3.1. Lecture 3 Power Transformers. limb. yoke. Power Transformers. Core structures. Winding connections. Equivalent circuits.


 Roderick Alexander
 2 years ago
 Views:
Transcription
1 3.1 Lecture 3 ower ransformers Core structures. Winding connections. Equivalent circuits. ower ransformers Core tructures of hreehase ransformers threephase transformer can be considered to be some combination of singlephase transformers, either as three separate units, or as a single unit with three sets of phase windings on a common magnetic core. single unit construction permits some considerable saving of materials, and is therefore the usual option. Using three separate singlephase units is sometimes necessary for very large transformers to overcome weight and size limitations of transport. While the three separate singlephase units cost more than the equivalent threephase unit, there is a saving in the cost of the spare transformer, usually mandatory for the security of supply. he standard configurations of threephase cores are: (a) hreelimb Core his is the most common arrangement, and uses the least amount of core material. he parts of the core joining the three limbs are known as the yokes. B C yoke limb Figure 3.1 hreelimb core
2 3. (b) FiveLimb Core In the threelimb arrangement the yokes have the same crosssectional area as the limbs. With two extra unwound limbs the top and bottom yokes can be reduced to half the crosssection of the three wound limbs. he unwound limbs also need to have only half the crosssection of the wound limbs, so the extra steel required for the unwound limbs comes mainly from the steel saved in the yokes. B C Figure 3. Fivelimb core he lower profile yokes lead to a reduction of height. herefore the fivelimb core is commonly used in large transformers, where the transport height is an important design limitation. Both of the arrangements (a) and (b) are known as core type, as opposed to the shell type below.
3 3.3 (c) hell ype Core his type uses almost as much core steel as three separate cores. It does have a design advantage of permitting winding construction with well supported coils, to provide mechanical strength to withstand shortcircuit forces. he shell type arrangement is comparatively rare, and used only for very large transformers. B C Figure 3.3 helltype core Winding Connections of hreehase ransformers he basic connections are delta, star, and zigzag (interconnected star). ny combination of these basic winding connections, with variations in polarities, may be found in a transformer. he connections of a particular transformer are indicated by a connection symbol, sometimes called a vector symbol. he possible connections result in various inherent phase displacements between primary and secondary voltages. he standard phase displacements are 0, 180, 30 and +30, but other values are possible (e.g. with the zigzag connection, or with a delta autotransformer).
4 3.4 he connection symbol for a twowinding transformer is composed as follows: HV symbol D for delta Y for star for zigzag HV neutral symbol if neutral terminal is accessible LV symbol d for delta y for star z for zigzag LV neutral symbol n if neutral terminal is accessible hase displacement symbol 0 for 0 6 for for for +30 he phase displacement symbol is a clock hour figure showing the position of the equivalent star voltage phasor for the LV winding, with the corresponding HV phasor in the reference position of zero or 1 o clock. Examples Yyn0 = starstar, HV neutral not available, LV neutral available, zero phase displacement. Yzn1 = HV star, HV neutral available, LV zigzag, LV neutral available, LV lags HV by 30. For multiwinding transformers the HV winding (the highest voltage) remains the reference for phase displacement, and its symbol is written first. Other symbols follow in diminishing order of rated voltages, and preferably separated with commas for clarity. Example transformer has three windings: 13 kv star (HV) with neutral brought out 36 kv star, in phase with HV, with the neutral brought out 7. kv delta, leading the HV by 30 he connection symbol for this transformer is: Y, yn0, d11.
5 3.5 For autotransformers, in which the two windings have a common part, the letter a is used to designate the lower voltage of the autoconnected pair, and is placed immediately after the symbol for the higher voltage of the pair. hreephase autotransformers are usually star connected. Examples D, yn11, a11 separate high voltage delta winding, and an intermediate to low voltage star autotransformer. he intermediate and low voltages lead the high voltage by 30. Y, a0, d1 HV autoconnected star winding with the neutral terminal brought out, and a separate delta winding. he equivalent star voltage of the delta winding lags the HV by 30. Diagram of connections as follows: B C a 4 B4 C4 C c b B 3 a a1 B3 b C3 a b c c b1 c B 3C 3C 31 3B1 3C1 3B
6 3.6 Reference and erminology 374 ower ransformers, art 4 appings and Connections (198) is the relevant ustralian tandard that deals with transformer winding connections. In 374 the term winding, for threephase transformers, refers to the three phase windings associated with one of the voltages assigned to the transformer. Hence the terms high voltage winding, low voltage winding, and intermediate voltage winding for the main windings of a transformer. hese terms, unlike primary and secondary do not imply any set direction of power flow. It is customary to add a third deltaconnected auxiliary winding to all large starstar transformers to decrease the zero sequence impedance. his third winding is generally known as the tertiary winding, although 374 does not use the term. Generally the tertiary winding has a lower MV rating than the main windings. he tertiary winding, if its terminals are brought out, can also be used to supply a small load.
7 3.7 Equivalent Circuits of ower ransformers inglehase ransformers (a) Ideal ransformers Many power transformer problems can be solved with sufficient accuracy by treating the transformers as ideal: I I V V Figure 3.4 wowinding ideal transformer For the twowinding ideal transformer: V V (3.1) I I (3.)
8 3.8 he threewinding ideal transformer is represented by: I I V V I V Figure 3.5 hreewinding ideal transformer and has ideal equations: V V V (3.3) I I I (3.4) Let: a primary to secondary turns ratio (3.5) a primary to tertiary turns ratio (3.6)
9 3.9 hen: econdary voltage referred to the primary V a V (3.7) ertiary voltage referred to the primary V a V (3.8) econdary current referred to the primary I I a (3.9) ertiary current referred to the primary I I a (3.10) Hence, for the ideal transformer: V V V (3.11) I I I (3.1) and the equivalent circuit, in terms of the referred values, is shown below: I I' V V' I' V' Figure 3.6 hreewinding ideal transformer with referred values
10 3.10 (b) ractical ower ransformers ractical transformers have significant leakage reactance X L and resistance R L. hey also draw magnetising current, but for most power system calculations this can be ignored. herefore we use the simplified equivalent circuits shown below for two and threewinding transformers. he equivalent circuit for a twowinding power transformer is: I = I' R L jx L V V' Figure 3.7 Equivalent circuit of a twowinding power transformer When using perunit values the term referred to the primary is superfluous, and we can replace V and I with V and I respectively. he equivalent circuit for a threewinding power transformer is: I R jx R jx I' V V' R jx I' V' Figure 3.8 Equivalent circuit of a threewinding power transformer
11 3.11 he equivalent circuit impedances: R R R jx jx jx (3.13) are not directly measurable, and have no physical meaning. hey are merely abstract components of the equivalent circuit. he measurable impedances are: (3.14) olving the simultaneous equations (3.14) gives: (3.15) where: (3.16) In the interest of generality we should note that transformer windings also have some effective capacitance. he capacitance is important in some types of transformer (e.g. high voltage testing transformers), but can be safely ignored in power transformers, as long as we are concerned only with steadystate performance.
12 3.1 hreehase ransformers ositive equence Equivalent Circuits For power system calculations the equivalent circuits of threephase transformers are drawn as one phase of the equivalent star network. he ratio a (for example) of a threephase transformer is the unloaded voltage ratio. Whether this is the true turns ratio depends on the winding connections. lso, an inherent phase displacement may be involved. hus we can regard the ratio a as a complex number. Example Consider a 33 / 11 kv Yd1 transformer. he HV winding is nominated as the primary. he voltage ratio , but the turns ratio of the windings is he clock hour figure = 1, therefore the LV lags the HV by 30, 11 or HV leads the LV by 30. Hence the complex ratio 330. he positive sequence diagram is drawn in terms of perunit quantities as follows: a HL I 1 I a a 30 V V a 1 = L = R L + jx L = the leakage impedance Figure 3.9 ositive sequence equivalent circuit of example transformer he subscripts and a refer to the HV and LV windings ( a phase). hese could be replaced by (1) and a(1) respectively to emphasize that the circuit is valid only for positive phase sequence.
13 3.13 hreehase ransformers egative equence Equivalent Circuits he negative sequence impedance of a transformer, because it is a passive component, always equals the positive sequence impedance, which is the leakage impedance of the windings. While the impedance is independent of the direction of phase rotation, reversing the phase rotation reverses the sign of the phase angle in the complex ratio. herefore the negative sequence equivalent circuit is obtained by reversing the sign of any phase shifters in the positive sequence equivalent circuit. For the transformer in the previous example, this illustrated in the following diagram: I () = 1 I a () a 30 V () V a () Figure 3.10 egative sequence equivalent circuit of example transformer
14 3.14 hreehase ransformers ero equence Equivalent Circuits Of all the standard core constructions the threelimb core is an exception in that it does not provide a closed iron path for the zero sequence flux. his fact introduces complications which we will ignore at first, and consider in a later section. fundamental difference between zero sequence and positive sequence performance of a transformer is the inherent phase displacement. With the usual standard connections, which have positive sequence phase displacements of 30, 0, or +30, the corresponding zero sequence phase displacement is always zero, and no phase shifters appear in the equivalent circuit. second difference is that the configuration of the zero sequence path(s) through the transformer may be different to the positive sequence path(s). he zero sequence paths depend on connections to each winding. We can construct a partial equivalent circuit for each type of winding connection, then put them together to match the configuration of the particular transformer. (a) tar Winding without eutral Connection If the neutral terminal is not used, then there is no path for the zero sequence currents, and the winding must be opencircuited in the zero sequence equivalent circuit: 0 to other winding(s) Figure 3.11
15 3.15 (b) tar Winding with eutral Earthed Directly ormal transformer action operates, and 0 1 = leakage impedance. 0 to other winding(s) Figure 3.1 (c) tar Winding with eutral Earthed via an Impedance = neutral earthing impedance and 0 1 = leakage impedance. 3 0 to other winding(s) Figure 3.13 (d) Delta Winding here is a closed zero sequence loop around the delta, but no zero sequence current can enter or leave via the line terminals. hus the winding is opencircuited as seen from the line terminals, but shortcircuited internally. 0 1 = leakage impedance. 0 to other winding(s) Figure 3.14
16 3.16 (e) igag Winding with eutral Earthed Directly he zigzag connection is shown below: B C B I I B I C 4 B4 C4 3 B3 C3 C B C 1 B1 C1 Figure 3.15 igag Winding Connection Windings 1 and 34, turns each, are wound on the limb of the magnetic circuit. Other limbs are wound similarly. hen the mmf produced by each winding is: F F F B C I I I B C I I I C B (3.17)
17 3.17 For positive sequence currents: F F F B C I I I 1 h h h h I 70 I I (3.18) he core mmfs lag the line currents by 30, which is the same as for a delta winding. For zero sequence currents: F F B F C 0 (3.19) here is no zero sequence mmf, hence no zero sequence flux, and no coupling to other windings. he zero sequence impedance 0 in this case is the leakage impedance between the subwindings 1 and to other winding(s) Figure 3.16
18 3.18 Example ero sequence network for a HV star to LV delta transformer. HV neutral solidly earthed. 0 a 0 1 = leakage impedance Example ero sequence network for a starstar transformer with delta tertiary winding. HV neutral solidly earthed, LV neutral earthed via impedance 3 a n a n. HV LV ertiary, a and are leakage impedances identical to those in the positive sequence circuit.
19 3.19 Effect of hreelimb Core on the ero equence Equivalent Circuits he threelimb core does not provide a closed path for the zero sequence flux, which has to return via a high reluctance path outside the steel core: Winding 1 Core Flux path in air Winding Figure 3.17 Flux path for a hreelimb ransformer he magnetic equivalent circuit is: F R 0 R core 3 R airgap 1 F 1 R 1 Figure 3.18 Magnetic equivalent circuit for a hreelimb ransformer he equivalent electric circuit can be derived directly from the magnetic circuit by the topological principle of duality. his topological technique is demonstrated in Figure node is marked within each mesh of the
20 3.0 magnetic circuit, and a reference node is marked outside the circuit. hese nodes are then joined by branches, one of which passes through each element of the magnetic circuit. For each reluctance in a mesh of the magnetic circuit, there is an inductance connected to the corresponding node of the electric circuit. Where a reluctance is common to two meshes in the magnetic circuit, the corresponding inductance connects the corresponding nodes of the electric circuit. For each magnetomotive force there is a corresponding emf between nodes. he electric equivalent circuit is therefore: 1 L 1 3 L V 1 L core L airgap V 0 Figure 3.19 Equivalent circuit of a threewinding power transformer where: V 1 primary voltage V secondary voltage L primary leakage inductance L L L 1 core secondary leakage inductance core magnetising inductance airgap airgap magnetising inductance (3.0) he large effective airgap makes the magnetising impedance much lower, and much more linear, than would be the case without the airgap. ctually L core has little effect, and L airgap dominates the magnetising impedance.
21 3.1 he low magnetising impedance has the same effect as a delta tertiary winding (of relatively high impedance) by providing an additional path to the zero sequence currents. he effect is further accentuated when the transformer with the threelimb core is placed in a metal tank. he tank forms a shortcircuited turn around a portion of the zero sequence flux, acting as another weakly coupled delta winding. s shown in Figure 3.19, the zero sequence performance of the threelimb core type transformer can not be adequately described by a single impedance, but requires three impedances in a (or equivalent ) network. In practice, the impedances required to construct the network may not be known, and in any case, the calculation is inaccurate because of nonlinearities. Reasonable results can generally be obtained by ignoring the effect of the threelimb core. notable exception is the case of a starstar transformer with one neutral floating. Example ero sequence network for a HV star to LV star transformer on a threelimb core. HV neutral solidly earthed, LV neutral not connected. a 0 (o.c.) here is no zero sequence path through the LV winding. he zero sequence opencircuit impedance is seen from the HV side. 0o.c. is predominantly a magnetising impedance, significant for a threelimb core, but practically infinity for other types. With threewinding transformers the effect of the threelimb core gets more complicated. With reference to the previous threewinding example, one might be tempted to add a magnetising impedance to the junction of the three partial leakage impedances, a and, but this does no give a valid equivalent circuit, which would require at least six impedances.
22 3. bility to upply Unbalanced Loads (a) inglephase linetoline load ssume a load between lines b and c. We can solve the problem by treating the load as a linetoline fault, and use the method of sequence networks to find the shortcircuit current I C : I C 3E 3E 1 1 j j 1 (3.1) 1 1 he opencircuit voltage is: V OC j 3E 1 (3.) Hence, the source impedance (by hévenin s heorem) is: V (3.3) OC source 1 I C ince 1 is always small the transformer has no difficulty in supplying the singlephase linetoline load.
23 3.3 (b) inglephase linetoneutral load ssume the load is on phase a. We can solve the problem by treating the load as a linetoearth fault, and the method of sequence networks to find the shortcircuit current I C : I C 3E 3E (3.4) 1 he opencircuit voltage is: V OC E 1 (3.5) Hence, the source impedance (by hévenin s heorem) is: source VOC 0 1 (3.6) I C 3 problem arises if 0 is large, e.g. if the neutral of a starstar transformer is not earthed. ot only does the voltage then collapse on the loaded phase because of excessive source impedance, but overvoltages are produced on the other two phases. In the extreme case (infinite 0 ) the magnitude of the voltages on the unloaded phases becomes 3 p.u.
24 3.4 ummary he different core constructions of threephase transformers lead to different electric and magnetic equivalent circuits, and therefore transformer behaviour. he effect of the winding connections of a transformer also affects its behaviour. he positive and negative sequence equivalent electric circuits of a transformer consist entirely of leakage impedance, but may involve a phase shift (depending on winding connections). he zero sequence equivalent electric circuits for a transformer are highly dependent on the winding connections. he threelimb core transformer has a equivalent zero sequence equivalent electric circuit, but in practice we ignore the effect of the threelimb core (unless the neutral of a starstar transformer is left floating). ransformers generally have no difficulty supplying singlephase linetoline loads. ransformers with large zero sequence impedances have difficulty supplying singlephase linetoneutral loads the voltage tends to collapse on the loaded phase and overvoltages occur on the other two. References Carmo, J.: ower Circuit heory otes, U, ruupold, E.: ower Circuit heory otes, U, 1993.
25 3.5 Exercises 1. For the shell type transformer shown, determine the magnitude of fluxes x ower transformers and y given that symmetrical 3phase voltages are applied to the windings, taking the main flux a to be 1 p.u. x y B C (a) With winding polarities shown. (b) With B phase wound in the same direction as and C.. singlephase threewinding transformer has the following ratings: HV LV V 10 kv, 400 kv 600 V, 400 kv 1. kv, 100 kv he transformer is fed from the LV side at 600 V. he V winding is loaded with a 15 resistor, and the HV winding is connected to a capacitive reactance of 60. Use ideal transformer modelling to determine: (a) ll three winding currents. (b) kv loading of each winding.
26 kv singlephase 800 V / 00 V transformer has leakage impedance of 1. j.0%. It is reconnected as a 800 V / 1000 V autotransformer. (a) What is the new kv rating? (b) What is the leakage impedance based on the new ratings? 4. singlephase 75 kv transformer has three windings 1,, & 3, rated at 400, 600 & 40 V respectively. hortcircuit test gave the following results: (i) Winding shorted, winding 3 open: I 31.5, V 10 V, 750 W (ii) Winding 3 shorted, winding open: I 31.5, V 135 V, 810 W (iii) Winding 3 shorted, winding 1 open: I 15.0, V 30 V, 815 W 1 Determine the constants, expressed as percent values, of the equivalent circuit for this transformer. eglect the excitation current and corrections for temperature.
27 singlephase transformer is rated 60 Hz, 100 kv, 1300 V / 00 V, and at those ratings has an impedance of 0.39 j6.1%. (a) What would happen if a second identical transformer were to be connected in parallel, but by mistake one of its windings had reverse polarity? ssume the 60 Hz HV supply maintains a constant voltage at 13. kv. (b) What would happen if the transformer were to be used at rated voltage in a 50 Hz system? (c) he transformer is to be connected to a 50 Hz 11 kv network. (i) What kv rating would you now assign to the transformer? (ii) What is the percent impedance at the revised rating? 6. he rating plate of a 375 MV transformer gives the following information: Winding Rated kv Rated MV Impedances on 375 MV base on principal tapping HV HVLV 16.47% LV HVV 47.37% V 11 5 LVV 9.64% Connection symbol: Y,a0,d1 a) ketch a circuit diagram, ignoring facilities for tap changing, but showing main winding connections and polarities. b) Calculate the complex ratios: HV / LV, HV / V, LV / V. c) ketch the positive sequence equivalent circuit, and calculate its component impedances. ssume all resistances and the noload current are negligible.
28 he transformer in Q6 delivers 100 MW 0 Mvar to the 13 kv bus at nominal voltage. he 11 kv winding is connected to a capacitor bank rated at 5 Mvar, 11 kv. Calculate the magnitude and phase of all line and phase currents, taking the a phase of the 13 kv bus as the reference. lso calculate the megawatts and megavars taken from the 330 kv bus. 8. For the transformer in Q6: (a) ketch the negative sequence equivalent circuit. (b) ketch the zero sequence equivalent circuit, assuming the neutral to be solidly earthed. 9. threephase 500 kv 33 kv / 500 V transformer has an impedance of 0.39 j6.1%. Calculate: (a) he maximum kv the transformer can supply to a single phase linetoline connected load at 500 V without exceeding the rated current. (b) he regulation with a single phase load as in (a), when the load power factor is: (i) 0.9 lagging (ii) 0.9 leading
Three phase circuits
Three phase circuits THREE PHASE CIRCUITS THREEPHASE ADVANTAGES 1. The horsepower rating of threephase motors and the kva rating of threephase transformers are 150% greater than singlephase motors
More informationFunctions, variations and application areas of magnetic components
Westring 18 3314 Büren Germany T +49 951 60 01 0 F +49 951 60 01 3 www.schaffner.com energy efficiency and reliability 1.1 Transformers The transformer is one of the traditional components of electrical
More information2. A conductor of length 2m moves at 4m/s at 30 to a uniform magnetic field of 0.1T. Which one of the following gives the e.m.f. generated?
Extra Questions  2 1. A straight length of wire moves through a uniform magnetic field. The e.m.f. produced across the ends of the wire will be maximum if it moves: a) along the lines of magnetic flux
More informationPower Technology Issue 106. Modeling of ThreeWinding Voltage Regulating Transformers for Positive Sequence Load Flow Analysis in PSS E
SIEMENS Siemens Energy, Inc. Power Technology Issue 106 Modeling of ThreeWinding Voltage Regulating Transformers for Positive Sequence Load Flow Analysis in PSS E Carlos GrandeMoran, Ph.D. Principal
More informationSYNCHRONOUS MACHINES
SYNCHRONOUS MACHINES The geometry of a synchronous machine is quite similar to that of the induction machine. The stator core and windings of a threephase synchronous machine are practically identical
More informationDigital Energy ITI. Instrument Transformer Basic Technical Information and Application
g Digital Energy ITI Instrument Transformer Basic Technical Information and Application Table of Contents DEFINITIONS AND FUNCTIONS CONSTRUCTION FEATURES MAGNETIC CIRCUITS RATING AND RATIO CURRENT TRANSFORMER
More informationTHE PERUNIT SYSTEM. (2) The perunit values for various components lie within a narrow range regardless of the equipment rating.
THE PERUNIT SYSTEM An interconnected power system typically consists of many different voltage levels given a system containing several transformers and/or rotating machines. The perunit system simplifies
More informationPower Technology Issue 104. Modeling of TwoWinding Voltage Regulating Transformers for Positive Sequence Load Flow Analysis in PSS E
SIEMENS Siemens Energy, Inc. Power Technology Issue 104 Modeling of TwoWinding Voltage Regulating Transformers for Positive Sequence Load Flow Analysis in PSS E Carlos GrandeMoran, Ph.D. Principal Consultant
More informationDHANALAKSHMI COLLEGE OF ENGINEERING DEPARTMENT OF ELECTRICAL AND ELECTRONICS ENGINEERING EE2302  ELECTRICAL MACHINES II UNITI SYNCHRONOUS GENERATOR
1 DHANALAKSHMI COLLEGE OF ENGINEERING DEPARTMENT OF ELECTRICAL AND ELECTRONICS ENGINEERING Constructional details Types of rotors EE2302  ELECTRICAL MACHINES II UNITI SYNCHRONOUS GENERATOR PART A 1.
More information1 Introduction. 2 The Symmetrical Component Transformation. J.L. Kirtley Jr.
Massachusetts Institute of Technology Department of Electrical Engineering and Computer Science 6.06 Introduction to Power Systems Class Notes Chapter 4 Introduction To Symmetrical Components J.L. Kirtley
More informationModule 7. Transformer. Version 2 EE IIT, Kharagpur
Module 7 Transformer Version EE IIT, Kharagpur Lesson 4 Practical Transformer Version EE IIT, Kharagpur Contents 4 Practical Transformer 4 4. Goals of the lesson. 4 4. Practical transformer. 4 4.. Core
More information13 ELECTRIC MOTORS. 13.1 Basic Relations
13 ELECTRIC MOTORS Modern underwater vehicles and surface vessels are making increased use of electrical actuators, for all range of tasks including weaponry, control surfaces, and main propulsion. This
More informationTRANSFORMER: THREE PHASE
CONTENTS Transformer : Three Phase 1211 C H A P T E R 33 Learning Objectives Threephase Transformers Threephase Transformer Connections Star/Star or Y/Y Connection DeltaDelta or Connection Wye/Delta
More informationExtra Questions  1. 1. What current will flow in a 20Ω resistor when it is connected to a 50V supply? a) 0.4A b) 1.6A c) 2.5A
Extra Questions  1 1. What current will flow in a 20Ω resistor when it is connected to a 50V supply? a) 0.4A b) 1.6A c) 2.5A 2. A current of 500mA flows in a resistance of 12Ω. What power is dissipated
More information8 Speed control of Induction Machines
8 Speed control of Induction Machines We have seen the speed torque characteristic of the machine. In the stable region of operation in the motoring mode, the curve is rather steep and goes from zero torque
More informationTransformers. Special transformers Reactors products
Transformers Special transformers Reactors products Reactors Custom designed, custom built ABB Oy Transformers has extensive experience and numerous references from different reactor applications, having
More informationModeling of Transmission Lines
Modeling of Transmission Lines Electric Power Transmission The electric energy produced at generating stations is transported over highvoltage transmission lines to utilization points. The trend toward
More informationThe Ideal Transformer. Description and Circuit Symbol
The Ideal Transformer Description and Circuit Symbol As with all the other circuit elements, there is a physical transformer commonly used in circuits whose behavior can be discussed in great detail. However,
More informationACCURACY OF POTENTIALTRANSFORMERS
8 VOLTAGE TRANSFORMERS Two types of voltage transformer are used for protectiverelaying purposes, as follows: (1) the "instrument potential transformer," hereafter to be called simply "potential transformer,"
More informationLab 14: 3phase alternator.
Lab 14: 3phase alternator. Objective: to obtain the noload saturation curve of the alternator; to determine the voltage regulation characteristic of the alternator with resistive, capacitive, and inductive
More informationChapter 12: Three Phase Circuits
Chapter 12: Three Phase Circuits 12.1 What Is a Three Phase Circuit? 12.2 Balance Three Phase Voltages 12.3 Balance Three Phase Y to Y Connection 12.4 Other Balance Three Phase Connections 12.5 Power in
More informationNO LOAD & BLOCK ROTOR TEST ON THREE PHASE INDUCTION MOTOR
INDEX NO. : M142 TECHNICAL MANUAL FOR NO LOAD & BLOCK ROTOR TEST ON THREE PHASE INDUCTION MOTOR Manufactured by : PREMIER TRADING CORPORATION (An ISO 9001:2000 Certified Company) 212/1, Mansarover Civil
More informationOutline. Systems and Signals 214 / 244 & Energy Systems 244 / 344. Ideal Inductor. Ideal Inductor (cont... )
Outline Systems and Signals 214 / 244 & Energy Systems 244 / 344 Inductance, Leakage Inductance, Mutual Inductance & Transformers 1 Inductor revision Ideal Inductor NonIdeal Inductor Dr. P.J. Randewijk
More informationElectrical Machines II. Week 1: Construction and theory of operation of single phase transformer
Electrical Machines II Week 1: Construction and theory of operation of single phase transformer Transformers Overview A transformer changes ac electric power at one frequency and voltage level to ac electric
More informationSeries & Parallel Impedance Parameters and Equivalent Circuits
Chroma ystems olutions, Inc. eries & arallel Impedance arameters and Equivalent Circuits Keywords: Impedance, capacitance, resistance Title: roduct Family: eries & arallel Impedance arameters and Equivalent
More informationOpen Phase Conditions in Transformers Analysis and Protection Algorithm
Open Phase Conditions in Transformers Analysis and Protection Algorithm Amir Norouzi GE Digital Energy Markham, ON amir.norouzi@ge.com Abstract This paper first provides an indepth analysis of open phase
More informationThe Synchronous Machine
Experiment No. 5 The Synchronous Machine Synchronous ac machines find application as motors in constant speed applications and, when interfaced to the power source with a variablefrequency converter system,
More informationFILTER CIRCUITS. A filter is a circuit whose transfer function, that is the ratio of its output to its input, depends upon frequency.
FILTER CIRCUITS Introduction Circuits with a response that depends upon the frequency of the input voltage are known as filters. Filter circuits can be used to perform a number of important functions in
More informationLCR Parallel Circuits
Module 10 AC Theory Introduction to What you'll learn in Module 10. The LCR Parallel Circuit. Module 10.1 Ideal Parallel Circuits. Recognise ideal LCR parallel circuits and describe the effects of internal
More informationInstrument Transformers Application Guide
Instrument Transformers Application Guide Edited by ABB AB High Voltage Products Department: Marketing & Sales Text: Knut Sjövall, ABB Layout, 3D and images: Mats Findell, ABB SE771 80 LUDVIKA, Sweden
More informationSAMPLE OF THE STUDY MATERIAL PART OF CHAPTER 3. Symmetrical Components & Faults Calculations
SAMPLE OF THE STUDY MATERIAL PART OF CHAPTER 3 3.0 Introduction Fortescue's work proves that an unbalanced system of 'n' related phasors can be resolved into 'n' systems of balanced phasors called the
More informationStandard nominal system voltages and maximum system voltages are included in ANSI C84.1 and listed in Tables 4 and 5 in this document.
5.5 Voltage ratings and taps 5.5.1 General Standard nominal system voltages and maximum system voltages are included in ANSI C84.1 and listed in Tables 4 and 5 in this document. 5.5.2 Voltage ratings The
More informationChapter 24. ThreePhase Voltage Generation
Chapter 24 ThreePhase Systems ThreePhase Voltage Generation Threephase generators Three sets of windings and produce three ac voltages Windings are placed 120 apart Voltages are three identical sinusoidal
More informationAC Generators. Basic Generator
AC Generators Basic Generator A basic generator consists of a magnetic field, an armature, slip rings, brushes and a resistive load. The magnetic field is usually an electromagnet. An armature is any number
More informationThe following table shows approximate percentage wise the
SHORTCIRCUIT CALCULATION INTRODUCTION Designing an electrical system is easy and simple, if only the normal operation of the network is taken into consideration. However, abnormal conditions which are
More informationAjay Kumar Garg Engineering College, Ghaziabad CLASS NOTES. Subject Name: ELECTROMECHANICAL ENERGY CONVERSIONI Subject Code: NEE 301
Ajay Kumar Garg Engineering College, Ghaziabad CLASS NOTES Subject Name: ELECTROMECHANICAL ENERGY CONVERSIONI Subject Code: NEE 301 Course: B. Tech. nd Year Branch: Electrical & Electronics Engineering
More informationBasic Electrical Technology Dr. L. Umanand Department of Electrical Engineering Indian Institute of Science, Bangalore. Lecture  33 3 phase System 4
Basic Electrical Technology Dr. L. Umanand Department of Electrical Engineering Indian Institute of Science, Bangalore Lecture  33 3 phase System 4 Hello everybody. So, in the last class we have been
More informationKeywords: synchronous generator, synchronous motor, automatic voltage regulator, V curves, synchronizing power, hunting, excitation system
SYNCHRONOUS MACHINES TzeFun Chan Hong Kong Polytechnic University, Hong Kong, China Keywords: synchronous generator, synchronous motor, automatic voltage regulator, V curves, synchronizing power, hunting,
More informationLecture Notes ELE A6
ecture Notes EE A6 Ramadan ElShatshat Three Phase circuits 9/12/2006 EE A6 Threephase Circuits 1 Threephase Circuits 9/12/2006 EE A6 Threephase Circuits 2 Advantages of Threephase Circuits Smooth
More informationFull representation of the real transformer
TRASFORMERS EQVALET CRCT OF TWOWDG TRASFORMER TR Dots show the points of higher potential. There are applied following conventions of arrow directions: for primary circuit the passive sign convention
More informationChapter 9 Balanced Faults
Chapter 9 alanced Faults 9.1 Introduction The most common types of fault are (in order) singlelinetoground fault, linetoline fault, and doublelinetoground fault. All of these are unbalanced faults.
More informationPHASOR DIAGRAMS HANDSON RELAY SCHOOL WSU PULLMAN, WA. RON ALEXANDER  BPA
PHASOR DIAGRAMS HANDSON RELAY SCHOOL WSU PULLMAN, WA. RON ALEXANDER  BPA What are phasors??? In normal practice, the phasor represents the rms maximum value of the positive half cycle of the sinusoid
More informationPower Quality Paper #3
The Effect of Voltage Dips On Induction Motors by: M D McCulloch 1. INTRODUCTION Voltage depressions caused by faults on the system affect the performance of induction motors, in terms of the production
More informationTHREEPHASE POWER SYSTEMS ECE 454/554: Power Systems Laboratory
THREEPHSE POER SYSTEMS ECE 5/55: Power Systems Laboratory Contributors: Dr... ElKeib Mr. Clifton Black Dr. Tim. Haskew Mr. Johnny Carlisle Mr. Neil Hutchins Objectives Learn how to perform measurements
More informationEEL303: Power Engineering I  Tutorial 4
1. Determine the voltage at the generating station and the efficiency of the following system (Figure 1): Both transformers have ratio of 2kV/11kV. The resistance on LV side of both Figure 1: transformers
More informationPower measurement in balanced 3 phase circuits and power factor improvement. 1 Power in Single Phase Circuits. Experiment no 1
Experiment no 1 Power measurement in balanced 3 phase circuits and power factor improvement 1 Power in Single Phase Circuits Let v = m cos(ωt) = cos(ωt) is the voltage applied to a RL circuit and i =
More informationMAGNETIC EFFECTS OF ELECTRIC CURRENT
CHAPTER 13 MAGNETIC EFFECT OF ELECTRIC CURRENT In this chapter, we will study the effects of electric current : 1. Hans Christian Oersted (17771851) Oersted showed that electricity and magnetism are related
More informationTogether we create reliable products, thus ensuring development of power industry of continents.
PRODUCT CATALOGUE Together we create reliable products, thus ensuring development of power industry of continents. By continuous improvement we transform our knowledge, energy and experience of the generations
More informationEquipment: Power Supply, DAI, Variable resistance (8311), Variable inductance (8321)
Lab 4: 3phase circuits. Objective: to study voltagecurrent relationships in 3phase circuits; to learn to make delta and Y connections; to calculate and measure real, apparent, and reactive powers. Equipment:
More informationDrive circuit basics + V. τ e. Industrial Circuits Application Note. Winding resistance and inductance
ndustrial Circuits Application Note Drive circuit basics For a given size of a stepper motor, a limited space is available for the windings. n the process of optimizing a stepper motor drive system, an
More informationGenetic Algorithm approach to find excitation capacitances for 3 phase smseig operating single phase loads
Genetic Algorithm approach to find excitation capacitances for 3 phase smseig operating single phase loads Authors & Affiliation: V.Ravi Kiran, V.Manoj and P.Praveen Kumar Asst. Professor, EEE Dept GMRIT,
More informationBALANCED THREEPHASE CIRCUITS
BALANCED THREEPHASE CIRCUITS The voltages in the threephase power system are produced by a synchronous generator (Chapter 6). In a balanced system, each of the three instantaneous voltages have equal
More informationSynchronous generators are built in large units, their rating ranging from tens to hundreds of megawatts.
II. Synchronous Generators Synchronous machines are principally used as alternating current (AC) generators. They supply the electric power used by all sectors of modern societies: industrial, commercial,
More informationShort Circuit Current Calculations
Introduction Several sections of the National Electrical Code relate to proper overcurrent protection. Safe and reliable application of overcurrent protective devices based on these sections mandate that
More informationINTERNATIONAL STANDARD
INTENATIONAL STANDAD IEC 600761 Edition 2.1 200004 Edition 2:1993 consolidated with amendment 1:1999 Power transformers Part 1: General This Englishlanguage version is derived from the original bilingual
More informationCircuit Analysis using the Node and Mesh Methods
Circuit Analysis using the Node and Mesh Methods We have seen that using Kirchhoff s laws and Ohm s law we can analyze any circuit to determine the operating conditions (the currents and voltages). The
More informationExperiment 1 The DC Machine
Experiment 1 The DC Machine ECEN 4517 R. W. Erickson and D. Maksimovic The purpose of this experiment is to become familiar with operating principles, equivalent circuit models, and basic characteristics
More informationIf there is no fault, then with proper connections account for the CT polarity, we should obtain circulatory current through CT secondary.
Module 10 : Differential Protection of Bus, Transformer and Generator Lecture 39 : Transformer Protection Introduction Differential protection of transformer was introduced in lecture 2. Traditionally,
More informationThe Flyback Converter
The Flyback Converter Lecture notes ECEN4517! Derivation of the flyback converter: a transformerisolated version of the buckboost converter! Typical waveforms, and derivation of M(D) = V/! Flyback transformer
More informationExperiment A5. Hysteresis in Magnetic Materials
HYSTERESIS IN MAGNETIC MATERIALS A5 1 Experiment A5. Hysteresis in Magnetic Materials Objectives This experiment illustrates energy losses in a transformer by using hysteresis curves. The difference betwen
More informationGenerator Stator Protection, under/over voltage, under /over frequency and unbalanced loading. Ramandeep Kaur Aujla S.NO 250447392
1 Generator Stator Protection, under/over voltage, under /over frequency and unbalanced loading By Ramandeep Kaur Aujla S.NO 250447392 ES 586b: Theory and applications of protective relays Department of
More informationTERMINAL MARKINGS AND INTERNAL WIRING DIAGRAMS SINGLE PHASE AND POLYPHASE MOTORS MEETING NEMA STANDARDS
INTRODUCTION The following represents the most uptodate information on motor terminal marking for proper connection to power source for all alternating current motors manufactured in accordance with
More informationGE Multilin technical note
Digital Energy Multilin GE Multilin technical note eutral voltage unbalance function at grounded wye capacitor banks GE publication number: GET8544 Copyright 00 GE Multilin eutral voltage unbalance function
More informationInstrument and control transformers: applications and selection
15 15/529 Instrument and control transformers: applications and selection Contents 15.1 Introduction 15/531 15.2 Types of transformers 15/531 15.2.1 Voltage transformers (VTs) 15/531 15.2.2 Current transformers
More information1. Title Electrical fundamentals II (Mechanics Repair and Maintenance)
1. Title Electrical fundamentals II (Mechanics Repair and Maintenance) 2. Code EMAMBG429A 3. Range The knowledge is needed for a wide range of aircraft repair and maintenance works,e.g. applicable to aircrafts,
More information7 Testing of Transformers
7 Testing of Transformers The structure of the circuit equivalent of a practical transformer is developed earlier. The performance parameters of interest can be obtained by solving that circuit for any
More informationInstrument Transformers By: Kiran Kelapure
Yadav Measurements Pvt. Ltd. Instrument Transformers By: Kiran Kelapure A specifically designed programme for Da Afghanistan Breshna Sherkat (DABS) Afghanistan 1 Electricity Metering technologies and systems
More informationELECTRICAL ENGINEERING Vol. I  Direct Current and Alternating Current Systems  N. Rajkumar DIRECT CURRENT AND ALTERNATING CURRENT SYSTEMS
DIRECT CURRENT AND ALTERNATING CURRENT SYSTEMS N. Rajkumar, Research Fellow, Energy Systems Group, City University Northampton Square, London EC1V 0HB, UK Keywords: Electrical energy, direct current, alternating
More informationSalman Bin Abdulaziz University College of Engineering. Electrical Engineering Department EE 3360 Electrical Machines (II)
CHAPTER # 3 SALIENTPOLE SYNCHRONOUS GENERATOR AND MOTOR 1 Introduction A cylindrical rotor synchronous machines has a uniform airgap, therefore its reactance remains the same, irrespective of the rotor
More information1 Introduction. 2 Two Phases. J.L. Kirtley Jr.
Massachusetts Institute of Technology Department of Electrical Engineering and Computer Science 6.061 Introduction to Power Systems Class otes Chapter 3 Polyphase etworks J.L. Kirtley Jr. 1 Introduction
More informationElectrical Power & Machines
d.c. Machines a.c. Single & Three Phase Machines Dissectible Machines Single & Three phase Transformers Measurement & Control Power Electronics Conventional & Virtual (PC based) Instrumentation Renewable
More informationVOLTAGE REGULATOR AND PARALLEL OPERATION
VOLTAGE REGULATOR AND PARALLEL OPERATION Generator sets are operated in parallel to improve fuel economy and reliability of the power supply. Economy is improved with multiple paralleled generators by
More informationTutorial One: Calculation of leakage inductance of transformer using FEM. 31.5 MVA, 132 kv/33kv, Y/, Ampereturns: 135024, No.
Tutorial One: Calculation of leakage inductance of transformer using FEM Consider a transformer with the following rating: 31.5 MVA, 132 kv/33kv, Y/, Ampereturns: 135024, No. of HV turns = 980 Although
More informationAPPLICATION NOTE  017
APPLICATION NOTE  017 PWM Motor Drives Theory and Measurement Considerations Pulse Width Modulated (PWM) power electronic techniques represent a large and increasing proportion of modern power electronics.
More informationEDEXCEL NATIONAL CERTIFICATE/DIPLOMA UNIT 5  ELECTRICAL AND ELECTRONIC PRINCIPLES NQF LEVEL 3 OUTCOME 4  ALTERNATING CURRENT
EDEXCEL NATIONAL CERTIFICATE/DIPLOMA UNIT 5  ELECTRICAL AND ELECTRONIC PRINCIPLES NQF LEVEL 3 OUTCOME 4  ALTERNATING CURRENT 4 Understand singlephase alternating current (ac) theory Single phase AC
More informationDESCRIPTION DWG DESCRIPTION DWG
DESCRIPTION DWG DESCRIPTION DWG Ferroresonance 3451/1 3451/2 3451/3 Electromagnetic Fields (EMF) 3462/1 HV & LV Insulators (Links) 3463/1 A ORIGINAL ISSUE B 14.07.09 APPROVED DATE J. Brooks 25.02.03 INDEX
More informationDIRECT CURRENT GENERATORS
DIRECT CURRENT GENERATORS Revision 12:50 14 Nov 05 INTRODUCTION A generator is a machine that converts mechanical energy into electrical energy by using the principle of magnetic induction. This principle
More informationThe Polyphase Induction Motor
Experiment No. 4 The Polyphase Induction Motor The polyphase induction motor is the most commonly used industrial motor, finding application in many situations where speed regulation is not essential.
More information7. Reactive energy compensation
593 7. Reactive energy compensation 594 7. REACTIVE ENERGY COMPENSATION Reactive energy compensation is an important element for reducing the electricity bill and improving the quality of the electrical
More informationW03 Analysis of DC Circuits. Yrd. Doç. Dr. Aytaç Gören
W03 Analysis of DC Circuits Yrd. Doç. Dr. Aytaç Gören ELK 2018  Contents W01 Basic Concepts in Electronics W02 AC to DC Conversion W03 Analysis of DC Circuits (self and condenser) W04 Transistors and
More informationFault Analysis I131. 2008 PowerWorld Corporation
Fault Analysis Analysis of power system parameters resulting from a ground or line to line fault somewhere in the system Simulator contains a tool for analyzing faults in an automatic fashion Can perform
More informationTransformer Modeling for Simulation of Low Frequency Transients
IEEE PES General Meeting July 1317, 23, Toronto Transformer Modeling for Simulation of Low Frequency Transients J.A. MARTINEZVELASCO Univ. Politècnica Catalunya Barcelona, Spain B.A MORK Michigan Tech..
More information1) Magnetic field lines come out of the south pole of a magnet and enter at the north pole.
Exam Name 1) Magnetic field lines come out of the south pole of a magnet and enter at the north pole. 2) Which of the following statements is correct? A) Earth's north pole is magnetic north. B) The north
More informationExperimental Question 1: Levitation of Conductors in an Oscillating Magnetic Field SOLUTION ( )
a. Using Faraday s law: Experimental Question 1: Levitation of Conductors in an Oscillating Magnetic Field SOLUTION The overall sign will not be graded. For the current, we use the extensive hints in the
More informationCHAPTER 5 SYNCHRONOUS GENERATOR
CHPTER 5 SYNCHRONOUS GENERTOR Summary: 1. Synchronous Generator Construction 2. The Speed of Rotation of a Synchronous Generator 3. The Internal Generated Voltage of a Synchronous Generator 4. The Equivalent
More informationThe generation and supply of electricity within the U.K is achieved through the use of a 3phase system.
Three Phase Electricity Supplies and Systems The generation and supply of electricity within the U.K is achieved through the use of a 3phase system. This consists of 3 separate phase conductors along
More informationFaculty of Engineering. 48572 Power Circuit Theory. Lab 2 ThreePhase Circuits
Faculty of Engineering Subject: 48572 ower ircuit Theory ssignment Number: 2 ssignment Title: Lab 2 Threehase ircuits Tutorial Group: Students Name(s) and Number(s) Student Number Family Name First Name
More informationTransformer Design & Design Parameters
Transformer Design & Design Parameters  Ronnie Minhaz, P.Eng. Power Transmission + Distribution GENERATION TRANSMISSION SUBTRANSMISSION DISTRIBUTION DISTRIBUTED POWER 115/10 or 20 kv 500/230 230/13.8
More informationMotor/Transformer Winding Repair
Workshop Practice Title and topics of HKSE 1 03.1.1.01.1 Fundamentals of specific trade Workshop organisation, industrial safety, quality assurance, introduction to accident prevention 2 03.1.1.21.1 Preparation
More information3Phase AC Calculations Revisited
AN110 Dataforth Corporation Page 1 of 6 DID YOU KNOW? Nikola Tesla (18561943) came to the United States in 1884 from Yugosiavia. He arrived during the battle of the currents between Thomas Edison, who
More informationPower Quality paper #4
THE BEHAVIOUR OF CONTACTORS DURING VOLTAGE DIPS by: IT De Villiers SYNOPSIS Electrically heldin contactors may drop out during voltage depressions. The time that contactors take to drop out depends on
More informationPHASOR DIAGRAMS II Fault Analysis Ron Alexander Bonneville Power Administration
PHASOR DIAGRAMS II Fault Analysis Ron Alexander Bonneville Power Administration For any technician or engineer to understand the characteristics of a power system, the use of phasors and polarity are essential.
More informationIntroduction to Paralleling of LTC Transformers by the Circulating Current Method
TAPCHANGER CONTROLS Application Note #11 Introduction to Paralleling of LTC Transformers by the Circulating Current Method 1.0 ABSTRACT This Application Note discusses the elements of paralleling load
More informationChapter 4: DC Generators. 9/8/2003 Electromechanical Dynamics 1
Chapter 4: DC Generators 9/8/2003 Electromechanical Dynamics 1 Armature Reaction Current flowing in the armature coils creates a powerful magnetomotive force that distorts and weakens the flux coming from
More information6. Synchronous machine dynamics
1 6. Synchronous machine dynamics In the middle of eighties, the present Type 59 synchronous machine model program was implemented and put into practical use in EMTP. In the first half of nineties, also
More informationMutual Inductance and Transformers F3 3. r L = ω o
utual Inductance and Transformers F3 1 utual Inductance & Transformers If a current, i 1, flows in a coil or circuit then it produces a magnetic field. Some of the magnetic flux may link a second coil
More informationDEFINING AND COMPUTING EQUIVALENT INDUCTANCES OF GAPPED IRON CORE REACTORS
ISEF 20  XV International Symposium on Electromagnetic Fields in Mechatronics, Electrical and Electronic Engineering Funchal, Madeira, September 3, 20 DEFINING AND COMPUTING EQUIVALENT INDUCTANCES OF
More informationINDUCTION REGULATOR. Objective:
INDUCTION REGULATOR Objective: Using a wound rotor induction motor an Induction Regulator, study the effect of rotor position on the output voltage of the regulator. Also study its behaviour under load
More information7CURRENT TRANSFORMERS
7CURRENT TRANSFORMERS Protective relays of the ac type are actuated by current and voltage supplied by current and voltage transformers. These transformers provide insulation against the high voltage
More informationLAB1 INTRODUCTION TO PSS/E EE 461 Power Systems Colorado State University
LAB1 INTRODUCTION TO PSS/E EE 461 Power Systems Colorado State University PURPOSE: The purpose of this lab is to introduce PSS/E. This lab will introduce the following aspects of PSS/E: Introduction to
More information