1 Installation Instructions Micro Point Programmable Controllers Catalog Numbers 2080-LC30-10QWB, 2080-LC30-10QVB Cette publication est disponible en français sous forme électronique (fichier PDF). Pour la FR télécharger, rendez-vous sur la page Internet indiquée ci-dessus. Questa pubblicazione è disponibile in Italiano in formato PDF. Per scaricarla collegarsi al sito IT Web indicato sopra. PT ZH Esta publicação está disponível em portugués como PDF. Vá ao endereço web que aparece acima para encontrar e fazer download da publicação. DE ES Diese Publikation ist als PDF auf Deutsch verfügbar. Gehen Sie auf die oben genannte Web-Adresse, um nach der Publikation zu suchen und sie herunterzuladen. Esta publicación está disponible en español como PDF. Diríjase a la dirección web indicada arriba para buscar y descarga esta publicación. ZC KO Table of Contents Topic Page Important User Information 2 Additional Resources 6 Overview 7 Controller Description 7 Status Indicators 8 Mount the Module 8 Wire the Controller 11 Specifications 13
2 2 Micro Point Programmable Controllers Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety Guidelines for the Application, Installation and Maintenance of Solid State Controls (Publication SGI-1.1 available from your local Rockwell Automation sales office or online at describes some important differences between solid state equipment and hard-wired electromechanical devices. Because of this difference, and also because of the wide variety of uses for solid state equipment, all persons responsible for applying this equipment must satisfy themselves that each intended application of this equipment is acceptable. In no event will Rockwell Automation, Inc. be responsible or liable for indirect or consequential damages resulting from the use or application of this equipment. The examples and diagrams in this manual are included solely for illustrative purposes. Because of the many variables and requirements associated with any particular installation, Rockwell Automation, Inc. cannot assume responsibility or liability for actual use based on the examples and diagrams. No patent liability is assumed by Rockwell Automation, Inc. with respect to use of information, circuits, equipment, or software described in this manual. Reproduction of the contents of this manual, in whole or in part, without written permission of Rockwell Automation, Inc., is prohibited. Throughout this manual, when necessary, we use notes to make you aware of safety considerations. WARNING: Identifies information about practices or circumstances that can cause an explosion in a hazardous environment, which may lead to personal injury or death, property damage, or economic loss. ATTENTION: Identifies information about practices or circumstances that can lead to personal injury or death, property damage, or economic loss. Attentions help you identify a hazard, avoid a hazard and recognize the consequences. SHOCK HAZARD: Labels may be on or inside the equipment (for example, drive or motor) to alert people that dangerous voltage may be present. BURN HAZARD: Labels may be on or inside the equipment (for example, drive or motor) to alert people that surfaces may reach dangerous temperatures. IMPORTANT IMPORTANT: Identifies information that is critical for successful application and understanding of the product.
3 Micro Point Programmable Controllers 3 Environment and Enclosure ATTENTION: This equipment is intended for use in a Pollution Degree 2 industrial environment, in overvoltage Category II applications (as defined in IEC ), at altitudes up to 2000 m (6562 ft) without derating. This equipment is considered Group 1, Class A industrial equipment according to IEC/CISPR 11. Without appropriate precautions, there may be difficulties with electromagnetic compatibility in residential and other environments due to conducted and radiated disturbances. This equipment is supplied as open-type equipment. It must be mounted within an enclosure that is suitably designed for those specific environmental conditions that will be present and appropriately designed to prevent personal injury resulting from accessibility to live parts. The enclosure must have suitable flame-retardant properties to prevent or minimize the spread of flame, complying with a flame spread rating of 5V A, V2, V1, V0 (or equivalent) if non-metallic. The interior of the enclosure must be accessible only by the use of a tool. Subsequent sections of this publication may contain additional information regarding specific enclosure type ratings that are required to comply with certain product safety certifications. In addition to this publication, see: Industrial Automation Wiring and Grounding Guidelines, Rockwell Automation publication , for additional installation requirements. NEMA Standard 250 and IEC 60529, as applicable, for explanations of the degrees of protection provided by different types of enclosure. Preventing Electrostatic Discharge ATTENTION: This equipment is sensitive to electrostatic discharge, which can cause internal damage and affect normal operation. Follow these guidelines when you handle this equipment: Touch a grounded object to discharge potential static. Wear an approved grounding wriststrap. Do not touch connectors or pins on component boards. Do not touch circuit components inside the equipment. Use a static-safe workstation, if available. Store the equipment in appropriate static-safe packaging when not in use.
4 4 Micro Point Programmable Controllers North American Hazardous Location Approval The following modules are North American Hazardous Location approved: 2080-LC30-10QWB, 2080-LC30-10QVB The following information applies when operating this equipment in hazardous locations: Products marked "CL I, DIV 2, GP A, B, C, D" are suitable for use in Class I Division 2 Groups A, B, C, D, Hazardous Locations and nonhazardous locations only. Each product is supplied with markings on the rating nameplate indicating the hazardous location temperature code. When combining products within a system, the most adverse temperature code (lowest "T" number) may be used to help determine the overall temperature code of the system. Combinations of equipment in your system are subject to investigation by the local Authority Having Jurisdiction at the time of installation. WARNING: EXPLOSION HAZARD Do not disconnect equipment unless power has been removed or the area is known to be nonhazardous. Do not disconnect connections to this equipment unless power has been removed or the area is known to be nonhazardous. Secure any external connections that mate to this equipment by using screws, sliding latches, threaded connectors, or other means provided with this product. Substitution of any component may impair suitability for Class I, Division 2. If this product contains batteries, they must only be changed in an area known to be nonhazardous. Informations sur l utilisation de cet équipement en environnements dangereux: Les produits marqués "CL I, DIV 2, GP A, B, C, D" ne conviennent qu'à une utilisation en environnements de Classe I Division 2 Groupes A, B, C, D dangereux et non dangereux. Chaque produit est livré avec des marquages sur sa plaque d'identification qui indiquent le code de température pour les environnements dangereux. Lorsque plusieurs produits sont combinés dans un système, le code de température le plus défavorable (code de température le plus faible) peut être utilisé pour déterminer le code de température global du système. Les combinaisons d'équipements dans le système sont sujettes à inspection par les autorités locales qualifiées au moment de l'installation. AVERTISSEMENT: RISQUE D EXPLOSION Couper le courant ou s'assurer que l'environnement est classé non dangereux avant de débrancher l'équipement. Couper le courant ou s'assurer que l'environnement est classé non dangereux avant de débrancher les connecteurs. Fixer tous les connecteurs externes reliés à cet équipement à l'aide de vis, loquets coulissants, connecteurs filetés ou autres moyens fournis avec ce produit. La substitution de tout composant peut rendre cet équipement inadapté à une utilisation en environnement de Classe I, Division 2. S'assurer que l'environnement est classé non dangereux avant de changer les piles.
5 Micro Point Programmable Controllers 5 WARNING: When used in a Class I, Division 2, hazardous location, this equipment must be mounted in a suitable enclosure with proper wiring method that complies with the governing electrical codes. If you connect or disconnect the serial cable with power applied to this module or the serial device on the other end of the cable, an electrical arc can occur. This could cause an explosion in hazardous location installations. Be sure that power is removed or the area is nonhazardous before proceeding. The local programming terminal port is intended for temporary use only and must not be connected or disconnected unless the area is assured to be nonhazardous. The USB port is intended for temporary local programming purposes only and not intended for permanent connection. If you connect or disconnect the USB cable with power applied to this module or any device on the USB network, an electrical arc can occur. This could cause an explosion in hazardous location installations. Be sure that power is removed or the area is nonhazardous before proceeding. The USB port is a nonincendive field wiring connection for Class I, Division2 Groups A, B, C and D. Exposure to some chemicals may degrade the sealing properties of materials used in the Relays. It is recommended that the User periodically inspect these devices for any degradation of properties and replace the module if degradation is found. If you insert or remove the plug-in module while backplane power is on, an electrical arc can occur. This could cause an explosion in hazardous location installations. Be sure that power is removed or the area is nonhazardous before proceeding. Refer to the Wiring Diagram for each plug-in module for additional details regarding removal or insertion under power. ATTENTION: To comply with the CE Low Voltage Directive (LVD), this equipment must be powered from a source compliant with the following: Safety Extra Low Voltage (SELV) or Protected Extra Low Voltage (PELV). To comply with UL restrictions, this equipment must be powered from a Class 2 or Limited Voltage Limited Current Source (LVLC).
6 6 Micro Point Programmable Controllers ATTENTION: Be careful when stripping wires. Wire fragments that fall into the controller could cause damage. Once wiring is complete, make sure the controller is free of all metal fragments. Do not remove the protective debris strips until after the controller and all other equipment in the panel near the module are mounted and wired. Remove strips before operating the controller. Failure to remove strips before operating can cause overheating. Electrostatic discharge can damage semiconductor devices inside the module. Do not touch the connector pins or other sensitive areas. The USB and serial cables are not to exceed 3.0 m (9.84 ft). Do not wire more than 2 conductors on any single terminal. Additional Resources Resource Micro830 and Micro850 Programmable Controllers User Manual, publication 2080-UM002 Micro800 AC Power Supply Installation Instructions, publication 2080-IN001 Micro800 Plug-in Modules User Manual, publication 2080-UM004 Industrial Automation Wiring and Grounding Guidelines, publication If you would like a manual, you can: Description A more detailed description of how to install and use your Micro830 and Micro850 programmable controllers. Information on installing and wiring the optional AC power supply. Installation, wiring descriptions, and specifications, for the different Micro800 plug-in modules. More information on proper wiring and grounding techniques. download a free electronic version from the Internet: purchase a printed manual by contacting your local Allen-Bradley distributor or Rockwell Automation representative
7 Micro Point Programmable Controllers 7 Overview The Micro point controller is an economical brick style controller with embedded inputs and outputs. It can accommodate up to two plug-in modules and accommodates any 24V DC output power supply that meets minimum specifications such as the optional Micro800 power supply, 2080-PS VAC. Controller Overview Controller Description Description Description 1 Status indicators 8 Right-side cover 2 Optional power supply slot 9 DIN rail mounting latch 3 Plug-in module latch 10 Mode switch 4 Plug-in module screw hole 11 Type B connector USB port 5 40 pin high speed plug-in connector 12 RS232/RS485 non-isolated combo serial port 6 I/O terminal block 13 Optional power supply 7 Mounting screw hole / mounting foot
8 8 Micro Point Programmable Controllers Status Indicators Power status Run status Input status Fault status Force status Serial communications status Output status Mount the Module Most applications require installation in an industrial enclosure to reduce the effects of electrical interference and environmental exposure. Locate your controller as far as possible from power lines, load lines, and other sources of electrical noise such as hard-contact switches, relays, and AC motor drives. For more information on proper grounding guidelines, see the Industrial Automation Wiring and Grounding Guidelines, publication Mounting Dimensions and DIN Rail Mounting 100 mm (3.94 in.) 80 mm (3.15 in.) 90 mm (3.54 in.) Mounting dimensions do not include mounting feet or DIN rail latches. Module Spacing Maintain spacing from objects such as enclosure walls, wireways and adjacent equipment. Allow 50.8 mm (2 in.) of space on all sides for adequate ventilation. An exception to this spacing guideline is allowed for the side at which you are connecting the optional power supply, 2080-PS VAC.
9 Micro Point Programmable Controllers 9 DIN Rail Mounting The module can be mounted using the following DIN rails: 35 x 7.5 mm x 1 mm (EN x 7.5). TIP For environments with greater vibration and shock concerns, use the panel mounting method, instead of DIN rail mounting. Before mounting the module on a DIN rail, use a flat-blade screwdriver in the DIN rail latch and pry it downwards until it is in the unlatched position. 1. Hook the top of the DIN rail mounting area of the controller onto the DIN rail, and then press the bottom until the controller snaps onto the DIN rail. 2. Push the DIN rail latch back into the latched position. Use DIN rail end anchors (Allen-Bradley part number 1492-EA35 or 1492-EAHJ35) for vibration or shock environments. To remove your controller from the DIN rail, pry the DIN rail latch downwards until it is in the unlatched position. Panel Mounting The preferred mounting method is to use four M4 (#8) screws per module. Hole spacing tolerance: ±0.4 mm (0.016 in.). Follow these steps to install your controller using mounting screws. 1. Place the controller against the panel where you are mounting it. Make sure the controller is spaced properly. 2. Mark drilling holes through the mounting screw holes and mounting feet then remove the controller. 3. Drill the holes at the markings, then replace the controller and mount it. Leave the protective debris strip in place until you are finished wiring the controller and any other devices.
10 10 Micro Point Programmable Controllers Panel Mounting Dimensions 86 mm (3.39 in.) 100 mm (3.94 in.) Use Surge Suppressors Because of the potentially high current surges that occur when switching inductive load devices, such as motor starters and solenoids, we recommend the use of some type of surge suppression to protect and extend the operating life of the controllers output contacts. Switching inductive loads without surge suppression can significantly reduce the life expectancy of relay contacts. By adding a suppression device directly across the coil of an inductive device, you prolong the life of the output or relay contacts. You also reduce the effects of voltage transients and electrical noise from radiating into adjacent systems. Refer to the Micro830/Micro850 Programmable Controllers User Manual, publication 2080-UM002, for suitable surge suppression methods and recommended surge suppressors.
12 12 Micro Point Programmable Controllers Control Drawing for Class 1 Division 2 Applications Hazardous Location Class 1 Division 2, Groups A, B, C, and D Micro800 Controller Non-Hazardous Location Any associated apparatus with Universal Serial Bus (USB) connection V max = 5V DC I max = 500 μa L i = 1 μh C i = 120 pf USB Port J3 USB Port V oc, I sc, L a and C a to be determined per Capacitance and Inductance Values table Capacitance and Inductance Values Nonincendive Associated Apparatus Equipment V max (or U i ) V oc or V t (or U o ) I max (or L i ) I sc or I t (or I o ) C i + C cable C a (or C o ) L i + L cable L a (or L o ) Capacitance and Inductance of the field wiring from the nonincendive equipment to the associated apparatus shall be calculated and must be included in the system calculations as shown in the table above. Where the cable capacitance and inductance per foot are not known, the following values shall be used: C cable = 60 pf/ft, L cable = 0.2 μh/ft. Wiring method must be in accordance with ANSI/NFPA70.
13 Micro Point Programmable Controllers 13 Specifications General Specifications Attribute 2080-LC30-10QWB 2080-LC30-10QVB Number of I/O 10 (6 inputs, 4 outputs) Dimensions, HxWxD Shipping weight, approx. Wire size 90 x 100 x 80 mm (3.54 x 3.94 x 3.15 in.) kg (0.666 lb) Min Solid 0.14 mm 2 (26 AWG) Stranded 0.14 mm 2 (26 AWG) Max 2.5 mm 2 (14 AWG) 1.5 mm 2 (16 AWG) 90 C (194 F ) insulation max Wiring category (1) 2 on signal ports 2 on power ports Wire type Use Copper Conductors only Terminal screw torque 0.6 Nm (4.4 lb-in) max using a 2.5 mm (0.10 in.) flat-blade screwdriver. Input circuit type 12/24V sink/source (standard) 24V sink/source (high-speed) Output circuit type Relay 24V DC sink transistor (standard and high-speed) Power consumption 5 W Power supply voltage range I/O rating Isolation voltage V DC Class 2, or Limited Voltage Limited Current Source (LVLC) Input 24V DC, 8.8 ma Output 2 A, 240 V AC, General Use 250V (continuous), Reinforced Insulation Type, Outputs to Aux and Network, Inputs to Outputs Type tested for V DC, Inputs to Aux and Network, 3250 V DC Outputs to Aux and Network, Inputs to Outputs Pilot duty rating C300, R150 N.A. Input 24V DC, 8.8 ma Output 2 A, 240 V DC, 1 A per point (Surrounding air temperature 30 C) 24 V DC, 0.3 A per point (Surrounding air temperature 65 C) 50V (continuous), Reinforced Insulation Type, I/O to Aux and Network, Inputs to Outputs Type tested for V DC, I/O to Aux and Network, Inputs to Outputs
14 14 Micro Point Programmable Controllers General Specifications Attribute 2080-LC30-10QWB 2080-LC30-10QVB Insulation stripping length Enclosure type rating North American temp code 7 mm (0.28 in.) Meets IP20 T4 (1) Use this Conductor Category information for planning conductor routing. Refer to Industrial Automation Wiring and Grounding Guidelines, publication Input Specifications Attribute High-speed DC input (Inputs 0 3) Number of inputs 4 2 Input group to backplane isolation Voltage category Off-state voltage, max On-state voltage range Standard DC input (inputs 4 and higher) Verified by one of the following dielectric tests: 1,414V DC for 2 s 75V DC working voltage (IEC Class 2 reinforced insulation) 24V DC sink/source 5V DC V 65 C (149 F) V 30 C (86 F) 1.5 ma V 65 C (149 F) V 30 C (86 F) Off-state current, max On-state current, min V DC V DC On-state current, nom V DC V DC On-state current, max V DC Nominal impedance 3 kω 3.74 kω IEC input compatibility Type 3 AC input filter setting 8 ms for all embedded inputs In Connected Components Workbench, go to the Embedded I/O configuration window to reconfigure the filter setting for each input group. Output Specifications Attribute 2080-LC30-10QWB 2080-LC30-10QVB Relay Output High-Speed Output (Outputs 0 1) Standard Output (Outputs 2 3) Number of outputs 4 2 2
15 Micro Point Programmable Controllers 15 Output Specifications Attribute 2080-LC30-10QWB 2080-LC30-10QVB Relay Output High-Speed Output (Outputs 0 1) Output voltage, min 5V DC, 5V AC 10.8V DC 10V DC Output voltage, max 125V DC, 265V AC 26.4V DC 26.4V DC Load current, min 10 ma 10 ma Load current, max 2.0 A 100 ma (high-speed operation) C C (standard operation) Surge current, per point See Relay Contacts Ratings on page C C (standard operation) 4.0 A for 10 ms every 1 30 C; every 2 65 C (1) Current, per common, max 5 A 2 A 4 A Current, per controller, max 1440V A 2 A 4 A Turn on time/ Turn off time, max 10 ms 2.5 μs 0.1 ms 1 ms Standard Output (Outputs 2 3) (1) Applies for general purpose operation only. Does not apply for high-speed operation. Relay Contacts Ratings Maximum Volts Amperes Amperes Volt-Amperes Make Break Continuous Make Break 120V AC 15 A 1.5 A 2.0 A 1800V A 180V A 240V AC 7.5 A 0.75 A 24V DC 1.0 A 1.0 A 28V A 125V DC 0.22 A
16 16 Micro Point Programmable Controllers Environmental Specifications Attribute Temperature, operating Temperature, surrounding air, max Temperature, non-operating Relative humidity Vibration Shock, operating Shock, non-operating Value IEC (Test Ad, Operating Cold), IEC (Test Bd, Operating Dry Heat), IEC (Test Nb, Operating Thermal Shock): C ( F) 65 C (149 F) IEC (Test Ab, Unpackaged Nonoperating Cold), IEC (Test Bb, Unpackaged Nonoperating Dry Heat), IEC (Test Na, Unpackaged Nonoperating Thermal Shock): C ( F) IEC (Test Db, Unpackaged Damp Heat): 5 95% non-condensing IEC (Test Fc, Operating): Hz IEC (Test Ea, Unpackaged Shock): 25 g IEC (Test Ea, Unpackaged Shock): DIN mount: 25 g PANEL mount: 45 g Emissions CISPR 11 Group 1, Class A ESD immunity IEC : 6 kv contact discharges 8 kv air discharges Radiated RF immunity IEC : 10V/m with 1 khz sine-wave 80% AM from MHz 10V/m with 200 Hz 50% Pulse 100% AM at 900 MHz 10V/m with 200 Hz 50% Pulse 100% AM at 1890 MHz 10V/m with 1 khz sine-wave 80% AM from MHz EFT/B immunity IEC : ±2 5 khz on power ports ±2 5 khz on signal ports Surge transient immunity IEC : ±1 kv line-line(dm) and ±2 kv line-earth(cm) on power ports ±1 kv line-line(dm) and ±2 kv line-earth(cm) on signal ports Conducted RF immunity IEC : 10V rms with 1 khz sine-wave 80% AM from 150 khz 80 MHz
17 Micro Point Programmable Controllers 17 Certifications Certification (when product is marked) (1) c-ul-us CE C-Tick KC Value UL Listed Industrial Control Equipment, certified for US and Canada. See UL File E UL Listed for Class I, Division 2 Group A,B,C,D Hazardous Locations, certified for U.S. and Canada. See UL File E European Union 2004/108/EC EMC Directive, compliant with: EN ; Meas./Control/Lab., Industrial Requirements EN ; Industrial Immunity EN ; Industrial Emissions EN ; Programmable Controllers (Clause 8, Zone A & B) European Union 2006/95/EC LVD, compliant with: EN ; Programmable Controllers (Clause 11) Australian Radiocommunications Act, compliant with: AS/NZS CISPR 11; Industrial Emissions Korean Registration of Broadcasting and Communications Equipment, compliant with: Article 58-2 of Radio Waves Act, Clause 3 (1) See the Product Certification link at for Declaration of Conformity, Certificates, and other certification details.
18 18 Micro Point Programmable Controllers Notes:
19 Micro Point Programmable Controllers 19 Notes:
20 Rockwell Automation Support Rockwell Automation provides technical information on the Web to assist you in using its products. At you can find technical manuals, a knowledge base of FAQs, technical and application notes, sample code and links to software service packs, and a MySupport feature that you can customize to make the best use of these tools. For an additional level of technical phone support for installation, configuration and troubleshooting, we offer TechConnect support programs. For more information, contact your local distributor or Rockwell Automation representative, or visit Installation Assistance If you experience a problem within the first 24 hours of installation, please review the information that's contained in this manual. You can also contact a special Customer Support number for initial help in getting your product up and running. United States Monday Friday, 8 a.m. 5 p.m. EST Outside United States Please contact your local Rockwell Automation representative for any technical support issues. New Product Satisfaction Return Rockwell Automation tests all of its products to ensure that they are fully operational when shipped from the manufacturing facility. However, if your product is not functioning and needs to be returned, follow these procedures. United States Outside United States Contact your distributor. You must provide a Customer Support case number (call the phone number above to obtain one) to your distributor in order to complete the return process. Please contact your local Rockwell Automation representative for the return procedure. Allen-Bradley, Rockwell Automation, Micro800, Micro830 and TechConnect are trademarks of Rockwell Automation, Inc. Trademarks not belonging to Rockwell Automation are property of their respective companies. PN Supersedes Publication 2080-IN002A-EN-P - September 2010 Copyright 2014 Rockwell Automation, Inc. All rights reserved. Printed in Singapore.
Installation Instructions Compact I/O End Caps/Terminators Catalog Numbers 1769-ECL, 1769-ECR Topic Page Important User Information 2 Environment and Enclosure 3 North American Hazardous Location Approval
Wiring Diagrams Micro800 RS232/485 Isolated Serial Port Plug-in Module Catalog Number 2080-SERIALISOL http://literature.rockwellautomation.com Cette publication est disponible en français sous forme électronique
Wiring Diagrams Micro800 1.5" LCD Display and Keypad Module Catalog Number 2080-LCD http://literature.rockwellautomation.com Cette publication est disponible en français sous forme électronique (fichier
Installation Instructions USB-to-Data Highway Plus Cable Catalog Number 1784-U2DHP Topic Page Important User Information 2 Environment and Enclosure 3 Install the Cable 5 Configure the DH+ Node Address
Installation Instructions FLEX I/O AC Digital Input Modules Catalog numbers 1794-IA8, 1794-IA8I, 1794-IA16 Table of Contents Topic Page Important User Information 2 Environment and Enclosure 3 Preventing
Installation Instructions ControlLogix Data Highway Plus-Remote I/O Communication Interface Module Catalog Number 1756-DHRIO/E Topic About the ControlLogix Data Highway Remote I/O Communication Interface
Backup Scanner Module Catalog Number 1747-BSN Installation Instructions 2 Backup Scanner Module Important User Information Because of the variety of uses for the products described in this publication,
Micro800 Programmable Controller Family Bulletin 2080 Selection Guide Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment.
FLEX I/O DeviceNet Adapter Module 1794-ADN Series C and 1794-ADNK Series C (Modules with a K in the last position of the catalog number are conformally coated to meet noxious gas requirements of ISA/ANSI-71.040
XM-160/161/162 Direct Vibration Module User Guide Firmware Revision 5 1440-VDRS06-00RH, 1440-VDRS06-06RH, 1440-VDRP06-00RH Important User Information Solid state equipment has operational characteristics
Installation Instructions POINT I/O Input Modules Catalog numbers 734-IB, 734-IB4, 734-IB8, Series C Table of Contents Topic Page Important User Information Environment and Enclosure 3 Preventing Electrostatic
Technical Data 1756 ControlLogix Power Supplies Specifications Standard Power Supplies Catalog Numbers 1756-PA72, 1756-PA75, 1756-PB72, 1756-PB75, 1756-PC75, 1756-PH75 Standard Slim Power Supplies Catalog
Installation Instructions MicroLogix 1762-IF4 Analog Input Module Catalog Number 1762-IF4 Table of Contents Topic Page Important User Information 2 North American Hazardous Location Approval 4 Additional
Installation Instructions FLEX I/O Dual Port EtherNet/IP Adapter Modules Catalog Numbers 1794-AENTR, 1794-AENTRXT Series A Table of Contents Topic Page Important User Information 2 Environment and Enclosure
Installation Instructions Ethernet PLC-5 Programmable Controllers Catalog Numbers 1785-L20E, 1785-L40E, 1785-L80E, Series F Contents For This Topic See Page About This Publication 1 Related User Manual
Installation Instructions Universal Serial Bus (USB) to DH-485 Interface Converter Catalog Number 1747-UIC Contents Overview..................................................3 Computer and Operating System
Installation Instructions Hard Disk Drive (HDD) Catalog Number 6189V-35HDDST80, 6189V-35HDDST160 Topic Page About This Publication 1 Important User Information 2 Electrostatic Discharge (ESD) Precautions
Installation Instructions POINT I/O 8 Channel High Density Current Input Module Catalog Number 1734-IE8C Topic Page Important User Information 2 Environment and Enclosure 3 Prevent Electrostatic Discharge
Installation Instructions ControlNet PCI Communication Interface Card Catalog Number 9904-PCIC This document describes how to install the 9904-PCIC ControlNet TM communication interface card. Topic: Page:
Installation Instructions DeviceNet Modules Catalog Numbers 1756-DNB, 1769-ADN, 1769-SDN Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical
Installation Instructions Compact 1769-ASCII Module Cat. No. 1769-ASCII Inside About the Module...4 Install the Module...5 Assemble the System...6 Mount Expansion I/O...8 Ground the Module...12 Connect
Installation Instructions SLC 500 Analog Input Module (Catalog Number 1746NI8) Inside Important User Information... 2 For More Information... 3 Hazardous Location Considerations... 4 Environnements dangereux...
Highlights & Features Protection Class II, Double Isolation (No Earth connection is required) Universal AC input voltage without power de-rating Efficiency > 87.0% @ 115Vac & 230Vac NEC Class 2 / Limited
Square D Clipsal DIN-Rail Four-Channel Auxiliary Input Unit SLCLE5504AUX for Use with Wired C-Bus Networks Instruction Bulletin Retain for future use. Square D Clipsal DIN-Rail Four-Channel Auxiliary Input
Data sheet Three-phase monitoring relay CM-PFE The CM-PFE is a three-phase monitoring relay that monitors the phase parameter phase sequence and phase failure in three-phase mains. 2CDC 251 005 S0012 Characteristics
User Manual SmartGuard 600 Controllers Catalog Numbers 1752-L24BBB, 1752-L24BBBE Important User Information Read this document and the documents listed in the additional resources section about installation,
2CDC 251 098 F0t06 a Rotary switch for the preselection of the time range of the ON time b Potentiometer with direct reading scale for the fine adjustment of the ON time c Rotary switch for the preselection
Installation Instructions POINT I/O EtherNet/IP Adapter Catalog Number 1734-AENT LED Indicators Safety End Cap Node Address Thumbwheel EtherNet Network RJ45 Connector DIN Rail Locking Screw (orange) RTB
Power Supply Unit, Primary Switched, Narrow Design MINI POWER provides: Extra narrow design with widths of 22.5 mm, 45 mm, and 67.5 mm (0.886, 1.772, and 2.657 in.) Global use due to a wide-range input
Installation Instructions NetLinx ControlNet 1784-PCIC Communication Card Catalog Number 1784-PCIC This document describes how to install and use the NetLinx 1784-PCIC ControlNet TM communication interface
Micro800 Programmable Controllers Bulletin 2080 Selection Guide Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety
Data sheet Electronic timer CT-AHD.12 OFF-delayed with 1 c/o (SPDT) contact The CT-AHD.12 is an electronic time relay with OFF-delay. It is from the CT-D range. With their MDRC profile and a width of only
Installation Instructions Chassis Interface Module for 1746 Local I/O (Catalog Number 1747-PCIL) Use this document to install the Chassis Interface module for 1746 Local I/O and connect it to a PCI Bus
User Manual Micro820 Programmable Controllers Catalog Numbers 2080-LC20-20QWB, 2080-LC20-20QBB, 2080-LC20-20AWB, 2080-LC20-20QWBR, 2080- LC20-20QBBR, 2080-LC20-20AWBR Important User Information Solid-state
Product datasheet Characteristics TM7BDM8B expansion block - TM7 - IP67-8 DI/DO - 24V DC - 0.5 A - M8 connector Main Range of product Product or component type Range compatibility Enclosure material Bus
Highlights & Features Protection Class II, Double Isolation (No Earth connection is required) Universal AC input voltage and full power up to 55 C Power will not de-rate for the entire input voltage range
Highlights & Features Protection Class II, Double Isolation (No Earth connection is required) Universal AC input voltage and full power up to 55 C Power will not de-rate for the entire input voltage range
Characteristics Single-function OFF-delay timer for DC contactors, without auxiliary voltage Width.5 mm CDC 5 6 F3 Approvals A culus E CCC CT-VBS a Circuit diagram b Marker label Marks a CE b C-Tick Order
Relés e Contatores de Estado Sólido SIRIUS Coletânea de dados técnicos ( product data sheet ) Agosto/212 SSR - 3RF21 22,5 mm Ponto Zero SSR - 3RF2 45 mm Ponto Zero SSR - 3RF22 45 mm Ponto Zero Trifásico
Redundancy Module QUT DIODE provides: 00% decoupling of power supplies connected in parallel Can be installed in potentially explosive areas Load currents up to 60 A supported Easy assembly by snapping
Characteristics multifunction control relay RM17-TE - range 183..528 V AC Complementary Reset time Maximum switching voltage Minimum switching current Maximum switching current [Us] rated supply voltage
38 Series - Relay interface modules 0.1-2 - 3-5 - 6-8 - 16 A 38 SERIES Common features Instant ejection of relay by plastic retaining clip Integral coil indication and protection circuit EMR Electromechanical
MasterINTERFACE 39 Series - Relay interface modules Common features Space saving 6.2 mm wide Connections for 16-way jumper link Integral coil indication and protection circuit Secure retention and easy
55 Series - General purpose relays 7-10 A Features 55.12 55.13 55.14 Printed circuit mount, general purpose 2, 3 & 4 Pole relays 55.12-2 Pole 10 A 55.13-3 Pole 10 A 55.14-4 Pole 7 A AC coils & DC coils
Characteristics multifunction voltage control relay RM35-U - range 15..600 V Complementary Reset time Maximum switching voltage [Us] rated supply voltage Supply voltage limits Power consumption in W Main
Characteristics voltage control relay RM17-U - range 65..260 V AC Complementary Reset time Maximum switching voltage [Us] rated supply voltage Supply voltage limits Power consumption in W Main Range of
Extract from the online catalog STEP-PS/1AC/12DC/1.5 Order No.: 2868567 DIN rail power supply unit 12 V DC/1.5 A, primary switched-mode, 1- phase Commercial data EAN 4046356292924 Pack 1 pcs. Customs tariff
8 172 TX-I/O Digital input modules TXM1.8D TXM1.16D Two fully compatible versions: TXM1.8D: 8 inputs, each with a three-color LED (green, yellow or red) TXM1.16D: As TXM1.8X, but 16 inputs, each with a
Data sheet Voltage monitoring relays CM-ESS.M For single-phase AC/DC voltages The CM-ESS.M is an electronic voltage monitoring relay that provides reliable monitoring of voltages as well as detection of
Characteristics three-phase network control relay RM4-T - range 200..500 V Complementary [Us] rated supply voltage Output contacts Setting accuracy of time delay Delay at power up Measuring cycle Marking
Installation Instructions (Cat. No. 1771-IAD Series D) Contents Use this document as a guide when installing the catalog number 1771-IAD series D input module. To See page Prevent Electrostatic Discharge
38 Relay interface modules 0.1-2 - 3-5 - 6-8 - 16 A 38 Common features Instant ejection of relay by plastic retaining clip Integral coil indication and protection circuit 6.2 mm wide EMR - DC, AC or AC/DC
Data sheet Three-phase monitoring relay CM-PE The three-phase monitoring relay CM-PE monitors the phase parameter phase failure as well as over- and undervoltage in three-phase mains. 2CDC 251 006 S0012
User Manual ControlLogix System Catalog Numbers 1756-L61, 1756-L62, 1756-L63, 1756-L63XT, 1756-L64, 1756-L65, 1756-L71, 1756-L72, 1756-L73, 1756-L73XT, 1756-L74, 1756-L75 Important User Information Solid-state
MILLENIUM Table of contents 1. INTRODUCTION 1 2. HARDWARE DESCRIPTION 2 3. INSTALLATION 5 4. CONNECTION 6 5. USER SAFETY AND PROTECTION OF EQUIPMENT 8 1. Introduction The MILLENIUM series has been designed
Data sheet Temperature monitoring relays CM-TCS Monitoring relays for monitoring temperatures with a PT100 sensor (2- or 3-wire connection) The temperature monitoring relays CM-TCS monitor overtemperature,
Telephone- and leased line modem for industrial applications TD-36 Modem for industrial PSTN- and leased line applications The TD-36 is an analogue V.34 PSTN modem as well as an industrial 2-wire leased
38 Series - Relay interface modules 0.1-2 - 3-5 - 6-8 - 16 A Common features Instant ejection of relay by plastic retaining clip Integral coil indication and protection circuit EMR Electromechanical Relays
Installation Instructions 1738 ArmorPOINT I/O Dual Port EtherNet/IP Adapter Catalog number 1738-AENTR, Series B Table of Contents Topic Page Important User Information 2 Environment and Enclosure 3 Preventing
48 Series - Relay interface modules 8 A Features 48.12 2 Pole Safety relay interface modules, 15.8 mm wide 48.12-2 Pole 8 A (screw terminal) DC sensitive coils Relay with forcibly guided contacts according
RHINO PSM Series Supplies Our versatile switching power supplies are DIN-rail mountable Features Industrial grade design Sturdy metal case to withstand harsh industrial environments Model PSM4-090S-N meets
Overview/Modes of Operation Bulletin 150 Smart Motor Controller The SMC-3 is a compact, simple to use, solid-state motor controller designed to operate 3-phase motors. It features a built-in overload relay
Smart "Compact" range with display CD12 Smart Part number 88974043 Highly visible blue LCD with 4 lines of 18 characters and configurable backlighting Allow the use of the entire library of specific functions
425 CONTROLS DATA MANAGEMENT PROCESS AUTOMATION EUROCUBE General purpose single phase thyristors and solid state relays Product data abc 425 EUROCUBE A complete range of low cost solid state relays and
PowerFlex 700S and 700H Frame 12 DC Bus Connector Kit Installation Instructions This document provides instructions for the installation of a DC bus connector kit for PowerFlex 700S and 700H frame 12 drives
Characteristics three-phase network control relay RM4-T - range 300..430 V Complementary [Us] rated supply voltage Control threshold undervoltage Control threshold overvoltage Output contacts Main Range
s 8 185 8185P01 TX-I/O ; DESIGO OPEN TX OPEN RS/485 module for integrating third-party systems and devices to DESIGO (V4 or higher) TXI1.OPEN Platform to integrate third-party systems and devices to the
NX-S@ NX safety stand-alone stand-alone into machine automation Expandable safety system up to 32 safety connections or 63 standard connections controller flexible system lets your freely mix safety I/O
Series - Low profile PCB relays 8-12 - 16 A 41 Features 41.31 41.52 41.61 1 & 2 Pole - Low profile (15.7 mm height) 41.31-1 Pole 12 A (3.5 mm pin pitch) 41.52-2 Pole 8 A (5 mm pin pitch) 41.61-1 Pole 16
nstallation nstructions FLEX /O solated nput Analog Module Cat. No. 1794-F4 mportant User nformation Solid state equipment has operational characteristics differing from those of electromechanical equipment.
Installation Instructions Cat. No. 1771-OD16 Series B This document provides information on: important pre-installation considerations power supply requirements installing the module using the module indicators
Troubleshooting Guide Diagnostic Utility for Rockwell Automation Industrial Computers Topics Page Where to Find the Utility 3 When to Run the Utility 3 Interpret Results 3 Prepare to Boot from the Industrial