# CHAPTER 3. BUILDING THERMAL LOAD ESTIMATION

Size: px
Start display at page:

## Transcription

1 CHAPTER 3. BUILDING THERMAL LOAD ESTIMATION 3.1 Purpose of Thermal Load Estimation 3.2 Heating Load versus Cooling Load 3.3 Critical Conditions for Design 3.4 Manual versus Computer Calculations 3.5 Heating Load Estimation 3.6 Cooling Load Estimation

2 3.1 Purpose of Thermal Load Estimation To estimate energy consumption amount. To determine capacity of the HVAC equipment. To estimate the operation cost of the building. To improve building energy performance during design phase.

3 3.2 Cooling Load vs Heating Load Great solar radiation T o = (in temperate weather zone) T i = 26 RH= high or low Little solar radiation T o = -10 (in temperate weather zone) T i = 20 RH= usually low

4 3.3 Critical Conditions for Design The designer must select an appropriate set of conditions for the load calculation: outside weather, solar effects, inside temperature and humidity, the status of building operations, and many other factors For heating, the critical design condition occurs during cold weather when there is little or no heating assistance from radiant solar energy or internal heat gains from lights, appliances, or people. For cooling load conditions, the critical design condition is the peak coincident occurrence of heat, humidity, solar effects, and internal heat gains from equipment, lights, and people. Several estimates must be performed for different times to determine the highest combination of individual loads.

5 3.3.1 Outdoor Design Temperature Outdoor weather conditions affect heating and air-conditioning loads. Historic extremes of temperature and humidity are the basis for design load calculations. Statistical data compiled for locations throughout the world are used by HVAC designers. Outdoor design temperatures are selected on the basis of a percent concept.

6 Percent concept 1) Heating load calculations: The percent concept assumes a heating season of December through February, which equals 2160 hours per year. It imply the weather will be at or above the listed condition only for the specified percentage of 2160 hours per year. Percentage values: 99% and 97.5% 2) Cooling load calculations: Summer is defined as June through September, which equals 2928 hours Percentage values: 1%, 2.5%, and 5%

7 3.3.2 Indoor Design Temperature ASHRAE Standard 55 specifies summer and winter comfort zones appropriate for clothing insulation levels of 0.5 and 0.9 clo [0.078 and 0.14 (m 2 K/W), respectively. Summer comfort operative temperature: Winter comfort operative temperature: Comfort relative humidity: 30 60% ASHRAE : American Society of Heating, Refrigerating and Air-Conditioning Engineers

8 3.4 Manual vs Computer Calculations Manual Calculation: To determine maximum heating and cooling loads to size HVAC equipment. Computer Calculation (Simulation): To estimate annual energy consumption by calculating hour-by-hour building heat gain/loss and HVAC operations. To improve building design and HVAC operation schemes by comparing thermal performances of several design alternatives.

9 3.5 Heating Load Estimation Heating loads are due to heat losses by: 1) Conductive heat loss through envelope (walls, windows, doors, floors, roof, etc.). 2) Infiltration, exfiltration and ventilation air.

10 Infiltration, Exfiltration and Ventilation Infiltration is the uncontrolled passage of outdoor air into a building through unintended leaks in the building envelope (e.g., cracks between wall sections, wallfloor connections, corners, the roof-wall interface, around windows and doors). Exfiltration is the opposite process. Infiltration and exfiltration are driven by air pressure differences that exist between the inside of a building relative to the outside of a building across the building envelope. These air pressure differences are the result of natural forces (e.g., wind and temperature) and a building s geometry, HVAC system design, and envelope tightness.

11 Ventilation is the process of "changing" or replacing air in any space to provide high indoor air quality (i.e. to control temperature, replenish oxygen, or remove moisture, odors, smoke, heat, dust, airborne bacteria, and carbon dioxide). Ventilation is used to remove unpleasant smells and excessive moisture, introduce outside air, to keep interior building air circulating, and to prevent stagnation of the interior air. Ventilation includes both the exchange of air to the outside as well as circulation of air within the building. It is one of the most important factors for maintaining acceptable indoor air quality in buildings. Methods for ventilating a building may be divided into mechanical/forced and natural types.

12 3.5.1 Conductive Heating Load Q UA t Q Uj Aj ( ti t n j 1 o ) Q = heating load (W) (kcal/h) A j = area of each envelope element (m 2 ) U = overall heat transfer coefficient (W/m 2 K) (kcal/m 2 h ) t i = indoor design air temperature (K) ( ) t o = outdoor design air temperature (K) ( )

13 U-Factor (Overall Heat Transfer Coefficient) R tot 1 h i d i k i R air 1 ho (m 2 K/W) (m 2 h C/kcal) Where, h i = indoor surface heat transfer coefficient (or film conductance) (kcal/m 2 h C) h o = outdoor surface heat transfer coefficient (kcal/m 2 h C) U 1 Rtot (W/m 2 K) (kcal/m 2 h C)

14

15

16 The complete table is available from the class website.

17 The complete table is available from the class website.

18 The complete table is available from the class website.

19

20 The complete table is available from the class website.

21 3.5.2 Infiltration Heating Load 1) Sensible Heating Load Q CMH ( ti to) Where, Q = heating load (W) (kcal/h) 0.24 = specific heat of dry air (kj/kgk) (kcal/kg ) 1.2 = specific weight of air (kg/m 3 ) CMH = airflow (m 3 /h) t i = indoor air temperature (K) ( ) t o = outdoor air temperature (K) ( )

22 2) Latent Heating Load Q CMH ( xi x ) o Where, Q = heating load (W) (kcal/h) 597= latent heat of vaporization of water at 0 (kj/kg) (kcal/kg) 1.2 = specific weight of air (kg/m 3 ) CMH = airflow (m 3 /h) x i = room humidity ratio of indoor air (kg/kg da ) x o = outdoor air humidity ratio of outdoor air (kg/kg da )

23 Airflow Estimation Airflow is estimated by using crack method and air change method 1) Crack method The crack method is more accurate than air change method. Outdoor air infiltrates the indoor space through cracks around doors, windows, and joints between walls and floors and even through the building material itself. The amount depends on the total area of the cracks, the type of crack and the pressure difference between the inside and outside. Airflow is calculated by : CMH CMH per meter meter of crack

24 2) Air change method Most Designers prefer to use simpler air change method Airflow into a space can be measured in air changes per hour CMH ACH Volume Where, CMH = airflow(m 3 /h) ACH = Air changes per hour Volume = space volume(m 3 ) Infiltration air changes per hour occurring under average conditions in residences Kind of room Single glass, No Weather-strip Storm Sash or Weather-stripped No windows or exterior doors Windows or exterior doors on 1 side Windows or exterior doors on 2 sides Windows or exterior doors on 3 sides Entrance halls 2 1.3

25 3.5.3 Ventilation Heating Load Outside air is introduced by the HVAC system to dilute air contaminants and to make up for exhaust. The ventilation load is calculated by the same equations used for infiltration. Ventilation is determined according to ASHRAE Standard 62. The complete table is available from the class website.

26 3.5.4 Miscellaneous Loads In addition to conduction, infiltration, and ventilation, heating loads should take into account miscellaneous factors such as losses through walls below grade and slabs on grade.

27

28

29 3.6 Cooling Load Estimation Heat gains include conduction, solar effects, outdoor air loads, and internal heat loads. Components of building cooling load

30 3.6.1 Heat Gain through Walls and Roofs (Opaque) A simple temperature difference between indoor and outdoor air will not account for solar heat. The outside surface is much warmer than the surrounding air, due to the solar radiation effect. Conduction calculating use TETD(Total equivalent temperature difference) TETD include solar effects as well as temperature difference TETD vary with the orientation, time of day, absorption property of the surface, and thermal mass of the building assembly

31 Q UA(TETD) Q n j 1 U j Aj (TETD) Where, Q = cooling load (W) (kcal/h) U = overall heat transfer coefficient (W) (kcal/m 2 h ) A = area of each envelope element (m 2 ) TETD = total equivalent temperature difference( )

32

33 3.6.2 Heat Gain through Glazing (Transparent or Translucent) Glazing materials usually have lower thermal resistance than the opaque building materials and they also admit solar radiation into the space. These heat loads are considered in two parts, simple conductive heat transfer due to the temperature differences between indoor air and outdoor air, and solar heat gain. Q A U ( ti to) ( SC)( A)( SHGF) SHGF = solar heat gain factor (W/m 2 ) SC = shading coefficient(dimensionless)

34 SHGF(solar heat gain factor) The amount of solar heat that will enter a clear single-pane window at a given time of year and time of day, facing the specified orientation.

35

36 SC(shading coefficient) The SC is the ratio of solar gain (due to direct sunlight) passing through a glass unit to the solar energy which passes through 3mm Clear Float Glass. It is referred to as an indicator to how the glass is thermally insulating (shading) the interior when there is direct sunlight on the panel or window.

37 Origin of Difference Between Magnitude of Instantaneous Heat Gain and Instantaneous Cooling Load

38 3.6.3 Infiltration and Ventilation The infiltration is much lower during hot weather than cold weather especially in highrise buildings. In winter, stack effect due to great temperature difference between indoor and outdoor airs cause more infiltration. Sensible heat and latent heat loads due to infiltration can be calculated by : Q sensible CMH ( ti to) Q latent CMH ( xi xo) Total heat, enthalpy (h) is the sum of sensible and latent heat. The enthalpy can be taken from a psychrometric chart or tables. Q 1. 2 CMH h h = change in enthalpy (kcal/kg da ) Outside air introduced for ventilation by the air-conditioning equipment result in sensible and latent loads calculated by the same equations as in the infiltration cooling load calculations.

39 3.6.4 Internal Heat Gains Heat is generated inside buildings by lights, appliances, and occupants. People liberate both sensible and latent heat. Latent heat results from exhaled moisture and evaporation of perspiration. The latent het loads depend on the level of activity.

40 Heat from lights and appliances can be calculated using the factor for conversion of electrical to thermal energy: Q 3.41 P P = power input to light fixture or appliance(w) Heat from building lighting and appliances may not be estimated precisely. Usually, the wattage per unit area (W/m2) is used.

41

42

43

### Software Development for Cooling Load Estimation by CLTD Method

IOSR Journal of Mechanical and Civil Engineering (IOSR-JMCE) ISSN: 2278-1684Volume 3, Issue 6 (Nov. - Dec. 2012), PP 01-06 Software Development for Cooling Load Estimation by CLTD Method Tousif Ahmed Department

### Residential HVAC System Sizing

Residential HVAC System Sizing William P. Goss University of Massachusetts, Amherst, Massachusetts, USA Corresponding email: goss@acad.umass.edu SUMMARY Heating, ventilating and air-conditioning (HVAC)

### Cooling Load Calculations and Principles

Cooling Load Calculations and Principles Course No: M06-004 Credit: 6 PDH A. Bhatia Continuing Education and Development, Inc. 9 Greyridge Farm Court Stony Point, NY 10980 P: (877) 322-5800 F: (877) 322-4774

### Residential HVAC Load Sizing Training October 14, 2015. David Kaiser Green Code Plan Reviewer

Residential HVAC Load Sizing Training October 14, 2015 David Kaiser Green Code Plan Reviewer DCRA - Green Building Division Regulations of green codes including: Green Building Act Green Construction Code

### Mechanical and Natural Ventilation

BBSE3006: Air Conditioning and Refrigeration II http://www.hku.hk/bse/bbse3006/ Mechanical and Natural Ventilation Dr. Sam C. M. Hui Department of Mechanical Engineering The University of Hong Kong E-mail:

### AIRCONDITIONING Cooling Loads Calculations

Calculations -1- AIRCONDITIONING Cooling s Calculations Employer : 4M SA Project Location : ASHRAE Office Room : Example from ASHRAE 2013 Handbook - Fundamentals : Chapter 18, Single Room Example (p. 18.37)

### Molds and mildew are fungi that grow

Appendix C: Moisture, Mold and Mildew Molds and mildew are fungi that grow on the surfaces of objects, within pores, and in deteriorated materials. They can cause discoloration and odor problems, deteriorate

### 3-D Modeller Rendered Visualisations

Recognised energy Dynamic Simulation Modelling (DSM) software DesignBuilder is a user interface to the EnergyPlus DSM. EnergyPlus builds on the most popular features and capabilities of BLAST and DOE-2

### HVAC Calculations and Duct Sizing

PDH Course M199 HVAC Calculations and Duct Sizing Gary D. Beckfeld, M.S.E., P.E. 2007 PDH Center 2410 Dakota Lakes Drive Herndon, VA 20171-2995 Phone: 703-478-6833 Fax: 703-481-9535 www.pdhcenter.com An

### Adaptive strategies for office spaces in the UK climate

International Conference Passive and Low Energy Cooling 631 Adaptive strategies for office spaces in the UK climate I. Gallou Environment & Energy Studies Programme, Architectural Association Graduate

### Optimum Solar Orientation: Miami, Florida

Optimum Solar Orientation: Miami, Florida The orientation of architecture in relation to the sun is likely the most significant connection that we can make to place in regards to energy efficiency. In

### FLORIDA SOLAR ENERGY CENTER

FLORIDA SOLAR ENERGY CENTER Creating Energy Independence Since 1975 Impact of Energy-Efficiency Parameters on Home Humidity Rob Vieira Florida Solar Energy Center A Research Institute of the University

### CHAPTER 4 LOAD CALCULATIONS 4.1 CONTEXT

CHAPTER 4 LOAD CALCULATIONS 4.1 CONTEXT The accurate calculation of heating and cooling loads is essential to provide a sound bridge between fundamental building design decisions and an operating building.

### THERMAL LOSSES Thermal Losses Calculations

Calculations -1- THERMAL LOSSES Thermal Losses Calculations Employer : 4M SA Project Location : ASHRAE Office Room : Example from ASHRAE 2013 Handbook - Fundamentals : Chapter 18, Single Room Example Peak

### Climate and Energy Responsive Housing in Continental Climates. The Suitability of Passive Houses for Iran's Dry and Cold Climate. Farshad Nasrollahi

Climate and Energy Responsive Housing in Continental Climates The Suitability of Passive Houses for Iran's Dry and Cold Climate Farshad Nasrollahi Table of Contents Abstract German Abstract Introduction

### Humid Air. Water vapor in air. Trace Glasses 1% Argon (A) Water vapor (H 2

Humid Air Water vapor in air Oxygen 21% Trace Glasses 1% Argon (A) Water vapor (H 2 O) Carbon dioxide (CO 2 ) Neon (Ne) Helium (He) Krypton (Kr) Hydrogen (H) Ozone (O 3 ) Nitrogen 78% Humid Air Water vapor

### DESIGN OF NATURAL VENTILATION WITH CFD CHAPTER SEVEN. Qingyan Chen. difficult to understand and model, even for simple

CHAPTER SEVEN L. Glicksman and J. Lin (eds), Sustainable Urban Housing in China, 116-123 2006 Springer. Printed in the Netherlands. DESIGN OF NATURAL VENTILATION WITH CFD Qingyan Chen INTRODUCTION As the

### Heating Load Calculation

Heating Load Calculation ME 425 Air Conditioning System Design Keith E. Elder, P.E. Heating Load Calculation The heating load calculation begins with the determination of heat loss through a variety of

### Lesson 36 Selection Of Air Conditioning Systems

Lesson 36 Selection Of Air Conditioning Systems Version 1 ME, IIT Kharagpur 1 The specific objectives of this chapter are to: 1. Introduction to thermal distribution systems and their functions (Section

### ANSI/ASHRAE Standard 140-2004 Building Thermal Envelope and Fabric Load Tests

ANSI/ASHRAE Standard 140-2004 Building Thermal Envelope and Fabric Load Tests DesignBuilder Version 1.2.0 (incorporating EnergyPlus version 1.3.0) - June 2006 1.0 Purpose The ANSI/ASHRAE Standard 140-2004

### Center for Energy Education Laboratory

Paper ID #7072 Center for Energy Education Laboratory Dr. Robert Gilbert, Sinclair Community College Robert B. Gilbert, Ph.D., LEED AP, BA, is an Associate Professor of Energy Management Technology, and

### EFA PSBP. Natural Ventilation Strategy. Introduction. 1.1 Relevant legislation. 1.1.1 The Building Regulations 2010

EFA PSBP Natural Ventilation Strategy Introduction The Baseline Designs Project will provide scheme design details for a number of Primary and Secondary School Exemplars. For the purposes of setting a

### The Influence of Insulation Styles on the Air Conditioning Load of Japanese Multi- Family Residences

The Influence of Insulation Styles on the Air Conditioning Load of Japanese Multi- Family Residences Yupeng Wang 1, and Hiroatsu Fukuda 2 1 Department of BCEE, Concordia University, Canada, Email: wangyupeng0628@gmail.com

### HOW AN ENERGY EFFICIENT HOME CAN HELP THE ENVIRONMENT

HOW AN ENERGY EFFICIENT HOME CAN HELP THE ENVIRONMENT During the last century, concern about the environment increased, as issues such as global warming and the Greenhouse Effect convinced us that the

### AIR CONDITIONING EFFICIENCY F8 Energy eco-efficiency opportunities in Queensland Foundries

AIR CONDITIONING EFFICIENCY F8 Energy eco-efficiency opportunities in Queensland Foundries Hot tips and cool ideas to save energy and money! Air conditioning units or systems are often used by foundries

### Air Conditioning Clinic

Air Conditioning Clinic Cooling and Heating Load Estimation One of the Fundamental Series April 2011 TRG-TRC002-EN Cooling and Heating Load Estimation One of the Fundamental Series A publication of Trane,

### DEVELOPMENT OF AN OPEN SOURCE HOURLY BUILDING ENERGY MODELING SOFTWARE TOOL

DEVELOPMENT OF AN OPEN SOURCE HOURLY BUILDING ENERGY MODELING SOFTWARE TOOL Brittany Hanam, MASc, EIT RDH Building Engineering Ltd. Vancouver, BC John Straube, PhD, P.Eng. Building Engineering Group, Civil

### Eco Pelmet Modelling and Assessment. CFD Based Study. Report Number 610.14351-R1D1. 13 January 2015

EcoPelmet Pty Ltd c/- Geoff Hesford Engineering 45 Market Street FREMANTLE WA 6160 Version: Page 2 PREPARED BY: ABN 29 001 584 612 2 Lincoln Street Lane Cove NSW 2066 Australia (PO Box 176 Lane Cove NSW

### Creating Efficient HVAC Systems

Creating Efficient HVAC Systems Heating and Cooling Fundamentals for Commercial Buildings Heating, ventilating, and air conditioning (HVAC) systems account for nearly half of the energy used in a typical

### Passive Solar Design and Concepts

Passive Solar Design and Concepts Daylighting 1 Passive Solar Heating Good architecture? The judicious use of south glazing coupled with appropriate shading and thermal mass. Summer Winter Passive solar

### Green Building Handbook for South Africa Chapter: Heating, Ventilation and Cooling Luke Osburn CSIR Built Environment

Green Building Handbook for South Africa Chapter: Heating, Ventilation and Cooling Luke Osburn CSIR Built Environment The heating, ventilation and cooling loads of typical commercial office space can range

### Greenhouse Glazing Effects on Heat Transfer for Winter Heating and Summer Cooling

Greenhouse Glazing Effects on Heat Transfer for Winter Heating and Summer Cooling David R. Mears, Ph.D. Bioresource Engineering Department of Plant Biology and Pathology Rutgers University 20 Ag Extension

### Simulation of hygroscopic materials in the HVAC system of an office building

Simulation of hygroscopic materials in the HVAC system of an office building IEA/ECBCS Annex 41 Porto Meeting Melanie Fauchoux, Carey Simonson and David Torvi Department of Mechanical Engineering, University

### Diego Ibarra Christoph Reinhart Harvard Graduate School of Design

Building Performance Simulation for Designers - Energy DesignBuilder // EnergyPlus Tutorial #2 Load Schedules GEOMETRY LOADS RESULTS Diego Ibarra Christoph Reinhart Harvard Graduate School of Design OVERVIEW

### Housing Fact Sheets. Moisture Condensation at the Windows

Moisture Condensation at the Windows Housing Fact Sheets This fact sheet discusses the causes of and remedies for wintertime condensation problems that occur on windows, glass, and other glazing materials

### ResearcH JournaL 2009 / VOL 01.01. www.perkinswill.com

ResearcH JournaL 2009 / VOL 01.01 www.perkinswill.com PERKINS+WILL RESEARCH JOURNAL / VOL 01.01 05. CONTEXT BASED DESIGN OF DOUBLE SKIN FACADES Climatic Considerations During the Design Process Ajla Aksamija,

### CONDENSATION IN REFRIDGERATED BUILDINGS

CONDENSATION IN REFRIDGERATED BUILDINGS By: Steve Salisbury Nov. 10, 2010 (revised Nov. 14, 2013) Introduction The following discussion reviews the basic causes of condensation in refrigerated buildings

### Residential Windows, 3 rd edition Corrected index 1

Residential Windows, 3 rd edition Corrected index 1 A absorptance definition, 78 determinants of, 78 79 energy performance and, 78 tinted glass, 84 acoustical properties of windows, 60 61 acrylic glazing

### PROTOCOL FOR BUILDING ENERGY ANALYSIS SOFTWARE For Class 3, 5, 6, 7, 8 and 9 buildings

PROTOCOL FOR BUILDING ENERGY ANALYSIS SOFTWARE For Class 3, 5, 6, 7, 8 and 9 buildings Version 2006.1 AUSTRALIAN BUILDING CODES BOARD JANUARY 2006 TABLE OF CONTENTS Foreword 1. Scope 2. Purpose and context

### Cooling Load Estimation and Air Conditioning Unit Selection for Hibir Boat

The International Journal Of Engineering And Science (IJES) Volume 3 Issue 5 Pages 63-72 2014 ISSN (e): 2319 1813 ISSN (p): 2319 1805 Cooling Load Estimation and Air Conditioning Unit Selection for Hibir

### Energy Use in Residential Housing: A Comparison of Insulating Concrete Form and Wood Frame Walls

PCA R&D Serial No. 415 Energy Use in Residential Housing: A Comparison of Insulating Concrete Form and Wood Frame Walls by John Gajda and Martha VanGeem 000 Portland Cement Association KEYWORDS Concrete,

### Carnegie Mellon University School of Architecture, Department of Mechanical Engineering Center for Building Performance and Diagnostics

Carnegie Mellon University School of Architecture, Department of Mechanical Engineering Center for Building Performance and Diagnostics A Presentation of Work in Progress 4 October 2006 in the Intelligent

### National Building Code of Canada 2010

National Building Code of Canada 2010 Emergency Change Issued by the Canadian Commission on Building and Fire Codes The table that follows lists two emergency changes that apply to the National Building

### Solar Energy Utilisation in Buildings

Solar Energy Utilisation in Buildings P. Karava, PhD Assistant professor Department of Civil and Environmental Engineering University of Western Ontario 2 Modern Buildings Change in architectural style

### Selecting Energy Efficient Replacement Windows in Nevada

Selecting Energy Efficient Replacement Windows in Nevada www.efficientwindows.org January 06 STAR Zones. Meet the Energy Code & Look for the STAR Windows must comply with your local energy code. Windows

### Energy Efficient HVAC-system and Building Design

Energy Efficient HVAC-system and Building Design Maija Virta 1, Harri Itkonen 1, Panu Mustakallio 1, Risto Kosonen 1 1 Halton Oy, Finland Corresponding email: maija.virta@halton.com SUMMARY This paper

### Comfort Conditioning & Indoor Air Quality

This article was published in ASHRAE Journal, May 2011. Copyright 2011 American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. Reprinted here by permission from ASHRAE at www.newellinstruments.com.

### Air Conditioning. The opportunity for energy efficiency. Low cost actions to reduce energy usage now

Fact Sheet #6 Air Conditioning In this fact sheet you will discover: The opportunity for energy efficiency How air conditioning works Low cost actions to reduce energy usage now Investments to reduce costs

### Selecting Energy Efficient New Windows in Florida

Selecting Energy Efficient New Windows in Florida www.efficientwindows.org January 06 Zones. Meet the Energy Code & Look for the Windows must comply with your local energy code. Windows that are certified

### Selecting Energy Efficient New Windows in Georgia

Selecting Energy Efficient New Windows in Georgia www.efficientwindows.org January 016 ENERGY STAR Zones 1. Meet the Energy Code & Look for the ENERGY STAR Windows must comply with your local energy code.

### Whole House Dehumidification for Occupant Comfort and Energy Savings

Downloaded from www.rsrews.com. Since 1968, RS Andrews has proudly served Atlanta's Heating, Air Conditioning & Plumbing Needs. Whole House Dehumidification for Occupant Comfort Energy Savings June 2009

### ENERGY PERFORMANCE MODELLING AND HEAT RECOVERY UNIT EFFICIENCY ASSESSMENT OF AN OFFICE BUILDING

THERMAL SCIENCE: Year 2015, Vol. 19, No. 3, pp. 865-880 865 ENERGY PERFORMANCE MODELLING AND HEAT RECOVERY UNIT EFFICIENCY ASSESSMENT OF AN OFFICE BUILDING by Norbert L. HARMATI a*, Radomir J. FOLI] a,

### COOLING AND HEATING OF BUILDINGS BY ACTIVATING THEIR THERMAL MASS WITH EMBEDDED HYDRONIC PIPE SYSTEMS -

pcoolingandheating COOLING AND HEATING OF BUILDINGS BY ACTIVATING THEIR THERMAL MASS WITH EMBEDDED HYDRONIC PIPE SYSTEMS - Bjarne W. Olesen, Ph.D. D. F. Liedelt "Velta" Summary Due to intensive use of

### Comparing Air Cooler Ratings Part 1: Not All Rating Methods are Created Equal

Technical Bulletin By Bruce I. Nelson, P.E., President, Colmac Coil Manufacturing, Inc. Comparing Air Cooler Ratings Part 1: Not All Rating Methods are Created Equal SUMMARY Refrigeration air coolers (evaporators)

### Energy Efficiency in Buildings

Energy Efficiency in Buildings Supplemental Guide to SANS 10400-XA & SANS 204 V. 3.0 Registered to: The Drawing Studio Image: digitalart / FreeDigitalPhotos.net Report Date: 26 August 2014 Practice Name:

### Selecting Energy Efficient New Windows in Arizona

Selecting Energy Efficient New Windows in Arizona www.efficientwindows.org January 016 ENERGY STAR Zones 1. Meet the Energy Code & Look for the ENERGY STAR Windows must comply with your local energy code.

### Glossary of Heating, Ventilation and Air Conditioning Terms

Glossary of Heating, Ventilation and Air Conditioning Terms Air Change: Unlike re-circulated air, this is the total air required to completely replace the air in a room or building. Air Conditioner: Equipment

### Cooling Load Calculation

for A Probabilistic Approach Taperit Tongshoob 1 Chirdpun Vitooraporn 2 Cooling Load Calculation Abstract 1 Ph.D Student 2 Lecturer at Building Technology Environment Laboratory, Mechanical Engineering

### RosevilleProject. LoE _ 2 Glass Products. You can reduce your cooling energy usage by 25% or more. Here is the proof.

RosevilleProject Glass Products You can reduce your cooling energy usage by 25% or more. Here is the proof. Hot-Button Issues Residents of California, Arizona, and Nevada don t need a weather forecast

### IECC Compliance Guide for Homes in Virginia

IECC Compliance Guide for Homes in Virginia Amended Version of 2012 International Energy Conservation Code July 14, 2014 Climate Zone Since the entire state of Virginia falls in the IECC Climate Zone 4,

### Selecting Energy Efficient New Windows in California

Selecting Energy Efficient New Windows in California www.efficientwindows.org Janurary 016 Zones 1. Meet the Energy Code & Look for the Windows must comply with your local energy code. Windows that are

### Building Performance Evaluation Guide Version 1.7

Building Performance Evaluation Guide Version 1.7 Prepared by Center for Energy and Environment January 2014 Minnesota Sustainable Building 2030: Building Performance Evaluation Guide p 1 1. Schematic

### WHOLE-HOUSE VENTILATION SYSTEMS

Technology Fact Sheet WHOLE-HOUSE VENTILATION SYSTEMS Improved control of air quality Buildings for the 21st Century Buildings that are more energy efficient, comfortable, and affordable that s the goal

### Venice Library Humidity Study. for Williams Building Diagnostics, LLC 305 15 th Street West Bradenton, FL 34205. Report April 13, 2015

for Williams Building Diagnostics, LLC 305 15 th Street West Bradenton, FL 34205 Report April 13, 2015 Moses & Associates, Inc. 2209 NW 40 th Terrace, Suite A Gainesville, FL 32605 FL License EB-0003097

### CHAPTER 4 VENTILATION

CHAPTER 4 VENTILATION SECTION 401 GENERAL 401.1 Scope. This chapter, in conjunction with the building code, shall govern the ventilation of spaces within a building intended to be occupied. Mechanical

### 9. ENERGY PERFORMANCE ASSESSMENT OF HVAC SYSTEMS

9. ENERGY PERFORMANCE ASSESSMENT OF HVAC SYSTEMS 9.1 Introduction Air conditioning and refrigeration consume significant amount of energy in buildings and in process industries. The energy consumed in

### ECHO System for Basements

ECHO System for Basements Homeowners looking for more space are all too familiar with the cold, damp and dingy basement. Now, the Enclosure Conditioned Housing (ECHO) System TM, winner of the Ottawa-Carleton

### THE EFFECT OF ENERGY RECOVERY ON INDOOR CLIMATE, AIR QUALITY AND ENERGY CONSUMPTION USING COMPUTER SIMULATIONS

THE EFFECT OF ENERGY RECOVERY ON INDOOR CLIMATE, AIR QUALITY AND ENERGY CONSUMPTION USING COMPUTER SIMULATIONS A Thesis Submitted to the College of Graduate Studies and Research in Partial Fulfillment

### Energy Efficient Building Design College of Architecture Illinois Institute of Technology, Chicago. Ceiling/Airspace

HEAT GAINS and LOSSES : ROOFS and WALLS Wall Roof Ts To Ts To Ti Ceiling/Airspace Ti Roof and wall are analyzed in the same way. In winter the heat loss is simple transmission based on the inside and outside

### Solar Homes Catch the Sun. Are you planning a new house? Discover how you can apply solar architecture principles to:

PASSIVE Solar Design Solar Homes Catch the Sun Are you planning a new house? Discover how you can apply solar architecture principles to: keep your heating bills to a minimum enjoy the comfort of a warm

### Yijun Gao, Wei Wu, Zongwei Han, Xianting Li *

Study on the performance of air conditioning system combining heat pipe and vapor compression based on ground source energy-bus for commercial buildings in north China Yijun Gao, Wei Wu, Zongwei Han, Xianting

### Element D Services Heating, Ventilating, and Air Conditioning

Load Calculation Criteria PART 1 - GENERAL 1.01 OVERVIEW A. This section includes requirements for calculating HVAC cooling and heating loads. B. Load calculations must be performed in accordance with

### Moisture Content in Insulated Basement Walls

Moisture Content in Insulated Basement Walls Peter Blom,PhD, SINTEF Building and Infrastructure; peter.blom@sintef.no, www.sintef.no/byggforsk Sverre B. Holøs M.Sc. SINTEF Building and Infrastructure;

### Here Lw = 58.5 db(a) Unit must be installed in a separate building services room. Extract air filter G4

Certificate Certified Passive House Component For cool, temperate climates, valid until 31 December 2015 Passive House Institute Dr. Wolfgang Feist 64283 Darmstadt GERMANY Category: Manufacturer: Product

### HEAT LOAD AND SOLAR GAIN PREDICTION FOR SOLID WALL DWELLINGS RETROFITTED WITH TRIPLE VACUUM GLAZING FOR SELECTED WINDOW TO WALL AREA RATIOS

HEAT LOAD AND SOLAR GAIN PREDICTION FOR SOLID WALL DWELLINGS RETROFITTED WITH TRIPLE VACUUM GLAZING FOR SELECTED WINDOW TO WALL AREA RATIOS Saim Memon Philip C. Eames Centre for Renewable Energy Systems

### Selecting Energy Efficient New Windows in Texas

Selecting Energy Efficient New Windows in Texas www.efficientwindows.org January 06 Zones. Meet the Energy Code & Look for the Windows must comply with your local energy code. Windows that are certified

### ELIMINATING AIR CONDITIONERS IN NEW SOUTHERN CALIFORNIA HOUSING

ELIMINATING AIR CONDITIONERS IN NEW SOUTHERN CALIFORNIA HOUSING Murray Milne, Research Professor Department of Architecture and Urban Design UCLA Los Angeles, CA 90095 milne@ucla.edu Tim Kohut, Project

### A global list. The Fortification Depot A CO 2 -reduction project

The Fortification Depot A CO 2 -reduction project A global list Passive measures: Windows, glazing, solar shading Insulation of walls, roofs, floors Improving air tightness 1 A global list Technical measures:

### BPC Green Builders. Green building for new and existing homes. Health Comfort Energy

BPC Green Builders Green building for new and existing homes Health Comfort Energy Mechanical Systems Installed HVAC Systems Primary energy source large, roof mounted, solar thermal array (AET flat plate)

### Air Conditioning Contractors of America

Air Conditioning Contractors of America WHO IS ACCA???? Industry Manuals Residential D, J, S, H, RS, T, P A manual J load calculation is a measurement of how much heating and cooling capacity a home will

### Vestibule Case Study. Vestibule Requirement Intent [2003 IECC, 2006 IECC, 2003 IBC, 2006 IBC, 90.1-2001, 90.1-2004]

Vestibule Case Study [2003 IECC, 2006 IECC, 2003 IBC, 2006 IBC, 90.1-2001, 90.1-2004] Vestibule Requirement Intent Page 1 of 14 The primary intent behind the requirement for a vestibule is to reduce infiltration

### The Importance of Building Criteria on Cooling Energy Demand of a Low Cost Residential House: Thailand Case Study

The Importance of Building Criteria on Cooling Energy Demand of a Low Cost Residential House: Thailand Case Study WARAPORN RATTANONGPHISAT 1,2,*, FEDERICO M. BUTERA 2, R.S. ADHIKARI 2 AND CHALERMPORN YOOPRATETH

### Benefits. Facilities Recommended for this Measure

Benefits Reduced electricity consumption Reduced water expenses Positive occupant feedback due to newer equipment throughout the district Potential rebates for equipment Window Replacement ECM Summary

### Radiant Heating and Cooling Systems BY KWANG WOO KIM, ARCH.D., MEMBER ASHRAE; BJARNE W. OLESEN, PH.D., FELLOW ASHRAE

TECHNICAL FEATURE Fundamentals at Work This article was published in ASHRAE Journal, February 2015. Copyright 2015 ASHRAE. Posted at www.ashrae.org. This article may not be copied and/or distributed electronically

### Makeup Air For Exhaust Systems In Tight Houses. Tony Jellen Engineering Projects

Makeup Air For Exhaust Systems In Tight Houses Tony Jellen Engineering Projects PA Housing & Land Development Conference February 23, 2012 Effects of Kitchen Ventilation on Residential Dwellings Anthony

### HOW TO CONDUCT ENERGY SAVINGS ANALYSIS IN A FACILITY VALUE ENGINEERING STUDY

HOW TO CONDUCT ENERGY SAVINGS ANALYSIS IN A FACILITY VALUE ENGINEERING STUDY Benson Kwong, CVS, PE, CEM, LEED AP, CCE envergie consulting, LLC Biography Benson Kwong is an independent consultant providing

### Theoretical Study on Separate Sensible and Latent Cooling Air-Conditioning System

Purdue University Purdue e-pubs International Refrigeration and Air Conditioning Conference School of Mechanical Engineering 2008 Theoretical Study on Separate Sensible and Latent Cooling Air-Conditioning

### 06150 PORVOO, FINLAND Pelican eco ED(D), Pelican eco EDE(D), Pelican eco EDW(D), Pelican eco EDX(D)

Certificate Certified Passive House Component For cool, temperate climates, valid until 31 December 2013 Passive House Institute Dr. Wolfgang Feist 64283 Darmstadt GERMANY Category: Manufacturer: Heat

### Greenhouse Cooling. Why is Cooling Needed?

Greenhouse Cooling Why is Cooling Needed? Solar radiation is the heat input for the earth can radiate as much as 277 Btu/ft 2 /hr onto the surface of the earth on summer s day in coastal and industrial

### Measuring The Right Thing For Humidity Control It s the Dew Point Stupid!

Page 1 of 6 Measuring The Right Thing For Humidity Control It s the Dew Point Stupid! By Mike Schell, AirTest Technologies Corp. A version of this article appeared in the June 2004 edition of Indoor Air

### Components HVAC General Standards HVAC Guidelines HVAC System Selection Life Cycle Cost Analysis

Components HVAC General System Selection Life Cycle Cost Analysis Outdoor Air Design Values Indoor Air Design Values Outdoor Air Ventilation Welding Ventilation Temperature Control Systems Ductwork HVAC

### Energy Savings in High-Rise Buildings Using High-Reflective Coatings

Energy Savings in High-Rise Buildings Using High-Reflective Coatings Executive Summary: Nevertheless, the simulation analyses showed that when designing a building for low energy consumption, even in cold

### SELECTIVE GLAZING FOR SUN CONTROL

SUN CONTROL GLAZING SELECTIVE GLAZING FOR SUN CONTROL Sun Factor 1st level performance for direct solar energy Solar energy control Solar control coating Only if the glass is exposed to sun rays! 2nd level

### FIRST RADIANT COOLED COMMERCIAL BUILDING IN INDIA CRITICAL ANALYSIS OF ENERGY, COMFORT AND COST

FIRST RADIANT COOLED COMMERCIAL BUILDING IN INDIA CRITICAL ANALYSIS OF ENERGY, COMFORT AND COST Guruprakash Sastry, Senior Manager Green Initiatives Infosys Limited, Bangalore, INDIA ABSTRACT Radiation

### EFFECTS OF INDOOR RELATIVE HUMIDITY ON REFRIGERATED DISPLAY CASE PERFORMANCE

P (5, EFFECTS OF INDOOR RELATIVE HUMIDITY ON REFRIGERATED DISPLAY CASE PERFORMANCE Ronald H. Howell, Professor Luis Rosario, Graduate Student Antonio Bula, Graduate Student Department of Mechanical Engineering

### Saving Heating Costs In Warehouses

2005, American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. (www.ashrae.org). Reprinted by permission from ASHRAE Journal, (Vol. 47, No. 12, December 2005). This article may not

### Moisture Control. It s The Dew Point. Stupid! Its not the humidity.

Moisture Control Its not the humidity. It s The Dew Point Stupid! Mike Schell EpiphanyTec Inc. Santa Barbara, CA mschell@epiphanytec.com 805 687-3175 Matching great technology to market need! Topics SHR

### HVAC Made Easy: A Guide to Heating & Cooling Load Estimation

PDHonline Course M196 (4 PDH) HVAC Made Easy: A Guide to Heating & Cooling Load Estimation Instructor: A. Bhatia, B.E. 2012 PDH Online PDH Center 5272 Meadow Estates Drive Fairfax, VA 22030-6658 Phone