1 WHITE PAPER #14 THE GREEN GRID METRICS: DATA CENTER INFRASTRUCTURE EFFICIENCY (DCIE) DETAILED ANALYSIS EDITOR: GARY VERDUN, DELL CONTRIBUTORS: DAN AZEVEDO, SYMANTEC HUGH BARRASS, CISCO STEPHEN BERARD, MICROSOFT MARK BRAMFITT, PG&E TAHIR CADER, SPRAYCOOL TOMMY DARBY, TI CHRISTINE LONG, APC NICK GRUENDLER, IBM BOB MACARTHUR, EMC PHIL MORRIS, SUN ANDY RAWSON, AMD JIM SIMONELLI, APC HARKEERET SINGH, BT JOHN WALLERICH, INTEL
2 PAGE 2 EXECUTIVE SUMMARY The Green Grid previously published THE GREEN GRID METRICS: DESCRIBING DATACENTER POWER EFFICIENCY white paper. The following is detailed analysis to support and strengthen the Data Center infrastructure Effi ciency (DCiE) metric. The intent is to enable data center managers collectively to derive and use DCiE as a global standard metric.
3 PAGE 3 TABLE OF CONTENTS INTRODUCTION... 4 BACKGROUND AND ASSUMPTIONS...5 DCIE OVERVIEW...5 DCIE SUBCOMPONENTS... 7 OBTAINING REQUIRED DATA...9 ESTIMATING POWER CONSUMPTION... 9 MEASURING POWER CONSUMPTION... 9 POWER METERING REQUIREMENTS FACTORS AFFECTING DCIE...10 DYNAMIC DATA CENTER TYPE OF DATA CENTER CLIMATE AND LOCATION...11 DATA CENTER DESIGN AND OPERATION MEASUREMENT PERIOD SOMETIMES DCIE SEEMS TO GO THE WRONG WAY...12 DRIVING DCIE EFFICIENCY...12 DCIE AND FUTURE TECHNOLOGY ADVANCEMENTS...13 MULTIUSE FACILITIES...13 SUMMARY...15 CONCLUSION... 15
4 PAGE 4 INTRODUCTION Previously, The Green Grid published a white paper entitled The Green Grid Metrics: Describing Data Center Power Effi ciency. The white paper discussed the need for a fi nite number of industry-accepted metrics that describe the effectiveness and effi ciency of data centers around the world. The white paper also provided an overview of a proposed metric called the Data Center infrastructure Effi ciency (DCiE). A phased approach will be adopted as The Green Grid provides increasingly detailed information with respect to quantifi cation of the DCiE. Table 1 provides a graphical representation of the approach. This White Paper represents the fi rst in a series of White Papers that will provide a more detailed analysis of the DCiE metric, and represents the Basic level in Table 1. Level 1(Basic) involves collecting power measurements on at least a monthly basis from the UPS equipment within the data center (the IT Load) and from the Main Distribution panel feeding all of the mechanical equipment used to cool and condition the data center. Level 2 (Intermediate) would involve collecting data on at least a daily basis using measurements taken at the s within the data center and from the distribution system used to power each of the pieces of equipment that make up the Facility equipment. Level 3 (Advanced) would involve collecting data from each individual piece of IT equipment within the data center and from each individual piece of facility s equipment on a continuous basis. For the Basic and Intermediate measurement processes, it is recommended that the measurements be taken at approximately the same time of day and when the loading in the data center is as consistent as possible with prior measurements. When making week to week comparisons, the day of the week should also be kept constant for comparable measurements. This White Paper starts with an overview of the DCiE, and includes a graphical representation of the subsystems included in the DCiE, a discussion of how to obtain the required data and a description of, and suggestions for, obtaining DCiE in multi-use facilities. The overriding goal of this and all subsequent papers is to educate data center operators on how to collect the necessary data and interpret the metric in order to drive a given facility to a higher level of effectiveness and effi ciency, i.e., a higher DCiE. BACKGROUND AND ASSUMPTIONS The recommendations below are based upon a dedicated data center facility. If working with a multiuse facility (ex. offi ce space and data center space combined) see Multiuse Facilities section later in this document to assist with the additional calculations. It is recommended that DCiE be monitored over a period of one year with ongoing measurements in order to compensate for peak and nominal loading changes that occur within the data center. If it s not possible to monitor power consumption over a full year, select a period
5 PAGE 5 of time not less than one month and verify that the loading within the data center is typical for your particular environment. It is important to understand the difference between cumulative and instantaneous measurements and the effect of variations (of load, of environment, etc.) on the overall infrastructure effi ciency. An instantaneous reading of power for the IT equipment and the total facility power ( e.g. in kw) will yield an instantaneous value for DCiE, however it should be expected that this will vary on daily, weekly, monthly or annual cycles depending on load, environment and other factors. More frequent instantaneous measurements will result in a better understanding of this variation and an insight into the factors that most infl uence the overall facility effi ciency. To get a useful single metric for DCiE the cumulative energy use should be measured (e.g. in kwhr) for a period that is longer than the cyclic variation in effi ciency, for many facilities this may be a full year. DCIE OVERVIEW Equation 1 DCiE is defi ned as the ratio of IT Equipment Power and Total Facilities Power as shown in Equation 1 above. The Total Facility Power is defi ned as the power measured at the utility meter the power dedicated solely to the datacenter (this distinction is important in mixed-use buildings that house data centers as one of a number of functions). The IT Equipment Power is defi ned as the power consumed by equipment that is used to manage, process, store or route data within the compute space. It is important to understand the components for the loads in the metrics, which can be described as follows: 1. IT Equipment Power: This includes the load associated with all of the IT equipment, i.e. compute, storage and network equipment, along with supplemental equipment i.e. KVM switches, monitors, and workstations/laptops used to monitor or otherwise control the data center. 2. Total Facility Power: This includes all IT Equipment power as described in number 1 above plus everything that supports the IT equipment load such as: a. Power delivery components i.e. UPS, switch gear, generators, s, batteries and distribution losses external to the IT equipment b. Cooling system components i.e. chillers, computer room air conditioning units (CRAC s), direct expansion air handler (DX) units, pumps, and cooling towers c. Other miscellaneous component loads such as datacenter lighting The following diagram (Figure 1) shows a typical data center with indicated measurement points for the proposed levels for measuring DCiE listed in Table 1. These points are indicated by meters in the diagram with associated levels indicated as Level 1 through Level 3 (L1-L3).
6 PAGE 6 AC Utility Feed A L 1 Substation 15 kv 480 V / 277 V Backup Generator 2 MW Backup Generator 2 MW Generator Switchgear Backup Generator 2 MW ATS 2500A Automatic Transfer Switch ATS 2500A Automatic Transfer Switches ATS 2500A L 2 L 2 Standby Switchboard, 2500 A, 480 V Mechanical Switch Gear Mechanical Switch Gear B UPS B Side 320 kw 400 Panel, 800A, 480 V UPS A Side 400 kw 500 UPS A Side 400 kw 500 UPS A Side 400 kw 500 L 1 L 1 L 1 L 1 Mechanical Equipment CRAC Units Glycol Pumps Maintenance Bypass Switch, 2500 A, 480 V Building Management Facility Power Mechanical Equipment L 3 L 3 L 3 L 3 L 3 L 3 L 3 L 3 CRAC Units Glycol Pumps Building Management Facility Power L 2 L 2 L 2 L 2 L 2 L 2 L 2 L 2 L 2 L 2 L 2 L 2 L 2 L 2 Redundant Feeds For IT Equipment Telco L 3 Backup Devices Storage L 3 L 3 Security Encryption L 3 KVM/ Console L 3 Servers Switches L 3 Routers L 3 Printers L 3 PC s & L 3 Workstations L 3 Figure 1 Note: You cannot accurately calculate DCiE using name plate ratings for any of the IT Equipment OR for any of the Mechanical Infrastructure components. Actual power measurements must be collected in order for DCiE to have any correlation to an operational data center.
7 PAGE 7 DCIE SUBCOMPONENTS In order for DCiE to become a global metric there are two important requirements all must follow: 1) Correctly classify each sub-component that comprises the metric s two core contributors 2) Obtain the data inputs that create DCiE s two core contributors in the same method, i.e. utilize a consistent method for data capture and always use actual measurements. DCiE Subcomponents Facility Data Center Productivity DCeP DCI The Data Center Productivity Metric is described in a separate GG white paper. IT Equipment Building Mgmt. Compute Devices Storage HVAC Physical Security Facility Power Network Devices IT Support Systems Telecommunications Miscellaneous Devices Figure 2 Table 2 below is designed to assist with correctly classifying each sub component: Organize the components to map to the DCiE Subcomponent Drawing shown in Figure 2 Organize the components from the largest offender to the smallest offender this will allow you to easily focus on the area s that need the most improvement in order to improve your DCiE
8 PAGE 8 Table 2
9 PAGE 9 OBTAINING REQUIRED DATA As defi ned in the Introduction, the DCiE is the ratio of the IT Power and the Total Facility Power. There are two fundamentally different methods for obtaining data necessary to make the DCiE calculation. One can either estimate the power by using available information on the equipment factoring in appropriate operational and ambient properties, or one can measure the actual power consumption of the required components. ESTIMATING POWER CONSUMPTION Power consumption for the various components necessary to populate the DCiE equation can be obtained using estimates such as effi ciency curves and estimated loading conditions. The Green Grid envisions this method to be useful in estimating expected DCiE and evaluating alternatives during design and planning stages for future data centers. The Green Grid does not recommend this approach for operational data centers and strongly recommends one of the following approaches. MEASURING POWER CONSUMPTION The Green Grid recommended approach for obtaining the data necessary to calculate DCiE is to measure actual power consumption for the entire data center and IT equipment. TGG recognizes that obtaining actual measurement is not a trivial task especially in existing data centers that do not have adequate instrumentation to collect the data. The minimum required measurement data would consist of two measurements one being total facility power (Point A in Figure 1) and IT equipment power (Point B in Figure 1). Although this would be adequate to calculate DCiE, The Green Grid believes that more data would be necessary to assess areas for potential improvements and evaluating changes intended to improve DCiE within a data center.
10 PAGE 10 POWER METERING REQUIREMENTS The typical specifi cations of power meters include the terms accuracy, resolution, crest factor and bandwidth, but most important to measuring the power use of equipment is requiring a suitable watt meter that reports the true power, via the simultaneous measurement of the input voltage, current and power factor (note that kva, the product of voltage and current alone is not an accurate representation of the power used). Many watt meters also have the capability to report energy usage which is the measurement of power over time (kwatt hours or Joules). Accuracy is specifi ed in terms of percent error in the measurement. While a low error is desirable and often needed, one must note the specifi ed range over which the accuracy is stated and whether or not it is specifi ed as the accuracy of full scale. Having a uniform percentage error over the full range of operation is more important. Measurements with a maximum of ±5% error can be useful in determining overall power usage trends for level 1 measurement, but it is recommended that meters used have at least a ±2% accuracy. Resolution is the term used for number of signifi cant digits that carry meaning contributing to the accuracy and often will vary with the measurement range. A 0.1 Watt resolution is recommended for the measurement of a single piece of IT equipment. This level is not obtainable for the meter of a multi- megawatt data center utility feed. An acceptable meter resolution for level one measurements is 0.05% of full scale. Crest factor of an AC current waveform is equal to the ratio of the peak current to the RMS current. The meter selected must be able to handle the equipment s crest factor without introducing distortion in the measurement due to the top of waveforms being clipped. Normally a full range rating of 3 is suffi cient, though lighter loading of single equipment meters may require crest factors in the range of 6 to 8. Bandwidth is a measure of the meters capability to handle measurements that contain high frequency harmonics created by the power converters in the data center equipment (both IT and infrastructure). A minimum bandwidth of 3kHz is recommended. Other considerations for power metering include choices impacting the ease of installation and of data collection. Power measurement systems generally implement contactless current sensors rather than shunts, because the latter cause power losses as well as installation and safety issues. The current transducers are normally transformers through which the electrical feed passes. Two common designs are solid and split-core transducers. A solid core sensor is less expensive and more accurate and the best choice for new permanent installations, while the split-core design is the more common choice for existing installations. Split-core transformers are designed for the ability to be retrofi tted into a live installation without disturbance (as opposed to a solid core transformer which would require the power cabling to be disconnected to be installed). Automatic Meter Reading (AMR) or Remote Meter Reading (RMR) allow users to have the equipment communicate the measurements and not have someone physically read a display or download a data fi le. AMR or RMR may be smart meters incorporating additional functions to report data in greater detail, such as power quality, outages and the ability to communicate data and alerts over a network smart meters will be needed to automate the measurement and calculation of DCiE. Note: DCiE and PUE can be represented using either power or energy. When it is calculated using power, it represents an instantaneous DCiE or PUE. When it is calculated using energy, it represents an average DCiE or PUE over the time period of the measurement.
11 PAGE 11 FACTORS AFFECTING DCIE The intent of DCiE is to assist decision makers for data center operations, IT or facilities in the effort to improve data center effi ciency. As with any data point, this is only one part of the entire data center picture. DCiE is valuable to monitor changes in one data center at an aggregated level. It can also help to identify large differences in effi ciency in similar data centers, though further investigation is required to understand why these variations exist. It is the fi rst step to better understand a data center s effi ciency. Subsequent investigation is required to determine the best approach for additional improvement in data center s effi ciency. DYNAMIC DATA CENTER Today s data center is in constant fl ux. Applications, as well as the IT equipment and infrastructure that support them, are continually evolving to better meet the business needs of the corporation. Therefore, the initial design of the data center is obsolete the day after the installation and commissioning is complete. Often, energy effi ciency calculations are based on a static design instead of the dynamic data center confi guration. The designed (static) verses actual (dynamic) nature of a data center must be considered. Improvements will come through incremental step changes in infrastructure over time. Also, it is important to keep in mind that as the load changes in the data center, the operating point of the subcomponents on their effi ciency curves will change. Measurements should not be taken if maintenance is being performed within the data center. This could negatively impact the DCiE measurement and provide unrealistic measurements. TYPE OF DATA CENTER The type of processing done in a data center can greatly impact the DCiE metric. The Green Grid is also working on a companion paper, Data Center Segmentation, to help various types of data centers compare DCiE to similar data centers. Is the data center primarily for testing, production, internal processes, networking? What is the primary business supported by the data center fi nancial, healthcare, telecom? What Tier level is required to support this business? Another aspect to consider is if the data center operations scheme includes disaster recovery, which would certainly affect effi ciency. Similarly, the physical attributes of the data center will impact DCiE. What is the typical temperature and humidity kept at in the data center? What type of cooling system is used and does it include free cooling? How old is the data center and the subcomponents in it? Was the building intended to be a data center, or was it retrofi tted to be used as one? How far is the data center from its power source? Many infrastructure subcomponents and IT equipments currently support energy reduction features are these employed in the data center? And are they effective? Are alternate energy sources being used? Are dummy loads being run, and if so, why and when? CLIMATE AND LOCATION Where a data center is located can have signifi cant impact on energy effi ciency achievability. The effi ciency of identical mechanical system can be drastically different depending on the climate the system is operating
12 PAGE 12 in. The climate and location of the data center also impacts the hours of free cooling available. Free cooling implies the ability to provide cooling to IT equipment by leveraging local ambient conditions in order to reduce energy use. Similarly, some mechanical systems are just not practical in some climates or locations. Location has a signifi cant impact on utility rates and even energy availability. DATA CENTER DESIGN AND OPERATION The design of the data center infrastructure cannot be underestimated in its impact on energy effi ciency. IT equipment density, power distribution architecture, cooling architectures, redundancy levels and fl oor layouts, to name a few, all have major impacts on effi ciency. Many of these topics will be further addressed in depth in other The Green Grid White Papers. Even the best design can result in poorer than designed effi ciency as operation changes take place. For example, increasing the density in a single rack above the specifi ed design value may result in air conditioners cooling the new hot spot. As a result, the cooling system is no longer in balance and is less effi cient. MEASUREMENT PERIOD Hourly, daily, weekly, monthly, and seasonal variances effect DCiE. To truly understand and successfully manage a data center s effi ciency, continuous real time monitoring should be used so that historical trending and statistical analysis can be done to determine where effi ciencies can be gained. However, this is not always practical or economically justifi able, but some form of repeatable, defi ned process should be in place to capture DCiE as often as possible for comparison purposes. Measurements should not be taken if maintenance is being performed within the data center. This could have a negative impact and provide unrealistic DCiE measurements. The Green Grid recommends automated, real-time monitoring with data captured every quarter hour. The quoted DCiE number is the average over a one year period. For data centers without real-time monitoring, DCiE is collected according to Table 1 per the intended level of implementation. SOMETIMES DCIE SEEMS TO GO THE WRONG WAY The common goal is reduce energy consumption, not defraud a metric. In some real world situations, the DCiE metric may go down if total power provided to a data center is not adjusted accordingly to a drop in IT power. It is important to remember to reduce the infrastructure subcomponent power consumption. Unlike other measures, there are no credits or percentage points awarded for generating energy, waste heat recovery, etc. While important, these are not the focus of the DCiE metric. The maximum DCiE is %, the minimum 0%. DCiE needs to be considered with total data center energy consumption in mind. The total energy consumption of a data center may go down, but DCIE may not refl ect an improvement. Similarly, total energy costs may increase, but per unit cost may decrease.
13 PAGE 13 DRIVING DCIE EFFICIENCY The purpose for collecting the required information and calculating a DCiE for any data center is to provide a means by which to compare one data center to another similar data center and more importantly to determine the effectiveness of any changes made within a given data center in terms of infrastructure power effi ciency. DCiE provides an indication of how much power is consumed by the facility infrastructure in order to distribute this power to the IT equipment, provide necessary cooling to the IT equipment and provide stability and redundancy in power delivery to the IT equipment. Currently, in typical data centers it is expected that DCiE will likely vary with levels of IT load. In order to improve DCiE and the energy effi ciency of a data center, it is necessary to make changes that affect the energy consumed by non-it equipment in the support of the IT equipment. Implementation of Level 1 in Table 1 is suffi cient to measure the DCiE of a facility and will provide the necessary data to determine the effectiveness of changes made to a data center. The added information provided in Levels 2 and 3 may be necessary, either all or in part, in order to identify those changes most likely to provide improvements. Changes made to improve DCiE should be made in the following order: 1. Follow best practices found in other The Green Grid White Papers 2. Increase granularity of power measurements such that power losses can be ranked by subsystems 3. Rank loss contributors by magnitude and investigate opportunities to make changes that will lower the energy consumed in these subsystems and still support the requirements of the IT equipment. DCIE AND FUTURE TECHNOLOGY ADVANCEMENTS The Green Grid will continually review and revise DCiE as advancements are made in technology and in data center design. It is assumed that things will change, and this metric will be updated to refl ect these changes. Other metrics may be added to assist in optimizing the effi ciency of a data center. For example, it would be helpful to know what percentage of the current data center capacity is currently being used. Similarly, graphing and reporting DCiE and other metrics could provide easy access to relevant data for operators. MULTIUSE FACILITIES The assumption at the beginning of this paper was that the data center was standalone and easily isolated. However, this is often not the case. Often, a data center is part of a larger building or structure that includes other functions. In these multiuse facilities, the applicable portion of the power used in the data center must be determined. If possible, a demarcation point for data center versus non-data center needs to be established. This should be straightforward for the electrical distribution path, but may be more challenging for the HVAC subcomponents. Ideally it would be possible to determine the exact portion of the HVAC power required by IT equipment vs. the rest of facility. Realistically this is not always possible to do. When the mechanical systems are shared, some method to allocate HVAC power between the data center or IT equipment and the rest of building is required.
14 PAGE 14 Industry estimates for HVAC power in a data center range from 20% to 45% of total data center consumption. i For basic level DCiE analysis it is expected that estimation is required. One method of doing this is using the ratio of IT equipment power to the total facility power multiplied by the total HVAC power to estimate the IT equipment HVAC power requirements. Using the same data center layout from Figure 1, the basic method for estimating HVAC power allocated to the data center is shown in Figure 3. Method For Estimating HVAC Power For a Multi-Use Facility AC Backup Generator 2 MW Backup Generator 2 MW Backup Generator 2 MW Utility Feed M1 Power Meter Substation 15 kv 480 V / 277 V Generator Switchgear Total Facility Power Measurement Location (M1) M1 = Total Facility Power Measurement M2 = Office Space Power Measurement M3 = IT Power Measurement M4 = IT Power Measurement M5 = IT Power Measurement ATS 2500 A Automatic Transfer Switch ATS 2500A Automatic Transfer Switches ATS 2500 A Standby Switchboard, 2500 A, 480 V Mechanical Switch Gear Mechanical Switch Gear UPS B Side 320 kw 400 M2 UPS A Side 400 kw 500 M3 UPS A Side 400 kw 500 M4 Power Meter Power Meter Power Meter UPS A Side 400 kw 500 M5 Power Meter Mechanical Equipment Mechanical Equipment Glycol Pumps CRAC Units Glycol Pumps CRAC Units Office Space (May or may not be fed with UPS power) IT Equipment HVAC Power Allocated to IT = ((M3 + M4 + M5) / Total Facility Power ) * (Total HVAC Power ) If Total HVAC power is unknown, it can be calculated by performing the following : Total HVAC Power = M1 (M2 + M3 + M4 + M5) Figure 3
15 PAGE 15 For intermediate DCiE analysis, the HVAC component can be calculated based on information collected from the HVAC components. The portion of cooling directed to the data center is determined by the percentage based on fl ow rate of heat transfer medium, number of cooling units, and size of cooling units. This will provide a more accurate estimation of the power dedicated to cooling the data center. For advanced DCiE analysis, the individual HVAC components supporting the data center would be instrumented to measure the actual power consumption. SUMMARY This paper provides information and guidelines necessary for end users to apply DCiE in their facilities. Areas addressed include the following: Multiple levels of DCiE Implementation are described which allow a phased approach to instrumenting data centers for DCiE data collection and calculation. This allows IT operators the ability to begin collecting data and using DCiE without the costs and time required to implement a fully instrumented data center Power Metering locations described for each of these implementation levels in a typical data center providing a phased approach to instrumentation and effort required to collect data and compute DCiE All expected equipment in data center is categorized as IT equipment or not IT Equipment providing clarity as to components should be categorized as infrastructure vs. IT equipment Methods of obtaining data to populate DCiE discussed describing usefulness and limitations of the methods Power Metering requirements are described to provide guidance in selecting appropriate power measuring equipment Factors affecting the DCiE value are discussed to provide a better understanding of what items affect DCiE. This knowledge can help identify sources of changes in DCiE and also provide guidance on potential areas for improvement Methods of addressing DCiE measurements in Multi-Use facilities are described in order to provide guidance in instrumenting multi-use facilities for DCiE measurement CONCLUSION The DCiE metric provides a very useful tool for evaluating and measuring the energy usage and effi ciency of the infrastructure equipment supporting IT equipment within a data center. This allows data center operators to address and reduce the energy usage related to the supporting infrastructure within a data center. Much of the detail in this paper addresses the Basic level of implementation for DCiE measurement. This level is specifi cally tailored to address the capabilities of existing equipment in data centers. The intent is to provide the capability to measure DCiE with the minimum amount of changes to existing data centers. Future white papers shall provide more detail on requirements and use of DCiE for intermediate and advanced levels of implementation.
16 PAGE 16 REFERENCES i LBNL Energy Effi cient Data Centers Power Chain Effi ciency, December 11, 2006 William Tschudi, APC white paper #144 & #154
WHITE PAPER #6 GREEN GRID DATA CENTER POWER EFFICIENCY METRICS: PUE AND DCIE EDITORS: CHRISTIAN BELADY, MICROSOFT CONTRIBUTORS: ANDY RAWSON, AMD JOHN PFLEUGER, DELL TAHIR CADER, SPRAYCOOL PAGE 2 ABSTRACT
WHITE PAPER #49 PUE : A COMPREHENSIVE EXAMINATION OF THE METRIC EDITORS: Victor Avelar, Schneider Electric Dan Azevedo, Disney Alan French, Emerson Network Power PAGE 2 The Green Grid Association would
WHITE PAPER #22 USAGE AND PUBLIC REPORTING GUIDELINES FOR THE GREEN GRID S INFRASTRUCTURE METRICS (PUE/DCIE) EDITORS: JON HAAS, INTEL JAMIE FROEDGE, EMERSON NETWORK POWER CONTRIBUTORS: JOHN PFLUEGER, DELL
The goals of the greening of the Data Center are to minimize energy consumption and reduce the emission of green house gases (carbon footprint) while maximizing IT performance. Energy efficiency metrics
february 20, 2007 GREEN GRID METRICS: Describing Datacenter Power Efficiency Technical Committee White Paper white paper 1 Abstract The Green Grid is an association of IT professionals seeking to dramatically
7 Best Practices for Increasing Efficiency, Availability and Capacity XXXX XXXXXXXX Liebert North America Emerson Network Power: The global leader in enabling Business-Critical Continuity Automatic Transfer
THE GREEN GRID DATA CENTER POWER EFFICIENCY METRICS: PUE AND DCiE 2007 The Green Grid. All rights reserved. No part of this publication may be used, reproduced, photocopied, transmitted, or stored in any
Guidance for Calculation of Efficiency (PUE) in Data Centers White Paper 158 Revision 1 by Victor Avelar > Executive summary Before data center infrastructure efficiency can be benchmarked using PUE or
White Paper Intel Information Technology Computer Manufacturing Data Center Efficiency Increasing Data Center Efficiency through Metering and Monitoring Power Usage To increase data center energy efficiency
scalable data centre energy management solution scalable data centre energy management solution EcoMeasure - Scalable Data Centre Energy Management & Efficiency Measurement Solution by Workspace Technology
Guidance for Calculation of Efficiency (PUE) in Data Centers White Paper 158 Revision 3 by Victor Avelar Executive summary Before data center infrastructure efficiency can be benchmarked using PUE or other
GHG Protocol Product Life Cycle Accounting and Reporting Standard ICT Sector Guidance Chapter : Guide for assessing GHG emissions of Data Centers DRAFT March 0 Table of Contents GHG Protocol ICT Sector
Measuring Power in your Data Center: The Roadmap to your PUE and Carbon Footprint Energy usage in the data center Electricity Transformer/ UPS Air 10% Movement 12% Cooling 25% Lighting, etc. 3% IT Equipment
Electrical Efficiency Modeling for Data Centers By Neil Rasmussen White Paper #113 Revision 1 Executive Summary Conventional models for estimating electrical efficiency of data centers are grossly inaccurate
WHITE PAPER #27 IMPACT OF VIRTUALIZATION ON DATA CENTER PHYSICAL INFRASTRUCTURE EDITOR: DENNIS BOULEY, APC BY SCHNEIDER ELECTRIC PAGE 2 EXECUTIVE SUMMARY Data center virtualization, which includes storage,
White Paper #13 A Framework for Data Center Energy Productivity Contributors: Dave Anderson, Verari Tahir Cader, Spraycool Tommy Darby, TI Nick Gruendler, IBM Rema Hariharan, AMD Anne Holler, VMware Chris
Siemens Answers: Sustainable Future How green is your data center? Istanbul June 01, 2010 Agenda 1 Solution 2 Siemens Data Center Approach 2 Designing with multiple power density zones can reduce energy
Existing and proposed metrics to provide effective understanding and reporting of data centre energy Liam Newcombe Data Centre Specialist Group 1 Introduction... 2 2 Summary... 6 3 Overview of metrics...
Reducing Data Center Energy Consumption By John Judge, Member ASHRAE; Jack Pouchet, Anand Ekbote, and Sachin Dixit Rising data center energy consumption and increasing energy costs have combined to elevate
Recommendations for Measuring and Reporting Overall Data Center Efficiency Version 1 Measuring PUE at Dedicated Data Centers 15 July 2010 Table of Contents 1 Introduction... 1 1.1 Purpose Recommendations
Calculating Total Power Requirements for Data Centers By Richard Sawyer White Paper #3 Executive Summary Part of data center planning and design is to align the power and cooling requirements of the IT
Classification of Data Center Operations Technology (OT) Management Tools White Paper by Kevin Brown and Dennis Bouley Executive summary Data centers today lack a formal system for classifying software
WHITE PAPER #23 PROPER SIZING OF IT POWER AND COOLING LOADS WHITE PAPER CONTRIBUTORS: JOHN BEAN, APC RON BEDNAR, EMERSON NETWORK POWER RICHARD JONES, CHATSWORTH PRODUCTS ROBB JONES, CHATSWORTH PRODUCTS
Recommendations for Measuring and Reporting Overall Data Center Efficiency Version 2 Measuring PUE for Data Centers 17 May 2011 Table of Contents 1 Introduction... 1 1.1 Purpose Recommendations for Measuring
EXECUTIVE STRATEGY BRIEF Operating highly-efficient datacenters is imperative as more consumers and companies move to a cloud computing environment. With high energy costs and pressure to reduce carbon
Applying Data Center Infrastructure Management in Collocation Data Centers Infrastructure Management & Monitoring for Business-Critical Continuity TM Applying Data Center Infrastructure Management (DCIM)
Common $en e: Solutions to Make Your Data Center Energy Effi cient Energy effi ciency is a life style. It s also common sense. In a data center, the name of the game is effi ciency and how many compute
Managing Data Centre Heat Issues Victor Banuelos Field Applications Engineer Chatsworth Products, Inc. 2010 Managing Data Centre Heat Issues Thermal trends in the data centre Hot Aisle / Cold Aisle design
Analysis of data centre cooling energy efficiency An analysis of the distribution of energy overheads in the data centre and the relationship between economiser hours and chiller efficiency Liam Newcombe
Tier 3+ 1 Title: Design of a Shared Tier III+ Data Center: A Case Study with Design Alternatives and Selection Criteria Abstract: Schoolcraft College is constructing a High Availability (HA) Data Center
Local Area Networks (LAN) Servers Data centers Internet centers (ISP/ASP/POP) Industrial PLCs EPOS (Electronic Point of Sale) Systems Emergency devices (lights/alarms) Electro-medical devices Telecommunication
Energy Efficiency and Availability Management in Consolidated Data Centers Abstract The Federal Data Center Consolidation Initiative (FDCCI) was driven by the recognition that growth in the number of Federal
Essential NCPI Requirements for Next Generation Data Centers By Ted Ives White Paper #14 1 Executive Summary The management of physical infrastructure in data centers can no longer be considered independently
Green Computing: Datacentres Simin Nadjm-Tehrani Department of Computer and Information Science (IDA) Linköping University Sweden Many thanks to Jordi Cucurull For earlier versions of this course material
Server Technology, Inc. Power Efficiency Gains by Deploying 415 VAC Power Distribution in North American Data Centers White Paper STI-100-008 2009-April-07 Headquarters Server Technology, Inc. 1040 Sandhill
Green Computing: Datacentres Simin Nadjm-Tehrani Department of Computer and Information Science (IDA) Linköping University Sweden Many thanks to Jordi Cucurull For earlier versions of this course material
Data Centre Infrastructure Assessment Prepared for: ACME INC SAMPLE REPORT Attention: Mr DC Manager This report represents a generic sample data centre audit for a generic customer by Focus Group Technologies.
Building a Real Data Center During the Great Recession Steven Carlini Sr Director, Data Center Global Solution Offer Management APC by Schneider Electric Schneider Electric at a glance global, innovative
Enabling an agile Data Centre in a (Fr)agile market Phil Dodsworth Director, Data Centre Solutions 2008 Hewlett-Packard Development Company, L.P. The information contained herein is subject to change without
WHITE PAPER Cooling Capacity Factor (CCF) Reveals Stranded Capacity and Data Center Cost Savings By Lars Strong, P.E., Upsite Technologies, Inc. Kenneth G. Brill, Upsite Technologies, Inc. 505.798.0200
Modular Data Center Solutions Scalable. Affordable. Flexible. Fast. Build the data center you need today with the flexibility to meet tomorrow s challenges The only constant in business is change. Fluctuations
Mass Combi Ultra Your own power station: For continuous power Compact and lightweight inverter/battery charger Seamless switching between generator and grid Separate second charger Integrated MPPT solar
Convergence of Complexity Optimize Existing Data Center Space Measure And Allocate Energy Cost Plan for new data centers or additional capacity How to make your Data Center Last Longer, Gartner, December
Re Engineering to a "Green" Data Center, with Measurable ROI Alan Mamane CEO and Founder Agenda Data Center Energy Trends Benchmarking Efficiency Systematic Approach to Improve Energy Efficiency Best Practices
DATA CENTER ASSESSMENT SERVICES ig2 Group Inc. is a Data Center Science Company which provides solutions that can help organizations automatically optimize their Data Center performance, from assets to
Green Data Centers GOING FORWARD ENERGY EFFICIENCY TRENDS André ROUYER Director of Standardization & Environment All content in this presentation is protected 2008 American Power Conversion Corporation
Guideline for Water and Energy Considerations During Federal Data Center Consolidations Prepared for the U.S. Department of Energy Federal Energy Management Program By Lawrence Berkeley National Laboratory
Data Center Power Distribution and Capacity Planning: Understanding what you know and don t know about power usage in your data center 2009, Raritan Inc. About This Series Raritan, a leading provider of
Selecting a UPS Topology for your Data Center by Dr. Daniel Becker, Ph.D., Methode Active Energy Solutions Uninterruptible Power Supplies (UPS) are both reaching into new markets and expanding in new ways
Harmonizing Global Metrics for Data Center Energy Efficiency Dan Azevedo, Symantec Chairman - Metrics & Measurements Work Group Industry Trends Energy Efficient IT The Climate Group: Smarter technology
Infrastructure Management & Monitoring for Business-Critical Continuity TM Revolutionizing Data Center Infrastructure Management The Trellis Platform A Real-Time Solution to Continuous Performance Improvement
Drives motors A guide to using variable-speed drives motors in data centres The power behind the data Private public businesses, from banks to supermarkets, to telecommunications companies internet providers
Energy Savings in the Data Center Starts with Power Monitoring As global competition intensifies, companies are increasingly turning to technology to help turn mountains of data into a competitive edge.
. Facility Criteria (RFP).0 Location Characteristics Criteria Requirements 1 Ownership and Management: Please identify the owner(s) and managers of the property and indicate if there is on-site management.
European Association for the Development of Renewable Energies, Environment and Power Quality (EA4EPQ) International Conference on Renewable Energies and Power Quality (ICREPQ 12) Santiago de Compostela
A Comparison of AC and DC Power Distribution in the Data Center Transcript Slide 1 Welcome to the Data Center University course on the A Comparison of AC and DC Power Distribution in the Data Center. Slide
Energy Efficiency and Green Data Centers Overview of Recommendations ITU-T L.1300 and ITU-T L.1310 Paolo Gemma Chairman of Working Party 3 of ITU-T Study Group 5 International Telecommunication Union Agenda
IBM Twin Data Center Complex Ehningen Peter John IBM BS email@example.com Overview Profile IBM owned facility 6447 m² IT-Space Infrastructure concurrent maintainable (Tier Level 3) Feed-ins of Power
UTH and IHU (CI)-WP4 Energy Efficiency Monitoring in Data Centers: Case Study at International Hellenic University Plenary Meeting Gent, February-2012 George Koutitas, Prof. L. Tassiulas, Prof. I. Vlahavas
Green Data Centre Design A Holistic Approach Stantec Consulting Ltd. Aleks Milojkovic, P.Eng., RCDD, LEED AP Tommy Chiu, EIT, RCDD, LEED AP STANDARDS ENERGY EQUIPMENT MATERIALS EXAMPLES CONCLUSION STANDARDS
Intel Intelligent Power Management Intel How High Temperature Data Centers & Intel Technologies save Energy, Money, Water and Greenhouse Gas Emissions Power and cooling savings through the use of Intel
How Does Your Data Center Measure Up? Energy Efficiency Metrics and Benchmarks for Data Center Infrastructure Systems Paul Mathew, Ph.D., Staff Scientist Steve Greenberg, P.E., Energy Management Engineer
Benchmarking results from Indian data centers Data Center Energy Efficiency 24 February, ACREX 2011, New Delhi Madhav Kamath. A Energy Efficiency Finance Lead USAID ECO-III Project Data Center Benchmarking
Data Centre Monitoring Made Easy Power & Environmental Monitoring Features & Benefits Packet Power provides the easiest, most cost effective way to capture detailed power and temperature information for
Overview of Green Energy Strategies and Techniques for Modern Data Centers Introduction Data centers ensure the operation of critical business IT equipment including servers, networking and storage devices.
Data Center Facility Basics Ofer Lior, Spring 2015 Challenges in Modern Data Centers Management, Spring 2015 1 Information provided in these slides is for educational purposes only Challenges in Modern
BCA-IDA Green Mark for Existing Data Centres Version EDC/1.0 To achieve GREEN MARK Award Pre-requisite Requirement All relevant pre-requisite requirements for the specific Green Mark Rating are to be complied
Server room guide helps energy managers reduce server consumption Jan Viegand Viegand Maagøe Nr. Farimagsgade 37 1364 Copenhagen K Denmark firstname.lastname@example.org Keywords servers, guidelines, server rooms,
An Improved Architecture for High-Efficiency, High-Density Data Centers By Neil Rasmussen White Paper #126 Executive Summary Data center power and cooling infrastructure worldwide wastes more than 60,000,000
Drives and motors A guide to using variable speed drives and motors in data centres Meeting your Carbon Reduction Commitment (CRC) The power behind the data Private and public businesses, from banks to
Improving Data Centers Energy Reliability & Efficiency December 2015 Background The challenges Alternative solutions SATEC approach Advantages Cases Summary Data Centers Energy Challenges Worldwide Data
AIA Provider: Colorado Green Building Guild Provider Number: 50111120 Office Efficiency: Get Plugged In AIA Course Number: EW10.15.14 Speaker: Geoff Overland Credit(s) earned on completion of this course
Nationwide Services Corporate Headquarters 410 Forest Street Marlborough, MA 01752 USA Tel: 800-342-5332 Fax: 508-303-0579 www.eecnet.com LEVEL 3 DATA CENTER ASSESSMENT Submitted by: Electronic Environments
Understanding Power Usage Effectiveness (PUE) & Data Center Infrastructure Management (DCIM) Salim Janbeh Physical Infrastructure Consultant email@example.com PANDUIT You Can t Manage What You Don t Measure:
Green Energy Solutions Power Electronics for Photovoltaic Inverter Systems 1 Energy Management Product Line-up Energy Management Product Line-up Power Conversion and Stabilization Frequency Converter Static
The Pros and Cons of Modular Systems Kevin Brown, Vice President Global Data Center Offer Schneider Electric Schneider Electric 1 Foundational BUSINESS OVERVIEW Rev 2 Desired characteristics of pre-fabricated
Engineers Ireland Cost of Data Centre Operation/Ownership 14 th March, 2013 Robert Bath Digital Realty Total Cost of Operation (TCO) Rental TCO - 10 Year Lease Term Power Cooling Connectivity Costs 26%
Understanding Date Center Power Usage Effectiveness This Dell Technical White Paper explains how to understand Power Usage Effectiveness (PUE) and how it applies to your Data Center. George Richards Dell
Data Center Energy Efficiency Looking Beyond PUE No Limits Software White Paper #4 By David Cole 2011 No Limits Software. All rights reserved. No part of this publication may be used, reproduced, photocopied,
Data Center Technology: Physical Infrastructure IT Trends Affecting New Technologies and Energy Efficiency Imperatives in the Data Center Hisham Elzahhar Regional Enterprise & System Manager, Schneider
Optimum Climate Control For Datacenter - Case Study T. Prabu March 17 th 2009 Agenda 2 About EDEC (Emerson) Facility Data Center Details Design Considerations & Challenges Layout Design CFD Analysis Of
Will installing wireless networking change my back-up power requirements? What data do I need to know in order to determine my wireless network back-up power requirements? What other issues should I consider
Increasing Data Center Efficiency by Using Improved High Density Power Distribution By Neil Rasmussen White Paper #128 Executive Summary A new approach to power distribution for high density server installations
Server Technology, Inc. Cabinet Power Monitoring, Management & Control Within the Data Center White Paper STI-100-011 2010-Sept-27 by Calvin Nicholson, Senior Director Software and Strategic Alliances,
Real-Time Energy Consumption Measurements in Data Centers ASHRAE TC9.9 and The Green Grid First printing released at the ASHRAE Winter Annual Meeting, Jan 23 27, 2010 ASHRAE/TGG. 2009. Real Time Energy
RiMatrix S Make easy. 2 RiMatrix S Rittal The System. The whole is more than the sum of its parts. The same is true of Rittal The System. With this in mind, we have bundled our innovative enclosure, power
edna Real-time enterprise data historian edna is an enterprise real-time data management software platform. It collects, stores, displays, analyzes, and reports on operational and asset health information