1 Page 1 of 21 Inspection Report Condo Association Property Address: Swamptown, IL Front View William Decker, IL Lic. #
2 Page 2 of 21 Date: 10/10/2008 Time: 1:00 PM Report ID: Sample 4 Property: Swamptown, IL Customer: Condo Association Real Estate Professional: The subject property is a 3 unit (the first floor unit is duplexed into the lower level) multiple condominium building originally built in The client (the condo association) requested an inspection to evaluate and document the condition of the property which displayed extensive mold growth and water infiltration. In summary, the building displays the classic signs of "wet building syndrome". This is caused by: 1) Use of "split faced block" as the exterior wall covering on the sides and rear of the building. While allowed, this building material is not recommended for use in this climate. Additionally, this wall covering was not sealed, as required. 2) The exterior masonry was not properly flashed. This has allowed extensive water intrusion into the building's interior areas. 3) Improper flashing of the masonry where the rear metal porches are attached. 4) Multiple exterior wall penetrations that were not properly sealed. 5) Improper flashing of the coping tile stones. 6) Improper flashing of roof penetrations for vents, electrical conduit and and water pipes. These items have lead to moisture penetration through the exterior walls, through the parapet wall coping stone and through the roof openings. There is extensive mold growth on the building's interior walls, ceilings and buckling wooden flooring. This is a maintenance inspection and is not part of a real estate transaction. This inspection was requested by the owners to examine some problems that they have with the house's condition, to document these problems and obtain advice on how to best prioritize and fix these problems. Comment Key Definitions The following definitions of comment descriptions represent this inspection report. All comments by the inspector should be read and considered when evaluating this property. Note:Any recommendations by the inspector to repair or replace or deal with a significantly deficient item suggests an evaluation by a licensed
3 Page 3 of 21 and insured contractor specifically qualified to determine the condition and safety of the described item, component or system. Please note that Home Inspectors in the State of Illinois are required to note any safety hazards, whether they comply with older, obsolete local building codes or not. Licensed and insured contractors are not. Repairs done by persons other that licensed and insured contractors carry with them added liability for the customer. All work done on the subject property should be accompanied by a copy of all invoices and warranties, such warranties should be transferable to the new owner and should include the contractor's license number and a copy of their insurance certification. Category Definitions: Inspected (IN) = The system, component or item was visually observed at a certain time and under certain conditions. Not Inspected (NI)= The system, component or item was not inspected and no representations of whether or not it was functioning are intended. The reason could be that the item was not connected (gas, water, electrical disconnected), obstructed, or not accessible. In any case, the reason that the item, system or component was not inspected is stated in the comments. Not Present (NP) = This system, component or item is not present in the subject property. Watch List or Maintenance (WL) =Either the system, component or item needs regular maintenance to remain functioning in a proper manner and those maintenance processes are noted or the item should be watched in anticipation of future problems. Repair or Replace (RR) = The item, component or unit is not functioning as intended or needs further inspection by a licensed and insured contractor. Most of these type of comments describe items that will lead to more serious problems if not addressed. Items, components or systems that can be repaired to satisfactory condition may not need replacement. Significantly Deficient (SD) = Defined by Illinois State Law as either a) not functioning or b) posing a safety hazard. It should be noted that a large number of significantly deficient items can be addressed at little cost. It is important to remember that the safety of a significantly deficient item is not based upon mere local building codes, which contain 'grandfathering' clauses, or the common 'accepted' practices of tradesmen, but on current national and international safety requirements and with the well being of the property and the client in mind. Please Note: If you have any questions or any thing is unclear, please do not hesitate to contact Decker Home Services and/or your specific inspector. We are happy to answer any of your questions and have a large knowledge base
4 Page 4 of 21 of information and experienced, qualified expert NACHI instructors and inspectors from around the entire country at our disposal. We consider it very important for you to fully and completely understand the condition of the subject property and will do all we can to help you in the process. Age Of Home: Under 5 Years (2005) Client Is Present: Yes Weather: Clear Temperature: Over 65 Rain in last 3 days: No Radon Test: No Mold Test: No Water Test: No Insect / Pest Inspection: No
5 Page 5 of Exterior The home inspector shall observe: Wall cladding, flashings, and trim; Entryway doors and a representative number of windows; Garage door operators; Decks, balconies, stoops, steps, areaways, porches and applicable railings; Eaves, soffits, and fascias; and Vegetation, grading, drainage, driveways, patios, walkways, and retaining walls with respect to their effect on the condition of the building. The home inspector shall: Describe wall cladding materials; Operate all entryway doors and a representative number of windows; Operate garage doors manually or by using permanently installed controls for any garage door operator; Report whether or not any garage door operator will automatically reverse or stop when meeting reasonable resistance during closing; and Probe exterior wood components where deterioration is suspected. The home inspector is not required to observe: Storm windows, storm doors, screening, shutters, awnings, and similar seasonal accessories; Fences; Presence of safety glazing in doors and windows; Garage door operator remote control transmitters; Geological conditions; Soil conditions; Recreational facilities (including spas, saunas, steam baths, swimming pools, tennis courts, playground equipment, and other exercise, entertainment, or athletic facilities); Detached buildings or structures; or Presence or condition of buried fuel storage tanks. The home inspector is not required to: Move personal items, panels, furniture, equipment, plant life, soil, snow, ice or debris that obstructs access or visibility. SIDING STYLE: BRICK SPLIT BLOCK APPURTENANCE: METAL PORCH DRIVEWAY: ALLEY SIDING MATERIAL: BRICK VENEER SPLIT BLOCK STONE Styles & Materials GARAGE DOOR MATERIAL: METAL EXTERIOR ENTRY DOORS: STEEL GARAGE DOOR TYPE: THREE AUTOMATIC Inspection Items 1.0 WALL COVERING AND TRIM - Inspect and Describe The exterior of the house was covered with finished brick and stone (front) and split faced block (sides and rear). The brick displayed areas of efflorescence ( Picture 1 ) mortar loss ( Picture 2 ) as well as non-professional installation ( Picture 3, misaligned inside corner ) and improper mortaring technique ( Picture 4 ). The front patio area coping tiles were not flashed and have allowed water to enter the brick, below, causing significant efflorescence ( Picture 5 ). The spilt block on the back and sides was not properly flashed. It had weep wicks missing and the flashing at the foundation level was not properly extended out from the wall ( Picture 6 ). It is assumed that the flashing at the upper levels was similarly installed. The wall displayed some retained moisture at upper level flash courses ( Picture 7, 8 ) with some moisture leakage past the flash courses. There were multiple areas where the exterior wall penetrations were not properly sealed. The hose bib was not properly sealed ( Picture 9 ) which has allowed water to enter and cause mold formation on the north wall of the rear basement area ( Picture 10, 11). The unsealed rear balcony stakes ( Picture 12 ) and the unsealed electrical and HVAC flues
6 Page 6 of 21 ( Picture 13 ) have allowed water to enter and cause mold formation on the rear basement wall ( Picture 14 ). The unflashed rear porch ledger boards ( Picture 15 ) have allowed water intrusion and mold growth at the top and side of the rear basement door ( Picture 16 ) and a split downspout had allowed excessive moisture on the south rear basement area ( Picture 17 ) has caused mold growth on the interior of this area ( Picture 18, 19 ). 1.0 Picture Picture Picture Picture Picture Picture 6
9 Page 9 of Picture WALL COVERING AND TRIM - Findings, Repair or Replace The masonry work on the building is sub-standard and was not done professionally. The split block used on the building is not a material that is recommended to be used in this climate and was not sealed at construction, as required. The unsealed split block, especially when combined with the recent record rainfall, has caused a significant water intrusion problem for thru building, with water entering through the block and the interior structural walls and into the insulation and the drywall and causing mold formation. Additionally, given the non-professional and sub-standard building techniques, there were multiple exterior wall penetrations that were not properly sealed. This has caused direct water leaking into the building, as evidenced by the extensive mold formation in the rear of the lower lever. It should be noted that the condition of the building is a direct violation of city ordinance , which was specifically written to deal with problems occurring in split block construction. It is recommended that the clients retain legal help in dealing with the costs of the repairs from the original builder. 1) RR - Recommend that the entire exterior wall coverings of the building be evaluated and repaired by a licensed and insured masonry contractor. 1.2 WINDOWS (Exterior) - Inspect and Describe The building was equipped with multiple glass block windows. The use of such windows and their installation without the upper masonry being supported by steel lintels ( Picture 1 ) is not a recommended construction technique.
10 Page 10 of Picture WINDOWS (Exterior) - Findings, Repair or Replace 1) RR - Recommend that steel lintels be installed above the glass block windows. As an upgrade, it is recommended that the glass block windows be replaced with more energy efficient windows. 1.4 DECKS, BALCONIES, STOOPS, STEPS, AREAWAYS, PORCHES AND APPLICABLE RAILINGS - Inspect and Describe The rear of the building was equipped with metal decks, secured to the building with the required metal rods. Where the deck's ledger boards were attached to the building, there was no flashing ( Picture 1 ). Proper installation of a deck or porch ledger board to a building requires metal flashing above the ledger to divert water running down the exterior wall away from the ledger board and the wall penetrations that holds the ledger board ( Picture 2 ). This problem is evidenced by the water infiltration into the rear basement area (see section 1.0) and the rust seen on the underside of the deck ( Picture 3 ). 1.4 Picture Picture 2
11 Page 11 of Picture DECKS, BALCONIES, STOOPS, STEPS, AREAWAYS, PORCHES AND APPLICABLE RAILINGS - Findings, Repair or Replace 1) RR - Recommend that the ledger boards for the rear decks / porches be equipped with the required flashing above their ledger boards and that the flashing be counter flashed into the mortar joints and that the work be done by licensed and insured masonry contractors. 2) RR - Recommend that the rear metal decks / porches be scraped, primed and painted by a licensed and insured painter who specializes in metal exterior painting.
12 Page 12 of Roofing The home inspector shall observe: Roof covering; Roof drainage systems; Flashings; Skylights, chimneys, and roof penetrations; and Signs of' leaks or abnormal condensation on building components. The home inspector shall: Describe the type of roof covering materials; and Report the methods used to observe the roofing. The home inspector is not required to: Walk on the roofing; or Observe attached accessories including but not limited to solar systems, antennae, and lightning arrestors. ROOF COVERING: MODIFIED BITUMEN CHIMNEY (exterior): METAL FLUE WITH SPARK ARRESTOR Styles & Materials VIEWED ROOF COVERING FROM: WALKED ROOF SKY LIGHT (S): NONE Inspection Items 2.0 ROOF COVERINGS - Inspect and Describe The roof is covered with modified bitumen roofing and covered, mostly, by a wooden deck resting directly on the roof covering. This is not an approved installation, will greatly shorten the life of the roof covering and will greatly increase the price of replacing the roof (because of the extra labor involved in removing the deck). The roof covering appears to be properly installed and flashed to termination bar on the side walls. There was no counter flashing above the termination bar. There was one section of torn roofing seen at the southeast corner of the roof. The deck has torn the roof covering. 2.1 ROOF COVERINGS - Findings Roof decks are not a good idea for flat roofs unless they are specifically engineered, at the time of the original building's design. They lead (as they have in this case) to premature roof failure. 1) RR - Recommend that the deck be removed and the roof leaks repaired. 2.2 FLASHINGS, SKYLIGHTS, CHIMNEYS AND ROOF PENETRATIONS - Inspect and Describe The roof had multiple roof penetrations, none of which were properly of professionally flashed ( Picture 1 ). There was water leakage through these flashings into the utility closet of the 3rd floor unit ( Picture 2, 3 ). The coping stone on the top of the roof's parapet wall was not properly sealed at its joints ( Picture 4 ) and there was no evidence of flashing under the stone. Both these conditions will allow water to enter the exterior walls.
13 Page 13 of Picture Picture Picture Picture FLASHINGS, SKYLIGHTS, CHIMNEYS AND ROOF PENETRATIONS - Findings 1) RR - Recommend that, as part of a roof repair, that the roof penetrations be properly and professionally sealed. Recommend that the work be done by a state licensed and insured roofer in accordance with best practices. 2) RR - Recommend that the coping stones on the parapet wall be properly flashed by a licensed and insured masonry contractor.
14 Page 14 of Interiors The home inspector shall observe: Walls, ceiling, and floors; Steps, stairways, balconies, and railings; Counters and a representative number of installed cabinets; and a representative number of doors and windows. The home inspector shall: Operate a representative number of windows and interior doors; and Report signs of abnormal or harmful water penetration into the building or signs of abnormal or harmful condensation on building components. The home inspector is not required to observe: Paint, wallpaper, and other finish treatments on the interior walls, ceilings, and floors; Carpeting; or Draperies, blinds, or other window treatments. CEILING MATERIALS: SHEETROCK INTERIOR DOORS: COMPOSITE WALL MATERIAL: SHEETROCK Styles & Materials WINDOW TYPES: CASEMENT GLASS BLOCK METAL EXTERIOR - WOODEN INTERIOR Inspection Items 3.0 CEILINGS - Inspect and Describe FLOOR COVERING(S): HARDWOOD T&G TILE Ceilings were finished with drywall and exhibited no signs of sag, warp, loose tape joints or nail pops. There were minor irregularities normally seen in new construction. Over all, the ceiling drywall job was an industry standard level II. Ceilings in the rear basement area and around the PVC vent flues in the 3rd floor unit displayed water intrusion. The ceiling / wall interfaces in the rear basement area also displayed mold growth. See section 3.2. The southeast corner of the 3rd floor unit displays signs of moisture intrusion ( Picture 1, 2 ) which is, most probably, caused by damage to the roof ( Picture 3 ) from the improperly installed roof deck. Modified bitumen roofs are not to be covered with roof decks. 3.0 Picture Picture 2
15 Page 15 of Picture CEILINGS - Findings, Repair or Replace There is some ceiling involvement with the moisture entering the north wall, but most of the ceiling mold is caused by other exterior wall penetrations that were not properly sealed. The southeast corner of the 3rd floor unit has water intrusion from the roof deck. Roof decks are not supposed to be installed on modified bitumen roofs because they tear the roof covering. 1) RR - Recommend that the water damaged ceilings be replaced after the moisture intrusion is stopped. 2) RR - Recommend that the roof deck be removed and the roof patched. 3.2 WALLS - Inspect and Describe Walls were finished with drywall and exhibited no signs of sag, warp, loose tape joints or nail pops. There were minor irregularities normally seen in new construction. Over all, the drywall job was an industry standard level II. The walls in the rear basement area, under the stairs in the front finished basement and the entire north wall of the building displayed signs of increased moisture content. This was seen in the upper stories (above grade level) as generalized increased moisture content with significant wooden stud saturation (16 to 23% WE) while the north wall of the lower level revealed higher moisture levels on the wall ( Picture 1, 2 ) and around the glass block window wells ( Picture 3, 4 ) with moisture readings between 19 and 32% WE. The north wall of the garage, where it is in contact with the adjacent garage wall displayed significant moisture intrusion ( Picture 5, 6 ). This is, most likely, caused by the exterior garage door being in contact with the adjacent garage. The walls in the rear basement area display advanced mold formation, with some colonies of Stacobactris evident (no samples were taken).
16 Page 16 of Picture 1 Basement, North wall 3.2 Picture 2 Basement, North wall, thermal 3.2 Picture 3 Baement, North wall 3.2 Picture 4 Basement, North wall, thermal 3.2 Picture 5 Garage, North wall. 3.2 Picture 6 Garage, North wall, thermal 3.3 WALLS - Findings The north walls of the building are moist, with most of the moisture concentrated in the rear basement and north wall of lower level finished area. The moisture in the upper floors is less and more diffuse, with only isolated, closed areas (such as closets and utility
17 Page 17 of 21 rooms affected). The upper floors should have only the affected walls removed. The lower level finished area should have the north wall and all the walls in the rear area removed. The studs inside the walls should be scraped, HEPA vacuumed and treated with a fungicide and, finally, coated with a mold encapsulating paint. A further consideration should be given to replacing the walls in these areas with fiberglass drywall which is resistant to mold growth. 1) RR - Recommend that the walls be evaluated by a certified mold remediation company. 2) RR - Recommend that the north garage wall be evaluated and repaired by a licensed and insured masonry contractor. 3) RR Recommend that the walls on the rear lower level area be completely removed and remediated by a certified mold remediation company. Recommend clearance testing after the work is complete. 3.4 FLOORS - Inspect and Describe The lower level floors of the 1st unit were hardwood tongue and groove. They displayed signs of buckling ( Picture 1 ) and water damage, especially along the north wall and in the hallway area. This is caused by a combination of the water intrusion and that the floors were installed directly on the concrete slab floor, which is not an approved installation. 3.4 Picture FLOORS - Findings, Repair or Replace 1) RR - Recommend that the hardwood floors in the lower level be removed and replaced once the floor level has been raised. The use of a floor raising product, such as Dricore, is highly recommended. 3.6 WINDOWS (Interior) - Inspect and Describe Some of the windows were glass block. They displayed signs of condensation moisture damage on the interior sill spaces. The use of glass block windows is not recommended.
18 Page 18 of 21 Prepared Using HomeGauge SHGI (c) : Licensed To Decker Home Services, LLC
19 Page 19 of 21 General Summary Customer Condo Association Property Address Swamptown, IL The following items or discoveries indicate that these systems or components do not function as intended or adversely affects the habitability of the dwelling; or appear to warrant further investigation by a specialist, or requires subsequent observation. This summary shall not contain recommendations for routine upkeep of a system or component to keep it in proper functioning condition or recommendations to upgrade or enhance the function, efficiency, or safety of the home. This Summary is not the entire report. The complete report may include additional information of concern to the customer. It is recommended that the customer read the complete report. 1. Exterior 1.1 WALL COVERING AND TRIM - Findings Inspected, Repair or Replace The masonry work on the building is sub-standard and was not done professionally. The split block used on the building is not a material that is recommended to be used in this climate and was not sealed at construction, as required. The unsealed split block, especially when combined with the recent record rainfall, has caused a significant water intrusion problem for thru building, with water entering through the block and the interior structural walls and into the insulation and the drywall and causing mold formation. Additionally, given the non-professional and sub-standard building techniques, there were multiple exterior wall penetrations that were not properly sealed. This has caused direct water leaking into the building, as evidenced by the extensive mold formation in the rear of the lower lever.
20 Page 20 of 21 It should be noted that the condition of the building is a direct violation of city ordinance , which was specifically written to deal with problems occurring in split block construction. It is recommended that the clients retain legal help in dealing with the costs of the repairs from the original builder. 1) RR - Recommend that the entire exterior wall coverings of the building be evaluated and repaired by a licensed and insured masonry contractor. 1.3 WINDOWS (Exterior) - Findings Inspected, Repair or Replace 1) RR - Recommend that steel lintels be installed above the glass block windows. As an upgrade, it is recommended that the glass block windows be replaced with more energy efficient windows. 1.5 DECKS, BALCONIES, STOOPS, STEPS, AREAWAYS, PORCHES AND APPLICABLE RAILINGS - Findings Inspected, Repair or Replace 1) RR - Recommend that the ledger boards for the rear decks / porches be equipped with the required flashing above their ledger boards and that the flashing be counter flashed into the mortar joints and that the work be done by licensed and insured masonry contractors. 2) RR - Recommend that the rear metal decks / porches be scraped, primed and painted by a licensed and insured painter who specializes in metal exterior painting. 3. Interiors 3.1 CEILINGS - Findings Inspected, Repair or Replace There is some ceiling involvement with the moisture entering the north wall, but most of the ceiling mold is caused by other exterior wall penetrations that were not properly sealed. The southeast corner of the 3rd floor unit has water intrusion from the roof deck. Roof decks are not supposed to be installed on modified bitumen roofs because they tear the roof covering. 1) RR - Recommend that the water damaged ceilings be replaced after the moisture intrusion is stopped. 2) RR - Recommend that the roof deck be removed and the roof patched. 3.5 FLOORS - Findings Inspected, Repair or Replace 1) RR - Recommend that the hardwood floors in the lower level be removed and replaced once the floor level has been raised. The use of a floor raising product, such as Dricore, is highly recommended.
21 Page 21 of 21 Home inspectors are not required to report on the following: Life expectancy of any component or system; The causes of the need for a repair; The methods, materials, and costs of corrections; The suitability of the property for any specialized use; Compliance or non-compliance with codes, ordinances, statutes, regulatory requirements or restrictions; The market value of the property or its marketability; The advisability or inadvisability of purchase of the property; Any component or system that was not observed; The presence or absence of pests such as wood damaging organisms, rodents, or insects; or Cosmetic items, underground items, or items not permanently installed. Home inspectors are not required to: Offer warranties or guarantees of any kind; Calculate the strength, adequacy, or efficiency of any system or component; Enter any area or perform any procedure that may damage the property or its components or be dangerous to the home inspector or other persons; Operate any system or component that is shut down or otherwise inoperable; Operate any system or component that does not respond to normal operating controls; Disturb insulation, move personal items, panels, furniture, equipment, plant life, soil, snow, ice, or debris that obstructs access or visibility; Determine the presence or absence of any suspected adverse environmental condition or hazardous substance, including but not limited to mold, toxins, carcinogens, noise, contaminants in the building or in soil, water, and air; Determine the effectiveness of any system installed to control or remove suspected hazardous substances; Predict future condition, including but not limited to failure of components; Since this report is provided for the specific benefit of the customer(s), secondary readers of this information should hire a licensed inspector to perform an inspection to meet their specific needs and to obtain current information concerning this property. Prepared Using HomeGauge SHGI (c) : Licensed To Decker Home Services, LLC
Page 1 of 14 Inspection Report Mr. John Homebuyer Property Address: 123 Main Street Houston TX 77007 Front View EDP Consulting Engineers, PLLC Gerald C. Reece, PE TREC #7825 14119 Willowsong Ct Missouri
Page 1 of 35 Inspection Report Mr. Happy Property Address: Joseph Poelsterl 450.010220 6334 W. Grace st Chicago Illinois 60634 1-773-454-6700 Page 2 of 35 Table of Contents Cover Page Table of Contents
Inspection Report Mr. Sample Sample Property Address: 1234 USA Drive Indianapolis IN 12345 1234 USA Drive Morris Home Inspection Group, LLC Cedric Morris HI01200039 Fishers, IN 46037 317-550-6281 Table
Page 1 of 25 Inspection Report Atlanta Strip Mall Property Address: Smyrna GA 30082 Page 2 of 25 South East Building Consultants Ray Thoroman Serving the entire State of Georgia 6 678-410-3005 Page 3 of
Summary of Oregon Home Inspector Certification Law and Standards of Practice for Home Inspections This is a summary of your rights and responsibilities when having a home inspection done by an Oregon certified
Page 1 of 24 Inspection Report Ms. Laurie Property Address: Spencer Oklahoma 73084 AAOK Home Inspections LLC Donald I. McCreary 70001429 3413 Terry Way Del City, OK 73115 405-778-4488 Page 2 of 24 Table
Page 1 of 53 Inspection Report Jacksonville Property Address: Jacksonville FL 32204 South East Building Consultants Ray Thoroman Inspecting Jacksonville FL and entire South East Page 2 of 53 Table of Contents
To be used as a first home visit for note taking. Visit www.homeinspectiondirect.com for more tips and information about buying a home and hiring a home inspector. This form in no way replaces a professional
STATE OF FLORIDA HOME INSPECTION STANDARDS OF PRACTICE: 61-30.801 Standards of Practice, General. (1) Home inspections performed to these Standards of Practice are intended to provide the client with information
Page 1 of 58 Inspection Report Prepared For: Atlanta Commercial Customer Property Address: Building 5 Marietta, GA 30066 Superior Home Inspections Ray Thoroman 8070 Ivy Shaw Dr. Gainesville,GA 30506 678-410-3005
Vision Home Inspection 324 Rams Run Shepherdsville KY 40165-7877 Inspector: James McFadden Property Inspection Report Client(s): Property address: Inspection date: View report summary This report is the
Inspection Report Justin Property Address: 987 Bluffs Drive Thistown Ia 65765 JP's Home Inspection Services Jeff Peiffer 925 46th St. Sioux City, Ia 51104 (712) 301-8220 987 Bluffs Drive Page 2 of 23 Table
Inspection Report Mr. JOHN SMITH Property Address: 12345 S. Main St Denver Co 12349 A Happy House Home Inspection, LLC Hans Coleman Centennial, Co 80015 720-988-4830 Table of Contents Cover Page...1 Table
Report for Dick and Jane Homeowner 1234 Lovers Lane, Houston, Texas 77000 March 17, 2004 I NI NP R Inspection Item I. STRUCTURAL SYSTEMS o o o A. Foundations (If all crawl space areas are not inspected,
Total Home Inspection Checklist Use a checklist like this to make sure that you are looking at all parts of the house. Check off those items that are in good condition and make notes about those that are
Rehab Inspection Report Page 1 Home Address: Construction Style: Number of bedrooms Square footage: Value of offer: Estimated rehab cost: Value of resale: Orientation of house: N S E W Note: orientation
Inspection Report Sample Property Address: XXXX N. Atolia Drive Tucson AZ 85743 House and Home Brian Pemble #45238 6909 E. Kingston Drive Tucson, AZ. 85710. 520-245-7897 Table of Contents Cover Page...1
(850) 297-1998 1716 Monticello Dr Tallahassee, Florida 32303 PROPERTY INSPECTION REPORT THIS INSPECTION IS A DETAILED LISTING OF AREAS VISUALLY INSPECTED AT:, Tallahassee FL Client Tallahassee, FL 32304
SECTION.1100 - NC HOME INSPECTOR STANDARDS OF PRACTICE AND CODE OF ETHICS.1101 DEFINITIONS The following definitions apply to this Section: (1) Automatic safety controls means devices designed and installed
South Carolina Home Inspector Standards of Practice The following Standards provide guidelines for the Residential Home Inspector and outline what the Residential Home Inspector should observe, identify,
Inspection Report Property Address: St. Marks Ave. Brooklyn NY 11213 Five Borough Home Inspection, LLC Derek Lomer NYS Licence Lic # 16000051234 790 Washington Ave., Unit 112 Brooklyn, NY, 11238 917-494-8474
CONDITION OF QUALITY ITEMS FOUNDATION Always look for moisture problems and any bulges or irregularities in the walls. Lines on the walls or floors may indicate water problems. Have these been cured? If
SC Standards of Practice SOUTH CAROLINA RESIDENTIAL BUILDERS COMMISSION HOME INSPECTOR STANDARDS OF PRACTICE Adopted by the Residential Builders Commission May 13, 1998 PURPOSE: The purpose of a residential
105 Dixie Dr., Chapel Hill, NC 27514 page1 of 32 Inspection Report Mr. John Cauthen Property Address: 105 Dixie Dr. Chapel Hill NC 27514 First Call Home Inspections LLC John B. Cauthen 8004 Morrell Lane,
Texas Premier Homes LIMITED BUILDER S WARRANTY COVERAGE AIR CONDITIONING LIMITED WARRANTY: Performance When air conditioning is included in the home, the system should be capable of maintaining a temperature
HEDDERMAN ENGINEERING, INC. www.heddermanengineering.com Office 281-355-9911, Fax 281-355-9903 email@example.com, 2011 TO: Mr. REF: CONDITION OF PROPERTY SURVEY Dear Mr. : At your request,
KPA The Joint Venture of EBA Engineering, Inc. and Kennedy Porter & Associates, Inc. 4813 Seton Drive, Baltimore, MD 21215 Phone: (410-358-7171) Fax: (410)358-7213 Building Condition Assessment: Baltimore,
Inspection Report Mr. Sample Customer Property Address: 1234 Sample Street Castle Rock Co 80000 1234 Sample Street, Castle Rock, CO 80000 Seven Stars Home Advisors Chad Chadwick 6839 W. Jackson Cr Rd Sedalia,
South Carolina Home Inspector Standards of Practice The following Standards provide guidelines for the Residential Home Inspector and outline what the Residential Home Inspector should observe, identify,
New Jersey Property Inspections LLC NJ State Home Inspector License # 24GI00105100 27 Neshanic Drive, Ringoes NJ 08551 908-642-2112/908-788-0055 PRE-INPECTION AGREEMENT READ THIS DOCUMENT CAREFULLY. IT
Inspecton Report Provided by: National Home Inspections Inspector: Bob Smith 456 S Main Denver, CO 46312 (645) 423-3242 firstname.lastname@example.org www.nationalhomeservices.com Property Address: 873
Edgewood Home Inspections, Inc. 407 W. Smith Valley Rd. #1032 Greenwood, IN 46142 (317) 833-6048 HOME INSPECTION REPORT Indianapolis IN 46000 Inspector's Name: License Number: Scott Kissel HI00800073 TABLE
Having inspected about 800 homes in the last four years, I have seen a lot of problems with many homes. Most of these problems are minor; however, there are some problems that are quite serious. One of
www.citiesinspection.com October 5, 2015 Dear Client, On 9/14/2015, Cities Inspection Service, Inc. completed a building inspection of the property located at 123 Oak Street, Someplace, Minnesota for you.
Inspection Report Ms. Onah Holmes 123 Maple Street Springfield, Ontario 123 Maple Street Page 2 of 30 Cover Page Table of Contents Table of Contents Intro Page 1 Roof 2 Exterior 3 Basement, Foundation,
SM MEDALLION INSPECTIONS helping people make informed decisions Pre-Drywall Inspection Report 5657 Garden Valley Place Milton, Georgia 30024 Prepared for Betsy and Paul Dougherty January12, 2015 Medallion
Home Inspection Report Report Number: 144 For The Property Located On: 123 Any Street 27587 Prepared For Exclusive Use By: Mr. Sample N/A,,, Report Prepared By: Edward Carapezza; License No.: 3447 Inspector
HEDDERMAN ENGINEERING, INC. 3011 Carrie Cove Ct., Spring, TX 77386 281-355-9911, fax 281-355-9903 Tim@heddermanengineering.com 2007 TO: Mr. REF: CONDITION OF PROPERTY SURVEY Dear Mr. : At your request,
COMPREHENSIVE PROPERTY INSPECTIONS Thank you for selecting CPI for your Deficiency Observation. A full home inspection was not performed on this property at the buyers request. This inspection is a limited
Page 1 of 37 Inspection Report Prepared For: Sampath Sample Property Address: Alpharetta, GA 30004 Atlanta Home Inspections Matthew A Thoroman 6625 Hwy. 53 E. Ste. 410-151 Dawsonville Ga 30534 (678)-410-8062
PROFESSIONAL ENGINEERING INSPECTIONS, INC. P. O. BOX 271492 HOUSTON, TEXAS 77277 Registered Engineering Firm #1503 http://www.profengineering.com (713) 664-1264 July 8, 2004 Mr. Simple Samson 2831 Octoberfest
ASHI STANDARD OF PROFESSIONAL PRACTICE FOR HOME INSPECTIONS 1. INTRODUCTION 1.1 This ASHI Standard of Professional Practice for Home Inspections (Standard) defines the scope of home inspections performed
A.C.E. Home Inspection Service www.acehomeweb.com St. Peters, MO 63376 (636) 978-9111 Inspector Name: Tim Knight, ASHI Member 202490 Inspection No: 12121212 Inspection Date: 1/1/2012 Client: Address: John
Report# 21009 Page 1 of 24 Home Inspection Report Property Address: 123 Maple Lane, St. Augustine, FL 32092 Prepared For: Mr. Smith Prepared By: EDGE Inspections www.edgeinspections.com PO Box 601055 Jacksonville,
PROPERTY INSPECTION OR ASSESSMENT OF DAMAGES ADDRESS: Somewhere, FL CLIENT: GAIA GC ID No: 2015000 DATE: 12/31/2015 INSPECTION OR ASSESSMENT BY: GAIA CONSTRUCTION INC. CGC 1516136 FLORIDA HI-2792 FLORIDA
117 S. Market St. Benton, AR 72015 * 501-315-2626 * Fax 501-315-0024 October 30, 2014 Mr. & Mrs. Daniel Vick 101 Southwind Cove Benton, AR Re: Report of Findings,, Benton, Arkansas, Dear Mr. Vick: This
Structure Survey Findings: Visible portions of the following were observed: foundations; structure to walls, columns, floors, roofs, overhang posts, and columns; attached or firmly abutting decks, balconies,
6/ /07 The Inspection of the property listed above must be performed in compliance with the rules of TREC. The inspection is of conditions which are present and visible at the time of the inspection, and
CLIENT Inspection Report 271 Front St. Alert Bay, B.C. Island Building Inspections 2013 V ANCOUVER I SLAND B. C. Elevation Photos For the Property at 271 Front Street Alert Bay, BC ELEVATION PICTURES Front
535.228. Standards of Practice: Minimum Inspection Requirements for Structural Systems (a) Foundations. The inspector shall: (1) inspect slab surfaces, foundation framing components, subflooring, and related
NOTICE - Read Entire Report Carefully. This is not a Buyer's Inspection! Current Owner Name: Mpls City Property Atn Cped (p Contact: Mpls City Property Atn Cped (p Business/Relationship: Owner Address:
PROPERTY INSPECTION PROFESSIONALS May 5, 2010 Client Client Address Re: Inspection Address, Chicago, Illinois Dear Mr. Client, On May 4, 2010, Tomacor completed a property inspection of the above referenced
A bout your HOUSE before you start Repairing And Replacing Materials Exterior Walls CE 28 h Exterior finish materials are expected to protect the house from the elements while providing an attractive appearance.
Building Inspectors Building Consultants Environmental Specialists 101 HARBOR LANE WEST NEW ROCHELLE, NY 10805 vvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvvv
Cover Page Property Inspection Report My street, Anytown GA, 30000 Inspection prepared for: John Doe Inspection Date: 7/18/2011 Time: 5pm Age: 25+ Size: >1500 Weather: Clear This ranch style home is in
RULES OF TENNESSEE DEPARTMENT OF COMMERCE AND INSURANCE DIVISION OF REGULATORY BOARDS CHAPTER 0780-5-12 HOME INSPECTORS TABLE OF CONTENTS 0780-5-12-.01 Purpose 0780-5-12-.07 Qualifying and Continuing Education
Page 1 of 33 Inspection Report Joe and Sue Property Address: Bothell WA 98011 Transparent Inspections Austin McFeeley 13221 Meridian Ave S Unit A Everett WA 98208 425-773-6637 Page 2 of 33 Table of Contents
Cleveland Cuyahoga County Healthy House Project Training Integrating Healthy Housing Considerations into Weatherization Inspections Jim LaRue Joint inspections for housing health hazards Weatherization
Inspection Report Property Address: 1234 Anywhere street Phoenix AZ Veteran Inspection Professionals Mark Mandery 040901 4725 W. Aire Libre Ave Glendale AZ, 85306 480-694-2111 Table of Contents Cover Page...1
Cover Page Vari Inspection Services Property Inspection Report Inspection prepared for: Sample Real Estate Agent: None - Date of Inspection: 5/13/2015 Inspector: Tony Vari License # HI8047 23110 STRD 54
#1) BEFORE Purchasing Land Here Is A Checklist Of Things You Should Check Zoning laws Deed restrictions on home size, foundation style, roof pitch, etc. Suitability (slope, wetland issues, etc.) Accessibility
Page 1 of 14 Article I. SECTION 1.01 INTRODUCTION PREFACE THE INTERNATIONAL SOCIETY OF HOME INSPECTORS, INC. (ISHI) IS A NOT-FOR-PROFIT PROFESSIONAL SOCIETY ESTABLISHED IN 1995. MEMBERSHIP IN ISHI IS VOLUNTARY
STATE OF SOUTH CAROLINA RESIDENTIAL PROPERTY CONDITION DISCLOSURE STATEMENT The South Carolina Code of Laws (Title 27, Chapter 50, Article 1) requires that an owner of residential real property (single
Inspection Date: Inspector: Building Information Building ID: No.: Used For: Year Roof Applied: Building Description: Permanent Temporary Building Type: Retail Industrial Residential Building Name: Building
Crawford Inspection Services C.C.B. # 76914 www.crawfordinspections.com Portland Area PO Box 665 West Linn, OR 97068 Ph: (503) 650-6957 Salem Area 5434 River Rd. N; #192 Keizer, OR 97303 Ph: (503) 362-5809
BUILDING ANALYSIS REPORT July 25, 2014 John Doe 1234 Smith Road Atlanta, Georgia 30396 Agent: Ausker and Barbara Morris AT Morris Realty Group, Inc. 3162 Johnson Ferry Road, Suite 260-25 Marietta, Georgia
APPENDIX 9 AFFORDABLE HOUSING PROGRAM INSPECTION CHECKLIST Participating Jurisdiction: Homeowner Name: Assisted Property Address: Date of Physical Inspection of Property: Total Square Footage of Property:
BOROUGH OF NATIONAL PARK APPLICATION FOR A CERTIFICATE OF OCCUPANCY FOR CHANGE OF OCCUPANCY ADDRESS OF PROPERTY FOR INSPECTION # BLOCK LOT VACANT YES NO CURRENT OWNER NAME ADDRESS TELEPHONE # PROSPECTIVE
Date: March 7, 2006 Report for [removed] The Preservation Resource Center Of New Orleans, in conjunction the National Trust for Historic Preservation, has conducted a condition survey of your property.
Water Management & Damage Prevention: A Guide for Homeowners This article provides homeowners with basic information to make these decisions and take the appropriate actions to keep their homes dry and
Exterior Elevated Elements Inspection Guidelines Planning and Development 1. Guideline Purpose These guidelines are intended to assist practicing professionals in complying with Berkeley Municipal Code
THE DISTRICT MUNICIPALITY OF MUSKOKA ONTARIO RENOVATES PROGRAM FOR HOMEOWNERS ELIGIBLE REPAIR PROJECT PARAMETERS 1. To have your project considered and payment processed, all projects requiring a Building