# SIZING OF WATER PIPING SYSTEM

Save this PDF as:

Size: px
Start display at page:

## Transcription

1 SIZING OF WATER PIPING SYSTEM SECTION E101 GENERAL E101.1 Scope. E This appendix outlines two procedures for sizing a water piping system (see Sections E103.3 and E201.1). The design procedures are based on the minimum static pressure available from the supply source, the head charges in the system caused by friction and elevation, and the rates of flow necessary for operation of various fixtures. E Because of the variable conditions encountered in hydraulic design, it is impractical to specify definite and detailed rules for sizing of the water piping system. Accordingly, other sizing or design methods conforming to good engineering practice standards are acceptable alternatives to those presented herein. SECTION E102 INFORMATION REQUIRED E102.1 Preliminary. Obtain the necessary information regarding the minimum daily static service pressure in the area where the building is to be located. If the building supply is to be metered, obtain information regarding friction loss relative to the rate of flow for meters in the range of sizes likely to be used. Friction loss data can be obtained from most manufacturers of water meters. E102.2 Demand load. E Estimate the supply demand of the building main and the principal branches and risers of the system by totaling the corresponding demand from the applicable part of Table E103.3(3). E Estimate continuous supply demands in gallons per minute (L/m) for lawn sprinklers, air conditioners, etc., and add the sum to the total demand for fixtures. The result is the estimated supply demand for the building supply. SECTION E103 SELECTION OF PIPE SIZE E103.1 General. Decide from Table what is the desirable minimum residual pressure that should be maintained at the highest fixture in the supply system. If the highest group of fixtures contains flush valves, the pressure for the group should not be less than 15 pounds per square inch (psi) (103.4 kpa) flowing. For flush tank supplies, the available pressure should not be less than 8 psi (55.2 kpa) flowing, except blowout action fixtures must not be less than 25 psi (172.4 kpa) flowing. E103.2 Pipe sizing. E Pipe sizes can be selected according to the following procedure or by other design methods conforming to acceptable engineering practice and approved by the administrative authority. The sizes selected must not be less than the minimum required by this code. E Water pipe sizing procedures are based on a system of pressure requirements and losses, the sum of which must not exceed the minimum pressure available at the supply source. These pressures are as follows: 1. Pressure required at fixture to produce required flow. See Sections and Static pressure loss or gain (due to head) is computed at psi per foot (9.8 kpa/m) of elevation change. Example: Assume that the highest fixture supply outlet is 20 feet (6096 mm) above or below the supply source. This produces a static pressure differential of 20 feet by psi/foot (2096 mm by 9.8 kpa/m) and an 8.66 psi (59.8 kpa) loss. 3. Loss through water meter. The friction or pressure loss can be obtained from meter manufacturers. 4. Loss through taps in water main. 5. Losses through special devices such as filters, softeners, backflow prevention devices and pressure regulators. These values must be obtained from the manufacturers. 6. Loss through valves and fittings. Losses for these items are calculated by converting to equivalent length of piping and adding to the total pipe length. 7. Loss due to pipe friction can be calculated when the pipe size, the pipe length and the flow through the pipe are known. With these three items, the friction loss can be determined. For piping flow charts not included, use manufacturers tables and velocity recommendations. Note: For the purposes of all examples, the following metric conversions are applicable: 1 cubic foot per minute = L/s 1 square foot = m 2 1 degree = rad 1 pound per square inch = kpa 1 inch = 25.4 mm 1 foot = mm 1 gallon per minute = L/m E103.3 Segmented loss method. The size of water service mains, branch mains and risers by the segmented loss method, must be determined according to water supply demand [gpm (L/m)], available water pressure [psi (kpa)] and friction loss caused by the water meter and developed length of pipe [feet (m)], including equivalent length of fittings. This design procedure is based on the following parameters: Calculates the friction loss through each length of the pipe INTERNATIONAL PLUMBING CODE 117

3 water supply system operation are lack of adequate pressure and noise. Problem: What size Type L copper water pipe, service and distribution will be required to serve a two-story factory building having on each floor, back-to-back, two toilet rooms each equipped with hot and cold water? The highest fixture is 21 feet (6401 mm) above the street main, which is tapped with a 2-inch (51 mm) corporation cock at which point the minimum pressure is 55 psi (379.2 kpa). In the building basement, a 2-inch (51 mm) meter with a maximum pressure drop of 11 psi (75.8 kpa) and 3-inch (76 mm) reduced pressure principle backflow preventer with a maximum pressure drop of 9 psi (621 kpa) are to be installed. The system is shown by Figure E103.3(1). To be determined are the pipe sizes for the service main and the cold and hot water distribution pipes. Solution: A tabular arrangement such as shown in Table E103.3(1) should first be constructed. The steps to be followed are indicated by the tabular arrangement itself as they are in sequence, columns 1 through 10 and lines A through L. Step 1 Columns 1 and 2: Divide the system into sections breaking at major changes in elevation or where branches lead to fixture groups. After point B [see Figure E103.3(1)], separate consideration will be given to the hot and cold water piping. Enter the sections to be considered in the service and cold water piping in Column 1 of the tabular arrangement. Column 1 of Table E103.3(1) provides a line-by-line recommended tabular arrangement for use in solving pipe sizing. The objective in designing the water supply system is to ensure an adequate water supply and pressure to all fixtures and equipment. Column 2 provides the pounds per square inch (psi) to be considered separately from the minimum pressure available at the main. Losses to take into consideration are the following: the differences in elevations between the water supply source and the highest water supply outlet, meter pressure losses, the tap in main loss, special fixture devices such as water softeners and backflow prevention devices and the pressure required at the most remote fixture outlet. The difference in elevation can result in an increase or decrease in available pressure at the main. Where the water supply outlet is located above the source, this results in a loss in the available pressure and is subtracted from the pressure at the water source. Where the highest water supply outlet is located below the water supply source, there will be an increase in pressure that is added to the available pressure of the water source. Column 3: According to Table E103.3(3), determine the gpm (L/m) of flow to be expected in each section of the system. These flows range from 28.6 to 108 gpm. Load values for fixtures must be determined as water supply fixture units and then converted to a gallon-per-minute (gpm) rating to determine peak demand. When calculating peak demands, the water supply fixture units are added and then converted to the gallon-per-minute rating. For continuous flow fixtures such as hose bibbs and lawn sprinkler systems, add the gallon-per-minute demand to the intermittent demand of fixtures. For example, a total of 120 water supply fixture units is converted to a demand of 48 gallons per minute. Two hose bibbs 5 gpm demand = 10 gpm. Total gpm rating = 48.0 gpm + 10 gpm = 58.0 gpm demand. Step 2 Line A: Enter the minimum pressure available at the main source of supply in Column 2. This is 55 psi (379.2 kpa). The local water authorities generally keep records of pressures at different times of day and year. The available pressure can also be checked from nearby buildings or from fire department hydrant checks. Line B: Determine from Table the highest pressure required for the fixtures on the system, which is 15 psi (103.4 kpa), to operate a flushometer valve. The most remote fixture outlet is necessary to compute the pressure loss caused by pipe and fittings, and represents the most downstream fixture along the circuit of piping requiring the available pressure to operate properly as indicated by Table Line C: Determine the pressure loss for the meter size given or assumed. The total water flow from the main through the service as determined in Step 1 will serve to aid in the meter selected. There are three common types of water meters; the pressure losses are determined by the American Water Works Association Standards for displacement type, compound type and turbine type. The maximum pressure loss of such devices takes into consideration the meter size, safe operating capacity (gpm) and maximum rates for continuous operations (gpm). Typically, equipment imparts greater pressure losses than piping. Line D: Select from Table E103.3(4) and enter the pressure loss for the tap size given or assumed. The loss of pressure through taps and tees in pounds per square inch (psi) are based on the total gallon-per-minute flow rate and size of the tap. Line E: Determine the difference in elevation between the main and source of supply and the highest fixture on the system. Multiply this figure, expressed in feet, by 0.43 psi (2.9 kpa). Enter the resulting psi loss on Line E. The difference in elevation between the water supply source and the highest water supply outlet has a significant impact on the sizing of the water supply system. The difference in elevation usually results in a loss in the available pressure because the water supply outlet is generally located above the water supply source. The loss is caused by the pressure required to lift the water to the outlet. The pressure loss is subtracted from the pressure at the water source. Where the highest water supply outlet is located below the water source, there will be an increase in pressure which is added to the available pressure of the water source. Lines F, G and H: The pressure losses through filters, backflow prevention devices or other special fixtures must be obtained from the manufacturer or estimated and entered on these lines. Equipment such as backflow prevention devices, check valves, water softeners, instantaneous or tankless water heaters, filters and strainers can impart a much greater pressure loss than the piping. The pressure losses can range from 8 psi to 30 psi INTERNATIONAL PLUMBING CODE 119

5 TABLE E.1 COLD WATER PIPE SECTION FITTINGS/VALVES PRESSURE LOSS EXPRESSED AS EQUIVALENT LENGTH OF TUBE (feet) HOT WATER PIPE SECTION FITTINGS/VALVES PRESSURE LOSS EXPRESSED AS EQUIVALENT OF TUBE (feet) A-B B-C / 2 Gate valves 3 A-B / 2 Gate valves / 2 Side branch tee / 2 Side branch tee / 2 Straight run tee 0.5 B-C 1-2 Straight run tee degree ell 0.5 C-F / 2 Side branch tee 12 C-F / 2 Side branch tee 7 C-D / 2 90-degree ell 7 C-D 1-1 / 2 90-degree ell 4 D-E / 2 Side branch tee 12 D-E / 2 Side branch tee 7 Step 9 Column 8: Select from Figure E103.3(3) the friction loss per 100 feet ( mm) of pipe for the gallon-per-minute flow in a section (Column 3) and trial pipe size (Column 5). Maximum friction head loss per 100 feet is determined on the basis of total pressure available for friction head loss and the longest equivalent length of run. The selection is based on the gallon-per-minute demand, the uniform friction head loss, and the maximum design velocity. Where the size indicated by hydraulic table indicates a velocity in excess of the selected velocity, a size must be selected which produces the required velocity. Step 10 Column 9: Multiply the figures in Columns 7 and 8 for each section and enter in Column 9. Total friction loss is determined by multiplying the friction loss per 100 feet ( mm) for each pipe section in the total developed length by the pressure loss in fittings expressed as equivalent length in feet. Note: Section C-F should be considered in the total pipe friction losses only if greater loss occurs in Section C-F than in pipe section D-E. Section C-F is not considered in the total developed length. Total friction loss in equivalent length is determined in Table E.2. Step 11 Line K: Enter the sum of the values in Column 9. The value is the total friction loss in equivalent length for each designated pipe section. Step 12 Line L: Subtract Line J from Line K and enter in Column 10. The result should always be a positive or plus figure. If it is not, repeat the operation using Columns 5, 6, 8 and 9 until a balance or near balance is obtained. If the difference between Lines J and K is a high positive number, it is an indication that the pipe sizes are too large and should be reduced, thus saving materials. In such a case, the operations using Columns 5, 6, 8 and 9 should again be repeated. The total friction losses are determined and subtracted from the pressure available to overcome pipe friction for trial pipe size. This number is critical as it provides a guide to whether the pipe size selected is too large and the process should be repeated to obtain an economically designed system. Answer: The final figures entered in Column 5 become the design pipe size for the respective sections. Repeating this operation a second time using the same sketch but considering the demand for hot water, it is possible to size the hot water distribution piping. This has been worked up as a part of the overall problem in the tabular arrangement used for sizing the service and water distribution piping. Note that consideration must be given to the pressure losses from the street main to the water heater (Section A-B) in determining the hot water pipe sizes. PIPE SECTIONS TABLE E.2 Cold Water FRICTION LOSS EQUIVALENT LENGTH (feet) Hot Water A-B = = 2.21 B-C = = 0.22 C-D = = 0.54 D-E = = 5.02 Total pipe friction losses (Line K) INTERNATIONAL PLUMBING CODE 121

6 For SI: 1 foot = mm, 1 gpm = L/m. FIGURE E103.3(1) EXAMPLE-SIZING INTERNATIONAL PLUMBING CODE

7 TABLE E103.3(1) RECOMMENDED TABULAR ARRANGEMENT FOR USE IN SOLVING PIPE SIZING PROBLEMS COLUMN Line Description Lb per square inch (psi) Gal. per min through section Length of section (feet) Trial pipe size (inches) Equivalent length of fittings and valves (feet) Total equivalent length col. 4 and col. 6 (100 feet) Friction loss per 100 feet of trial size pipe (psi) Friction loss in equivalent length col. 8 x col. 7 (psi) Excess pressure over friction losses (psi) A B C D E F G H I J Service and cold water distribution piping a Minimum pressure available at main Highest pressure required at a fixture (Table 604.3) Meter loss 2 meter Tap in main loss 2 tap (Table E103A) Static head loss psi Special fixture loss backflow preventer Special fixture lossfilter Special fixture lossother Total overall losses and requirements (Sum of Lines B through H) Pressure available to overcome pipe friction (Line A minus Lines B to H) DESIGNATION Pipe section (from diagram) Cold water Distribution piping FU AB BC CD CF b DE b / / / / / K L Total pipe friction losses (cold) Difference (Line J minus Line K) Pipe section (from diagram) Diagram Hot water Distribution Piping A B B C C D C F b D E b / / / / K L Total pipe friction losses (hot) Difference (Line J minus Line K) For SI: 1 inch = 25.4 mm, 1 foot = mm, 1 psi = kpa, 1 gpm = L/m. a. To be considered as pressure gain for fixtures below main (to consider separately, omit from I and add to J ). b. To consider separately, in K use C-F only if greater loss than above INTERNATIONAL PLUMBING CODE 123

8 TABLE E103.3(2) LOAD VALUES ASSIGNED TO FIXTURES a FIXTURE OCCUPANCY TYPE OF SUPPLY CONTROL LOAD VALUES, IN WATER SUPPLY FIXTURE UNITS (wsfu) Cold Hot Total Bathroom group Private Flush tank Bathroom group Private Flush valve Bathtub Private Faucet Bathtub Public Faucet Bidet Private Faucet Combination fixture Private Faucet Dishwashing machine Private Automatic Drinking fountain Offices, etc. 3 / 8 valve Kitchen sink Private Faucet Kitchen sink Hotel, restaurant Faucet Laundry trays (1 to 3) Private Faucet Lavatory Private Faucet Lavatory Public Faucet Service sink Offices, etc. Faucet Shower head Public Mixing valve Shower head Private Mixing valve Urinal Public 1 flush valve Urinal Public 3 / 4 flush valve Urinal Public Flush tank Washing machine (8 lb) Private Automatic Washing machine (8 lb) Public Automatic Washing machine (15 lb) Public Automatic Water closet Private Flush valve Water closet Private Flush tank Water closet Public Flush valve Water closet Public Flush tank Water closet Public or private Flushometer tank For SI: 1 inch = 25.4 mm, 1 pound = kg. a. For fixtures not listed, loads should be assumed by comparing the fixture to one listed using water in similar quantities and at similar rates. The assigned loads for fixtures with both hot and cold water supplies are given for separate hot and cold water loads and for total load. The separate hot and cold water loads being three-fourths of the total load for the fixture in each case INTERNATIONAL PLUMBING CODE

9 TABLE E103.3(3) TABLE FOR ESTIMATING DEMAND SUPPLY SYSTEMS PREDOMINANTLY FOR FLUSH TANKS SUPPLY SYSTEMS PREDOMINANTLY FOR FLUSH VALVES Load Demand Load Demand (Water supply fixture units) (Gallons per minute) (Cubic feet per minute) (Water supply fixture units) (Gallons per minute) (Cubic feet per minute) (continued) 2006 INTERNATIONAL PLUMBING CODE 125

10 TABLE E103.3(3)continued TABLE FOR ESTIMATING DEMAND SUPPLY SYSTEMS PREDOMINANTLY FOR FLUSH TANKS SUPPLY SYSTEMS PREDOMINANTLY FOR FLUSH VALVES Load Demand Load Demand (Water supply fixture units) (Gallons per minute) (Cubic feet per minute) (Water supply fixture units) (Gallons per minute) (Cubic feet per minute) , , , , , , , , , , , , , , , , , , For SI: TABLE E103.3(4) LOSS OF PRESSURE THROUGH TAPS AND TEES IN POUNDS PER SQUARE INCH (psi) SIZE OF TAP OR TEE (inches) GALLONS PER MINUTE 5 / 8 3 / / / inch = 25.4 mm, 1 pound per square inch = kpa, 1 gallon per minute = L/m INTERNATIONAL PLUMBING CODE

11 TABLE E103.3(5) ALLOWANCE IN EQUIVALENT LENGTHS OF PIPE FOR FRICTION LOSS IN VALVES AND THREADED FITTINGS (feet) PIPE SIZE (inches) FITTING OR VALVE 1 / 2 3 / / / / degree elbow degree elbow Tee, run Tee, branch Gate valve Balancing valve Plug-type cock Check valve, swing Globe valve Angle valve For SI: 1 inch = 25.4 mm, 1 foot = mm, 1 degree = rad. TABLE E103.3(6) PRESSURE LOSS IN FITTINGS AND VALVES EXPRESSED AS EQUIVALENT LENGTH OF TUBE a (feet) FITTINGS VALVES NOMINAL OR STANDARD SIZE (inches) Standard EII 90-Degree Tee 90 Degree 45 Degree Side Branch Straight Run Coupling Ball Gate Butterfly Check 3 / / / / / / / / For SI: 1 inch = 25.4 mm, 1 foot = mm, 1 degree = rad. a. Allowances are for streamlined soldered fittings and recessed threaded fittings. For threaded fittings, double the allowances shown in the table. The equivalent lengths presented above are based on a C factor of 150 in the Hazen-Williams friction loss formula. The lengths shown are rounded to the nearest half-foot INTERNATIONAL PLUMBING CODE 127

12 FIGURE E103.3(2) FRICTION LOSS IN SMOOTH PIPE a (TYPE K, ASTM B 88 COPPER TUBING) For SI: 1 inch = 25.4 mm, 1 foot = mm, 1 gpm = L/m, 1 psi = kpa, 1 foot per second = m/s. a. This chart applies to smooth new copper tubing with recessed (streamline) soldered joints and to the actual sizes of types indicated on the diagram INTERNATIONAL PLUMBING CODE

13 FIGURE E103.3(3) FRICTION LOSS IN SMOOTH PIPE a (TYPE L, ASTM B 88 COPPER TUBING) For SI: 1 inch = 25.4 mm, 1 foot = mm, 1 gpm = L/m, 1 psi = kpa, 1 foot per second = m/s. a. This chart applies to smooth new copper tubing with recessed (streamline) soldered joints and to the actual sizes of types indicated on the diagram INTERNATIONAL PLUMBING CODE 129

14 FIGURE E103.3(4) FRICTION LOSS IN SMOOTH PIPE a (TYPE M, ASTM B 88 COPPER TUBING) For SI: 1 inch = 25.4 mm, 1 foot = mm, 1 gpm = L/m, 1 psi = kpa, 1 foot per second = m/s. a. This chart applies to smooth new copper tubing with recessed (streamline) soldered joints and to the actual sizes of types indicated on the diagram INTERNATIONAL PLUMBING CODE

15 FIGURE E103.3(5) FRICTION LOSS IN FAIRLY SMOOTH PIPE a For SI: 1 inch = 25.4 mm, 1 foot = mm, 1 gpm = L/m, 1 psi = kpa, 1 foot per second = m/s. a. This chart applies to smooth new steel (fairly smooth) pipe and to actual diameters of standard-weight pipe INTERNATIONAL PLUMBING CODE 131

16 FIGURE E103.3(6) FRICTION LOSS IN FAIRLY ROUGH PIPE a For SI: 1 inch = 25.4 mm, 1 foot = mm, 1 gpm = L/m, 1 psi = kpa, 1 foot per second = m/s. a. This chart applies to fairly rough pipe and to actual diameters which in general will be less than the actual diameters of the new pipe of the same kind INTERNATIONAL PLUMBING CODE

17 FIGURE E103.3(7) FRICTION LOSS IN FAIRLY ROUGH PIPE a For SI: 1 inch = 25.4 mm, 1 foot = mm, 1 gpm = L/m, 1 psi = kpa, 1 foot per second = m/s. a. This chart applies to very rough pipe and existing pipe and to their actual diameters INTERNATIONAL PLUMBING CODE 133

18 SECTION E201 SELECTION OF PIPE SIZE E Size of water-service mains, branch mains and risers. The minimum size water service pipe shall be 3 / 4 inch (19.1 mm). The size of water service mains, branch mains and risers shall be determined according to water supply demand [gpm (L/m)], available water pressure [psi (kpa)] and friction loss due to the water meter and developed length of pipe [feet (m)], including equivalent length of fittings. The size of each water distribution system shall be determined according to the procedure outlined in this section or by other design methods conforming to acceptable engineering practice and approved by the code official: 1. Supply load in the building water-distribution system shall be determined by total load on the pipe being sized, in terms of water-supply fixture units (w.s.f.u.), as shown in Table E103.3(2). For fixtures not listed, choose a w.s.f.u. value of a fixture with similar flow characteristics. 2. Obtain the minimum daily static service pressure [psi (kpa)] available (as determined by the local water authority) at the water meter or other source of supply at the installation location. Adjust this minimum daily static pressure [psi (kpa)] for the following conditions: 2.1. Determine the difference in elevation between the source of supply and the highest water supply outlet. Where the highest water supply outlet is located above the source of supply, deduct 0.5 psi (3.4 kpa) for each foot (0.3 m) of difference in elevation. Where the highest water supply outlet is located below the source of supply, add 0.5 psi (3.4 kpa) for each foot (0.3 m) of difference in elevation Where a water pressure reducing valve is installed in the water distribution system, the minimum daily static water pressure available is 80 percent of the minimum daily static water pressure at the source of supply or the set pressure downstream of the pressure reducing valve, whichever is smaller Deduct all pressure losses due to special equipment such as a backflow preventer, water filter and water softener. Pressure loss data for each piece of equipment shall be obtained through the manufacturer of such devices Deduct the pressure in excess of 8 psi (55 kpa) due to installation of the special plumbing fixture, such as temperature controlled shower and flushometer tank water closet. Using the resulting minimum available pressure, find the corresponding pressure range in Table E The maximum developed length for water piping is the actual length of pipe between the source of supply and the most remote fixture, including either hot (through the water heater) or cold water branches multiplied by a factor of 1.2 to compensate for pressure loss through fittings. Select the appropriate column in Table E201.1 equal to or greater than the calculated maximum developed length. 4. To determine the size of water service pipe, meter and main distribution pipe to the building using the appropriate table, follow down the selected maximum developed length column to a fixture unit equal to, or greater than the total installation demand calculated by using the combined water supply fixture unit column of Table E Read the water service pipe and meter sizes in the first left-hand column and the main distribution pipe to the building in the second left-hand column on the same row. 5. To determine the size of each water distribution pipe, start at the most remote outlet on each branch (either hot or cold branch) and, working back toward the main distribution pipe to the building, add up the water supply fixture unit demand passing through each segment of the distribution system using the related hot or cold column of Table E Knowing demand, the size of each segment shall be read from the second left-hand column of the same table and maximum developed length column selected in Steps 1 and 2, under the same or next smaller size meter row. In no case does the size of any branch or main need to be larger that the size of the main distribution pipe to the building established in Step INTERNATIONAL PLUMBING CODE

19 METER AND SERVICE PIPE (inches) TABLE E201.1 MINIMUM SIZE OF WATER METERS, MAINS AND DISTRIBUTION PIPING BASED ON WATER SUPPLY FIXTURE UNIT VALUES (w.s.f.u.) DISTRIBUTION PIPE (inches) MAXIMUM DEVELOPMENT LENGTH (feet) Pressure Range 30 to 39 psi / 4 1 / 2 a / 4 3 / / / / / / / / / / / / / METER AND SERVICE PIPE (inches) DISTRIBUTION PIPE (inches) MAXIMUM DEVELOPMENT LENGTH (feet) Pressure Range 40 to 49 psi / 4 1 / 2 a / 4 3 / / / / / / / / / / / / / (continued) 2006 INTERNATIONAL PLUMBING CODE 135

20 METER AND SERVICE PIPE (inches) TABLE E201.1continued MINIMUM SIZE OF WATER METERS, MAINS AND DISTRIBUTION PIPING BASED ON WATER SUPPLY FIXTURE UNIT VALUES (w.s.f.u.) DISTRIBUTION PIPE (inches) MAXIMUM DEVELOPMENT LENGTH (feet) Pressure Range 50 to 60 psi / 4 1 / 2 a / 4 3 / / / / / / / / / / / / / METER AND SERVICE PIPE (inches) DISTRIBUTION PIPE (inches) MAXIMUM DEVELOPMENT LENGTH (feet) Pressure Range Over / 4 1 / 2 a / 4 3 / / / / / / / / / / / / / For SI: 1 inch = 25.4, 1 foot = mm. a. Minimum size for building supply is 3 / 4 -inch pipe INTERNATIONAL PLUMBING CODE

### APPENDIX A RECOMMENDED RULES FOR SIZING THE WATER SUPPLY SYSTEM

APPENDIX A RECOMMENDED RULES FOR SIZING THE WATER SUPPLY SYSTEM Because of the variable conditions encountered, it is impractical to lay down definite detailed rules of procedure for determining the sizes

### Pipe Sizes For Water Distribution System Design

Appendix D Pipe Sizes For Water Distribution System Design D-. This appendix contains information to help determine pipe sizes when designing a water distribution system. Use Table D- and Tables D- through

### SIZING AND CAPACITIES OF GAS PIPING

APPENDIX A (IFGS) SIZING AND CAPACITIES OF GAS PIPING (This appendix is informative and is not part of the code.) A.1 General. To determine the size of piping used in a gas piping system, the following

### One of the fundamental design elements that every

Preliminary Design Information Before starting the water system design, you must assemble a collection of information. This includes information from the owner, the local utility, and the architect. Things

### CHAPTER 2: The Plumbing System

CHAPTER 2: The Plumbing System SECTION I: SIZING REQUIREMENTS Establish building dimensions Building height can be determined either by architectural drawings or # of floors times height/floor. (ex: 1

### Introduction to Water Pipe Sizing

ONTARIO PLUMBING INSPECTORS ASSOCIATION INC. In the public service since 1920 Introduction to Understanding the Many Methods to Size Water Pipe Presented by: Rainier Bratsch-Blundel, CPSI Plumbing Professor

DETERMINING TOTAL DYNAMIC HEAD The total dynamic head of a water system must be considered when determining the size of pumping equipment to be installed. It determines the various head losses that the

### DWELLING UNIT FIRE SPRINKLER SYSTEMS

DWELLING UNIT FIRE SPRINKLER SYSTEMS AT2904.1 General. Where installed, residential fire sprinkler systems, or portions thereof, shall be in accordance with NFPA 13D or Section AT2904, which shall be considered

### WC flushing cistern single or dual flush 0.13 0.05 2 to fill in 2 minutes WC trough cistern 0.15 per WC 0.10 2 Wash basin tap size 1 2

HAC_C0.qxd 7/4/08 9: Page 74 Chapter Pipe sizing Pipes and fittings should be sized so that the flow rates for individual draw-offs are equal to the design flow rates shown in table.. During simultaneous

### PLUMBING CODE REQUIREMENTS AND SIZING GUIDE FOR RESIDENTIAL WATER SOFTENERS. Second Edition. Prepared by

PLUMBING CODE REQUIREMENTS AND SIZING GUIDE FOR RESIDENTIAL WATER SOFTENERS Second Edition Prepared by NAHB Research Center, Inc. 400 Prince Georges Boulevard Upper Marlboro, MD 20774-8731 DISCLAIMER This

### WATER MEASUREMENT USING TWO INCH (50 mm) DRAIN TESTS

GAP.14.1.2.2 A Publication of Global Asset Protection Services LLC WATER MEASUREMENT USING TWO INCH (50 mm) DRAIN TESTS INTRODUCTION A hydrant or other large-volume flow test is necessary for proper water

### SIZING AND CAPACITIES OF GAS PIPING (Not Adopted by the State of Oregon)

(IFGS) SIZING AND CAPACITIES OF GAS PIPING (Not Adopted by the State of Oregon) (This appendix is informative and is not part of the code. This appendix is an excerpt from the 2006 International Fuel Gas

### SIZING AND CAPACITIES OF GAS PIPING

CALIFORNIA RESIDENTIAL CODE MATRIX ADOPTION TABLE APPENDIX A SIZING AND CAPACITIES OF GAS PIPING (Matrix Adoption Tables are non-regulatory, intended only as an aid to the user. See Chapter 1 for state

### CHAPTER 9 VENTS. copper drainage tube Type DWV, Schedule 40 plastic piping, or borosilicate glass.

CHAPTER 9 VENTS 901 GENERAL 901.1 Scope The provisions of this chapter shall govern the materials, design, construction, and installation of vents. 901.2 Protection of Trap Seals The protection of trap

### Isometric Plumbing Drawings

Building Inspections Isometric Plumbing Drawings All commercial building permit applications, in which the plumbing system has not been designed by a mechanical engineer, must include two sets of isometric

### Georgia State Amendments to the International Plumbing Code

Georgia State Amendments to the International Plumbing Code (2006 Edition) Georgia Department of Community Affairs Local Government Assistance Division 60 Executive Park South, N.E. Atlanta, Georgia 30329-2231

### Choosing a Pump for Rainwater Harvesting

Choosing a Pump for Rainwater Harvesting Introduction Water harvesting is the practice of capturing rainwater runoff, normally from a rooftop, and storing it in a tank or cistern for use around a home

### WATER SUPPLY AND DISTRIBUTION

CHAPTER 29 WATER SUPPLY AND DISTRIBUTION SECTION P2901 GENERAL P2901.1 Potable water required. Dwelling units shall be supplied with potable water in the amounts and pressures specified in this chapter.

### Plumbing Installations. A homeowner guide to the City of Winnipeg plumbing requirements for a single-family dwelling

Plumbing Installations A homeowner guide to the City of Winnipeg plumbing requirements for a single-family dwelling February 2001 contents General Information 3 Inspection 4 New Drain and Vent Installations

### LEAK DETECTION GUIDE

LEAK DETECTION GUIDE Your Guide to Home Water Conservation CITY OF BELLEVUE UTILITIES WATER & SEWER DEPARTMENTS LEAK DETECTION GUIDE PAGE: 1 WHERE TO START If you receive a high water bill, or think there

### The Irrigation Innovators

FRICTION TABLES The Irrigation Innovators 0 0 0...0.... 0....0. 0... 0.....0... 0. 0.....0....... 0.....0.. 0. 0.....0.. 0..... 0....0..0 0. 0........00..0....0.0.0 0.... 0. 0.0 0..0....0..........0..

### Sizing Plumbing Water System

PDHonline Course M126 (3 PDH) Sizing Plumbing Water System Instructor: A. Bhatia, B.E. 2012 PDH Online PDH Center 5272 Meadow Estates Drive Fairfax, VA 22030-6658 Phone & Fax: 703-988-0088 www.pdhonline.org

### Household Water Audit. Homeowner Guide To Assessing Water Use

Household Water Audit Homeowner Guide To Assessing Water Use WHAT IS A HOUSEHOLD WATER AUDIT? A household water audit is a great apportunity to conduct a detailed assessment of water use at your household

### Pacific Pump and Power

Pacific Pump and Power 91-503 Nukuawa Street Kapolei, Hawaii 96707 Phone: (808) 672-8198 or (800) 975-5112 Fax: (866) 424-0953 Email: sales@pacificpumpandpower.com Web: www.pacificpumpandpower.com Table

### ONTARIO PLUMBING INSPECTORS ASSOCIATION INC. In the public service since 1920. Wet Venting. Incorporating Stack Venting and NPC Harmonization

ONTARIO PLUMBING INSPECTORS ASSOCIATION INC. In the public service since 1920 Wet Venting Incorporating Stack Venting and NPC Harmonization Presented by: Rainier Bratsch-Blundel, CPSI Plumbing Professor

### What to Expect From the Examination. How to Study the Plumbing Codes

Texas State Board of Plumbing Examiners Plumbing Inspector Examination Review Course The following Examination Review Course is designed to assist an applicant in preparing for the Plumbing Inspector examination.

### Plumbing Installations A homeowner guide to the City of Winnipeg plumbing requirements for a single-family dwelling

PLANNING, PROPERTY AND DEVELOPMENT DEPARTMENT Plumbing Installations A homeowner guide to the City of Winnipeg plumbing requirements for a single-family dwelling October 2014 contents General Information

### SPRINKLER SYSTEM PLANS AND CALCULATIONS CHECK LIST

SPRINKLER SYSTEM PLANS AND CALCULATIONS CHECK LIST 1. Working plans shall be drawn to an indicated scale, on sheets of uniform size, with a plan of each floor, and shall show those items from the following

### Plumbing. Helpful Hints Residential Construction. Lincoln County. Bert Polk Plumbing Inspector

Plumbing Helpful Hints Residential Construction Bert Polk Plumbing Inspector Lincoln County 2015 Waste and vent fittings Vent 90 medium 90 long 90 1/16 bend,1/8 bend,1/6 bend, medium 90 san tee combination

### Water System Design PSD 177. Continuing Education from Plumbing Systems & Design MAY 2011 PSDMAGAZINE.ORG

Water System Design PSD 177 Continuing Education from Plumbing Systems & Design MAY 2011 PSDMAGAZINE.ORG CONTINUING EDUCATION The objective in designing the water supply systems for any project is to ensure

### Plumbing Code Sections For Commercial Food Facilities

Plumbing Code Sections For Commercial Food Facilities SCOPE The following list of requirements summarizes the plumbing issues that are commonly addressed in commercial retail food facilities by health

### DOMESTIC WATER PIPE SIZING

INFORMATION BULLETIN / PUBLIC - PLUMBING CODE REFERENCE NO.: LAPC 610.5 & 610.11 Effective: 01-01-2014 DOCUMENT NO.: P/PC 2014-009 Revised: Previously Issued As: P/PC 2011-009 DOMESTIC WATER PIPE SIZING

### 2012 British Columbia Plumbing Code Update

2012 British Columbia Plumbing Code Update 2012 British Columbia Plumbing Code is published as a separate document and is broken down into Divisions similar to BCBC 2 Division A Part 1 Compliance Part

### Pressure Drop Basics & Valve Sizing

Pressure Drop Basics & Valve Sizing What is Pressure Drop? The difference in pressure between two points in a system, caused by resistance to flow. What Pressure Drop is Not? Pressure drop is pressure

### 138.255 Section 4 Page 2. Flow in Pipes

Flow in Pipes 138.255 Section 4 Page 2 Flow in Pipes 1.0 INTRODUCTION In this module we are focusing on the fundamental principles of headloss and we learn how to use headloss charts to estimate the headloss

### SECTION 22000. Hot Water Heaters (Hot Water Recirculation Systems and Point-of-Use Water Heaters)

SECTION 22000 Hot Water Heaters (Hot Water Recirculation Systems and Point-of-Use Water Heaters) PART I - GENERAL A. Description This section includes requirements for materials for installation of Hot

### Principles of Hydraulic Analysis for Fire Protection Sprinkler Systems

Principles of Hydraulic Analysis for Fire Protection Sprinkler Systems Alan Johnston Hydratec, Inc. Code MP5517 The advent of Building Information Modeling (BIM) has highlighted the value of integrating

### Element D Services Plumbing

PART 1 - GENERAL 1.01 OVERVIEW A. This section addresses domestic cold, hot and hot water return distribution systems within and to five feet beyond building perimeter. PART 2 - DESIGN CRITERIA 2.01 GENERAL

### GAS PIPING INSTALLATIONS

CHAPTER 4 GAS PIPING INSTALLATIONS SECTION 40 GENERAL 40. Scope. This chapter shall govern the design, installation, modification and maintenance of piping systems. The applicability of this code to piping

### Design of Potable Water Plumbing Systems

Design of Potable Water Plumbing Systems Course No: M04-023 Credit: 4 PDH A. Bhatia Continuing Education and Development, Inc. 9 Greyridge Farm Court Stony Point, NY 10980 P: (877) 322-5800 F: (877) 322-4774

### Codes and High Performance Hot Water Systems. Gary Klein Affiliated International Management, LLC 916 549 7080 gary@aim4sustainability.

Codes and High Performance Hot Water Systems Gary Klein Affiliated International Management, LLC 916 549 7080 gary@aim4sustainability.com Annual Energy Use for Heating Water Natural Gas Gallons Per Day

### PROPOSED Plumbing Fee Ordinance Amendment

PROPOSED Plumbing Fee Ordinance Amendment Section 4 01 13 IDAHO STATE PLUMBING CODE AMENDMENT; PERMIT FEES. 103.4.1 Section 103.4.1 of the Idaho State Plumbing Code is amended to read as follows: Section

### Home comfort: water heating

Home comfort: water heating Water heating usage Hot water. It s one of those luxuries we give little thought to until we run out. This information is provided to help you get the most value and comfort

### Piping Systems. General considerations

SRAC Publication No. 373 May 2013 Revision PR VI Piping Systems J. David Bankston, Jr. and Fred Eugene Baker 1 A piping system allows the controlled movement of water from one location to another. It consists

### Plumbing Supply Piping Planning Tool Reducing Water Wasted Waiting for Hot

Plumbing Supply Piping Planning Tool Reducing Water Wasted Waiting for Hot Craig Selover Selover Consulting craig@dotmc.us H:248 542-3010 C:248 917-1380 Floor Plan Floor Plan All Piping WaterSense,HERS,

### WATER & SEWER SERVICES

WATER/SEWER ENGINEERING SECTION PHONE (703) 228-3677 WATER & SEWER SERVICES INFORMATION & APPLICATION PACKAGE REVISED MAY 2014 1 MAY 2014 Dear Customer: Thank you for taking the time to read this information

### Proposed Revision to International Residential Code 2012 (as proposed to the ICC for IRC 2015)

Proposed Revision to International Plumbing Code 2012 (as proposed to the ICC for IPC 2015 1 ) Table 604.4 Proponent: Edward R. Osann, Natural Resources Defense Council (eosann@nrdc.org); Harry Misuriello,

### Utility Service Application

Utility Service Application for Multi-family/Non-residential Developments Thank you for contacting the City of Tampa for your water and wastewater utility service needs. We have assembled this package

### To many people, a home s plumbing system is perceived as being extremely

Chapter 1 Understanding Plumbing In This Chapter Knowing what you re getting yourself into Touring residential plumbing systems To many people, a home s plumbing system is perceived as being extremely

### Method to Determine PERFORMANCE OF INDIRECT-FIRED WATER HEATERS March 2003 Edition

Supplement to TESTING STANDARD Method to Determine PERFORMANCE OF INDIRECT-FIRED WATER HEATERS March 2003 Edition [NOTE: This supplement incorporates testing and calculations to determine heat source friction

### SUBCOURSE EDITION EN5110 PREPARE A PLUMBING TAKEOFF LIST (PLUMBING I)

SUBCOURSE EDITION EN5110 A PREPARE A PLUMBING TAKEOFF LIST (PLUMBING I) PREPARE A PLUMBING TAKEOFF LIST SUBCOURSE EN 5110 PLUMBER MOS 51K 1 and 2 US Army Engineer School Fort Leonard Wood, Missouri 12

### FIRE PROTECTION SYSTEMS INSTALLATION OF RESIDENTIAL SPRINKLERS

FIRE PREVENTION STANDARD OFFICE OF THE FIRE MARSHAL FIRE PROTECTION SYSTEMS INSTALLATION OF RESIDENTIAL SPRINKLERS SCOPE: This standard applies to the design and installation of automatic fire sprinkler

### Automatic Fire Sprinkler Submittal Requirements

Automatic Fire Sprinkler Submittal Requirements All commercial and industrial buildings with a total floor area of 5000 sq. ft. shall have an approved automatic sprinkler system installed. The Windsor-Severance

### Top 10+ Mistakes of DWV plumbing design

Top 10+ Mistakes of DWV plumbing design Listed below are the some of the most frequently missed items, noticed by our inspectors, at plumbing rough-in when non-plumbers attempt plumbing design. Most of

### Understanding and Designing Plumbing Systems

Lesson A3 15 Understanding and Designing Plumbing Systems Unit A. Mechanical Systems and Technology Problem Area 3. Construction Systems Lesson 15. Understanding and Designing Plumbing Systems New Mexico

### PLAN CHECK CORRECTION SHEET FOR PLUMBING SYSTEMS 2014 LAPC

PLAN CHECK CORRECTION SHEET FOR PLUMBING SYSTEMS 2014 LAPC This is intended to provide uniform application of the codes by the plan check staff and to help the public apply the codes correctly. Section:

### This document was scanned from hard copy to portable document format (PDF) and edited to 99.5% accuracy. Some formatting errors not detected during

FA-155 / May 1995 This document was scanned from hard copy to portable document format (PDF) and edited to 99.5% accuracy. Some formatting errors not detected during the optical character recognition process

### Leak Detector Guide. Your Guide to Home Water Conservation

E v e r y D r o p C o u n t s! Leak Detector Guide Your Guide to Home Water Conservation M i a m i - D a d e W a t e r a n d S e w e r D e p a r t m e n t A High Bill Usually Means a Leak Did you know

### FIRE SPRINKLERS IN TOWNHOMES/CONDOMINIUMS

CITY OF BLAINE SAFETY SERVICES Fire Inspections 10801 Town Square Drive Blaine MN 55449 Business Phone 763-785-6187 Fax 763-717-2634 City of Blaine Fire Prevention Inspection Policy FIRE SPRINKLERS IN

### Cost Estimation for Materials and Installation of Hot Water Piping Insulation

Cost Estimation for Materials and Installation of Hot Water Piping Insulation Prepared for Pacific Northwest National Laboratory Under Contract Number: 18O9O2 By Gary Klein, Managing Partner Affiliated

### REGISTRATION EXAMINATION, JUNE 2009 PLUMBING QUESTION AND ANSWER BOOKLET. Time allowed THREE hours

Affix label with Candidate Code Number here. If no label, enter candidate Number if known No. 99 REGISTRATION EXAMINATION, JUNE 009 PLUMBING INSTRUCTIONS QUESTION AND ANSWER BOOKLET Time allowed THREE

### Saving Water and Energy in Residential Hot Water Distribution Systems. Gary Klein California Energy Commission

Saving Water and Energy in Residential Hot Water Distribution Systems Gary Klein California Energy Commission What Do You Want from your Hot Water System? Safety Not too hot Not too cold No harmful bacteria

### A High Bill Usually Means a Leak

A High Bill Usually Means a Leak Did you know that approximately 50 percent of all households have some kind of plumbing leak? Most of these leaks are due to worn out washers, flappers or faulty tank valves,

### PLAN REVIEW AND APPROVAL FOR FOOD ESTABLISHMENTS PLUMBING REQUIREMENTS FOR FOOD ESTABLISHMENT PREMISES

PLAN REVIEW AND APPROVAL FOR FOOD ESTABLISHMENTS PLUMBING REQUIREMENTS FOR FOOD ESTABLISHMENT PREMISES Health Systems Protection Rev. 07/2006 35-05-20/06/07/18 OFFICE OF FOOD PROTECTION 417 FEDERAL ST

### FOOD ESTABLISHMENT GUIDE FOR DESIGN, INSTALLATION, AND CONSTRUCTION RECOMMENDATIONS

FOOD ESTABLISHMENT GUIDE FOR DESIGN, INSTALLATION, AND CONSTRUCTION RECOMMENDATIONS PART 9 - HOT WATER SUPPLY REQUIREMENTS The hot water supply shall be sufficient to satisfy the continuous and peak hot

### PMA ONLINE TRAINING Venting for Plumbing Systems

PMA ONLINE TRAINING Venting for Plumbing Systems One Hour Continuing Education Venting PMA training disclaimer The information provided in this document is intended for use as a guideline and is not intended

### C I T Y O F S E L M A F I R E D E P A R T M E N T

C I T Y O F S E L M A F I R E D E P A R T M E N T Informational Bulletin Regarding Residential Fire Sprinkler Systems for One and Two Family Homes: Frequently Asked Questions ADMINISTRATIVE PROVISIONS:

### Fire Pump Plan Review March 2010

Fire Pump Plan Review March 2010 Date of Review: / / Permit Number: Business/Building Name: Address of Project: Designer Name: Designer s Phone: Contractor: Contractor s Phone: Occupancy Classification:

### Job Ready Assessment Blueprint. Plumbing. Test Code: 3061 / Version: 01

Job Ready Assessment Blueprint Plumbing Test Code: 3061 / Version: 01 Measuring What Matters Specific Competencies and Skills Tested in this Assessment: Professionalism Exhibit professional behavior Describe

### UNIVERSITY OF MISSOURI. 2. Fire Safety systems such as smoke detectors and fire alarms are intended to increase the level of life safety.

GENERAL: 1. All fire protection systems shall be installed in accordance with the International Fire Code and applicable NFPA standards. This guideline provides additional requirements for the design and

### 2016 BUILDING PERMIT FEES*

2016 PERMIT FEES* Fees are based on the cost of construction and shall be based on a value not less than the value determined using the Building Valuation Data Report published by ICC. Application Fee

### Water Pressure Reducing Valves

F-23QA 23 Questions and Answers about Water Pressure Reducing Valves \$ HOW THEY Save WATER Save ENERGY Save WASTEWATER Save MAINTENANCE Save MONEY ENERGY WATER Conserve Both Automatically with Water Pressure

### TANKLESS WATER HEATER INSTALLATION DIAGRAMS

TANKLESS WATER HEATER INSTALLATION DIAGRAMS Installation Diagrams Tankless Installation / Optional Return Small 10-15 Gallon Point-of-Use Water Single and Optional Return : One single, small capacity water

### Slide 1. Slide 2. Slide 3 288,817,200,000. Thank you for attending the session on Hot Water Re-Circulation.

Slide 1 Thank you for attending the session on Hot Water Re-Circulation. Hot Water Re-Circulation National Conference Center Lansdowne, VA March 25 th & 26 th, 2010 Slide 2 AGENDA Water Waste Statistics

### City of South Salt Lake Fire Marshal Regulations for Water Based Fire Protection and Water Supply Systems

City of South Salt Lake Fire Marshal Regulations for Water Based Fire Protection and Water Supply Systems Rev. Oct. 2012 1 Fire Flow 508.1 Required water supply. An approved water supply capable of supplying

### Summary Of The Reduction Of Lead In Drinking Water Act And Frequently Asked Questions

The Reduction of Lead in Drinking Water Act was enacted on January 4, 2011 to amend Section 1417 of the Safe Drinking Water Act (SDWA or Act) respecting the use and introduction into commerce of lead pipes,

### PWSID PWS Name Name Title Address Phone

The Deerwood Service Company operates a community water supply system that maintains the infrastructure to supply 67 homes at buildout, and currently supplies drinking water to 31 homes located within

### NOTE: The Hydrant in the circle is the test Hydrant. Residual and Static flows are measured here. Loop

NOTE: The Hydrant in the circle is the test Hydrant. Residual and Static flows are measured here. Figure 1 Loop Test Hydrant (Choose Either) Measure Residual & Static Pressures Dead End Main - Water One

### Minor losses include head losses through/past hydrants, couplers, valves,

Lecture 10 Minor Losses & Pressure Requirements I. Minor Losses Minor (or fitting, or local ) hydraulic losses along pipes can often be estimated as a function of the velocity head of the water within

Teacher Assessment Blueprint Plumbing Test Code: 5175 / Version: 01 Copyright 2010 NOCTI. All Rights Reserved. General Assessment Information Blueprint Contents General Assessment Information Written Assessment

### SANTA ROSA FIRE DEPARTMENT FIRE PREVENTION BUREAU PLAN REVIEW CHECKLIST RESIDENTIAL FIRE SPRINKLERS NFPA 13D

July 1, 2010 SANTA ROSA FIRE DEPARTMENT FIRE PREVENTION BUREAU PLAN REVIEW CHECKLIST RESIDENTIAL FIRE SPRINKLERS NFPA 13D Address: Permit #: Inspector: Date: Status: Inspector: Date: Status: A-Approved;

### Friction Loss Charts 2008

Irrigation Association Friction Loss Charts 2008 Tables are based upon the following Hazen-Williams Equation: H f = 0.2083 100 C 1.852 Q1.852 D 4.866 The result is multiplied by 0.433 to give pounds per

### DPO Hydraulics Refresher

DPO Hydraulics Refresher References: Pumping Apparatus Driver/Operator Handbook-IFSTA Essentials of Firefighting Handbook-IFSTA Fire Stream Practices-IFSTA INTRODUCTION To produce effective fire streams,

### Indirect-Fired Storage Water Heater Models WH-30 through WH-80 INSTALLATION AND OPERATING INSTRUCTIONS

Indirect-Fired Storage Water Heater Models WH-30 through WH-80 INSTALLATION AND OPERATING INSTRUCTIONS Contents Page Ratings and Specifications..................... 2 Installation Requirements......................

### Residential Plumbing BCN 1058

Residential Plumbing BCN 1058 CHAPTER 7 Plumbing Fixtures and Sizing the Drain, Waste, and Vent System MICHAEL KNOTEK 74 Plumbing Fixtures and Sizing the Drain, Waste, and Vent System PLUMBING FIXTURES

### Fire Pump Layout and Sizing. Victoria B. Valentine, P.E.

Fire Pump Layout and Sizing Victoria B. Valentine, P.E. Learning Outcomes Identify the appropriate sections of NFPA 20 that apply to sizing and layout of fire pumps. Identify the components of a fire pump

### Plumbing Apprenticeship Program Curriculum

Plumbing Apprenticeship Program Curriculum Plumbing Level One 02101-05 Introduction to the Plumbing Profession (5 Hours) Introduces the trainee to plumbing, starting with the history of plumbing from ancient

### Efficient Hot-Water Piping

Efficient Hot-Water Piping Smarter layouts and right-sized pipes save time, water, and energy by Gary Klein How long are you willing to wait for hot water when you turn on the tap? That s a question I

### hose-to-hose coupling pump-to-hose coupling

pipe_02 A homeowner plans to pump water from a stream in their backyard to water their lawn. A schematic of the pipe system is shown in the figure. 3 m 1 m inlet pipe-to-pump coupling stream re-entrant

### MOBILE FIRE - RESCUE DEPARTMENT FIRE CODE ADMINISTRATION

MOBILE FIRE - RESCUE DEPARTMENT FIRE CODE ADMINISTRATION Fire Pump Plan Review 2009 International Fire Code and NFPA 20 Date of Review / / BLD201 - Project Address: Project Name: Contractor s Business

### Treatment Mound Design Considerations & Details

Design Considerations & Details 10001 84th Avenue, Clairmont, AB T0H 0W0 Phone: 780.513.3950 Fax: 780.539.7686 www.countygp.ab.ca Permit Number: PRPSW The following information is to accompany the Private

### Practice Problems on Pumps. Answer(s): Q 2 = 1850 gpm H 2 = 41.7 ft W = 24.1 hp. C. Wassgren, Purdue University Page 1 of 16 Last Updated: 2010 Oct 29

_02 A centrifugal with a 12 in. diameter impeller requires a power input of 60 hp when the flowrate is 3200 gpm against a 60 ft head. The impeller is changed to one with a 10 in. diameter. Determine the

### Pressure Reducing Valve Calculation Example

Pressure Reducing Valve Calculation Example Procedure to Calculate the Pressure Values required to factory set a Pressure Reducing Valve. 1) First calculate the maximum static pressure available on the

### ELECTRIC/DIESEL FIRE PUMP CHECK LIST

BUILDING NAME: DESIGNER: SCO REPRESENTATIVE: PUMP MANUF.: LOCATION: INSTALLER: DATE: OWNER NAME: INSTALLATION Certificate for flushing and hydrostatic test furnished Piping been hydrostatically tested

### INTERNATIONAL RESIDENTIAL CODE PLUMBING

INTERNATIONAL RESIDENTIAL CODE PLUMBING RP1-07/08 P2503.5.1 Proposed Change as Submitted: Proponent: Michael Cudahy, representing Plastic Pipe and Fittings Association Revise as follows: P2503.5.1 Rough

### Surge Pressure in Plumbing Pipe Materials

Surge Pressure in Plumbing Pipe Materials Prepared for Plastics Pipe Institute, Inc. 15 Decker Court, Suite 825 Irving, Texas 7562 Prepared by NAHB Research Center 4 Prince George s Blvd. Upper Marlboro,

### City of Elk River BASEMENT Office Use Only

City of Elk River BASEMENT Office Use Only Fire and Building Safety Division (FABS) Building Permit Application Notes Scan Permit Total Date Permit # PID # \$ Site Address Suite/Unit Structure Type Single

### WATER SUPPLY AND DISTRIBUTION

CHAPTER 6 WATER SUPPLY AND DISTRIBUTION SECTION PC 601 GENERAL 601.1 Scope. This chapter shall govern the materials, design and installation of water supply systems, both hot and cold, for utilization