Flow. J.L. Kirtley Jr.
Massachusetts Institute of Technology Department of Electrical Engineering and Computer Science 6.061 Introduction to Power Systems Class Notes Chapter 5 Introduction To Load Flow J.L. Kirtley Jr. 1 Introduction
More informationVer 3537 E1.1 Analysis of Circuits (2014) E1.1 Circuit Analysis. Problem Sheet 1 (Lectures 1 & 2)
Ver 3537 E. Analysis of Circuits () Key: [A]= easy... [E]=hard E. Circuit Analysis Problem Sheet (Lectures & ). [A] One of the following circuits is a series circuit and the other is a parallel circuit.
More informationPowerWorld Transmission Line Parameter Calculator
PowerWorld Transmission Line Parameter Calculator Introduction The PowerWorld Transmission Line Parameter Calculator is a tool designed to compute characteristic line parameters given the type of the conductor
More informationRF Generator. figure 2
Why is impedance matching important: In general sputtering or etching applications, power generators are used to transfer either DC, Medium Frequency (typically in the several khz range) or RF (usually
More informationCritical thinfilm processes such as deposition and etching take place in a vacuum
WHITEPAPER INTRODUCING POWER SUPPLIES AND PLASMA Critical thinfilm processes such as deposition and etching take place in a vacuum SYSTEMS chamber in the presence of a plasma. A plasma is an electrically
More informationSection 5.0A Factoring Part 1
Section 5.0A Factoring Part 1 I. Work Together A. Multiply the following binomials into trinomials. (Write the final result in descending order, i.e., a + b + c ). ( 7)( + 5) ( + 7)( + ) ( + 7)( + 5) (
More informationThe Smith chart. Smith chart components. The normalized impedance line CHAPTER
26 CHAPTER The Smith chart The mathematics of transmission lines, and certain other devices, becomes cumbersome at times, especially when dealing with complex impedances and nonstandard situations. In
More informationUnderstanding the Fundamental Principles of Vector Network Analysis. Application Note 12871. Table of Contents. Page
Understanding the Fundamental Principles of Vector Network Analysis Application Note 12871 Table of Contents Page Introduction 2 Measurements in Communications Systems 2 Importance of Vector Measurements
More informationA COMPARISON ON PERFORMANCE OF TCSC/SSSC FOR A RADIAL SYSTEM
IMPACT: International Journal of Research in Engineering & Technology (IMPACT: IJRET) ISSN(E): 318843; ISSN(P): 3474599 Vol. 3, Issue 9, Sep 015, 718 Impact Journals A COMPARISON ON PERFORMANCE OF TCSC/SSSC
More informationSection 1.1. Introduction to R n
The Calculus of Functions of Several Variables Section. Introduction to R n Calculus is the study of functional relationships and how related quantities change with each other. In your first exposure to
More informationuser guide of ARTERE (power flow computation)
Dept. of Electrical Engineering and Computer Science (Institut Montefiore) user guide of ARTERE (power flow computation) Updated February 2014 1 1. Starting ARTERE A doubleclick on the ARTERE icon starts
More informationTransformer Modeling Using Simulator
Transformer Modeling Using Simulator PowerWorld Program Users Work Group August 23, 2011 Presented by John Gross Phone: 5094954591 Email: john.gross@avistacorp.com General Purpose and Operation Maintain
More informationRLC Resonant Circuits
C esonant Circuits Andrew McHutchon April 20, 203 Capacitors and Inductors There is a lot of inconsistency when it comes to dealing with reactances of complex components. The format followed in this document
More informationOPTIMAL POWER FLOW ALGORITHMS
OPTIMAL POWER FLOW ALGORITHMS Hans Glavitsch, Rainer Bacher Swiss Federal Institute of Technology CH8092 Zürich, Switzerland 1 PROBLEM DEFINITION 1.1 Optimal power flow problem 1.1.1 The ordinary power
More informationLoad Flow Analysis on IEEE 30 bus System
International Journal of Scientific and Research Publications, Volume 2, Issue 11, November 2012 1 Load Flow Analysis on IEEE 30 bus System Dharamjit *, D.K.Tanti ** * Department of Electrical Engineering,
More informationStudents Manual for the Exam. General Engineering and Electrical Civil Engineering Discipline
Students Manual for the Exam General Engineering and Electrical Civil Engineering Discipline  October March 2014 2013  COPYRIGHT NOTICE COPYRIGHTS 2013 NATIONAL CENTER FOR ASSESSMENT IN HIGHER EDUCATION
More informationNETWORK RECONFIGURATION FOR LOSS REDUCTION IN THREEPHASE POWER DISTRIBUTION SYSTEMS
NETWORK RECONFIGURATION FOR LOSS REDUCTION IN THREEPHASE POWER DISTRIBUTION SYSTEMS A Thesis Presented to the Faculty of the Graduate School of Cornell University in Partial Fulfillment of the Requirements
More informationMatpower 4.1 User s Manual
Matpower 4.1 User s Manual Ray D. Zimmerman Carlos E. MurilloSánchez December 14, 2011 2010, 2011 Power Systems Engineering Research Center (Pserc) All Rights Reserved Contents 1 Introduction 7 1.1 Background................................
More information