1 Installation Instructions FLEX I/O Digital Input Modules Catalog numbers 1794-IB8, 1794-IB16, 1794-IB32 Table of Contents Topic Page Important User Information 2 Environment and Enclosure 3 Preventing Electrostatic Discharge 3 European Hazardous Location Approval 4 North American Hazardous Location Approval 5 Install Your Digital Input Module 7 Configure Your Input Module 13 Specifications 16
2 2 FLEX I/O Digital Input Modules Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical equipment. Safety Guidelines for the Application, Installation, and Maintenance of Solid-State Controls (Publication SGI-1.1 available from your local Rockwell Automation Sales Office or online at describes some important differences between solid-state equipment and hard-wired electromechanical devices. Because of this difference, and also because of the wide variety of uses for solid-state equipment, all persons responsible for applying this equipment must satisfy themselves that each intended application of this equipment is acceptable. In no event will Rockwell Automation, Inc. be responsible or liable for indirect or consequential damages resulting from the use or application of this equipment. The examples and diagrams in this manual are included solely for illustrative purposes. Because of the many variables and requirements associated with any particular installation, Rockwell Automation, Inc. cannot assume responsibility or liability for actual use based on the examples and diagrams. No patent liability is assumed by Rockwell Automation, Inc. with respect to use of information, circuits, equipment, or software described in this manual. Reproduction of the contents of this manual, in whole or in part, without written permission of Rockwell Automation, Inc., is prohibited. Throughout this manual, when necessary, we use notes to make you aware of safety considerations. WARNING: Identifies information about practices or circumstances that can cause an explosion in a hazardous environment, which may lead to personal injury or death, property damage, or economic loss. ATTENTION: Identifies information about practices or circumstances that can lead to personal injury or death, property damage, or economic loss. Attentions help you identify a hazard, avoid a hazard, and recognize the consequences. SHOCK HAZARD: Labels may be on or inside the equipment (for example, drive or motor) to alert people that dangerous voltage may be present. BURN HAZARD: Labels may be on or inside the equipment (for example, drive or motor) to alert people that surfaces may reach dangerous temperatures. IMPORTANT Identifies information that is critical for successful application and understanding of the product.
3 FLEX I/O Digital Input Modules 3 Environment and Enclosure ATTENTION: This equipment is intended for use in a Pollution Degree 2 industrial environment, in overvoltage Category II applications (as defined in IEC publication ), at altitudes up to 2000 m (6562 ft) without derating. This equipment is considered Group 1, Class A industrial equipment according to IEC/CISPR Publication 11. Without appropriate precautions, there may be potential difficulties ensuring electromagnetic compatibility in other environments due to conducted as well as radiated disturbance. This equipment is supplied as open-type equipment. It must be mounted within an enclosure that is suitably designed for those specific environmental conditions that will be present and appropriately designed to prevent personal injury resulting from accessibility to live parts. The enclosure must have suitable flame-retardant properties to prevent or minimize the spread of flame, complying with a flame spread rating of 5VA, V2, V1, V0 (or equivalent) if non-metallic. The interior of the enclosure must be accessible only by the use of a tool. Subsequent sections of this publication may contain additional information regarding specific enclosure type ratings that are required to comply with certain product safety certifications. In addition to this publication, see: Industrial Automation Wiring and Grounding Guidelines, Rockwell Automation publication , for additional installation requirements. NEMA Standard 250 and IEC 60529, as applicable, for explanations of the degrees of protection provided by different types of enclosure. Preventing Electrostatic Discharge ATTENTION: This equipment is sensitive to electrostatic discharge, which can cause internal damage and affect normal operation. Follow these guidelines when you handle this equipment: Touch a grounded object to discharge potential static. Wear an approved grounding wriststrap. Do not touch connectors or pins on component boards. Do not touch circuit components inside the equipment. Use a static-safe workstation, if available. Store the equipment in appropriate static-safe packaging when not in use.
4 4 FLEX I/O Digital Input Modules European Hazardous Location Approval The following modules are European Zone 2 approved: 1794-IB8, 1794-IB16. European Zone 2 Certification (The following applies when the product bears the Ex Marking) This equipment is intended for use in potentially explosive atmospheres as defined by European Union Directive 94/9/EC and has been found to comply with the Essential Health and Safety Requirements relating to the design and construction of Category 3 equipment intended for use in potentially explosive atmospheres, given in Annex II to this Directive. Compliance with the Essential Health and Safety Requirements has been assured by compliance with EN and EN WARNING: Observe the following additional Zone 2 certification requirements. This equipment is not resistant to sunlight or other sources of UV radiation. This equipment must be installed in an enclosure providing at least IP54 protection when applied in Zone 2 environments. This equipment shall be used within its specified ratings defined by Allen-Bradley. Provision shall be made to prevent the rated voltage from being exceeded by transient disturbances of more than 40% when applied in Zone 2 environments This equipment must be used only with ATEX certified backplanes. Secure any external connections that mate to this equipment by using screws, sliding latches, threaded connectors, or other means provided with this product. Do not disconnect equipment unless power has been removed or the area is known to be nonhazardous.
5 North American Hazardous Location Approval FLEX I/O Digital Input Modules 5 The following modules are North American Hazardous Location approved: 1794-IB8, 1794-IB16, 1794-IB32. The following information applies when operating this equipment in hazardous locations: Informations sur l utilisation de cet équipement en environnements dangereux: Products marked "CL I, DIV 2, GP A, B, C, D" are suitable for use in Class I Division 2 Groups A, B, C, D, Hazardous Locations and nonhazardous locations only. Each product is supplied with markings on the rating nameplate indicating the hazardous location temperature code. When combining products within a system, the most adverse temperature code (lowest "T" number) may be used to help determine the overall temperature code of the system. Combinations of equipment in your system are subject to investigation by the local Authority Having Jurisdiction at the time of installation. Les produits marqués "CL I, DIV 2, GP A, B, C, D" ne conviennent qu'à une utilisation en environnements de Classe I Division 2 Groupes A, B, C, D dangereux et non dangereux. Chaque produit est livré avec des marquages sur sa plaque d'identification qui indiquent le code de température pour les environnements dangereux. Lorsque plusieurs produits sont combinés dans un système, le code de température le plus défavorable (code de température le plus faible) peut être utilisé pour déterminer le code de température global du système. Les combinaisons d'équipements dans le système sont sujettes à inspection par les autorités locales qualifiées au moment de l'installation. EXPLOSION HAZARD Do not disconnect equipment unless power has been removed or the area is known to be nonhazardous. Do not disconnect connections to this equipment unless power has been removed or the area is known to be nonhazardous. Secure any external connections that mate to this equipment by using screws, sliding latches, threaded connectors, or other means provided with this product. Substitution of components may impair suitability for Class I, Division 2. If this product contains batteries, they must only be changed in an area known to be nonhazardous. RISQUE D EXPLOSION Couper le courant ou s'assurer que l'environnement est classé non dangereux avant de débrancher l'équipement. Couper le courant ou s'assurer que l'environnement est classé non dangereux avant de débrancher les connecteurs. Fixer tous les connecteurs externes reliés à cet équipement à l'aide de vis, loquets coulissants, connecteurs filetés ou autres moyens fournis avec ce produit. La substitution de composants peut rendre cet équipement inadapté à une utilisation en environnement de Classe I, Division 2. S'assurer que l'environnement est classé non dangereux avant de changer les piles.
6 6 FLEX I/O Digital Input Modules ATTENTION: FLEX I/O is grounded through the DIN rail to chassis ground. Use zinc plated yellow-chromate steel DIN rail to assure proper grounding. The use of other DIN rail materials (for example, aluminum or plastic) that can corrode, oxidize, or are poor conductors, can result in improper or intermittent grounding. Secure DIN rail to mounting surface approximately every 200 mm (7.8 in.) and use end-anchors appropriately. ATTENTION: To comply with the CE Low Voltage Directive (LVD), this equipment must be powered from a source compliant with the following: Safety Extra Low Voltage (SELV) or Protected Extra Low Voltage (PELV). Compatibility The following communication adapters are required to ensure compatibility with the 1794-IB32: Remote I/O ControlNet DeviceNet Ethernet PROFIBUS ControlLogix Family 1794-ASB series E or later 1794-ASB2 series D or later 1794-ACN15 series C, firmware revision 4.1 or later 1794-ACNR15 series C, firmware revision 4.1 or later 1794-ADN Series B, firmware revision 2.4 or greater for out-of-box compatibility 1794-AENT series A, firmware revision 2.4 or later 1794-APB series A, version 1.1 of the GSD file (You can download the GSD file at RSLogix5000 programming software, version 11 or later
7 FLEX I/O Digital Input Modules 7 Install Your Digital Input Module Description Description 1 Keyswitch 5 Alignment bar 2 Terminal base 6 Groove 3 Flexbus connector 7 Latching mechanism 4 Module The module mounts on a 1794 terminal base. ATTENTION: During mounting of all devices, be sure that all debris (metal chips, wire strands, etc.) is kept from falling into the module. Debris that falls into the module could cause damage on power up. 1. Rotate the keyswitch (1) on the terminal base (2) clockwise to position 2 as required for this type of module. 2. Make certain the flexbus connector (3) is pushed all the way to the left to connect with the neighboring terminal base/adapter. You cannot install the module unless the connector is fully extended.
8 8 FLEX I/O Digital Input Modules 3. Make sure the pins on the bottom of the module are straight so they will align properly with the connector in the terminal base. WARNING: If you insert or remove the module while backplane power is on, an electrical arc can occur. This could cause an explosion in hazardous location installations. Be sure that power is removed or the area is nonhazardous before proceeding. 4. Position the module (4) with its alignment bar (5) aligned with the groove (6) on the terminal base. 5. Press firmly and evenly to seat the module in the terminal base unit. The module is seated when the latching mechanism (7) is locked into the module. Connect Wiring for the 1794-IB8 and 1794-IB16 using a 1794-TB3 or 1794-TB3S 1. Connect individual input wiring to numbered terminals on the 0 15 row (A) as indicated in the Wiring Connections for 1794-IB8 and 1794-IB16 table. 2. Connect the associated +V DC power lead of the input device to the corresponding terminal on the row (C) for each input as indicated in the Wiring Connections for 1794-IB8 and 1794-IB16 table. (The +V power terminals of row (C) are internally connected together.) 3. Connect the associated input common (3-wire devices only) to the corresponding terminal on the row (B) for each input as indicated in the Wiring Connections for 1794-IB8 and 1794-IB16 table. (Commons are internally connected together.) 4. Connect +V DC power to terminal 34 on the row (C). 5. Connect DC common to terminal 16 on the row (B). 6. If daisychaining power to the next terminal base, connect a jumper from terminal 51 (+V DC) on this base unit to terminal 34 on the next base unit. 7. If continuing DC common to the next base unit, connect a jumper from terminal 33 (common) on this base unit to terminal 16 on the next base unit.
9 FLEX I/O Digital Input Modules 9 Wiring Connections for 1794-IB8 and 1794-IB16 (use with 1794-TB3 or 1794-TB3S Terminal Base Unit) Input (1) Input Terminal Voltage Terminal Common Terminal (2) Input 0 A-0 C-35 B-17 Input 1 A-1 C-36 B-18 Input 2 A-2 C-37 B-19 Input 3 A-3 C-38 B-20 Input 4 A-4 C-39 B-21 Input 5 A-5 C-40 B-22 Input 6 A-6 C-41 B-23 Input 7 A-7 C-42 B-24 Input 8 A-8 C-43 B-25 Input 9 A-9 C-44 B-26 Input 10 A-10 C-45 B-27 Input 11 A-11 C-46 B-28 Input 12 A-12 C-47 B-29 Input 13 A-13 C-48 B-30 Input 14 A-14 C-49 B-31 Input 15 A-15 C-50 B-32 +V DC C-34...C-51 Common B-16...B-33 (1) 1794-IB8: Inputs 0 7; 1794-IB16: Inputs (2) 2-wire input devices use signal and supply terminals; 3-wire devices use signal, return and supply terminals.
10 10 FLEX I/O Digital Input Modules 1794-TB3 and 1794-TB3S Terminal Base Wiring for 1794-IB8 and 1794-IB16 Inputs A 16 -V Common 34 Voltage In +V Commons Voltage Connect V common to terminal B-16. Connect +V to terminal C-34. Use B-33 and C-51 to daisy-chain to the next terminal base unit. -V Common B C Voltage Out +V (1794-TB3 shown) 2-Wire and 3-Wire Input Wiring for 1794-IB8 and 1795-IB A B C A B C = Sink input = Common = +V DC 2-Wire Device (Sourcing Output) 3-Wire Device (Sourcing Output) Connect Wiring for the 1794-IB32 using a 1794-TB32 or 1794-TB32S 1. Connect individual input wiring (IN0 IN15) to numbered terminals on the 0 15 row (A) as indicated in the Wiring Connections for 1794-IB32 table. 2. Connect the associated power to the +V1 terminal (35, 37, 39, or 41) on the row (C) as indicated in the Wiring Connections for 1794-IB32 table. 3. Connect the associated common for IN0 IN15 to COM1 (terminal 36, 38, 40, or 42) on the row (C) as indicated in the Wiring Connections for 1794-IB32 table.
11 FLEX I/O Digital Input Modules Connect individual input wiring (IN16 IN31) to numbered terminals on the row (B) as indicated in the Wiring Connections for 1794-IB32 table. Do not connect to terminals 16 or Connect the associated power to the +V2 terminal (43, 45, 47, or 49) on the row (C) as indicated in the Wiring Connections for 1794-IB32 table. 6. Connect the associated common for IN16 IN31 to COM2 (terminal 44, 46, 48, or 50) on the row (C). 7. If continuing input wiring power for IN0 IN15 to the next terminal base, connect a jumper from terminal 41 (+V1) on this terminal base unit to the power terminal on the next terminal base unit. (Refer to the installation instructions for the specific terminal base unit. 8. If continuing input wiring IN0 IN15 common to the next terminal base, connect a jumper from terminal 42 (COM1) on this terminal base unit to the common terminal on the next terminal base unit. 9. If continuing input wiring power for IN16 IN31 to the next terminal base, connect a jumper from terminal 49 (+V2) on this terminal base unit to the power terminal on the next terminal base unit. (Refer to the installation instructions for the specific terminal base unit. 10. If continuing input wiring IN16 IN31 common to the next terminal base, connect a jumper from terminal 50 (COM2) on this terminal base unit to the common terminal on the next terminal base unit. Wiring Connections for 1794-IB32 (use with 1794-TB32 or 1794-TB32S Terminal Base Unit) Input Signal Input Signal Input 0 A-0 IN 16 B-17 Input 1 A-1 IN 17 B-18 Input 2 A-2 IN 18 B-19 Input 3 A-3 IN 19 B-20 Input 4 A-4 IN 20 B-21 Input 5 A-5 IN 21 B-22 Input 6 A-6 IN 22 B-23 Input 7 A-7 IN 23 B-24 Input 8 A-8 IN 24 B-25
12 12 FLEX I/O Digital Input Modules Wiring Connections for 1794-IB32 (use with 1794-TB32 or 1794-TB32S Terminal Base Unit) Input Signal Input Signal Input 9 A-9 IN 25 B-26 Input 10 A-10 IN 26 B-27 Input 11 A-11 IN 27 B-28 Input 12 A-12 IN 28 B-29 Input 13 A-13 IN 29 B-30 Input 14 A-14 IN 30 B-31 Input 15 A-15 IN 31 B-32 +V1 DC power (1) (inputs IN0 IN15) COM1 DC Return (inputs IN0 IN15) +V2 DC power (inputs IN16 IN31) COM2 DC Return (inputs IN16 IN31) Power terminals 35, 37, 39, and 41 for IN0 IN15. +V1 connected to terminals 35, 37, 39, and 41. Common terminals 36, 38, 40, and 42 for IN0 IN15. V1 Return connected to terminals 36, 38, 40, and 42. Power terminals 43, 45, 47, and 49 for IN16 IN31. +V2 connected to terminals 43, 45, 47, and 49. Common terminals 44, 46, 48, and 50 for IN16 IN31. V2 Return connected to terminals 44, 46, 48, and 50. (1) 2-wire input devices use signal and supply terminals; 3-wire devices use signal, return and supply terminals TB32 and 1794-TB32S Terminal Base Wiring for 1794-IB NC NC Inputs Inputs 34 NC V1 COM1 +V1 COM1 +V1 COM1 +V1 COM1 +V2 COM2 +V2 COM2 +V2 COM2 +V2 COM2 NC +V1 = Terminals 35, 37, 39, and 41 (1794-TB32 shown) +V2 = Terminals 43, 45, 47, and 49 COM1 = Terminals 36, 38, 40, and 42 COM2 = Terminals 44, 46, 48, and 50 NC = No connections (terminals 16, 33, 34, and 51)
13 Configure Your Input Module FLEX I/O Digital Input Modules 13 Configure your input module by setting bits in the configuration word (write word). Image Table Memory Map for the 1794-IB8 Module Dec Oct Read 1 Not used I7 I6 I5 I4 I3 I2 I1 I0 Write 1 Not used Input Filter Where I = Input Image Table Memory Map for the 1794-IB16 Module Dec Oct Read 1 I15 I14 I13 I12 I11 I10 I9 I8 I7 I6 I5 I4 I3 I2 I1 I0 Read 2 C = Counter Input value of input 15 Write 1 Not used CF CR Input Filter Input Filter Where Note: I = Input C = Counter value for input 15 CF = Counter fast where 1 = fast input (raw data), 0 standard input filtered data CR = Counter reset C, CR, and CF not available when used with any series 1794-ASB or 1794-ASB2 remote I/O adapter modules. Image Table Memory Map for the 1794-IB32 Module Dec Oct Read 1 I15 I14 I13 I12 I11 I10 I9 I8 I7 I6 I5 I4 I3 I2 I1 I0 Read 2 I31 I30 I29 I28 I27 I26 I25 I24 I23 I22 I21 I20 I19 I18 I17 I16 Write 1 Not used Input Filter FT Not used Where I = Input status FT = Input filter time
14 14 FLEX I/O Digital Input Modules Set the Input Filter Time To set the input filter time, set the associated bits in the output image table (complementary word) for the module. O: Dec Oct. FT = IB32 FT = 0 7 (1794-IB8) FT = FT = 0 11 (1794-IB16) 1794-IB16 For example, to increase the off-to-on filter time to 4 ms for all inputs at address rack 1, module group 0, (using 1794-IB32 as an example), set bits and program as shown below. Write filter time on system startup. I: FLL Fill File Source Destination Length #O:010 1 Write FT to complement of input module IB = 4 Octal or 4 Decimal 1794-IB IB = 44 Octal or 36 Decimal = 4 Octal or 4 Decimal Refer to the Input Filter Time table for other bit settings.
15 FLEX I/O Digital Input Modules 15 Input Filter Time Bits Description Filter Time Inputs (1794-IB8) 1794-IB8, 1794-IB16, 1794-IB Inputs (1794-IB16) Inputs (1794-IB16) Inputs (1794-IB32) Off to On/On to Off Filter Time 0 (Default) 0.25 ms Filter Time ms Filter Time 2 1 ms Filter Time 3 2 ms Filter Time 4 4 ms Filter Time 5 8 ms Filter Time 6 16 ms Filter Time 7 32 ms
16 16 FLEX I/O Digital Input Modules Specifications Specifications 1794-IB8 Attribute Number of inputs Recommended terminal base unit On-state voltage, min On-state voltage, nom On-state voltage, max On-state current, min On-state current, nom On-state current, max Off-state voltage, max Off-state current, max Nominal input impedance Isolation voltage FlexBus current Power dissipation, max Thermal dissipation, max Value 8, current, sinking 1794-TB3, 1794-TB3S, 1794-TB3K, 1794-TB3SK, 1794-TBKD, 1794-TB37DS 10V DC 24V DC 31.2V DC 2.0 ma 8.0 ma 12.0 ma 5.0V DC 1.5 ma 4.6 kω 50V (continuous), Basic Insulation Type Type 850V DC for 60 s, between field side and system No isolation between individual channels 20 5V DC V DC V DC Specifications 1794-IB16 Attribute Number of inputs Recommended terminal base unit On-state voltage, min On-state voltage, nom On-state voltage, max On-state current, min On-state current, nom Value 16, current, sinking 1794-TB3, 1794-TB3S, 1794-TB3K, 1794-TB3SK, 1794-TBKD, 1794-TB37DS 10V DC 24V DC 31.2V DC 2.0 ma 8.0 ma
17 FLEX I/O Digital Input Modules 17 Specifications 1794-IB16 Attribute On-state current, max Off-state voltage, max Off-state current, max Nominal input impedance Isolation voltage FlexBus current Power dissipation, max Thermal dissipation, max Value 12.0 ma 5.0V DC 1.5 ma 4.6 kω 50V (continuous), Basic Insulation Type Type 707V DC for 60 s, between field side and system No isolation between individual channels 30 5V DC V DC V DC Specifications 1794-IB32 Attribute Number of inputs Recommended terminal base unit On-state voltage, min On-state voltage, nom On-state voltage, max On-state current, min On-state current, nom On-state current, max Off-state voltage, max Off-state current, max Nominal input impedance Isolation voltage FlexBus current Power dissipation, max Thermal dissipation, max Value 32, current, sinking 1794-TB32, 1794-TB32S, 1794-TB62DS, 1794-TB62EXD4X V DC 24V DC 31.2V DC 2.0 ma V DC 6.0 ma 5.0V DC 1.5 ma 22.2 kω 50V (continuous), Basic Insulation Type Type 2121V DC for 2 s, between field side and system No isolation between individual channels 30 5V DC V DC V DC
18 18 FLEX I/O Digital Input Modules General Specifications Attribute Value Input filter time Refer to Input Filter Time table Terminal base screw torque Determined by installed terminal base Dimensions, approx. (H x W x D) 94 x 94 x 69 mm (3.7 x 3.7 x 2.7 in.) Indicators (field side indication) 8 yellow status indicators 1794-IB8 16 yellow status indicators 1794-IB16 32 yellow status indicators 1794-IB32 External DC power supply voltage, nom 24V DC External DC power voltage range V DC (includes 5% AC ripple) 1794-IB8, 1794-IB V DC (includes 5% AC ripple) 1794-IB32 North American temperature code T3C 1794-IB8, 1794-IB32 T4A 1794-IB16 IEC temperature code T IB8 only T IB16 only Keyswitch position 2 Enclosure type rating None (open-style) Wire size Determined by installed terminal base Wiring category (1) 2 on signal ports (1) Use this conductor category information for planning conductor routing as described in Industrial Automation Wiring and Grounding Guidelines, publication Environmental Specifications Attribute Operating temperature Storage temperature Relative humidity Vibration Value IEC (Test Ad, Operating Cold), IEC (Test Bd, Operating Dry Heat), IEC (Test Nb, Operating Thermal Shock): C ( C) 1794-IB8, 1794-IB C ( F) 1794-IB32 IEC (Test Ab, Unpackaged Non-operating Cold), IEC (Test Bb, Unpackaged Non-operating Dry Heat), IEC (Test Na, Unpackaged Non-operating Thermal Shock): C ( F) IEC (Test Db, Unpackaged Damp Heat): 5 95% non-condensing IEC (Test Fc, Operating): Hz
19 FLEX I/O Digital Input Modules 19 Environmental Specifications Attribute Value Shock, operating IEC (Test Ea, Unpackaged shock): 30 g Shock, nonoperating IEC (Test Ea, Unpackaged shock): 50 g Emissions CISPR 11: Group 1, Class A (with appropriate enclosure) ESD immunity IEC : 6 kv contact discharges 8 kv air discharges Radiated RF immunity (1794-IB8, 1794-IB16) IEC : 10V/m with 1 khz sine-wave 80% AM from MHz 10V/m with 200 Hz 50% Pulse 100% 900 MHz 10V/m with 200 Hz 50% Pulse 100% 1890 MHz 3V/m with 1 khz sine-wave 80% AM from MHz (1794-IB32) 10V/m with 1 khz sine-wave 80% AM from MHz EFT/B immunity IEC : ±2 5 khz on power ports ±2 5 khz on signal ports Surge transient immunity IEC : ±1 kv line-line(dm) and ±2 kv line-earth(cm) on signal ports Conducted RF immunity IEC : 10V rms with 1 khz sine-wave 80% AM from 150 khz 80 MHz
20 20 FLEX I/O Digital Input Modules Certifications Certifications (when product is marked) (1) c-ul-us CSA CE Ex TÜV KC EAC RCM Value UL Listed Industrial Control Equipment, certified for US and Canada. See UL File E UL Listed for Class I, Division 2, Group A, B, C, D Hazardous Locations, certified for US and Canada. See UL File (1794-IB8 and 1794-IB16 only) CSA Certified Process Control Equipment. See CSA File LR54689C. CSA Certified Process Control Equipment for Class I, Division 2, Group A, B, C, D Hazardous Locations. See CSA File LR69960C. European Union 2004/108/EC EMC Directive, compliant with: EN ; Meas./Control/Lab., Industrial Requirements EN ; Industrial Immunity EN ; Industrial Emissions EN ; Programmable Controllers (Clause 8, Zone A & B) (1794-IB8) European Union 94/9/EC ATEX Directive, compliant with: EN :2010; Potentially Explosive Atmospheres, Protection n EN :2009; General Requirements LCIE 01ATEX6020X II 3 G Ex na IIC T3 Gc (1794-IB16) European Union 94/9/EC ATEX Directive, compliant with: EN :2010; Potentially Explosive Atmospheres, Protection n EN :2009; General Requirements DEMKO 14ATEX X EN :2012+A11:2013 IECEx UL X IEC , 6th Edition IEC , 4th Edition II 3 G Ex na IIC T4 Gc (1794-IB16 only) TÜV Certified for Functional Safety: up to and including SIL 2 Korean Registration of Broadcasting and Communications Equipment, compliant with: Article 58-2 of Radio Waves Act, Clause 3 Russian Customs Union TR CU 020/2011 EMC Technical Regulation Australian Radiocommunications Act, compliant with: AS/NZS CISPR 11; Industrial Emissions
21 FLEX I/O Digital Input Modules 21 (1) See the Product Certification link at for Declarations of Conformity, Certificates, and other certification details. Derating Chart for 1794-IB Vin On-State Voltage (V DC) AmbientTemperature o C The area within the curve represents the safe operating range for the module under various conditions of user supplied 24V DC supply voltages and ambient temperature. = Normal mounting safe operating range, (includes ). = Other mounting positions (including inverted horizontal) safe operating range Normal Mounting Horizontal Other Mounting (including Vertical, and Inverted Horizontal Mounting) Voltage (max.) Temperature (max.) Normal Other Voltage (max.) Temperature (max.) Normal Other
22 Rockwell Automation Support Rockwell Automation provides technical information on the Web to assist you in using its products. At you can find technical manuals, a knowledge base of FAQs, technical and application notes, sample code and links to software service packs, and a MySupport feature that you can customize to make the best use of these tools. For an additional level of technical phone support for installation, configuration and troubleshooting, we offer TechConnect support programs. For more information, contact your local distributor or Rockwell Automation representative, or visit Installation Assistance If you experience a problem within the first 24 hours of installation, please review the information that's contained in this manual. You can also contact a special Customer Support number for initial help in getting your product up and running. United States or Canada Outside United States or Canada Use the Worldwide Locator at or contact your local Rockwell Automation representative. New Product Satisfaction Return Rockwell Automation tests all of its products to ensure that they are fully operational when shipped from the manufacturing facility. However, if your product is not functioning and needs to be returned, follow these procedures. United States Outside United States Contact your distributor. You must provide a Customer Support case number (call the phone number above to obtain one) to your distributor to complete the return process. Please contact your local Rockwell Automation representative for the return procedure. Documentation Feedback Your comments will help us serve your documentation needs better. If you have any suggestions on how to improve this document, complete this form, publication RA-DU002, available at Allen-Bradley, Rockwell Automation, FLEX I/O, and TechConnect are trademarks of Rockwell Automation, Inc. Trademarks not belonging to Rockwell Automation are property of their respective companies. Supersedes Publication 1794-IN093C-EN-P - December 2009 Copyright 2015 Rockwell Automation, Inc. All rights reserved.
Installation Instructions Compact I/O End Caps/Terminators Catalog Numbers 1769-ECL, 1769-ECR Topic Page Important User Information 2 Environment and Enclosure 3 North American Hazardous Location Approval
Installation Instructions USB-to-Data Highway Plus Cable Catalog Number 1784-U2DHP Topic Page Important User Information 2 Environment and Enclosure 3 Install the Cable 5 Configure the DH+ Node Address
nstallation nstructions PONT /O 4V dc xpansion Supply atalog Number 1734-P4D, Series nside... For See Page mportant User nformation Preventing lectrostatic Discharge 3 nvironment and nclosure 4 North American
Backup Scanner Module Catalog Number 1747-BSN Installation Instructions 2 Backup Scanner Module Important User Information Because of the variety of uses for the products described in this publication,
Installation Instructions 1769-L35E CompactLogix Controller (Catalog Numbers 1769-L35E) Inside... Before You Begin... 3 How to Handle CompactLogix Components... 3 Make Sure that You Have All the Components...
Installation Instructions SLC 500 Analog Input Module (Catalog Number 1746NI8) Inside Important User Information... 2 For More Information... 3 Hazardous Location Considerations... 4 Environnements dangereux...
Installation Instructions Ethernet PLC-5 Programmable Controllers Catalog Numbers 1785-L20E, 1785-L40E, 1785-L80E, Series F Contents For This Topic See Page About This Publication 1 Related User Manual
Installation Instructions Micro830 10 Point Programmable Controllers Catalog Numbers 2080-LC30-10QWB, 2080-LC30-10QVB http://rockwellautomation.com/literature Cette publication est disponible en français
XM-160/161/162 Direct Vibration Module User Guide Firmware Revision 5 1440-VDRS06-00RH, 1440-VDRS06-06RH, 1440-VDRP06-00RH Important User Information Solid state equipment has operational characteristics
Installation Instructions Universal Serial Bus (USB) to DH-485 Interface Converter Catalog Number 1747-UIC Contents Overview..................................................3 Computer and Operating System
Micro800 Programmable Controllers Bulletin 2080 Selection Guide Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety
Product datasheet Characteristics TM7BDM8B expansion block - TM7 - IP67-8 DI/DO - 24V DC - 0.5 A - M8 connector Main Range of product Product or component type Range compatibility Enclosure material Bus
Overview/Modes of Operation Bulletin 150 Smart Motor Controller The SMC-3 is a compact, simple to use, solid-state motor controller designed to operate 3-phase motors. It features a built-in overload relay
User Manual Micro820 Programmable Controllers Catalog Numbers 2080-LC20-20QWB, 2080-LC20-20QBB, 2080-LC20-20AWB, 2080-LC20-20QWBR, 2080- LC20-20QBBR, 2080-LC20-20AWBR Important User Information Solid-state
Installation Instructions Hard Disk Drive (HDD) Catalog Number 6189V-35HDDST80, 6189V-35HDDST160 Topic Page About This Publication 1 Important User Information 2 Electrostatic Discharge (ESD) Precautions
FLEX I/O Isolated Analog Modules 1794-IF4I, -OF4I, IF2XOF2I, -IF4IXT, -IF4ICFXT, -OF4IXT, IF2XOF2IXT User Manual Important User Information Solid state equipment has operational characteristics differing
Characteristics multifunction control relay RM17-TE - range 183..528 V AC Complementary Reset time Maximum switching voltage Minimum switching current Maximum switching current [Us] rated supply voltage
Characteristics multifunction voltage control relay RM35-U - range 15..600 V Complementary Reset time Maximum switching voltage [Us] rated supply voltage Supply voltage limits Power consumption in W Main
Highlights & Features Protection Class II, Double Isolation (No Earth connection is required) Universal AC input voltage without power de-rating Efficiency > 87.0% @ 115Vac & 230Vac NEC Class 2 / Limited
User Manual EtherNet/IP and ControlNet to PROFIBUS PA Linking Devices Catalog Numbers 1788-EN2PAR, 1788-CN2PAR Important User Information Read this document and the documents listed in the additional resources
Extract from the online catalog STEP-PS/1AC/12DC/1.5 Order No.: 2868567 DIN rail power supply unit 12 V DC/1.5 A, primary switched-mode, 1- phase Commercial data EAN 4046356292924 Pack 1 pcs. Customs tariff
Foxboro Evo Process Automation System Product Specifications PSS 31H-2Z32 FBM232 Field Device System Integrator Module, 10/100 Mbps Ethernet, Single The FBM232 Field Device System Integrator (FDSI) module
Data sheet Electronic timer CT-AHD.12 OFF-delayed with 1 c/o (SPDT) contact The CT-AHD.12 is an electronic time relay with OFF-delay. It is from the CT-D range. With their MDRC profile and a width of only
38 Relay interface modules 0.1-2 - 3-5 - 6-8 - 16 A 38 Common features Instant ejection of relay by plastic retaining clip Integral coil indication and protection circuit 6.2 mm wide EMR - DC, AC or AC/DC
Installation Instructions ControlNet PCI Communication Interface Card Catalog Number 9904-PCIC This document describes how to install the 9904-PCIC ControlNet TM communication interface card. Topic: Page:
Square D Clipsal DIN-Rail Four-Channel Auxiliary Input Unit SLCLE5504AUX for Use with Wired C-Bus Networks Instruction Bulletin Retain for future use. Square D Clipsal DIN-Rail Four-Channel Auxiliary Input
Stratix 5700 Network Address Translation Quick Start Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety Guidelines
Data sheet Three-phase monitoring relay CM-PFE The CM-PFE is a three-phase monitoring relay that monitors the phase parameter phase sequence and phase failure in three-phase mains. 2CDC 251 005 S0012 Characteristics
D46 Isolating Barriers for our sensors A5S1 in Ex-areas Series KEY FEATURES ATEX / IECEx certified, also approval for UL / CSA and EAC (Russia, Kazakhstan and Belarus Customs Union) Protection grade Ex
PowerFlex 700S and 700H Frame 12 DC Bus Connector Kit Installation Instructions This document provides instructions for the installation of a DC bus connector kit for PowerFlex 700S and 700H frame 12 drives
Installation Instructions Chassis Interface Module for 1746 Local I/O (Catalog Number 1747-PCIL) Use this document to install the Chassis Interface module for 1746 Local I/O and connect it to a PCI Bus
Specifications Specifications Standard Features Optional Features Installation Setup Communications Power Wiring Control Wiring Keypad Software Starting and Stopping Modes Protection and Diagnostics Metering
38 Series - Relay interface modules 0.1-2 - 3-5 - 6-8 - 16 A 38 SERIES Common features Instant ejection of relay by plastic retaining clip Integral coil indication and protection circuit EMR Electromechanical
MasterINTERFACE 39 Series - Relay interface modules Common features Space saving 6.2 mm wide Connections for 16-way jumper link Integral coil indication and protection circuit Secure retention and easy
Telephone- and leased line modem for industrial applications TD-36 Modem for industrial PSTN- and leased line applications The TD-36 is an analogue V.34 PSTN modem as well as an industrial 2-wire leased
1SR 430 824 F9300 Features Monitoring of three-phase mains for phase sequence and failure Powered by the measuring circuit 2 c/o (SPDT) contacts 1 LED for status indication Approvals R: yellow LED - relay
User Manual MicroLogix 1100 Embedded Web Server Bulletin 1763 Controllers Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical equipment.
MTE SERIES RLW World REACTORS USER MANUAL PART NO. INSTR 030 REL. 090930 2009 MTE Corporation IMPORTANT USER INFORMATION NOTICE MTE Series RLW reactors are components designed to improve the reliability
Characteristics Single-function OFF-delay timer for DC contactors, without auxiliary voltage Width.5 mm CDC 5 6 F3 Approvals A culus E CCC CT-VBS a Circuit diagram b Marker label Marks a CE b C-Tick Order
Highlights & Features Universal AC input voltage Power will not de-rate for the entire input voltage range Power Boost of 150% for 3 seconds Full corrosion resistant aluminium chassis SEMI F47 certified
Installation Instructions NetLinx ControlNet 1784-PCIC Communication Card Catalog Number 1784-PCIC This document describes how to install and use the NetLinx 1784-PCIC ControlNet TM communication interface
Documentation for KL2602 and KL2622 Two-channel Relay Output Terminals for 230 V AC / 30 V DC Version: 1.4 Date: 2013-03-20 Table of contents Table of contents 1 Foreword 1 1.1 Notes on the documentation
Relés e Contatores de Estado Sólido SIRIUS Coletânea de dados técnicos ( product data sheet ) Agosto/212 SSR - 3RF21 22,5 mm Ponto Zero SSR - 3RF2 45 mm Ponto Zero SSR - 3RF22 45 mm Ponto Zero Trifásico
T7560A,B,C Digital Wall Module HONEYWELL EXCEL 5000 OPEN SYSTEM BEFORE INSTALLATION All wiring must comply with local electrical codes and ordinances or as specified on installation wiring diagrams. Digital
Safety Relay Unit ( I/O Unit Type) CQM1-SF200/CS1W-SF200 CSM_CQM1-SF200_CS1W-SF200_DS_E_2_1 A Safety Relay Unit That Functions as a I/O Unit. Less Installation Space and Wiring Required. Safety Relay Unit
Energy Management Energy Meter Type EM23 DIN Class 1 (kwh) according to EN62053-21 Class B (kwh) according to EN50470-3 Class 2 (kvarh) according to EN62053-23 Accuracy ±0.5 RDG (current/voltage) Energy
55 Series - General purpose relays 7-10 A Features 55.12 55.13 55.14 Printed circuit mount, general purpose 2, 3 & 4 Pole relays 55.12-2 Pole 10 A 55.13-3 Pole 10 A 55.14-4 Pole 7 A AC coils & DC coils
AC 800M EtherNet/IP DeviceNet Linking Device LD 800DN SP1134 Power and productivity for a better world TM AC 800M EtherNet/IP DeviceNet Linking Device LD 800DN NOTICE This document contains information
Installation Instructions (Cat. No. 1771-IAD Series D) Contents Use this document as a guide when installing the catalog number 1771-IAD series D input module. To See page Prevent Electrostatic Discharge
DeltaV Distributed Control System Product Data Sheet March 2015 S-series Mass Connection Solutions Fast, easy and error-free cabinet wiring Modular design, improves reliability Lowers overall termination
425 CONTROLS DATA MANAGEMENT PROCESS AUTOMATION EUROCUBE General purpose single phase thyristors and solid state relays Product data abc 425 EUROCUBE A complete range of low cost solid state relays and
INSTALLATION GUIDE AXIS T81B22 DC 30W Midspan ENGLISH About this Document This document includes instructions for installing AXIS T81B22 on your network. Previous experience of networking will be beneficial
Data sheet Voltage monitoring relays CM-ESS.M For single-phase AC/DC voltages The CM-ESS.M is an electronic voltage monitoring relay that provides reliable monitoring of voltages as well as detection of
FLUORESCENT UV- RING LIGHT OPERATING INSTRUCTION Caution! UV-radiation of this device is in the range of UV-A (320-400 nm). Direct exposure to eyes shall therefore be avoided. UV protection glasses shall
and Accelerometers Bently Nevada Asset Condition Monitoring Description The and Accelerometers are general purpose, casemounted seismic transducers designed for use with Trendmaster Pro Constant Current
User Manual Guard I/O EtherNet/IP Safety Modules Catalog Numbers 1791ES-IB8XOBV4, 1791ES-IB16, 1732ES-IB12XOB4, 1732ES-IB12XOBV2 Important User Information Read this document and the documents listed in
User Manual DeviceNet Network Configuration Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical equipment. Safety Guidelines for the
PowerLogic power-monitoring units Power Meter Series 700 Technical data sheet 2007 Functions and characteristics E90463 The PowerLogic Power Meter Series 700 offers all the measurement capabilities required
Thermistor motor protection CM-E Range Thermistor motor protection Thermistor motor protection relays Benefits and advantages Selection table Operating principle and fields of application for thermistor
MILLENIUM Table of contents 1. INTRODUCTION 1 2. HARDWARE DESCRIPTION 2 3. INSTALLATION 5 4. CONNECTION 6 5. USER SAFETY AND PROTECTION OF EQUIPMENT 8 1. Introduction The MILLENIUM series has been designed
Technical Description Transistor D.C. Chopper Controller Type GS 24 S Table of contents 1. Getting started guide 2. General information 2.1. Characteristics 2.2. Accessories 3. Information about the Machine
Data sheet Temperature monitoring relays CM-TCS Monitoring relays for monitoring temperatures with a PT100 sensor (2- or 3-wire connection) The temperature monitoring relays CM-TCS monitor overtemperature,
Technical Datasheet SNK668D0 Catalogue Page SNK678S0 ZS Screw Clamp Terminal Blocks Feed-through Save space by connecting conductors up to mm² AWG in just mm 0.47 in spacing. SNK68V004 SNK004F0000 D CAD
Application Technique Safety Function: Door Monitoring Products: Trojan 5 Switch, GuardLogix Controller Safety Rating: CAT. 3, PLd to ISO 13849-1: 2008 Topic Page Important User Information 2 General Safety
User Manual ControlLogix System Catalog Numbers 1756-L61, 1756-L62, 1756-L63, 1756-L63XT, 1756-L64, 1756-L65, 1756-L71, 1756-L72, 1756-L73, 1756-L73XT, 1756-L74, 1756-L75 Important User Information Solid-state
ATEX category II 1 G, Ex zone 0 ATEX category II 1 D, Ex zone 20 SIL2 as per IEC 61508 Threaded barrel, M18 x 1 Chrome-plated brass DC 2-wire, nom. 8.2 VDC Output acc. to DIN EN 60947-5-6 (NA- MUR) M12
Rack mounted telephone- and leased line modem for industrial applications TR-6 Rack modem for industrial PSTNand /-wire leased line applications The TR-6 is an analogue V. 9 -rack PSTN modem as well as
EPM3 Phase Sequence and Motor Rotation Tester Users Manual 1 L1 L2 L3 2 3 A B C CAT 600V 3-PHASE TESTER 5 TEST M1 M2 BATT M3 EPM3 MOTOR ROTATION TESTER EPM3 MOTOR ROTATION DETERMINED WHILE FACING MOTOR
OPERATING INSTRUCTIONS AND SPECIFICATIONS NI 9475 8-Channel, 60 V, High-Speed, Sourcing Digital Output Module Français Deutsch ni.com/manuals This document describes how to use the National Instruments
MCR1900 Media Converter 19-Slot Chassis Installation Guide Part #5500304-11 Copyright Statement This document must not be reproduced in any way whatsoever, either printed or electronically, without the
Application : The RISH CON - Hz transducer is used for frequency measurement. The output signal is proportional to measured frequency and is either load independent DC Current or load independent DC Voltage.
DVPPF02-H2 PROFIBUS DP Slave Communication Module Application Manual Warning Please read this instruction carefully before use and follow this instruction to operate the device in order to prevent damages
User Manual GuardLogix Controllers Catalog Numbers 1756-L61S, 1756-L62S, 1756-L63S, 1756-LSP, 1756-L71S, 1756-L72S, 1756-L73S, 1756-L7SP, 1756-L73SXT, 1756-L7SPXT Important User Information Solid-state
Silvertel V1.1 November 2012 Datasheet Pb 1 Features IEEE802.3at and IEEE802.3af compliant Maximum 30W output power Dual In-Line (DIL) package size 50.6mm (L) x 30mm (W) Overload, short-circuit and thermal
Introduction This guide is to assist the reader with the most basic form of installation and connection to switches in this series. As there is more than one switch in this series, the diagrams might slightly
0102 Model Number Features 15 mm quasi flush Usable up to SIL2 acc. to IEC 61508 Accessories BF 30 Mounting flange, 30 mm V1-G-N-2M-PUR Female cordset, M12, 2-pin, NAMUR, PUR cable V1-W-N-2M-PUR Female