1 Installation Instructions ControlNet PCI Communication Interface Card Catalog Number 9904-PCIC This document describes how to install the 9904-PCIC ControlNet TM communication interface card. Topic: Page: Important User Information 2 European Communities (EC) Directive Compliance 3 European Communities (EC) Directive Compliance 3 Install the Card Inside the Computer 5 Connect the Card 7 Interpret the Status Indicators on the 9904-PCIC 12 Interpret the Status Indicators on the 9904-PCIC 12 CSA Hazardous Location Approval 15 Specifications 17 If you connect the card directly to a ControlNet network, you may also need to refer to ControlNet International specifications and the manufacturer s documentation for tap installation and cable planning and installation. The 9904-PCIC communication interface card lets a PCI Local bus compatible computer communicate directly with other ControlNet products.
2 2 ControlNet PCI Communication Interface Card Important User Information Because of the variety of uses for the products described in this publication, those responsible for the application and use of this control equipment must satisfy themselves that all necessary steps have been taken to assure that each application and use meets all performance and safety requirements, including and applicable laws, regulations codes and standards. The illustrations, charts, sample programs and layout examples shown in this guide are intended solely for purposes of example. Since there are many variables and requirements associated with any particular installation we do not assume responsibility or liability (to include intellectual property liability) for actual use based upon the examples shown in this publication. NEMA Standards Publication No. ICS , Safety Guidelines for the Application, Installation, and Maintenance of Solid State Control, describes some important differences between solid-state equipment and electromechanical devices that should be taken into consideration when applying products such as those described in this publication. Throughout this document we use notes to make you aware of safety considerations: ATTENTION: Identifies information about practices or circumstances that can lead to personal injury or death, property damage or economic loss. Attention statements help you to: identify a hazard avoid a hazard recognize the consequences Important: Identifies information that is critical for successful application and understanding of the product.
3 ControlNet PCI Communication Interface Card 3 European Communities (EC) Directive Compliance If this product has the CE mark it is approved for installation within the European Union and EEA regions. It has been designed and tested to meet the following directives. EMC Directive This product is tested to meet the Council Directive 89/336/EC Electromagnetic Compatibility (EMC) by applying the following standards, in whole or in part, documented in a technical construction file: EN EMC Generic Emission Standard, Part 2 Industrial Environment EN EMC Generic Immunity Standard, Part 2 Industrial Environment This product is intended for use in an industrial environment. Low Voltage Directive This product is tested to meet Council Directive 73/23/EEC Low Voltage, by applying the safety requirements of EN Programmable Controllers, Part 2 - Equipment Requirements and Tests. This equipment is classified as open equipment and must be mounted in an enclosure during operation to provide safety protection.
4 4 ControlNet PCI Communication Interface Card Handling the Card ATTENTION: The card uses CMOS technology, which is highly sensitive to electrostatic discharge (ESD). ESD may be present whenever you handle the card. When you handle the card without any ESD protection you can cause internal circuit damage that may not be apparent when you install or initially use the card. Take these precautions to guard against ESD damage: Before you handle the card, touch a grounded object to discharge and built-up static charge. Avoid touching the backplane connector or interface connector pins located on the card. If the card is not in use, store it in the anti-static clamshell that the card was shipped in. Important: Remember, a computer with ac power disconnected is not a grounded object.
5 ControlNet PCI Communication Interface Card 5 Install the Card Inside the Computer Before you install the card, be certain that you: know how to install hardware in your computer consult your computer s documentation for hardware installation instructions To install the card, you need to: access to the computer s expansion slots possess either a Phillip-head or a flat-head screwdriver insert the card into the computer Access the Computer s PCI Local Bus Expansion Slots To install the card, you must access the computer s PCI local bus expansion slots. Follow these general steps, or refer to your computer s user guide for instructions on how to: 1. Turn off the power to the host computer with the power switch. 2. Remove the computer s cover. 3. Select a vacant PCI local bus expansion slot. 4. Remove the slot s expansion cover. Loosen the screw on the back (rear bracket) of the computer.
6 6 ControlNet PCI Communication Interface Card Insert the Card To insert the card inside the computer: 1. Follow the card handling instructions on page Insert the card into the edge connector and tighten the expansion slot screw. 3. Turn on the computer to be certain that it comes up correctly. If the computer: then: powers up go to step 4 hangs up you probably have a memory or I/O conflict you should remove all other cards and try again If you continue to experience difficulty, contact a representative where you purchased this product. 4. Replace the computer s cover (when the computer boots up correctly).
7 ControlNet PCI Communication Interface Card 7 Connect the Card After you have installed the card, you can connect it: to a device already connected to the ControlNet network (page 8) directly to a ControlNet network, which requires a tap (page 11) Figure 1 describes the 9904-PCIC card connectors and indicators. Figure PCIC card Diagnostic status indicators Network Access Port (NAP) RJ-45 connector for connecting programming terminals to devices on a ControlNet network Channel A Redundant media BNC connectors A BNC connectors for connecting directly to ControlNet network Channel B B Do not connect more than one ControlNet network to this card. ControlNet
8 8 ControlNet PCI Communication Interface Card ATTENTION: Do not connect more than one ControlNet network to this card. If you attempt to connect a second network to this card, your communication system will operate erratically. See page 12 for information about status indicators. Indicators diagnose only redundant media BNC connections. Important: If you use a non-redundant cable system, all ControlNet devices must be on the same channel, channel A. Connect to a Device on the ControlNet Network The 9904-CP cable (Figure 2) connects a host computer to another ControlNet device. It has two RJ-45 8 pin connectors. Figure CP cable RJ-45 8-pin connectors Connector 1 Connector CP cable ATTENTION: Use only the 9904-CP cable when you connect a programming terminal to the network through the network access port (NAP). If you use a different cable, it could result in possible network failures or product damage.
9 ControlNet PCI Communication Interface Card 9 Table A shows the wiring for the cable. Table A Wiring for 9904-CP connector cable Connector 1 Wire Number Signal Mnemonic Signal Name 1 ISO-GND Isolated Ground 2 N.C. No Connection 3 PTTX-H Transmit Data High 4 PTTX-L Transmit Data Low 5 PTRX-L Receive Data Low 6 PTRX-H Receive Data High 7 N.C. No Connection 8 ISO-GND Isolated Ground Connector 2 Wire Number Signal Mnemonic Signal Name 1 ISO-GND Isolated Ground 2 N.C. No Connection 3 PTRX-H Receive Data High 4 PTRX-L Receive Data Low 5 PTTX-L Transmit Data Low 6 PTTX-H Transmit Data High 7 N.C. No Connection 8 ISO-GND Isolated Ground
10 10 ControlNet PCI Communication Interface Card When you use the RJ-45 connector you can connect the card to a ControlNet network, without a tap, through the Network Access Port (or NAP) of a programmable controller, I/O adapter, or other ControlNet compliant devices (Figure 3 and Figure 4). Figure 3 Connect a computer to a ControlNet network through a programmable controller or an I/O adapter programming terminal 9904-PCIC 9904-CP cable 1 ControlNet network ControlNet product 1 The 9904-CP cable can be plugged into any ControlNet product s NAP to provide programming capability on the ControlNet network. When you connect a programming terminal through this cable, it is counted as a node and must have a unique address. ATTENTION: If you connect the product to a cable system that does not support redundant media, connect the tap dropline to the BNC connector labeled channel A. Channel B is left open. If the cable system is redundant, connect the product so that all devices on the network use the same cable for the same channel. That is, all channel A connectors connect to one cable; all channel B connectors connect to the other.
11 ControlNet PCI Communication Interface Card 11 Figure 4 Connect a host computer to ControlNet through the 9904-PCIC card Desktop host computer 9904-PCIC 9904-PCIC Desktop host computer 9904-CP cable ControlNet network Connect the Card Directly to the ControlNet Network To connect the card directly to a ControlNet network as shown in Figure 5, refer to The ControlNet Specification and follow the manufacturer s documentation for tap installation and cable planning and installation. You can obtain the ControlNet Specification from ControlNet International, PMB State Road 7 #F6, Boca Raton, FL USA or visit Figure 5 Connect the card directly to the ControlNet network 9904-PCIC Desktop host computer 9904-TPR, -TPS, -TPYR, or -TPYS tap ControlNet network
12 12 ControlNet PCI Communication Interface Card Interpret the Status Indicators on the 9904-PCIC The status indicators on the card give you information about the card and the network when you re connected via the BNC connectors. Table B outlines the states and explains what each state means to you and the action you should take, if any, to correct that state. ControlNet status interpretation steady - indicator is on continuously in the defined state. alternating - the two indicators alternate between the two defined states at the same time (applies to both indicators viewed together). The two indicators are always in opposite states, out of phase. flashing - the indicator alternates between the two defined states (applies to each indicator viewed independent of the other). If both indicators flash, they must flash together, in phase. Important: When you connect the module to a ControlNet network using the network access port (NAP) only, the LEDs are meaningless.
13 ControlNet PCI Communication Interface Card 13 Table B ControlNet status interpretation Cause: Action: A and B off no power none or apply power to the PC PCIC driver not started start PCIC driver verify that the PCIC driver has been configured properly faulted card check operating system event log for details of fault (if the PC s operating system supports an event log) cycle power to the PC verify that you have firmly inserted the PCIC card into a PCI local bus expansion slot and that the expansion slot screw is tightened. If fault persists, contact a representative where you purchased this product. steady red faulted card cycle power to the PC verify that you have firmly inserted the PCIC card into a PCI local bus expansion slot and that the expansion slot screw is tightened If fault persists, contact a representative where you purchased this product. alternating red/green self-test none alternating red/off incorrect node configuration duplicate ControlNet node address check PCIC node address and other ControlNet configuration parameters
14 14 ControlNet PCI Communication Interface Card Table B ControlNet status interpretation continued A or B Cause: off channel disabled steady green normal operation flashing green/off temporary network errors Action: program network for redundant media, if required none check media for broken cables, loose connectors, missing terminators, etc. If condition persists, refer to ControlNet International specifications. flashing red/off media fault check media for broken cables, loose connectors, missing terminators, etc. If condition persists, refer to ControlNet International specifications. no other nodes add other nodes to the network present on network flashing red/green incorrect node address incorrect network configuration change PCIC node address so that it is less than or equal to UMAX 1 stop and restart the PCIC driver reconfigure the ControlNet network so that UMAX 1 is greater than or equal to the PCIC node address 1 UMAX is the highest node address on a ControlNet network that can transmit data.
15 ControlNet PCI Communication Interface Card 15 CSA Hazardous Location Approval CSA certifies products for general use as well as for the use in hazardous locations. Actual CSA certification is indicated by the product label as shown below, and not by statements in any user documentation. Example of the CSA certification product label CL 1 DIV 2 GP A,B,C,D TEMP To comply with CSA certification for use in hazardous locations, the following information becomes a part of the product literature for this CSA-certified industrial control product. This equipment is suitable for use in Class 1, Division 2, Groups A, B, C, D, or non-hazardous locations only. The products having the appropriate CSA markings (that is, Class 1, Division 2, Groups A, B, C, D), are certified for use in other equipment where the suitability of combination (that is, application or use) is determined by the CSA or the local inspection office having jurisdiction. Important: Due to the modular nature of a programmable control system, the product with the highest temperature rating determines the overall temperature code rating of a programmable control system in a Class1, Division 2 location. The temperature code rating is marked on the product label as shown. Temperature code rating CL 1DIV 2 GP A,B,C,D TEMP Look for temperature code rating here The following warnings apply to products having CSA certification for use in hazardous locations. WARNING: Explosion hazard Substitution of components may impair suitability for Class 1, Division 2. Do not replace components unless power has been switched off or the area is known to be non-hazardous. Do not disconnect equipment unless power has been switched off or the area is known to be non-hazardous. Do not disconnect connectors unless power has been switched off or the area is known to be non-hazardous. Secure any user-supplied connectors that mate to external circuits on this equipment by using screws, sliding latches, threaded connectors, or other means such that any connection can withstand a 15 Newton (3.4lb.) separating force applied for a minimum of one minute. Batteries must be changed only in an area known to be non-hazardous. CSA logo is a registered trademark of the Canadian Standards Association.
16 16 ControlNet PCI Communication Interface Card Approbation d utilisation dans des emplacements dangreux par la CSA La CSA certifie les produits d utilisation générale aussi bien que ceux qui s utilisent dans des emplacements dangereux. La certification CSA en vigueur est indiquée par l étiquette du produit et non par des affirmations dans la documentation à l usage des utilisateurs. Exemple d étiquette de certification d un produit par la CSA. CL 1 DIV 2 GP A, B, C, D TEMP Pour satisfaire à la certification de la CSA dans des endroits dangereux, les informations suivantes font partie intégrante de la documentation ce produit industriel de contrôle certifié par la CSA. Cet équipement convient à l utilisation dan des emplacements de Classe1, Division 2, Groupes A, B, C, D, ou ne convient qu à utilisation dans des endroits non dangereux. Les produits portant le marquage appropié de la CSA (c est à dire, Classe1, Division 2, Groupes A, B, C, D) sont certifiés à l utilisation pour d autres équipement où la convenance de combinasion (application ou utilisation) est déterminée par la CSA ou le bureau local d inspection qualifié. Important: Par suite de la nature modulaire du système de contrôle programmable, le produit ayant le taux le plus éléve de température détermine le taux d ensemble du code de température du système de contrôle d un programmable dans un emplacement de Classe 1, Division 2. Le taux du code de température est indiqué sur l étiquette du produit. Taux du code de température Les advertissements suivants s appliquent aux produits ayant la certification CSA pour leur utilisation dans des emplacements dangereux. Le sigle CSA est la marque deposee de l Association des Standards pour le Canada. CL 1 DIV 2 GP A, B, C, D TEMP Le taux du code température est indiqué ici AVERTISSEMENT: Risque d explosion La substitution de compansants peut rendre ce matériel inacceptable pour lesemplacements de Classe 1, Division 2. Couper le courant ou s assurer quel emplacement est désigné non dangeraux avant de replacer lescomposants. Avant de débrancher l équipement, couper le courant ou s assurer que l emplacement est désigné non dangereux. Avant de débrancer les connecteurs, couper le courant ou s assurer que l emplacement est reconnu non dangereux. Attacher tous connectours fournis par l utilisateur et reliés aux circuits externes of the appareil à l aide de vis, loquets coulissants, connecteurs filetés ou autres moyens permettant aux connexions de résister à une force de séparation de 15 Newtons (3,4 lb. - 1,5 kg) appliquée pendant au moins une minute. Afin d eviter tout risque d explosion, s assurer que l emplacement est designe non dangereux avant de changer la batterie.
17 ControlNet PCI Communication Interface Card 17 Specifications The operating parameters describe the environment within the PCIC s slot. Refer to the documentation for your computer for environmental requirements. The card should not exceed those specifications. General Specifications Characteristic Value Power Requirements 5 V dc, 700 ma Maximum, Class 2 Conductor Category 2 Use this conductor category information when you plan conductor routing as described in the ControlNet International specification. Environmental Specifications Operating Nonoperating Slot Temperature 0 to 50 C (32 to 122 F) -40 to 85 C (-40 to 185 F) Humidity 5 to 95% without condensation 5 to 95% without condensation Vibration 10 th 150 Hz, constant.012 in displacement 10 to 150 Hz, constant 2.0G acceleration not applicable Shock 30G peak/11 ms 50G peak/11 ms Agency Certification (when product or packaging is marked) UL Recognized Industrial Control Component N223 Certified Component Process Control Equipment Certified Component Class I, Division 2, Groups A, B, C, D Marked for all applicable directives Marked for all applicable acts
18 ControlNet is a trademark of ControlNet International. Publication PN Printed in the U.S.A.
Installation Instructions NetLinx ControlNet 1784-PCIC Communication Card Catalog Number 1784-PCIC This document describes how to install and use the NetLinx 1784-PCIC ControlNet TM communication interface
Installation Instructions (Cat. No. 1771-IAD Series D) Contents Use this document as a guide when installing the catalog number 1771-IAD series D input module. To See page Prevent Electrostatic Discharge
Installation Instructions Chassis Interface Module for 1746 Local I/O (Catalog Number 1747-PCIL) Use this document to install the Chassis Interface module for 1746 Local I/O and connect it to a PCI Bus
Installation Instructions Compact I/O End Caps/Terminators Catalog Numbers 1769-ECL, 1769-ECR Topic Page Important User Information 2 Environment and Enclosure 3 North American Hazardous Location Approval
Backup Scanner Module Catalog Number 1747-BSN Installation Instructions 2 Backup Scanner Module Important User Information Because of the variety of uses for the products described in this publication,
Installation Instructions SLC 500 Analog Input Module (Catalog Number 1746NI8) Inside Important User Information... 2 For More Information... 3 Hazardous Location Considerations... 4 Environnements dangereux...
Wiring Diagrams Micro800 RS232/485 Isolated Serial Port Plug-in Module Catalog Number 2080-SERIALISOL http://literature.rockwellautomation.com Cette publication est disponible en français sous forme électronique
Sun Enterprise Optional Power Sequencer Installation Guide For the Sun Enterprise 6500/5500 System Cabinet and the Sun Enterprise 68-inch Expansion Cabinet Sun Microsystems, Inc. 901 San Antonio Road Palo
AC 800M EtherNet/IP DeviceNet Linking Device LD 800DN SP1134 Power and productivity for a better world TM AC 800M EtherNet/IP DeviceNet Linking Device LD 800DN NOTICE This document contains information
UR Series LED Upgrade Kit Includes: 48" Linear Option IMPORTANT SAFEGUARDS When using electrical equipment, basic safety precautions should always be followed including the following: READ AND FOLLOW ALL
Installation Instructions USB-to-Data Highway Plus Cable Catalog Number 1784-U2DHP Topic Page Important User Information 2 Environment and Enclosure 3 Install the Cable 5 Configure the DH+ Node Address
OPERATING INSTRUCTIONS CompactRIO crio-9052 CompactRIO StarFabric Interface 1 POWER BACKUP STATUS FPGA V1 C V2 2 C Rx INPUT 9 35 V 17 W MAX 3 Tx NI crio-9052 CompactRIO StarFabric Interface 1 LEDs 2 Power
SECTION 7 - REPAIR/REPLACEMENT PROCEDURES INTRODUCTION Although the modular power system is designed to give long, troublefree service, some components may need to be replaced periodically. This section
Installation Instructions ControlLogix Data Highway Plus-Remote I/O Communication Interface Module Catalog Number 1756-DHRIO/E Topic About the ControlLogix Data Highway Remote I/O Communication Interface
XM-160/161/162 Direct Vibration Module User Guide Firmware Revision 5 1440-VDRS06-00RH, 1440-VDRS06-06RH, 1440-VDRP06-00RH Important User Information Solid state equipment has operational characteristics
Installation Instructions FLEX I/O AC Digital Input Modules Catalog numbers 1794-IA8, 1794-IA8I, 1794-IA16 Table of Contents Topic Page Important User Information 2 Environment and Enclosure 3 Preventing
Moxa PoE Injector INJ-24 Series Hardware Installation Guide Second Edition, March 2011 2011 Moxa Inc. All rights reserved. P/N: 1802000240011 Overview The Moxa PoE Injector INJ-24 Series is a 1-port PoE
Installation Instructions Cat. No. 1771-OD16 Series B This document provides information on: important pre-installation considerations power supply requirements installing the module using the module indicators
Installation Instructions Ethernet PLC-5 Programmable Controllers Catalog Numbers 1785-L20E, 1785-L40E, 1785-L80E, Series F Contents For This Topic See Page About This Publication 1 Related User Manual
Sun StorEdge A5000 Installation Guide for Windows NT Server 4.0 Sun Microsystems, Inc. 901 San Antonio Road Palo Alto, CA 94303-4900 USA 650 960-1300 Fax 650 969-9131 Part No. 805-7273-11 October 1998,
BitStorm 6051 Installation Instructions Document Number 6051-A2-GZ40-10 July 2002 About the BitStorm 6051 The BitStorm system enables simultaneous high-speed digital data access and analog voice service
Revision A Direct AC Wiring Option Installation Guide The direct AC wiring option enables you to wire AC power directly in to the ADP InTouch. The option kit contains the following parts. 25mm 12mm Caution:
Regulatory Compliance Statement 0560 EU Declaration of Conformity The declaration of conformity may be consulted at www.kobo.com/userguides SAR Limits The exposure standard for wireless devices employs
Wiring Diagrams Micro800 1.5" LCD Display and Keypad Module Catalog Number 2080-LCD http://literature.rockwellautomation.com Cette publication est disponible en français sous forme électronique (fichier
AXIS 291 1U Video Server Rack Installation Guide About This Document This document describes how to install Axis blade video servers in the AXIS 291 1U Video Server Rack. Updated versions of this document
EHD TRACK LEVEL, (SET LEVEL ON PLASTIC HEADER. DO NOT PLACE LEVEL ON ALUMINUM TRACK.) TRACK IS FLUSH WITH TOP OF HEADER JUNCTION BOX IDLER PULLEY LOCATOR PINS LOCATOR PINS OPERATOR DOOR STOP JUNCTION BOX
MCR1900 Media Converter 19-Slot Chassis Installation Guide Part #5500304-11 Copyright Statement This document must not be reproduced in any way whatsoever, either printed or electronically, without the
Express5800/120Ed Rack Mount Kit Installation Procedures PN: 455-01607-001 Proprietary Notice and Liability Disclaimer The information disclosed in this document, including all designs and related materials,
Sun Management Center Change Manager 1.0.1 Release Notes Sun Microsystems, Inc. 4150 Network Circle Santa Clara, CA 95054 U.S.A. Part No: 817 0891 10 May 2003 Copyright 2003 Sun Microsystems, Inc. 4150
Start Here Installation and Documentation Reference Sun StorEdgeTM 6120 Array 1 Access the Online Documentation These documents and other related documents are available online at http://www.sun.com/documentation
8 172 TX-I/O Digital input modules TXM1.8D TXM1.16D Two fully compatible versions: TXM1.8D: 8 inputs, each with a three-color LED (green, yellow or red) TXM1.16D: As TXM1.8X, but 16 inputs, each with a
Installation Instructions DeviceNet Modules Catalog Numbers 1756-DNB, 1769-ADN, 1769-SDN Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical
FLEX I/O DeviceNet Adapter Module 1794-ADN Series C and 1794-ADNK Series C (Modules with a K in the last position of the catalog number are conformally coated to meet noxious gas requirements of ISA/ANSI-71.040
Series Six Plus Programmable Controller Gl?K-0147B June 1989 Central Processor Unit 8-Slot Rack 1l-Slot Rack General Description The Central Processor Unit (CPU) for the Series Six Plus Programmable Logic
GSM-EXT Cable Assembly Installation Guide For Documentation and Online Support: http://www.security.honeywell.com/hsc/resources/mywebtech General Information The GSM-EXT cable assembly is used to connect
Artisan Technology Group is your source for quality new and certified-used/pre-owned equipment FAST SHIPPING AND DELIVERY TENS OF THOUSANDS OF IN-STOCK ITEMS EQUIPMENT DEMOS HUNDREDS OF MANUFACTURERS SUPPORTED
ReachDSL ALM Hotwire ReachDSL Modem, Model 6390 with Inline Phone Filter Installation Instructions Document Number 6390-A2-GN10-00 May 2002 Package Checklist Verify that your package contains the following:
TM Hotwire 5216 Remote Termination Unit (RTU) Customer Premises Installation Instructions Document Number 5216-A2-GN10-10 February 1998 Before You Begin An optional POTS (Plain Old Telephone Service) splitter
Square D Clipsal DIN-Rail Four-Channel Auxiliary Input Unit SLCLE5504AUX for Use with Wired C-Bus Networks Instruction Bulletin Retain for future use. Square D Clipsal DIN-Rail Four-Channel Auxiliary Input
HP UPS R1500 Generation 3 Installation Instructions Part Number 650952-001 NOTE: The rating label on the device provides the class (A or B) of the equipment. Class B devices have a Federal Communications
Installation Instructions Universal Serial Bus (USB) to DH-485 Interface Converter Catalog Number 1747-UIC Contents Overview..................................................3 Computer and Operating System
Installation Instructions POINT I/O EtherNet/IP Adapter Catalog Number 1734-AENT LED Indicators Safety End Cap Node Address Thumbwheel EtherNet Network RJ45 Connector DIN Rail Locking Screw (orange) RTB
1-Port DS3 IMA Module Description and Technical Specifications Purpose of This Document This document identifies and describes the 1-Port DS3 IMA module and related safety information. It also includes
Installation Instructions Hard Disk Drive (HDD) Catalog Number 6189V-35HDDST80, 6189V-35HDDST160 Topic Page About This Publication 1 Important User Information 2 Electrostatic Discharge (ESD) Precautions
AI120 AIswitch Series 120 Chassis Guide INSTALLATION GUIDE Westell Technologies Part # 030-300715 Rev. A Copyright 2015 by Westell Technologies. All Rights Reserved. Westell, Kentrox and Optima Management
Mercury Helios 2 ASSEMBLY MANUAL & USER GUIDE TABLE OF CONTENTS INTRODUCTION...1 1.1 MINIMUM SYSTEM REQUIREMENTS 1.1.1 Apple Mac Requirements 1.1.2 PC Requirements 1.1.3 Supported PCIe Cards 1.2 PACKAGE
MANUFACTURER DATA SHEET High Speed Counter Manufacturer: Allen-radley/Rockwell Model Number: 1746-HSCE See www.geomartin.com for additional PDF datasheets Martin Part Number: E-014901-03 VendorPartNumber:
Introduction This guide is to assist the reader with the most basic form of installation and connection to switches in this series. As there is more than one switch in this series, the diagrams might slightly
Power Supply Guide Version 1.0 for D-Show Digidesign 2001 Junipero Serra Boulevard Daly City, CA 94014-3886 USA tel: 650 731 6300 fax: 650 731 6399 Technical Support (USA) tel: 650 731 6100 fax: 650 731
Installation Instructions POINT I/O Input Modules Catalog numbers 734-IB, 734-IB4, 734-IB8, Series C Table of Contents Topic Page Important User Information Environment and Enclosure 3 Preventing Electrostatic
TM HotWire Model 7900 10-Slot Standalone Shelf Installation Instructions Document Number 7900-A2-GN10-10 About the HotWire 7900 10-Slot Standalone Shelf The HotWire 7900 10-Slot Standalone Shelf is designed
Operation Instructions PowerCool Series TOP VIEW BOTTOM VIEW PDCOOL-05RA PDCOOL-00RK PDCOOL-5R PDCOOL-0R ALSO AVAILABLE Thank you for purchasing the PowerCool Series component cooler and power distribution.
CodeBug is a fun, engaging, entry level introduction to coding, physical computing and electronics. In just a few clicks you can program the versatile little CodeBug wearable computer to display your own
Options for ABB drives, converters and inverters User s manual FDPI-02 diagnostics and panel interface Table of contents Table of contents 3 1. FDPI-02 diagnostics and panel interface Safety..............................................
Cisco TelePresence MCU 4500 Series safety and compliance information On this page: Safety information symbols Operating guidelines Safety warnings Technical specifications Compliance information WEEE information
StorTrends 3400 Hardware Guide for Onsite Support MAN-3400-SS 11/21/2012 Copyright 1985-2012 American Megatrends, Inc. All rights reserved. American Megatrends, Inc. 5555 Oakbrook Parkway, Building 200
Gateway Port Replicator User Guide Using the Port Replicator Identifying features Connecting and disconnecting the port replicator 1 Using the Port Replicator Top Power button Component Icon Description
User Manual SmartGuard 600 Controllers Catalog Numbers 1752-L24BBB, 1752-L24BBBE Important User Information Read this document and the documents listed in the additional resources section about installation,
AC Power Supply For 5-Slot Housing and 9000 Series Access Carrier Installation Instructions Document Number 9000-A2-GN17-50 August 2000 Before You Begin Both the 5-slot housing and the 9000 Series Access
Rack Mount Kit Install Guide: Intel Entry Server Chassis SC5295-E UP/DP/WS/BRP Intel Entry Server Chassis SC5299-E DP/WS/BRP A Guide for Technically Qualified Assemblers of Intel Identified Subassemblies/Products
RHINO PSM Series Supplies Our versatile switching power supplies are DIN-rail mountable Features Industrial grade design Sturdy metal case to withstand harsh industrial environments Model PSM4-090S-N meets
SunFDDI 6.0 on the Sun Enterprise 10000 Server Sun Microsystems, Inc. 901 San Antonio Road Palo Alto, CA 94303-4900 USA 650 960-1300 Fax 650 969-9131 Part No.: 806-3610-11 November 1999, Revision A Send
Installation Instructions FLEX I/O Dual Port EtherNet/IP Adapter Modules Catalog Numbers 1794-AENTR, 1794-AENTRXT Series A Table of Contents Topic Page Important User Information 2 Environment and Enclosure
NT1 Type 400 NT1 Type 400 Standalone 1212016L1 NT1 Type 400 Circuit Pack 1212010 USER MANUAL 61212016L1-1B January 1999 This device complies with Part 15 of the FCC rules. Operation is subject to the following
767 Diagnostic System 3.5v 767 Wall Transformer Patent Pending Listed to: UL 60601-1 CSA C22.2 No. 601 Thank you for purchasing the Welch Allyn 3.5v 767 Wall Transformer. This manual is meant to provide
Nevco, Inc. Installation Manual Serial No. Model GLH-5 Size: Each module is 18 L x 19 ¾ H x 4 D (.46 x.50 x.10 meters) Approximate hanging weight: 11 lbs each (5 kg) Power requirements 120V,.4 Amps each
User Manual Safe Torque Off Option (Series B) for PowerFlex 40P and PowerFlex 70 Enhanced Control AC Drives Catalog Number 20A-DG01 Topic Page General Description 2 What Is the DriveGuard Safe Torque Off
FUSION R400 RAID USB 3.0 1U Rackmount 4-Drive Hardware RAID 5 SATA Storage System with USB 3.0 Interface User s Guide For Windows Contents 1 Fusion R400 RAID USB 3.0 Features 1 2 Drive Installation and
Technical Support Please refer to the Support Information card that shipped with your product. By registering your product at www.netgear.com/register, we can provide you with faster expert technical support
4x3.5" Hot-Swap Drive Cage Kit Installation Guide for Intel Server Chassis/System Order Number: G23758-002 G23758-002 This document provides instructions for installing the following accessory kit: FUP4X35HSDK
ADI 9510-B Advantium 2 Plus Alarm INSTALLATION AND OPERATING INSTRUCTIONS Carefully Read These Instructions Before Operating Carefully Read These Controls Corporation of America 1501 Harpers Road Virginia
33.6W Power over Ethernet Waterproof Adapter PoE Plus Single Port Injector for Outdoor Application Features Compliant with the IEEE802.3at Standard -40 to +60 C Temperature Range Diagnostic LEDs Full Protection
Intel RAID Maintenance Free Backup Unit 4 Quick Installation User's Guide Thank you for buying an Intel RAID Maintenance Free Backup Unit 4. The Intel RAID Maintenance Free Backup Unit 4 supports the Intel
Sun StorEdge RAID Manager 6.2.21 Release Notes formicrosoftwindowsnt Sun Microsystems, Inc. 901 San Antonio Road Palo Alto, CA 94303-4900 USA 650 960-1300 Fax 650 969-9131 Part No. 805-6890-11 November
Installation Instructions UIM-2T1 T1 Loop Bonding Uplink Interface Module CAUTION Net to Net Technologies strongly recommends the use of proper electrostatic discharge (ESD) precautions when handling this
MANUFACTURER DATA SHEET Analog I/O Module Manufacturer: Allen-Bradley/Rockwell Model Number: 1746-NI4 See www.geomartin.com for additional PDF datasheets Martin Part Number: E-014624-18 VendorPartNumber:
NOTES BODi rs BD004 Series Bandwidth-on-Demand Internet with Reliability and Survivability Quick Start Guide This is a Class A device and is not intended for use in a residential environment. Important
Telephone- and leased line modem for industrial applications TD-36 Modem for industrial PSTN- and leased line applications The TD-36 is an analogue V.34 PSTN modem as well as an industrial 2-wire leased
FortiFone QuickStart Guide for FON-670i and FON-675i FortiFone QuickStart Guide for FON-670i and FON-675i Revision 2 September 25, 2015 Copyright 2015 Fortinet, Inc. All rights reserved. Fortinet, FortiGate,
WorkHorse SERIES 1 FERRORESONANT BATTERY CHARGERS Installation and Operating Instructions Applied Energy Solutions, LLC. One Technology Place Caledonia, New York 14423 (585) 538-4421 www.appliedenergysol.com
GE Lighting Solutions Installation Guide Lumination TM LED Luminaires (BL42, BL44 and BL45 Series) Features Long life (50,000 hour rated life) 5 year warranty Dry location rated BEFORE YOU BEGIN Read these
First Data FD130 Terminal Quick Set-up Guide Thanks for choosing a First Data Terminal. First Data Terminals are some of the fastest, most secure point-of-sale terminals available. Installation is quick
DX4010V2 EN Installation Instructions RS-232/USB Serial Interface Module DX4010V2 Installation Instructions Trademarks Trademarks BlackBox is either a registered trademark or a trademark of BlackBox Corporation
Your consent to our cookies if you continue to use this website.