1 Building Performance Simulation for Designers - Energy DesignBuilder // EnergyPlus Tutorial #2 Load Schedules GEOMETRY LOADS RESULTS Diego Ibarra Christoph Reinhart Harvard Graduate School of Design
2 OVERVIEW This document is the second document of a series of tutorials created as a guide for building energy performance simulation beginners. Its focus audience are designers interested in studying the effect of early design decisions such a orientation, shape and façade layout on the energy efficiency of their projects. Throughout the document we will be using DesignBuilder/ EnergyPlus as our simulation tool.
3 OVERVIEW This specific document, Tutorial #2 Load Schedules, will help you to develop and quantitative understanding of: The impact of occupants and other internal loads on indoor environmental conditions in a non-air conditioned space; The impact of occupants and other internal loads on the energy demand of a fully conditioned space; The value of the shoe-box modeling approach to compare basic energy conservation measures (ECM s).
4 SET - UP In case you do not have DesignBuilder already installed on your computer, please refer to the first document of this tutorial series. In that document you will find all the instructions required to set-up DesignBuilder on your computer. Make sure to pay close attention to all the steps and execute them carefully. You may download a FREE 30-day evaluation version of the latest DesignBuilder version from the DesignBuilder Software website. This document is based on DesignBuilder v BETA (release date: 09/26/08). INFO DesignBuilder Software requires you to provide some general information about yourself before you can download the evaluation version. You must be logged in before attempting to download. If you do not have a login and password, you will have to register first.
5 INDEX THE SHOW-BOX MODEL SETTING INTERNAL LOADS SIMULATIONS ANALYZE RESULTS INFO It is recommended that you work through the four sections in the order provided. Further information can be accessed through distributed throughout the text.
6 SHOEBOX MODEL Establishing an appropriate base case building is the first step in evaluating low-energy design and other sustainability strategies during the design process. Furthermore, goals for resource use and costs are set relative to the base case. This task can be difficult, because there is no universal approach. At the early stages of design, detailed knowledge of the building s energy systems is not available (nor its necessary to carry out exploratory energy performance studies). Early in the programming phase, the base case is often a building in the shape of a shoebox with the same assumptions as those called for in the actual building program.
7 SHOEBOX MODEL A "Shoebox" energy model is an initial, oversimplified energy model of a building in which the actual building (or part of the building) is represented as a rectangular box. At this early point one should already work with actual climate data, building type, usage patterns, and utility rates for the projects (if known). The shoebox energy model especially valuable during the schematic design phase before the building form has been determined. It can be build very quickly and can therefore be used to inform early design decisions to optimize building energy performance.
8 SHOEBOX MODEL In this tutorial you will be working with a building model which was created according to the shoebox approach. This approach will allow us to quickly quantify the impact of load schedules for occupancy and other internal loads on the interior environmental conditions of a space. We will be using the same shoebox model in later tutorials while exploring the impact of other ECMs on the energy balance of a space. The assumption is that if (for example) evaporative cooling is effective for the shoebox model, it is likely to be effective for the actual building as well. Again, the intention is to be able to do a quick sensitivity study early on in the design when key design decisions are made. INFO The exact efficacy of measures in a shoe box model compared to a real-design depends on certain assumptions, such as, floor area, envelope surface, etc.
9 SHOEBOX MODEL Note that DesignBuilder has some useful preset building types ( Single Zone and Parametric Building ) to carry out quick shoebox type energy studies in early stages of design. These building types can be found when selecting insert new building. However, in this document we will not be using these templates as we intend to further build on the same model in future tutorials in order to better understand the interdependency of different design variable on the overall energy performance and indoor environmental conditions of a building. INFO The current version of DesignBuilder v does not have the Parametric Building modelling option fully operational.
10 SHOEBOX MODEL We will be working with a file template especially set-up for this tutorial. You can download the template from the course website (follow the instructions detailed further in this document to start working using this template). At the end of this section you should be able to: Understand the basis of a shoe-box modeling approach. Understand the different indoor environmental conditions of a free-floating space and a fully conditioned space.
11 SHOEBOX MODEL Selecting a Template 1. From the course website, download the template named Energy.2.LoadSchedules and save it to a folder of your choice on you PC (see INFO note). To open the file just start DB and you will find the template in the home screen. INFO DesignBuilder will automatically search your machine for all.csb files. You may want to save the file to the default DB folder for templates c:/program files/designbuilder/data/templates
12 SHOEBOX MODEL The template is composed by two shoebox-like spaces built as separate blocks under separate building type. (This is necessary to be able to later compare Fuel Breakdowns). Both spaces are 8.0m x 8.0m x 3.0m with all surfaces set as adiabatic (no heat transfer occurs), except for the south façade and ceiling. I.e. the model represents a top floor, southfacing perimeter space in a mid-sized building. No external obstructions are considered. INFO The roof was not set as an adiabatic surface to increase the impact of the envelope on the thermal behavior of the space. This way, when the optimization of the building envelope is investigated in Tutorial 3 Building Envelope, the improvements of the thermal performance will be more noticeable.
13 SHOEBOX MODEL The construction properties in both spaces are set to IECC External Wall: 3 layers (13mm gypsum plasterboard, 89mm XPS extruded polystyrene and 6mm lightweight metallic cladding, U- value: 0,350 (W/m2K). Exterior Glazing: generic single clear 6mm glazing, U-value: (W/m2K) INFO Thermal properties of the construction are set to a low-market standard for Boston s current construction practices to benefit the later understanding of the impact of envelope optimization. The envelope optimization will be carried out in Tutorial #3 Building Envelope. For more information on the International Energy Conservation Code (IECC) go to
14 SHOEBOX MODEL One shoebox space is set to be naturally ventilated and the other one is set to be fully conditioned (mechanically cooled and heated). The naturally ventilated space is set up so that the natural ventilation is activated (windows are opened) when the outside temperature is below the natural ventilation cooling point of 24C. The fully conditioned space is set up so that the environmental set points (HVAC thermostat) is set to 20C for heating and 24C for cooling INFO Note that when using the calculated natural ventilation model option windows and vents are only opened when: The inside air temperature is above this cooling set point temperature AND the inside air temperature is greater than the outside air temperature AND the operation schedule allows for ventilation.
15 SHOEBOX MODEL Each space is virtually subdivided in 2 symmetrical zones, a core zone and a façade zone. A virtual partition is used so that the local effect of the solar gain in the perimeter zone may be calculated. In the absence of virtual partitions, the risk of overheating could be underestimated due to the distribution of solar gain throughout the open plan space. INFO A virtual partition is an air wall between 2 zones which is introduced to mathematically sub-divide the space, i.e. to tell EnergyPlus to solve the energy and mass equations for two separate areas within a larger open space. Virtual partitions are commonly used for separating perimeter zones from core zones, when there are to be different HVAC provisions within a space or when carrying out daylighting, solar overheating or comfort studies.
16 SIMULATIONS Workflow: 1. First, you will run an annual simulation to review the thermal behavior and energy consumption of both structures without internal loads. 2. Then you will set-up the corresponding internal loads for both spaces and run an annual simulation again, this time to review how the thermal and energy profiles are affected. 3. Finally, you will run a cooling simulation for a design week period to review the internal environmental conditions of both conditioned and unconditioned spaces under extreme conditions
17 SIMULATIONS Running an annual simulation 2. Run an annual simulation at the building level to compare the indoor environmental conditions and energy demand of both, unconditioned and fully conditioned spaces. Note that at this point no internal loads are set up. - No occupancy - No artificial lighting - No plug loads (computer, faxes, photocopy machines, task lights, etc) - No natural ventilation (due to no occupants)
18 SHOEBOX MODEL Results annual simulation Naturally Ventilated Space: Core Zone
19 SHOEBOX MODEL Results annual simulation Naturally Ventilated Space: Perimeter Zone
20 SHOEBOX MODEL Results annual simulation Naturally Ventilated Space When comparing the internal environmental conditions of the naturally ventilated core zone and façade zone: One can see that free floating summer characteristic of the space (both zones), where the temperature rises over 35C. One can also see that this condition does not prevail in winter due to the intervention of heating. As a result the inside air temperature doesn t drop below 18C. (The considered heating system is hot water radiator based.) In addition, one can see that both zones have almost the same comfort conditions (as expected since a virtual partition assumes air flow). One must note that this temperature is not in the comfort range with maximum temperature of 35C in the core and the façade zones.
21 SHOEBOX MODEL Results annual simulation Naturally Ventilated Space In the heat balance, the core zone losses, as expected, occur mainly through though the ceiling (-100kWh). The sum of the heat losses (roof and internal natural ventilation with the façade zone) are balanced by the heating system input. Some negligible energy gain/losses are observed due to the thermal mass of the floor and walls. The heat balance of the façade zones shows that the main energy gains are due to solar heat gains, with kWh. This gains are distributed along the whole year, with a small decrease during the summer due to the higher solar angle. At the same time, the window glazing is responsible for most of the heat losses, with a monthly peak of -387kWh in January.
22 SHOEBOX MODEL Results annual simulation Fully Conditioned Space: Core zone
23 SHOEBOX MODEL Results annual simulation Fully Conditioned Space: Perimeter zone
24 SHOEBOX MODEL Results annual simulation Fully Conditioned Space When comparing the internal environmental conditions of fully conditioned core zone and façade zone: The fully conditioned characteristic of the space (in both zone), is evident since the dry bulb air temperatures don t rise over the 26C during the summer months and don t drop down bellow 19C in winter. As in the naturally ventilated space, both zones, the core and façade, have almost the same comfort conditions (1.4C difference in winter). However, due to the cooler air temperatures (26C) one can see that the high surface temperature of the glazing in the south façade has a bigger impact in the operative temperature of the façade zone. In this space the operative temperature rises 0.76C compared to a rise of only 0.17C in the Nat Vent façade zone.
25 SHOEBOX MODEL Results annual simulation Fully Conditioned Space In the heat balance of the core zone, one can clearly see the energy required for heating and cooling the core to the temperatures set in the thermostat (heating and cooling setpoint temperatures) This values are expressed by the Zone/Sys Sensible Heating 115 kwh and Zone/Sys Sensible Cooling -84 kwh. On the other hand, in the façade zone, the high solar heat gains ( kWh) and the high energy losses through window glazing (-418kWh in January), make the energy required for heating and cooling the core to the setpoint temperatures differ drastically: Zone/Sys Sensible Heating 188 kwh and Zone/Sys Sensible Cooling -228 kwh. This demonstrates why HVAC systems are designed using thermal zones to sub-divide spaces with different heat gains/losses.
26 INTERNAL LOADS In this section you will now set up internal loads for both spaces, run an annual simulation again, and the thermal and energy profiles are affected. The internal loads to be added to the spaces are: - Occupants - Turn on Natural Ventilation according to occupants schedules (model operable windows as if occupants will operate them manually) - Artificial Lighting - Plug Loads (Computers, screens, task lights, etc)
27 INTERNAL LOADS Setting Activities and Occupancy 3. At the building level go to the activity tab > Occupancy and set the occupancy to 0.11 people/m2. 4. Turn the Office equipment tab ON and choose 25 w/m2. All plug loads will me lumped in this value (Computers, screens, task lights, etc) You should not modify the assigned schedules for Occupancy or Office equipment. INFO
28 INTERNAL LOADS Setting Lighting Loads 5. At the building level go to the Lighting tab > Lighting Template and select IECC Then, go to the general lighting tab and select 13W/m2. 6. Turn off the Task and Display lighting tab and the Lighting Control.
29 INTERNAL LOADS Setting HVAC Controls 7. At the Nat Vent (block) level go to the HVAC tab > Natural Ventilation > Schedule and change the current schedule to Office_Open_Occ. You can find it in the right hand menu under the Office folder.
30 INTERNAL LOADS Running an annual simulation with loads 8. Run an annual simulation at the building level to compare the indoor environmental conditions and energy demand of both, unconditioned and fully conditioned spaces. Note that at this point internal loads have been set up. - Occupancy: 0.11 per/m2 - Artificial lighting: 13 W/m2 - Plug loads (computer, faxes, photocopy machines, task lights, etc): 25 W/m2 - Natural ventilation has been scheduled with: Open Office Occupancy profiles
34 SIMULATIONS Annual Simulation Results Naturally Ventilated Space With Internal Loads When comparing the internal environmental conditions of the naturally ventilated core zone and the façade zone, this time with internal loads: One can see the clear impact of having internal loads in the interior environmental conditions of the space. Even when occupants can activate Natural Ventilation (by opening 50% of the windows), the interior air temperature rises up to 44C in summer and 23C in winter (outside temp. -3C), due to the high internal loads.
35 SIMULATIONS Annual Simulation Results Naturally Ventilated Space With Internal Loads At this point we are not trying to determine possible strategies to improve the natural ventilation performance of the space, but rather understand the impact of internal loads on a naturally ventilated space. As one can see, the internal loads now cause the space to require mainly cooling strategies over 10 months of the year. Is important to remember that cooling design and heating design simulations are required to further study the daily thermal behavior of the space. By carrying out those simulations one can determine whether heating strategies will be at all required in the space, as well as what are the maximum comfort conditions expected to occur in the space under extreme conditions.
36 SIMULATIONS Results annual simulation Naturally Ventilated Space In the heat balance, now the main heat gains in the core zone are the office equipment with 200 kwh, followed by General lighting with100 kwh. The heat losses by interior convection to the façade zone and by conduction through the ceiling are fairly constant This is to be expected since heat transfer is driven by the temperature difference between interior/exterior or one zone with another, and as the temperature difference between interior and exterior is maintained fairly constant throughout the year. This, along with the fact that the interior temperature is always above the heating set point, which causes the heat flux to be maintained in one direction during the year (monthly totals).
39 SIMULATIONS Results annual simulation Fully Conditioned Space When comparing the internal environmental conditions of fully conditioned core and façade zones: The fully conditioned characteristic of the space (in both zones), is evident since the dry bulb air temperatures don t rise over the 26C during the summer months and don t drop down bellow 18C in winter. As in the naturally ventilated space, both zones, the core and façade, have almost the same comfort conditions (1.4C difference in winter). However, due to the cooler air temperatures (26C) one can see that the high surface temperature of the glazing in the south façade has a bigger impact in the operative temperature of the façade zone. In this space the operative temperature rises 0.76C compared to a rise of only 0.17C in the Nat Vent façade zone.
40 SIMULATIONS Results annual simulation Fully Conditioned Space In the heat balance of the core zone, one can clearly see the energy required for heating and cooling the core to the temperatures set in the thermostat (heating and cooling set point temperatures) With internal loads the space turns clearly into a cooling dominated all year long. On the other hand, in the façade zone, the high solar heat gains ( kWh) and the high energy losses through window glazing (-418kWh in January), make the energy required for cooling the core to the set point temperatures differ drastically: Core Sensible Cooling load kwh and Façade Sensible Cooling load kwh. This is a 32% higher cooling load for the façade than the core, which proves why HVAC systems are designed using thermal zones to sub-divide spaces with different heat gains/losses.
43 SIMULATIONS Compare the Annual Energy Consumption of the both spaces with Internal Loads. The fuel breakdown comparison between the naturally ventilated space and the fully conditioned space show the energy demand by end use. One can see the proportion of energy use for cooling/heating the space versus the energy demand of internal loads. Through the brief analysis sequence provided in this document you should be able to relate the annual energy demands with the internal environmental conditions of each space. For example, the naturally ventilated space has an annual energy demand of 7,500 kwh, compared to the about 12,100 kwh of the fully conditioned space, however, as shown in previous slides, it is not able to meet comfort conditions.
44 EXERCISE Cooling Design Simulation Naturally Ventilated Space and Fully Conditioned Space Now that have run annual energy simulation for both spaces, with and without internal loads, you are encouraged to repeat the analysis for both spaces with internal loads for a Summer Typical Week. Review the simulations interpret the results regarding: The impact of occupancy profiles and their related internal loads schedules on the internal comfort conditions of both spaces. The impact of occupancy profiles and their related internal loads schedules on the energy demand of both spaces. Predominant heat gains and losses in each space and for the different thermal zones.
45 CONCLUSION In this document you have used DesignBuilder to run annual and weekly simulations of two spaces with different heating and cooling strategies. You where able to verify the impact of internal loads on the interior environmental conditions of a space and its energy demand.
46 CONCLUSION This document provided a quick, non-exhaustive overview of the building energy performance simulation capabilities offered by DesignBuilder/EnergyPlus. Should you decide to use this tool in the future consult the REFERENCE section for further reading. Remember: It is your responsibility to learn the assumptions and limitations of the programs you are using. Preparing and running a simulation take time. Before rushing into doing a simulation you should have a clear idea of how the simulations results can help you resolve a specific design question that you could not answer otherwise.
47 NEXT STEP Now you should continue with tutorial #3 in which you will learn how to customize data templates and components (glazing, constructions, schedules, shading devices, etc). Remembers, an energy model can be no more accurate than the assumptions that lie behind both the proposed building and the baseline building model. Even though the model performs complex calculations accurately on this assumptions, the result will be misleading if the assumptions are faulty.
48 ACKNOWLEDGEMENT The development of this document has been supported by the following organizations. Harvard Graduate School of Design: The GSD has been putting special attention to the advancement of environmental building performance, supporting a number of researches in the matter. ( The Presidential Instructional Technology Fellows : The Presidential Instructional Technology Fellows (PITFs) program was established to recruit and train fellows in conjunction with the Schools to work with faculty to develop digital course materials with immediate educational benefits. PITFs leverage existing software tools developed here at Harvard and provide outreach( ge12917).
Building Performance Simulation for Designers - Energy DesignBuilder // EnergyPlus Tutorial #3 Construction Assemblies, Load Reduction & Shading GEOMETRY LOADS RESULTS Diego Ibarra Christoph Reinhart Harvard
Building Performance Simulation for Designers - Energy DesignBuilder // EnergyPlus Tutorial #1 Getting Startedt GEOMETRY LOADS RESULTS Diego Ibarra C Christoph Reinhart Harvard Graduate School of Design
ANSI/ASHRAE Standard 140-2004 Building Thermal Envelope and Fabric Load Tests DesignBuilder Version 1.2.0 (incorporating EnergyPlus version 1.3.0) - June 2006 1.0 Purpose The ANSI/ASHRAE Standard 140-2004
Recognised energy Dynamic Simulation Modelling (DSM) software DesignBuilder is a user interface to the EnergyPlus DSM. EnergyPlus builds on the most popular features and capabilities of BLAST and DOE-2
DesignBuilder EMS - Intro Functionality not provided in standard E+ can be programmed Programming language called E+ Runtime Language (Erl) DesignBuilder extensions added to form DB Erl E+ interprets and
Residential HVAC Load Sizing Training October 14, 2015 David Kaiser Green Code Plan Reviewer DCRA - Green Building Division Regulations of green codes including: Green Building Act Green Construction Code
Climate and Energy Responsive Housing in Continental Climates The Suitability of Passive Houses for Iran's Dry and Cold Climate Farshad Nasrollahi Table of Contents Abstract German Abstract Introduction
CTU Prague, Faculty of Civil Engineering Department of Materials Engineering and Chemistry Thermal properties of contemporary lightweight cavity bricks: a semi-scale experimental study Z. Pavlík, J. Fořt,
Integrated Environmental Solutions Ltd. VE Compliance FAQ The Building Regulations 2010: Conservation of fuel and power Approved Document L2A (2013 edition for use in England) Top Tips for Achieving Compliance
THERMAL SCIENCE: Year 2015, Vol. 19, No. 3, pp. 865-880 865 ENERGY PERFORMANCE MODELLING AND HEAT RECOVERY UNIT EFFICIENCY ASSESSMENT OF AN OFFICE BUILDING by Norbert L. HARMATI a*, Radomir J. FOLI] a,
PCA R&D Serial No. 415 Energy Use in Residential Housing: A Comparison of Insulating Concrete Form and Wood Frame Walls by John Gajda and Martha VanGeem 000 Portland Cement Association KEYWORDS Concrete,
Energy Savings in High-Rise Buildings Using High-Reflective Coatings Executive Summary: Nevertheless, the simulation analyses showed that when designing a building for low energy consumption, even in cold
Design Guidance for New Windows in a Cold Climate Introduction The energy impact due to windows in a home depends on several design decisions climate, window orientation, window area, shading conditions,
Eleventh International IBPSA Conference Glasgow, Scotland July 27-3, 29 IMPACT OF INSULATION ON BUILDING ENERGY CONSUMPTION Jong-Jin Kim and Jin Woo Moon TCAUP, University of, Ann Arbor, USA ABSTRACT The
ResearcH JournaL 2009 / VOL 01.01 www.perkinswill.com PERKINS+WILL RESEARCH JOURNAL / VOL 01.01 05. CONTEXT BASED DESIGN OF DOUBLE SKIN FACADES Climatic Considerations During the Design Process Ajla Aksamija,
HOW TO CONDUCT ENERGY SAVINGS ANALYSIS IN A FACILITY VALUE ENGINEERING STUDY Benson Kwong, CVS, PE, CEM, LEED AP, CCE envergie consulting, LLC Biography Benson Kwong is an independent consultant providing
Heating and cooling challenge in nzeb Experiences from built houses and detailed building simulations calls for a careful and integrated approach when designing heating and cooling systems for nearly zero
Building simulation as an assisting tool in designing an energy efficient building: a case study Michael Pollock, Ya Roderick, David McEwan, Craig Wheatley Integrated Environmental Solutions Limited, West
ABSTRACT Decision-making Methodology & Selection Tools for High-performance Window Systems in U.S. Climates Kerry L. Haglund 1 Selecting a glazing system requires an understanding of a series of variables
Fact Sheet #6 Air Conditioning In this fact sheet you will discover: The opportunity for energy efficiency How air conditioning works Low cost actions to reduce energy usage now Investments to reduce costs
Building Energy Modelling prescriptive An alternative to Design for SANS 10400-XA Contents Complying with the new building energy standard - SANS 10400-XA 3 Compliance options Two rational design routes
THE NATIONAL BUILDING REGULATIONS PART XA: ENERGY EFFICIENCY. Presentation by Peter Henshall-Howard: HEAD: BUILDING DEVELOPMENT MANAGEMENT. A Diagrammatic representation of the relationship between the
Residential HVAC System Sizing William P. Goss University of Massachusetts, Amherst, Massachusetts, USA Corresponding email: email@example.com SUMMARY Heating, ventilating and air-conditioning (HVAC)
Evaluation of Double Skin Glass Facades in terms of Cost Efficiency with respect to Energy Consumption Ikbal Cetiner, MSc., Research Assistant 1 Murat Aygun, PhD., Assoc. Prof. 2 1 Istanbul Technical University.
Proceedings of Conference: Adapting to Change: New Thinking on Comfort Cumberland Lodge, Windsor, UK, 9-11 April 2010. London: Network for Comfort and Energy Use in Buildings, http://nceub.org.uk Natural
GOOD PRACTICE GUIDE 194 Building your own energy efficient house Why save energy How to achieve integrated design Checklist for a low energy home Further information GOOD PRACTICE GUIDE 194 2001 2001 EDITION
The Importance of Building Criteria on Cooling Energy Demand of a Low Cost Residential House: Thailand Case Study WARAPORN RATTANONGPHISAT 1,2,*, FEDERICO M. BUTERA 2, R.S. ADHIKARI 2 AND CHALERMPORN YOOPRATETH
Opening the Bonnet Prof Darren Woolf WYSINWYG 1 WYSINWYG What You See Is NOT What You Get: Looking inside the Pandora s Box Prof Darren Woolf WYSINWYG 2 WYSIWYG implies a user interface that allows the
TESTING AND VALIDATION OF A NEW BUILDING ENERGY SIMULATION PROGRAM Michael J. Witte, Robert H. Henninger, and Jason Glazer GARD Analytics, Inc. Park Ridge, IL 668 USA Drury B. Crawley U.S. Department of
COMPARISON OF DIFFERENT TYPE OF CONFIGURATIONS FOR PHOTOVOLTAIC FAÇADE IN COMPOSITE CLIMATIC ZONE OF INDIA (NEW DELHI) Himanshu Gupta, Sumit Sharma, Sanjay Mathur, Jyotirmay Mathur Malaviya National Institute
Effect of Building Material and Wall Construction on the Energy Consumption Mahmoud A. Hassan 1* Nabil M. Guirguis 1 Amr. Ibrahim 2 Ahmed A. Fahim 1 1 Housing and Building National Research Center, Dokki,
Energy Efficient Hospital Patient Room Design: Effect of Room Shape on Windowto-Wall Ratio in a Desert Climate Ahmed Sherif Hanan Sabry Rasha Arafa Ayman Wagdy [Department of Construction and Architectural
Copyright Agrément South Africa, September 2011 The master copy of this document appears on the website: http://www.agrement.co.za SANS 10400: The application of the National Building Regulations: Protocol
IOSR Journal of Mechanical and Civil Engineering (IOSR-JMCE) ISSN: 2278-1684Volume 3, Issue 6 (Nov. - Dec. 2012), PP 01-06 Software Development for Cooling Load Estimation by CLTD Method Tousif Ahmed Department
Building Information Modeling - Energy Modeling, Lifecycle Energy Usage & Cost Analysis EcoBuild/AEC-ST S600 May 22, 2008 L.A. Presented By Christopher Rippingham, DPR Construction, Inc. Moderated By Andy
THE EFFECT OF WINDOW POSITION AND WINDOW SIZE ON THE ENERGY DEMAND FOR HEATING, COOLING AND ELECTRIC LIGHTING R.M.J. Bokel Department of Architecture, Delft Technical University, Delft, The Netherlands,
Center for Energy and Environment Energy Savings with Window Retrofits Presentation to Energy Design Conference & Expo Duluth, MN February 25, 2014 Agenda v Background v Introduction: What are window retrofits?
Building simulation Case Studies Paul Linden & Guilherme Carrilho da Graça NaturalWorks Inc www.natural-works.com Natural Ventilation Design San Francisco Federal Office Building MORPHOSIS San Francisco
DesignBuilder Simulation + CFD Training Guide DesignBuilder 2008-2011 No part of the manual is to be copied or reproduced in any form without the express agreement of DesignBuilder Software Contents DesignBuilder
A Method to Quantify the Energy Performance in the Urban Quarters Dilay Kesten 1,*, Aysegül Tereci 1 and Ursula Eicker 1 1 Centre of Applied Research - Sustainable Energy Technology (zafh.net), Stuttgart
DEPARTMENT OF TECHNOLOGY AND BUILT ENVIRONMENT SIMULATION OF FtX VENTILATION TECHNIQUE IN A TYPICAL SWEDISH HOUSE Adrián Ferreras Pascual June 2010 Master s Thesis in Energy Systems Master Programme in
Effects of Solar Photovoltaic Panels on Roof Heat Transfer A. Dominguez, J. Kleissl, & M. Samady, Univ of California, San Diego J. C. Luvall, NASA, Marshall Space Flight Center Building Heating, Ventilation
PENNSYLVANIA GREEN ENERGY LOAN FUND Procedures Manual for Quantifying Energy Savings A. Introduction A building project applying for a GELF energy loan must demonstrate that it will result in a 25% reduction
Copyright Agrément South Africa, December 2009 The master copy of this document appears on the website: http://www.agrement.co.za Protocol for the Certification of Energy Simulation Software: First edition,
PLEA2013-29th Conference, Sustainable Architecture for a Renewable Future, Munich, Germany 10-12 September 2013 Parametric Analysis of School Classroom Typologies' Energy Performance MAUREEN TREBILCOCK
797 Double skin façade glazed office buildings; A parametric study for optimized energy and thermal comfort performance H. Poirazis Lund University, Sweden ABSTRACT Highly glazed buildings are often considered
White Paper Nest Learning Thermostat Efficiency Simulation for Ireland Nest Labs September 2014 Introduction This white paper gives an overview of potential energy savings using the Nest Learning Thermostat
Passive Solar Design and Concepts Daylighting 1 Passive Solar Heating Good architecture? The judicious use of south glazing coupled with appropriate shading and thermal mass. Summer Winter Passive solar
ENERGY AUDIT Project : Industrial building United Arab Emirates (Case study) Contact person (DERBIGUM): Leonard Fernandes DERBIGUM project reference : UAE -2014 - EA 103 Author : Daniel Heffinck (DERBIGUM)
Building Energy Analysis Report Report Generated by Efilm, an EnergyPlus based program. Date: 6/8/2012 Project Information Title: Building Filmed in 2012 Address: City/State/Zip: New York, NY 10001 Analyst
equest Introductory Tutorial equest Introductory Tutorial, version 3.64 JAMES J. HIRSCH & ASSOCIATES December 2010 James J. Hirsch & Associates 12185 Presilla Road. Camarillo, CA 93012-9243 Phone 805.553.9000
Selecting Energy Efficient New Windows in California www.efficientwindows.org Janurary 016 Zones 1. Meet the Energy Code & Look for the Windows must comply with your local energy code. Windows that are
Integrated Dynamic Skylight Solutions to Reduce Energy Consumption and Improve Indoor Lighting Quality in US Buildings Erica Cochran, Zhengzhao Pei, Flore Marion, Angela Kolosky, Vivian Loftness and Azizan
White Paper Nest Learning Thermostat Efficiency Simulation for France Nest Labs September 2014 Introduction This white paper gives an overview of potential energy savings using the Nest Learning Thermostat
Retrofit EnerLogic Low-e Window Films Steve DeBusk Global Architectural Technical Services Manager May 18, 2015 ORNL Envelope Stakeholder Workshop Eastman Overview Eastman Global specialty chemical company.
Prepared for: Colorado Governor s Energy Office ENERGY MODELING: A GUIDE FOR THE BUILDING PROFESSIONAL Prepared by: M.E. GROUP and Hutton Architecture Studio Date: May 2011 www.rechargecolorado.com ENERGY
FSEC Publication DN-6 May 1994 Radiant Energy Transfer and Radiant Barrier Systems in Buildings 1 Philip Fairey 2 INTRODUCTION In Florida and other southern climates we depend on a number of strategies
ENERGY AUDIT IN THE KACST BUILDING S. M. Hasnain, S. H. Alawaji, A. M. Al-Ibrahim and S. M. Smiai Energy Research Institute (ERI) King Abdulaziz City for Science and Technology (KACST) P.O. Box 6086, Riyadh
WINDOW SELECTION METHODOLOGIES AND OPTIMIZATION IN HIGH-PERFORMANCE COMMERCIAL BUILDINGS Kerry L. Haglund 1 Recent research estimates that windows in commercial buildings are responsible for almost 1.5%
Market Potential Study for Water Heater Demand Management Rebecca Farrell Troutfetter, Frontier Associates LLC, Austin, TX INTRODUCTION Water heating represents between 13 and 17 percent of residential
Radiant Cooling & Heating w/ Capillary Tubing Chilly at Work? Office Formula Was Devised for Men What Is The Function Of The HVAC System? Offset space heat loss/gain Maintain the space within thermal comfort
Energy Efficiency in Buildings Supplemental Guide to SANS 10400-XA & SANS 204 V. 3.0 Registered to: The Drawing Studio Image: digitalart / FreeDigitalPhotos.net Report Date: 26 August 2014 Practice Name:
FLORIDA SOLAR ENERGY CENTER Creating Energy Independence Since 1975 Impact of Energy-Efficiency Parameters on Home Humidity Rob Vieira Florida Solar Energy Center A Research Institute of the University
Factors affecting energy consumption of buildings Ralf Lindberg, Minna Korpi, Juha Vinha ABSTRACT The thermal insulation requirements of the Building Code of Finland have been tightened several times since
1 LOW EXERGY CEILING HEATING/COOLING SYSTEMS FOR FUTURE BUILDINGS Per Gundersen, M.Sc. Peter G. Schild, Dr.Ing. Norwegian Building Research Institute (NBI) P:O: 123 Blindern, NO-314, Norway e-mail: Per.Gundersen@byggforsk.no
FACTORS AFFECTING ENERGY CONSUMPTION OF BUILDINGS 1 Ralf Lindberg, Professor Minna Korpi, M.Sc. Juha Vinha, Dr.Tech. June 11, 2008 Department of Civil Engineering, Tampere University of Technology 2 BACKGROUND
Selecting Energy Efficient New Windows in Georgia www.efficientwindows.org January 016 ENERGY STAR Zones 1. Meet the Energy Code & Look for the ENERGY STAR Windows must comply with your local energy code.
International Conference on Planning for Low Carbon Cities 22 May 2009 Holistic Approach in Delivering Government Buildings The Low Carbon Concept Ir. HO Sai-king, Assistant Director (Building Services),
Selecting Energy Efficient New Windows in Arizona www.efficientwindows.org January 016 ENERGY STAR Zones 1. Meet the Energy Code & Look for the ENERGY STAR Windows must comply with your local energy code.
research highlight June 2012 Technical Series 12-103 Highly Energy Efficient Building Envelope Retrofits for Houses introduction In Canada approximately 30% of all energy is consumed in buildings, with
AIR CONDITIONING EFFICIENCY F8 Energy eco-efficiency opportunities in Queensland Foundries Hot tips and cool ideas to save energy and money! Air conditioning units or systems are often used by foundries
SUN CONTROL GLAZING SELECTIVE GLAZING FOR SUN CONTROL Sun Factor 1st level performance for direct solar energy Solar energy control Solar control coating Only if the glass is exposed to sun rays! 2nd level
Design of an Eco Friendly and Self Sufficient Cabin This project is a real programme which is to develop a prototype of an eco friendly cabin. In this project, I choose two sites, Aberdeen and Brighton,
Construction Technology Update No. 71 Selecting Residential Window Glazing for Optimum Energy Performance By M.M. Armstrong, A.H. Elmahdy, M.C. Swinton and A. Parekh This Update discusses the results of
6420 Thermal Analysis of Buildings Design Rules of Thumb Model Energy Considerations Christoph Reinhart L01 Building Energy Simulation Analysis Course Objectives This seminar will introduce students to
The higher offices are not sufficiently cooled the first level offices are correctly cooled 600 W/m2 at 11h00 SOUTH facade Architectural and climatic control systems choices Efficient use of energy simulation
Strategies for an Environment Friendly Low Energy Retrofitting of a Health Care Facility in the Hot Climate of UAE Author 1 Author 2 Author 3 Anissa. Tabet Aoul, Kheira Hassan,Ahmed El Syed, Fatma ABSTRACT