1 Installation Instructions USB-to-Data Highway Plus Cable Catalog Number 1784-U2DHP Topic Page Important User Information 2 Environment and Enclosure 3 Install the Cable 5 Configure the DH+ Node Address 11 Consider the Traffic Analyzer Software 11 About Using Multiple Cables 12 Status Indicators 13 Specifications 15 Additional Resources 18 About the Cable The 1784-U2DHP USB-to-Data Highway Plus Cable lets you connect a computer to a Data Highway Plus (DH+) network via an unused USB port on the computer. You can also use the cable to connect the computer to PLC-5 processors (except for Classic PLC-5 processors, such as PLC-5/10, PLC-5/12, PLC-5/15, and PLC-5/25) or SLC 5/04 processors. Communication on the DH+ link requires the RSLinx Classic software DF1 serial 1770-KF2/1785-KE drive.
2 2 USB-to-Data Highway Plus Cable Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical equipment. Safety Guidelines for the Application, Installation and Maintenance of Solid State Controls (Publication SGI-1.1 available from your local Rockwell Automation sales office or online at describes some important differences between solid-state equipment and hard-wired electromechanical devices. Because of this difference, and also because of the wide variety of uses for solid-state equipment, all persons responsible for applying this equipment must satisfy themselves that each intended application of this equipment is acceptable. In no event will Rockwell Automation, Inc. be responsible or liable for indirect or consequential damages resulting from the use or application of this equipment. The examples and diagrams in this manual are included solely for illustrative purposes. Because of the many variables and requirements associated with any particular installation, Rockwell Automation, Inc. cannot assume responsibility or liability for actual use based on the examples and diagrams. No patent liability is assumed by Rockwell Automation, Inc. with respect to use of information, circuits, equipment, or software described in this manual. Reproduction of the contents of this manual, in whole or in part, without written permission of Rockwell Automation, Inc., is prohibited. Throughout this manual, when necessary, we use notes to make you aware of safety considerations. WARNING: Identifies information about practices or circumstances that can cause an explosion in a hazardous environment, which may lead to personal injury or death, property damage, or economic loss. ATTENTION: Identifies information about practices or circumstances that can lead to personal injury or death, property damage, or economic loss. Attentions help you identify a hazard, avoid a hazard and recognize the consequences. SHOCK HAZARD: Labels may be on or inside the equipment, for example, drive or motor, to alert people that dangerous voltage may be present. IMPORTANT BURN HAZARD: Labels may be on or inside the equipment, for example, drive or motor, to alert people that surfaces may reach dangerous temperatures. Identifies information that is critical for successful application and understanding of the product.
3 USB-to-Data Highway Plus Cable 3 Environment and Enclosure ATTENTION: This equipment is intended for use in overvoltage Category II applications (as defined in IEC ), at altitudes up to 2000 m (6562 ft) without derating. This equipment is considered Group 1, Class A industrial equipment according to IEC/CISPR 11. Without appropriate precautions, there may be difficulties with electromagnetic compatibility in residential and other environments due to conducted and radiated disturbances. This equipment is supplied as enclosed equipment. It should not require additional system enclosure when used in locations consistent with the enclosure type ratings stated in the Specifications section of this publication. Subsequent sections of this publication may contain additional information regarding specific enclosure type ratings, beyond what this product provides, that are required to comply with certain product safety certifications. In addition to this publication, see: Industrial Automation Wiring and Grounding Guidelines, Rockwell Automation publication , for additional installation requirements. NEMA Standard 250 and IEC 60529, as applicable, for explanations of the degrees of protection provided by different types of enclosure. Preventing Electrostatic Discharge ATTENTION: This equipment is sensitive to electrostatic discharge, which can cause internal damage and affect normal operation. Follow these guidelines when you handle this equipment: Touch a grounded object to discharge potential static. Do not touch connectors or pins on component boards. Store the equipment in appropriate static-safe packaging when not in use.
4 4 USB-to-Data Highway Plus Cable At the end of its life, this equipment should be collected separately from any unsorted municipal waste. IMPORTANT The cable will not connect to Classic PLC-5 processors, such as PLC-5/10, PLC-5/12, PLC-5/15, and PLC-5/25, without an adapter. An adapter can be purchased separately from third-party companies. To comply with the CE Low Voltage Directive (LVD), this equipment must be powered from a source compliant with safety extra low voltage (SELV) or protected extra low voltage (PELV). The 1784-U2DHP cable replaces both the 1784-PCMK communication card and 1784-PCM6 cable (for computers without PCMCIA slots). 8-pin DIN Cable 2.44 m (8 ft) Status Indicators Communication Rate Switch USB Cable 0.61 m (2 ft)
5 USB-to-Data Highway Plus Cable 5 The cable operates at DH+ communication rates of 57.6 Kbps, Kbps, and Kbps. IMPORTANT The DH+ communication rate is read only when power is applied. To change the communication rate, you must disconnect the cable from the USB port, use the Communication Rate switch to change the communication rate setting, then reconnect the cable to the USB port. The 1784-U2DHP cable supports these DH+ network cable lengths. DH+ Communication Rate Max. DH+ Network Cable Length 57.6 Kbps 3048 m (10,000 ft) Kbps 1524 m (5000 ft) Kbps 762 m (2500 ft) Install the Cable Follow the procedures on the following pages to install the cable. Obtain the Device Driver for the Cable Follow these steps to download the device driver for the cable. IMPORTANT If RSLinx Classic software, version 2.53 or later, is installed on the computer, the device driver is already installed on the computer. Skip this section. 1. Visit 2. Click the 1784_u2dhp.inf file. 3. Save the file to a directory on the computer on which you want to install the cable.
6 6 USB-to-Data Highway Plus Cable Connect and Configure the Cable 1. Insert the end of the cable having the USB connector into an unused USB port on a computer. The Found New Hardware wizard appears. TIP If you do not see the Found New Hardware wizard, the drivers have already been installed. If RSLinx Classic software, version 2.53 or later, is installed on the computer, the device driver was installed at C:\Program Files\Rockwell Software\RSLINX\PnP_Drivers\1784-U2DHP. If you do not see the Found New Hardware wizard, proceed to step 9. Otherwise, continue with the next step. 2. Select No, not this time and click Next. 3. Select Install from a list or specific location and click Next. 4. Select Search for the best driver. 5. Check only the Include this location checkbox. 6. Browse to the location where you saved the 1784_u2dhp.inf file and click OK. 7. Click Next. 8. Click Finish. TIP If you see a Microsoft Windows error message that displays code 10, disconnect the cable from the USB port, then reconnect the cable to the USB port, so that the Windows operating system recognizes the device.
7 USB-to-Data Highway Plus Cable 7 9. Insert the other end of the cable having the 8-pin mini DIN connector to a device on your Data Highway Plus network. 8-pin DIN Connector USB Connector ATTENTION: The USB cable is not to exceed 3.0 m (9.84 ft). 10. Verify which computer COM port the cable is using. TIP The operating system of the computer you are using assigns a COM port to the cable. a. Right-click My Computer and choose Manage. b. Select Device Manager. c. Click the + to the left of Ports. d. Make note of the port (for example, COM3) for the 1784-U2DHP cable. Configure the RSLinx Classic Software Driver for the Cable Configure the cable driver for use with your DH+ networked device.
8 8 USB-to-Data Highway Plus Cable RSLinx Classic Software, Version 2.52 and Earlier Do these steps to configure the cable device driver by using RSLinx Classic software, version 2.52 and earlier. 1. Open RSLinx Classic software and then, from the Communication menu, choose Configure Drivers. 2. From the Available Driver Types pull-down menu, choose RS-232 DF1 Devices. 3. Click Add New. 4. Enter a name for the driver you just added and click OK. The Configure RS-232 DF1 Devices dialog box appears.
9 5. Enter configuration information in each field. USB-to-Data Highway Plus Cable 9 In this field Do this Comm Port Select the COM port you verified in step 10 on page 7. Device Station Number (node address) Error Checking Protocol Baud Rate Parity Stop Bits Select 1770-KF2/1785-KE/SCANport. Enter the DH+ Station Number for this cable. The default is 0. The 1784-U2DHP cable can use any DH+ network address from octal. The first packet sent from RSLinx Classic software to the 1784-U2DHP cable sets the DH+ network address the first time that RSLinx Classic software communicates through the 1784-U2DHP cable after power is applied. See Configure the DH+ Node Address on page 11. Select CRC. Select Full Duplex. Not used. Not used. Not used. 6. Click OK. RSLinx Classic Software, Version 2.53 and Later Do these steps to configure the cable device driver by using RSLinx Classic software, version 2.53 and later. 1. Open RSLinx Classic software and then,from the Communication menu, choose Configure Drivers. 2. From the Available Driver Types pull-down menu, choose 1784-U2DHP for DH+ devices. 3. Click Add New. 4. Enter a name for the driver you just added and then click OK.
10 10 USB-to-Data Highway Plus Cable The Configure 1784-U2DHP dialog box appears. 5. Enter configuration information in each field. In this field Do this Comm Port Select the COM port you verified in step 10 on page 7. Station Number (node address) Enter the DH+ Station Number for this cable. The default is 0. The 1784-U2DHP cable can use any DH+ network address from 0 77 octal. The first packet sent from RSLinx Classic software to the 1784-U2DHP cable sets the DH+ network address the first time that RSLinx Classic software communicates through the 1784-U2DHP cable after power is applied. See Configure the DH+ Node Address on page Click OK. IMPORTANT Do not disconnect the cable without first using RSLinx Classic software to stop the driver. Disconnecting the cable without stopping the driver can shut down or cause RSLinx Classic software to become unresponsive.
11 Configure the DH+ Node Address USB-to-Data Highway Plus Cable 11 The cable DH+ node address (station number) is automatically set the first time the cable sees traffic from RSLinx software to the DH+ network. To change the node address of the cable, you must do these steps. 1. In RSLinx Classic software, from the Communication menu, choose Configure Drivers. 2. Choose the driver and click Stop. 3. Click Configure. 4. Enter the new node address and click OK. 5. Cycle power to the cable by disconnecting the 1784-U2DHP cable USB connector from the USB port, then reconnecting it. 6. Verify the driver is still selected and click Start. 7. Initiate traffic from RSLinx Classic software to the DH+ network. a. From the Communication menu, choose RSWho. b. Choose the driver from the list. Consider the Traffic Analyzer Software The 1784-U2DHP cable is designed to work with Frontline s NetDecoder traffic analyzer software. For more information on Frontline s product, go to or
12 12 USB-to-Data Highway Plus Cable About Using Multiple Cables Once you have installed the device driver for a 1784-U2DHP cable, a unique COM port will be created and associated with that module (for example, COM9). If you connect a different 1784-U2DHP cable to the same computer, a new COM port will be created and associated with the new cable (for example, COM10). Each time you connect a new 1784-U2DHP cable to the computer, refer to step 10 on page 7 to determine the correct COM port for the additional cables. When you are using multiple 1784-U2DHP cables on the same computer, you must do one of these procedures. Change the RSLinx Classic software driver settings to specify the appropriate COM port for the connected cable. Configure multiple RSLinx Classic software drivers. Product Dimensions The following illustration shows the product dimensions. Enclosure Length: 7.62 cm (3 in.) Width: 5.08 cm (2 in.) Thickness: 2.54 cm (1 in.) 8-pin DIN Cable Length 2.44 m (8 ft) USB Cable Length 0.61 m (2 ft)
13 Status Indicators The following table describes the cable status indicators. USB-to-Data Highway Plus Cable 13 Power DH+ Network USB Cable Status Indicators Indicator State Description USB Solid green The cable is configured, but no network traffic is present. Blinking green Off Network traffic is present. Unable to transfer data. Disconnected from host. In one of the following states: Default Powered Address Suspend Power Solid green The cable is powered. Off No power to the cable.
14 14 USB-to-Data Highway Plus Cable Cable Status Indicators Indicator State Description DH+ Network Off Node address not present. Blinking green Solid green Blinking red Solid red Not connected to the DH+ network. Incorrect DH+ communication rate selected. Break or short in wiring. Communicating with the DH+ network. Duplicate node detected. Internal diagnostic test failed.
15 USB-to-Data Highway Plus Cable 15 Specifications Technical Specifications U2DHP Attribute Value Enclosure type rating Meets IP30 Power dissipation, max W max Supply voltage 5.00V DC 5.25V DC, max Supply current 125 ma Power consumption, max W Isolation voltage 30V (continuous), Basic Insulation Type DH+ to USB, Type tested at 500V AC for 60 s Wiring category 2 - on communication ports (1) (1) Use this Conductor Category information for planning conductor routing. Refer to Industrial Automation Wiring and Grounding Guidelines, publication
16 16 USB-to-Data Highway Plus Cable Environmental Specifications U2DHP Attribute Temperature, operating IEC (Test Ad, Operating Cold), IEC (Test Bd, Operating Dry Heat), IEC (Test Nb, Operating Thermal Shock) Temperature, nonoperating IEC (Test Ab, Unpackaged Nonoperating Cold), IEC (Test Bb, Unpackaged Nonoperating Dry Heat), IEC (Test Na, Unpackaged Nonoperating Thermal Shock) Relative humidity IEC (Test Db, Unpackaged Damp Heat) Shock, nonoperating IEC (Test Ed, Unpackaged Shock) Emissions CISPR 11 ESD immunity IEC Radiated RF immunity IEC Value 0 55 C ( F) C ( F) 5 95% noncondensing 1000 mm (3.28 ft) Group 1, Class A 8 kv air discharges 10V/m with 1 khz sine-wave 80% AM from MHz 10V/m with 200 Hz 50% Pulse 100% AM at 900 MHz 10V/m with 200 Hz 50% Pulse 100% AM at 1890 MHz 10V/m with 1 khz sine-wave 80% AM from MHz
17 Environmental Specifications U2DHP USB-to-Data Highway Plus Cable 17 Attribute EFT/B immunity IEC Surge transient immunity IEC Conducted RF immunity IEC Value ±2 kv at 5 khz on DH+ port ±2 kv line-earth (CM) on DH+ port 10V rms with 1 khz sine-wave 80% AM from 150 khz 80 MHz on DH+ port Certifications U2DHP Certification (1) c-ul-us CE C-Tick Value UL Listed Industrial Control Equipment, certified for US and Canada. See UL File E European Union 2004/108/EC EMC Directive, compliant with: EN 61326; Meas./Control/Lab., Industrial Requirements EN ; Industrial Immunity EN ; Industrial Emissions EN ; Programmable Controllers (Clause 8, Zone A & B) AS/NZS CISPR 11; Industrial Emissions (1) When marked. See the Product Certification link at for Declarations of Conformity, Certificates, and other certification details.
18 18 USB-to-Data Highway Plus Cable Additional Resources These documents contain additional information concerning related Rockwell Automation products. Resource Industrial Automation Wiring and Grounding Guidelines, publication Product Certifications website, Description Provides general guidelines for installing a Rockwell Automation industrial system. Provides declarations of conformity, certificates, and other certification details.
19 USB-to-Data Highway Plus Cable 19 Notes:
20 Rockwell Automation Support Rockwell Automation provides technical information on the Web to assist you in using its products. At you can find technical manuals, a knowledge base of FAQs, technical and application notes, sample code and links to software service packs, and a MySupport feature that you can customize to make the best use of these tools. For an additional level of technical phone support for installation, configuration, and troubleshooting, we offer TechConnect support programs. For more information, contact your local distributor or Rockwell Automation representative, or visit Installation Assistance If you experience a problem within the first 24 hours of installation, please review the information that's contained in this manual. You can also contact a special Customer Support number for initial help in getting your product up and running. United States or Canada Outside United States or Canada Use the Worldwide Locator at or contact your local Rockwell Automation representative. New Product Satisfaction Return Rockwell Automation tests all of its products to ensure that they are fully operational when shipped from the manufacturing facility. However, if your product is not functioning and needs to be returned, follow these procedures. United States Outside United States Contact your distributor. You must provide a Customer Support case number (call the phone number above to obtain one) to your distributor to complete the return process. Please contact your local Rockwell Automation representative for the return procedure. Documentation Feedback Your comments will help us serve your documentation needs better. If you have any suggestions on how to improve this document, complete this form, publication RA-DU002, available at Allen-Bradley, Rockwell Software, Rockwell Automation, Data Highway Plus, RSLinx Classic, PLC-5, SLC, and TechConnect are trademarks of Rockwell Automation, Inc. Trademarks not belonging to Rockwell Automation are property of their respective companies. Rockwell Otomasyon Ticaret A.Ş., Kar Plaza İş Merkezi E Blok Kat: İçerenköy, İstanbul, Tel: +90 (216) Publication 1784-IN045C-EN-P - May 2010 PN Supersedes Publication 1784-IN045B-EN-P - March 2009 Copyright 2010 Rockwell Automation, Inc. All rights reserved. Printed in the U.S.A.
Installation Instructions Universal Serial Bus (USB) to DH-485 Interface Converter Catalog Number 1747-UIC Contents Overview..................................................3 Computer and Operating System
User Manual MicroLogix 1100 Embedded Web Server Bulletin 1763 Controllers Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical equipment.
Troubleshooting Guide Diagnostic Utility for Rockwell Automation Industrial Computers Topics Page Where to Find the Utility 3 When to Run the Utility 3 Interpret Results 3 Prepare to Boot from the Industrial
Installation Instructions Compact I/O End Caps/Terminators Catalog Numbers 1769-ECL, 1769-ECR Topic Page Important User Information 2 Environment and Enclosure 3 North American Hazardous Location Approval
Installation Instructions Hard Disk Drive (HDD) Catalog Number 6189V-35HDDST80, 6189V-35HDDST160 Topic Page About This Publication 1 Important User Information 2 Electrostatic Discharge (ESD) Precautions
Micro800 Programmable Controllers Bulletin 2080 Selection Guide Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety
Stratix 5700 Network Address Translation Quick Start Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety Guidelines
Technical Data 1756 ControlLogix Power Supplies Specifications Standard Power Supplies Catalog Numbers 1756-PA72, 1756-PA75, 1756-PB72, 1756-PB75, 1756-PC75, 1756-PH75 Standard Slim Power Supplies Catalog
Quick Start Stratix 5700 Switch Configuration Important User Information Read this document and the documents listed in the additional resources section about installation, configuration, and operation
User Manual DeviceNet Network Configuration Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical equipment. Safety Guidelines for the
Technical Data WinPFT File Transfer Utility (Catalog No. 2711-ND7) Overview WINPFT is a stand-alone Windows utility which lets you transfer applications developed for standard PanelView terminals or Dataliner
Installation Instructions 1738 ArmorPOINT I/O Dual Port EtherNet/IP Adapter Catalog number 1738-AENTR, Series B Table of Contents Topic Page Important User Information 2 Environment and Enclosure 3 Preventing
s 8 185 8185P01 TX-I/O ; DESIGO OPEN TX OPEN RS/485 module for integrating third-party systems and devices to DESIGO (V4 or higher) TXI1.OPEN Platform to integrate third-party systems and devices to the
DVPPF02-H2 PROFIBUS DP Slave Communication Module Application Manual Warning Please read this instruction carefully before use and follow this instruction to operate the device in order to prevent damages
8 172 TX-I/O Digital input modules TXM1.8D TXM1.16D Two fully compatible versions: TXM1.8D: 8 inputs, each with a three-color LED (green, yellow or red) TXM1.16D: As TXM1.8X, but 16 inputs, each with a
Foxboro Evo Process Automation System Product Specifications PSS 31H-2Z32 FBM232 Field Device System Integrator Module, 10/100 Mbps Ethernet, Single The FBM232 Field Device System Integrator (FDSI) module
Logix5000 Controllers Ladder Diagram Programming: Relay Ladder Programming Manual Important User Information Solid state equipment has operational characteristics differing from those of electromechanical
Reference Manual Rockwell Automation Library of Process Objects: Pressure/Temperature Compensated Flow (P_PTComp) Version 3.1 Important User Information Read this document and the documents listed in the
Telephone- and leased line modem for industrial applications TD-36 Modem for industrial PSTN- and leased line applications The TD-36 is an analogue V.34 PSTN modem as well as an industrial 2-wire leased
Quick Guide Fiber Optic Cable Installation Introduction Fiber optic cables can be easily damaged if they are improperly handled or installed. It is imperative that certain procedures be followed in the
Release Notes DeviceNet Communication Card Catalog Number 1784-PCD Use These Release Notes These release notes contain information about the 1784-PCD card (Series A, B, and C) and version 4.03 of the driver.
Extract from the online catalog STEP-PS/1AC/12DC/1.5 Order No.: 2868567 DIN rail power supply unit 12 V DC/1.5 A, primary switched-mode, 1- phase Commercial data EAN 4046356292924 Pack 1 pcs. Customs tariff
Square D Clipsal DIN-Rail Four-Channel Auxiliary Input Unit SLCLE5504AUX for Use with Wired C-Bus Networks Instruction Bulletin Retain for future use. Square D Clipsal DIN-Rail Four-Channel Auxiliary Input
ADACSNET USB Control Module Installation Guide Termination Switch 2-Pin SensorNet Connection Features and Hookup The USB Control Module contains the following: - USB port: Connects to the host computer.
Orbit PCI Mk 2 Network Card User Manual Part No. 502566 Issue 4 Information in this document is subject to change without notice. Companies, names and data used in examples herein are fictitious unless
Micro800 Programmable Controller Family Bulletin 2080 Selection Guide Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment.
Application Technique Safety Function: Door Monitoring Products: Trojan 5 Switch, GuardLogix Controller Safety Rating: CAT. 3, PLd to ISO 13849-1: 2008 Topic Page Important User Information 2 General Safety
Migration Guide Legacy PanelView to PanelView Plus 6 Catalog Number Conversions Topic Page About This Publication 1 Platform Replacements 2 HMI Software 4 Catalog Number Conversion Tables 4 PanelView Standard
Backup Scanner Module Catalog Number 1747-BSN Installation Instructions 2 Backup Scanner Module Important User Information Because of the variety of uses for the products described in this publication,
Overview/Modes of Operation Bulletin 150 Smart Motor Controller The SMC-3 is a compact, simple to use, solid-state motor controller designed to operate 3-phase motors. It features a built-in overload relay
Installation Instructions RSLogix Guard PLUS! Programming Software Catalog Numbers 1753-PCS-PAR and 1753-PCS-USB Before You Begin 1. Make sure your personal computer meets the system requirements below.
FactoryTalk ViewPoint Quick Start Guide Publication FTVP-QS002F-EN-E - September 2015 Supersedes Publication FTVP-QS002E-EN-E Important user information Read this document and the documents listed in the
Product datasheet Characteristics TM7BDM8B expansion block - TM7 - IP67-8 DI/DO - 24V DC - 0.5 A - M8 connector Main Range of product Product or component type Range compatibility Enclosure material Bus
Installation Guide FactoryTalk Batch Material Manager Installation Guide Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical equipment.
Application Technique Safety Function: Magnetic Door Switch Monitoring Products: MC1 Magnetically-coded Door Switch, Guardmaster Dual-input Safety Relay Safety Rating: CAT. 3, PLd to EN ISO 13849-1: 2008
Characteristics Single-function OFF-delay timer for DC contactors, without auxiliary voltage Width.5 mm CDC 5 6 F3 Approvals A culus E CCC CT-VBS a Circuit diagram b Marker label Marks a CE b C-Tick Order
Ethernet Transceiver Communicate With SEL Devices Using Ethernet Networks The Ethernet Transceiver is an EIA-232 serial-to-10base-t converter. The is powered by 5 Vdc provided on Pin 1 of the serial communications
Wireless Router Setup Manual NETGEAR, Inc. 4500 Great America Parkway Santa Clara, CA 95054 USA 208-10082-02 2006-04 2006 by NETGEAR, Inc. All rights reserved. Trademarks NETGEAR is a trademark of Netgear,
Moxa PoE Injector INJ-24 Series Hardware Installation Guide Second Edition, March 2011 2011 Moxa Inc. All rights reserved. P/N: 1802000240011 Overview The Moxa PoE Injector INJ-24 Series is a 1-port PoE
Allen-Bradley PanelView 1200/1400e Transfer Utility User Manual (Cat. No. 2711E ND7) Important User Information Because of the variety of uses for the products described in this publication, those responsible
Highlights & Features Protection Class II, Double Isolation (No Earth connection is required) Universal AC input voltage without power de-rating Efficiency > 87.0% @ 115Vac & 230Vac NEC Class 2 / Limited
AC 800M EtherNet/IP DeviceNet Linking Device LD 800DN SP1134 Power and productivity for a better world TM AC 800M EtherNet/IP DeviceNet Linking Device LD 800DN NOTICE This document contains information
PanelView e Transfer Utility (Cat. No. 2711E-ND7) User Manual Important User Information Because of the variety of uses for the products described in this publication, those responsible for the application
2CDC 251 098 F0t06 a Rotary switch for the preselection of the time range of the ON time b Potentiometer with direct reading scale for the fine adjustment of the ON time c Rotary switch for the preselection
APS-Arduino Shield Evaluation Board for the APS Stepper Motor Power Stage ID 10016767 Manual 2120-A002 EN phytron APS-Arduino Shield Evaluation Board for the APS Stepper Motor Power Stage TRANSLATION OF
Installation Instructions FLEX I/O AC Digital Input Modules Catalog numbers 1794-IA8, 1794-IA8I, 1794-IA16 Table of Contents Topic Page Important User Information 2 Environment and Enclosure 3 Preventing
Technical Data SMC -3 Specifications Bulletin Number 150 Topic Page Product Overview 2 Standards Compliance and Certifications 2 Features 3 Catalog Number Explanation 4 Wiring Diagrams 6 General Specifications
Rack mounted telephone- and leased line modem for industrial applications TR-6 Rack modem for industrial PSTNand /-wire leased line applications The TR-6 is an analogue V. 9 -rack PSTN modem as well as
C13 C13 Document ID: 2CMC486004M0201 2013-06-19 Disclaimer Copyrights Trademarks Contact The information in this document is subject to change without notice and should not be construed as a commitment
User Manual ControlLogix Remote I/O Communication Module Catalog Number 1756-RIO Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical
2-Port RS232/422/485 Combo Serial to USB2.0 Adapter (w/ Metal Case and Screw Lock Mechanism) Installation Guide 1. Introduction Thank you for purchasing this 2-Port RS232/422/485 Combo Serial to USB Adapter.
i800 AC Current Clamp Instruction Sheet Introduction The i800 AC Current Clamp, the Clamp, has been designed for use with multimeters, recorders, power analyzers, safety testers, etc., for accurate non-intrusive
LONWORKS Fiber Optic Converter LRW-102 and LRW-102/PP LONWORKS to fibre optic link, multidrop and redundant ring applications The LRW-102 is a fibre optic modem designed for multidrop and redundant ring
MACTek Corporation USB HART Interface DM01003100AA February, 2003 LIMITED WARRANTY VIATOR Interface for HART MACTek Corporation warrants this Interface and all of its component against defects in materials
Programming Manual Logix5000 Controllers Import/Export Project Components Catalog Numbers 1768-L43, 1768-L45 Important user information Read this document and the documents listed in the additional resources
Preface Contents SIMATIC NET CP 243-2 AS-Interface Master Manual Technical Description and Installation Instructions Interface to the User Program 2 in the S7-200 CPU Access to the Data of the AS-i Slaves
Data sheet Electronic timer CT-AHD.12 OFF-delayed with 1 c/o (SPDT) contact The CT-AHD.12 is an electronic time relay with OFF-delay. It is from the CT-D range. With their MDRC profile and a width of only
Perle Protocol Transparent Media Converter Modules Installation Guide C-4GPT-DSFP CM-4GPT-DSFP Part# 5500335-10 Overview This document contains instructions necessary for the installation and operation
Highlights & Features Protection Class II, Double Isolation (No Earth connection is required) Universal AC input voltage and full power up to 55 C Power will not de-rate for the entire input voltage range
Relés e Contatores de Estado Sólido SIRIUS Coletânea de dados técnicos ( product data sheet ) Agosto/212 SSR - 3RF21 22,5 mm Ponto Zero SSR - 3RF2 45 mm Ponto Zero SSR - 3RF22 45 mm Ponto Zero Trifásico
PowerFlex 1203-USB Converter Firmware Revision 1.xxx User Manual Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety
MicroLogix 1400 Embedded Web Server Bulletin 1766 Controllers User Manual Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment.
Your consent to our cookies if you continue to use this website.