Comparison of two calculation methods used to estimate cooling energy demand and indoor summer temperatures

Save this PDF as:

Size: px
Start display at page:

Download "Comparison of two calculation methods used to estimate cooling energy demand and indoor summer temperatures"

Transcription

1 Comparison of two calculation methods used to estimate cooling energy demand and indoor summer temperatures Kai Sirén and Ala Hasan Helsinki University of Technology, Finland Corresponding SUMMARY As a part of the Finnish implementation of the Energy Performance of Buildings Directive, a computational exercise was carried out to choose a simple method for cooling energy estimation. Three different variants of the hourly calculation method and the monthly method were implemented. A model office building was used as the object for the cooling energy predictions. The IDA-ICE building energy software was used to produce reference results. The predicted space cooling energy numbers for a three-month summer-period were compared with the reference results. The comparison shows that the simplest one-capacity variant of the hourly method is underestimating the reference results up to 25% and overestimating up to 30%. A more detailed four-capacity variant is underestimating up to 21% and overestimating up to 19%. The monthly calculation method is not underestimating but overestimating the reference up to 75%. The hourly method is able to estimate the indoor summer maximum temperatures with a deviation less than two degrees from the reference. INTRODUCTION The 2003 published Energy Performance of Buildings Directive (EPBD) [1] is calling for a methodology for calculation of the integrated energy performance of buildings. The methodology shall be set at national or regional level. The Finnish approach was to develop a simple and transparent calculation method, which could be easily implemented. The heating energy calculation was principally based on an existing, simple and standardised method [2] working with a monthly calculation period. For cooling energy demand calculation a choice between two methods had to be done. The first method, running with a time-step of one hour, is based on a simplified thermal resistance-capacitance model of the building zone. It is in principle capable to predict the cooling energy demand and to follow the daily temperature changes inside the building. The second alternative is a variant of the monthly heating energy calculation method [2] now applied to estimate cooling energy demand. Proposals of both methods for EPBD use have been published [3, 4] but with a very restricted evidence of performance. Especially the local weather conditions and the culture for implementing buildings and their heating, cooling and ventilation systems influence the calculated results. For this reason it was important to have some further evidence and comparison results. The objective of the study was to compare the two cooling energy demand calculation methods to have some facts and arguments for the Finnish EPBD methodology implementation work.

2 METHODOLOGY The principle of the comparison study was to calculate the cooling energy demand of a welldefined building zone using the different methods and to compare these results with the results obtained with a reference. As a reference IDA Indoor Climate and Energy 3.0 (IDA- ICE) building simulation software was used [5]. It is a detailed whole-building simulator allowing all issues fundamental to building energy calculation: shape, envelop, glazing, HVAC systems, controls, light, etc. The mathematical models are described in terms of equations in neutral-model-format (NMF), which makes it easy to replace and upgrade program modules. IDA ICE has been shown to perform well in several computational comparisons [6, 7]. The object of the computation exercise was one floor of a model office building, Fig 1. The dimensions, component properties, and load profiles of this building are described in detail in a model building report [8]. For the purpose of the implementation of the cooling energy calculation methods, four zones in the floor were selected: two office rooms (R1 and R2) with a floor area of 10.5 m 2 each and two open plan offices (O1 and O2) with a floor area of 295 m2 each, as shown by Fig. 1. N Office room R m 2 16 m Open plan office O1 295 m 2 Open plan office O2 295 m 2 55 m Office room R m 2 Figure 1. Model building floor plan and studied zones. Two different constructions were specified for the model building. Construction 1 was a standard construction according to the model building [8] with light walls and a heavy concrete floor/ceiling. A second construction, Construction 2 was defined to find out the influence of the building mass on the calculation results. In Construction 2 walls are identical with Construction 1, but the floor and ceiling are considerably lighter. Table 1 shows the ceiling/floor for Construction 2.

3 Table 1. Ceiling/floor thermo physical properties for Construction 2. Thickness (mm) Thermal conductivity (W/m K) Density (kg/m 3 ) Heat capacity (J/kg K) 1 floor covering chipboard steelwork + air gap mineral wool sound insulation plasterboard The effective thermal thickness of the construction components was defined according to the simplified calculation of heat capacity Annex A of ISO [9]. The masses and thermal capacities for the office room and the open plan office for the two constructions are shown in Table 2. C m is the effective heat capacity for the room and A floor is the floor area. Table 2. Masses and thermal capacities of construction components. Construction 1 Construction 2 Office room Open office Office room Open office Mass of external wall (kg) Mass of internal walls (kg) Mass of floor and ceiling (kg) C m / A floor (kj / Km 2 ) Components for heating and cooling exist in each room of the building. Ventilation air through a mechanical ventilation system is supplied to each room. The controlled ventilation air supply temperature is a function of the exhaust air temperature, where a linear relation exists for supply between 21 C and 17 C and exhaust between 22 C and 24 C, respectively. The ventilation supply has a daily and a weekly schedule. The heating and cooling systems and the ventilation maintain the indoor air temperature between specified set limits of 21 C and 24 C around the year. A part of the input data, like internal gains, is defined in the model building description [8]. As weather data Helsinki 1979 weather was used. Other input data like solar heat gain through the window structure and infiltration are taken according to the reference software to focus on the calculation of the building zone thermal behaviour. The input data is arranged as hourly or monthly data, according to the method.

4 HOURLY CALCULATION METHOD The hourly calculation method for cooling is based on the conservation of energy at the temperature node points of a simple resistance-capacitance model of the building zone. The base for this model was adopted from [3]. Because the base model did not include the description of mechanical ventilation, which is the usual way of system implementation in Finland, this feature was added to the model Variant_1, Fig 2. The model runs on an hourly basis where the calculation time step is one hour and the input/output data are arranged as hourly data. The thermal mass of the calculation zone is lumped into one thermal capacitance. The heat transfer connections between the thermal nodes are described with four resistances. The mathematical solution is based on the Crank- Nicolson difference scheme. Both heating and cooling modes can be calculated, as well as variable room air temperature and variable cooling system operation. A node point and a heat capacity flow for mechanical ventilation supply are also included. Tsu Hven Ti Hinf φhc Te Hwin Ts Hsi φi heat gains φs Hms φm Hem Tm Cm, Am Figure 2. Hourly method, model Variant_1. In Fig. 2, T e is outdoor air temperature, T i indoor air temperature, T m mass temperature, T s is a star (operative) temperature, H ven ventilation heat flow, H inf the infiltration heat flow, H win the window thermal conductance, Hem the external structure thermal conductance, and H ms and H is thermal conductances between respective node points. The heating power added or cooling power removed from the room is φ hc, heat gains to the internal nodes are φ i, φ s and φ m, the effective heat capacity for the zone C m and the equivalent area for the zone capacity A m. The computation procedure [3] begins with calculation of the internal gains, including the solar heat gain. The gains are allocated to the internal node points according to certain weights. The heating/cooling power is kept equal to zero at the first stage. The mass-node temperature is determined from the Crank-Nicolson energy conservation equation for the mass-node. The star temperature and the air temperature are determined from the node energy conservation equations. If the resulting air temperature T i is in the temperature control set

5 limits, the need for heating or cooling is zero and the calculation can proceed to the next hour. If the resulting air temperature is above the higher set limit, the air temperature is set equal to the upper limit (24 o C) and the cooling energy needed to keep this temperature level is calculated. In case of heating the procedure is analogous. To find out whether increasing the number of the node points gives any advantage in the cooling energy demand calculation, the model Variant_1 was further modified into a fourcapacity model Variant_2, Fig 3. The star node was rejected because the model was used for energy calculations and there was no need for an operative temperature. Two capacity nodes representing the building mass (walls, ceiling, floor) in more detail were added and the air node was also given a heat capacity. The calculation procedure is in principle similar than for the previous variant. There are four differential conservation equations instead of one and no equation for star node. The solution is based on a difference scheme. To keep the mathematical manipulation as simple as possible, the usual matrix inversion is avoided by a sequential solution of the equations. The gains are identical but allocated in a slightly different way to the node points. Tsu Hven Hinf φi φhc Tiw Te Hwin Ti Hiw Cm4 Hwe Tew Hwi Cm1 Hfc Cm3 Cm2 Fig. 3. Hourly method, model Variant_2. Finally a third model Variant_3 was made out of Variant_2 by disengaging the external structure from the outdoor air point Te and engaging it to a new sol-air temperature node T sa to account for the absorbed solar radiation on the external wall structures. The determination of the sol-air temperature was based on the energy balance of the building external surface. MONTHLY CALCULATION METHOD The monthly method to calculate cooling energy demand [4] is based on earlier methods used for heating energy calculation [2]. The time period for the calculation is one month. All input

6 data is one-month average or cumulative values. The main principle of the method is the longterm energy balance for the building zone. Without cooling the cumulative energy from the heat gains (solar + internal) equal the heat losses. The indoor temperature is free floating and exceeds the set temperature from time to time. Introducing cooling to the zone keeps the internal temperature below or equal to the set temperature. The cooling energy is less than the gains because a part of the losses is compensating the gains: Q = Q η Q (1) c g l l where Q c is cooling energy demand, Q g is thermal energy from gains, Q l is loss term and η l is the utilization factor for heat losses. It has been shown [4] that equation (1) can be converted into Q = (1 η ) Q (2) c g g where η g is now the utilization factor for heat gains initially used for the heating demand calculations. The utilization factor η g depends on the gain-loss ratio, the time constant of the zone and two parameters a 0 and τ 0. Different values for these parameters have been used [4,10,11] depending on the application. Here the values a 0 = 1.83 and τ 0 =83.3 for cooling of non-residential buildings according to NEN 2916 standard were adopted [4]. RESULTS With the hourly method and the reference software a period of four months May August was calculated using the hourly weather data of Helsinki The first month was a preperiod to let the structure temperatures find their natural temperature levels. The three following months were for energy calculation. The monthly method was utilising the monthly average temperatures and cumulative energy values derived from the same hourly weather data. Results for the space cooling energy demand during the period June, July and August for the different calculation methods, zones and building constructions are shown in Table 3. In case of the single office rooms Table 3 shows that all three implementations of the hourly method mainly underestimate the reference values. Variant_3 seems to perform best except in case of the North facing lighter Construction 2, where it overestimates the reference value by 17 %. This is a consequence of the sol-air temperature, which is the only difference between Variant_2 and Variant_3. The monthly method predicts the cooling energy demand very close to the reference values for the south facing office rooms but overestimates up to 76% for the north facing rooms where the gains are much smaller. Both methods overestimate the reference cooling energy demand numbers for the open space office case. The percentage difference is larger for the North facing office than for the South facing office. The construction type seems not to have any significant effect on the hourly method results. The monthly method overestimates less for the light structure Construction 2.

7 Table 3 Predicted space cooling energy demand for the period June August. Calculation method constr. 1 constr. 2 Office room R1 facing South cooling energy cooling/ kwh reference Office room R2 facing North cooling energy cooling/ kwh reference Open office O1 facing South cooling energy cooling/ kwh reference Open office O2 facing North cooling energy cooling/ kwh reference Hourly V_ Hourly V_ Hourly V_ Monthly IDA Hourly V_ Hourly V_ Hourly V_ Monthly IDA In general, the rate of overestimation of the reference values is increasing with decreasing structure capacity and decreasing gains for the hourly calculation method, and vice versa. The monthly calculation method behaves in a different way. The rate of overestimation is increasing with increasing structure capacity and decreasing gains. One important factor in assessing the need for active cooling is the behaviour of the indoor air temperature during the summer period. If this temperature is exceeding the specified limits without cooling, there obviously is a need for cooling. The hourly calculation method is able to provide this information. The temperature limits, which are used for energy calculation, are inactivated and the indoor air temperature is let to float during the computation. The results for the period June August show that the hourly Variant_1 is overestimating the maximum indoor temperature by 2.2 o C compared with the reference result. The hourly Variant_2 is overestimating the maximum temperature only by 1.8 o C. The monthly method is not able to provide useful information related to temperature maximum or minimum values. CONCLUSIONS A computational exercise for the assessment of two simplified calculation methods, the hourly method and the monthly method has been carried out. The space cooling energy demand for four different zones of an office building was predicted with three variants of the hourly method and the monthly method. The IDA-ICE building energy software was used as a reference. The predicted cooling energies for a three-month period vary from 75% to 175% compared to the reference results. The hourly method implementations underestimate the reference values for a heavy structure and high gain and overestimate for a light structure and small gain values. The monthly method mainly overestimates, the more the smaller the internal gains.

8 As a part of the Finnish implementation for the cooling energy calculation method of the Energy Performance of Buildings Directive, a one-capacity variant of the hourly calculation method was further developed, tested and proposed for the Finnish authorities. For the Finnish implementation of the EPBD the monthly calculation method was chosen. REFERENCES 1. Directive 2002/91/EC of the European Parliament and of the Council of 16. December 2002 on the energy performance of buildings. Official Journal of the European Communities, L1, , pp ISO Thermal performance of buildings Calculation of energy use for space heating. International Organisation for Standardisation, J. C. Visier and J. R. Millet. Proposal for a simplified hourly calculation method, report DDD/CVA R, CSTB, Centre Scientifique et Technique du Batimont, July D. van Dijk, M. Spiekman and P. de Wilde. Monthly method to calculate cooling demand for EP regulations, TNO, Building and Construction Research, Department of Sustainable Energy and Buildings, Delft, The Netherlands, February M Achermann and G Zweifel. RADTEST Radiant Cooling and Heating Test Cases. A report of Task 22, sub Task C. Building Energy Analysis Tools. Comparative Evaluation Tests, M Achermann. Validation of IDA ICE Version Hochschule Technik+Architektur Luzern J. Heinonen, J. Kurnitski and T. Tissari. RET model office building for energy calculations, Helsinki University of Technology, HVAC-laboratory, ISO Thermal performance of building components - Dynamic thermal characteristics- Calculation methods, 1999.

Evaluation of Double Skin Glass Facades in terms of Cost Efficiency with respect to Energy Consumption

Evaluation of Double Skin Glass Facades in terms of Cost Efficiency with respect to Energy Consumption Ikbal Cetiner, MSc., Research Assistant 1 Murat Aygun, PhD., Assoc. Prof. 2 1 Istanbul Technical University.

Crawl space heat and moisture behaviour

Crawl space heat and moisture behaviour Miimu Airaksinen, Dr., Technical Research Centre of Finland, VTT miimu.airaksinen@vtt.fi, www.vtt.fi KEYWORDS: crawl space, moisture, evaporation from ground, ground

ANSI/ASHRAE Standard 140-2004 Building Thermal Envelope and Fabric Load Tests

ANSI/ASHRAE Standard 140-2004 Building Thermal Envelope and Fabric Load Tests DesignBuilder Version 1.2.0 (incorporating EnergyPlus version 1.3.0) - June 2006 1.0 Purpose The ANSI/ASHRAE Standard 140-2004

CHAPTER 3. BUILDING THERMAL LOAD ESTIMATION

CHAPTER 3. BUILDING THERMAL LOAD ESTIMATION 3.1 Purpose of Thermal Load Estimation 3.2 Heating Load versus Cooling Load 3.3 Critical Conditions for Design 3.4 Manual versus Computer Calculations 3.5 Heating

Factors affecting energy consumption of buildings

Factors affecting energy consumption of buildings Ralf Lindberg, Minna Korpi, Juha Vinha ABSTRACT The thermal insulation requirements of the Building Code of Finland have been tightened several times since

Eco Pelmet Modelling and Assessment. CFD Based Study. Report Number 610.14351-R1D1. 13 January 2015

EcoPelmet Pty Ltd c/- Geoff Hesford Engineering 45 Market Street FREMANTLE WA 6160 Version: Page 2 PREPARED BY: ABN 29 001 584 612 2 Lincoln Street Lane Cove NSW 2066 Australia (PO Box 176 Lane Cove NSW

Measurement and simulations of air pressure in a two-storey detached house and in a five-storey apartment building

Annex 41 MOIST-ENG, Working meeting, 16-18 April 2007, Florianopolis, Brazil Measurement and simulations of air pressure in a two-storey detached house and in a five-storey apartment building Targo Kalamees

Energy efficiency potential of radiant and convective room units with utilization of building thermal mass in cooling design conditions

Energy efficiency potential of radiant and convective room units with utilization of building thermal mass in cooling design conditions Panu Mustakallio #1, Zhecho Bolashikov *2, Tetiana Mialyk #3, Risto

Software Development for Cooling Load Estimation by CLTD Method

IOSR Journal of Mechanical and Civil Engineering (IOSR-JMCE) ISSN: 2278-1684Volume 3, Issue 6 (Nov. - Dec. 2012), PP 01-06 Software Development for Cooling Load Estimation by CLTD Method Tousif Ahmed Department

Saving Heating Costs In Warehouses

2005, American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. (www.ashrae.org). Reprinted by permission from ASHRAE Journal, (Vol. 47, No. 12, December 2005). This article may not

COMPARISON OF THE THERMAL ENVIRONMENT IN ROOMS WITH CHILLED BEAM AND RADIANT PANEL SYSTEMS

COMPARISON OF THE THERMAL ENVIRONMENT IN ROOMS WITH CHILLED BEAM AND RADIANT PANEL SYSTEMS Risto Kosonen, Panu Mustakallio Arsen Melikov 2, Marcin Duszyk 2 Oy Halton Group Ltd., Helsinki, Finland. 2 International

FACTORS AFFECTING ENERGY CONSUMPTION OF BUILDINGS

FACTORS AFFECTING ENERGY CONSUMPTION OF BUILDINGS 1 Ralf Lindberg, Professor Minna Korpi, M.Sc. Juha Vinha, Dr.Tech. June 11, 2008 Department of Civil Engineering, Tampere University of Technology 2 BACKGROUND

Double skin façade glazed office buildings; A parametric study for optimized energy and thermal comfort performance

797 Double skin façade glazed office buildings; A parametric study for optimized energy and thermal comfort performance H. Poirazis Lund University, Sweden ABSTRACT Highly glazed buildings are often considered

Thermal insulation performance of reflective material layers in well insulated timber frame structures

Thermal insulation performance of reflective material layers in well insulated timber frame structures Sivert Uvsløkk, Senior Scientist. SINTEF Bygforsk; sivert.uvslokk@sintef.no Heidi Arnesen, Research

Energy Efficient HVAC-system and Building Design

Energy Efficient HVAC-system and Building Design Maija Virta 1, Harri Itkonen 1, Panu Mustakallio 1, Risto Kosonen 1 1 Halton Oy, Finland Corresponding email: maija.virta@halton.com SUMMARY This paper

Adaptive strategies for office spaces in the UK climate

International Conference Passive and Low Energy Cooling 631 Adaptive strategies for office spaces in the UK climate I. Gallou Environment & Energy Studies Programme, Architectural Association Graduate

Diego Ibarra Christoph Reinhart Harvard Graduate School of Design

Building Performance Simulation for Designers - Energy DesignBuilder // EnergyPlus Tutorial #2 Load Schedules GEOMETRY LOADS RESULTS Diego Ibarra Christoph Reinhart Harvard Graduate School of Design OVERVIEW

Building codes are presently moving towards new

Heating and cooling challenge in nzeb Experiences from built houses and detailed building simulations calls for a careful and integrated approach when designing heating and cooling systems for nearly zero

DYNAMIC SIMULATION REGARDING THE CONDENSATION RISK ON A COOLING CEILING INSTALLED IN AN OFFICE ROOM. Tiberiu Catalina 1, Joseph Virgone 1

DYNAMIC SIMULATION REGARDING THE CONDENSATION RISK ON A COOLING CEILING INSTALLED IN AN OFFICE ROOM Tiberiu Catalina 1, Joseph Virgone 1 1 Centre de Thermique de Lyon CETHIL, UMR 5008, INSA de Lyon, Université

Kinetic Molecular Theory. A theory is a collection of ideas that attempts to explain certain phenomena.

Kinetic Molecular Theory A theory is a collection of ideas that attempts to explain certain phenomena. A law is a statement of specific relationships or conditions in nature. After centuries of questioning

Drury B. Crawley U.S. Department of Energy Washington, DC 20585 USA

TESTING AND VALIDATION OF A NEW BUILDING ENERGY SIMULATION PROGRAM Michael J. Witte, Robert H. Henninger, and Jason Glazer GARD Analytics, Inc. Park Ridge, IL 668 USA Drury B. Crawley U.S. Department of

A MONTHLY METHOD FOR CALCULATING ENERGY PERFORMANCE IN THE CONTEXT OF EUROPEAN BUILDING REGULATIONS

Ninth International IBPSA Conference Montréal, Canada August 15-18, 2005 A MONTHLY METHOD FOR CALCULATING ENERGY PERFORMANCE IN THE CONTEXT OF EUROPEAN BUILDING REGULATIONS H. van Dijk, M. Spiekman and

Impact of Insulation on Reduction of Energy Consumption in Buildings Based on Climate in Iran

American-Eurasian J. Agric. & Environ. Sci., 14 (): 97-103, 014 ISSN 1818-6769 IDOSI Publications, 014 DOI: 10.589/idosi.aejaes.014.14.0.098 Impact of Insulation on Reduction of Energy Consumption in Buildings

USING ENERGY SIMULATION TO OPERATIVE TEMPERATURE EVALUATION. Vladimir Zmrhal, Frantisek Drkal

USING ENERGY SIMULATION TO OPERATIVE TEMPERATURE EVALUATION Vladimir Zmrhal, Frantisek Drkal Department of Environmental Engineering, Faculty of Mechanical Engineering, Czech Technical University in Prague

Module 3.8. Window U-value

Module 3.8 Window U-value Learning Outcomes On successful completion of this module learners will be able to - Describe the concept of U-values and alternative energy rating system for windows. 2 Calculation

Passive House for a cold climate

Jyri Nieminen VTT jyri.nieminen@vtt.fi, http://www.vtt.fi/ Riikka Holopainen VTT riikka.holopainen@vtt.fi, http://www.vtt.fi/ Kimmo Lylykangas Helsinki University of Technology kimmo.lylykangas@hut.fi,

Areas. Net heated area

NB: Unofficial translation, legally binding only in Finnish and Swedish Annex to the explanatory memorandum for the Ministry of the Environment Decree on improving the energy performance of buildings undergoing

Passive Solar Design and Concepts

Passive Solar Design and Concepts Daylighting 1 Passive Solar Heating Good architecture? The judicious use of south glazing coupled with appropriate shading and thermal mass. Summer Winter Passive solar

Energy Efficiency in Buildings

Energy Efficiency in Buildings Supplemental Guide to SANS 10400-XA & SANS 204 V. 3.0 Registered to: The Drawing Studio Image: digitalart / FreeDigitalPhotos.net Report Date: 26 August 2014 Practice Name:

Simulation of the Effects of Occupant Behaviour on Indoor Climate and Energy Consumption

Simulation of the Effects of Occupant Behaviour on Indoor Climate and Energy Consumption Rune Vinther Andersen, Bjarne Olesen and Jørn Toftum International Centre for Indoor Environment and Energy, Department

LOW EXERGY CEILING HEATING/COOLING SYSTEMS FOR FUTURE BUILDINGS

1 LOW EXERGY CEILING HEATING/COOLING SYSTEMS FOR FUTURE BUILDINGS Per Gundersen, M.Sc. Peter G. Schild, Dr.Ing. Norwegian Building Research Institute (NBI) P:O: 123 Blindern, NO-314, Norway e-mail: Per.Gundersen@byggforsk.no

SIMULATION OF FtX VENTILATION TECHNIQUE IN A TYPICAL SWEDISH HOUSE

DEPARTMENT OF TECHNOLOGY AND BUILT ENVIRONMENT SIMULATION OF FtX VENTILATION TECHNIQUE IN A TYPICAL SWEDISH HOUSE Adrián Ferreras Pascual June 2010 Master s Thesis in Energy Systems Master Programme in

Effect of Building Material and Wall Construction on the Energy Consumption

Effect of Building Material and Wall Construction on the Energy Consumption Mahmoud A. Hassan 1* Nabil M. Guirguis 1 Amr. Ibrahim 2 Ahmed A. Fahim 1 1 Housing and Building National Research Center, Dokki,

Improved properties of rock mineral wool for fire resistant sandwich panels

Improved properties of rock mineral wool for fire resistant sandwich panels Kresimir Antolic EPAQ, Dublin, 24 25.10.2013 Main activity is consulting in the field of sandwich panels and steel constructions

Window Thermal Performance Optimization in Governmental Emirati Housing Prototype in Abu Dhabi, UAE

Window Thermal Performance Optimization in Governmental Emirati Housing Prototype in Abu Dhabi, UAE Abuimara, Tareq A 1 ; Tabet Aoul, Kheira A. 1 1 Department of Architectural Engineering, United Arab

FINAL DRAFT pren 15255

EUROPEAN STANDARD NORME EUROPÉENNE EUROPÄISCHE NORM FINAL DRAFT pren 15255 April 2007 ICS 91.120.10 English Version Thermal performance of buildings - Sensible room cooling load calculation - General criteria

CONCRETE FOR ENERGY EFFICIENT AND COMFORTABLE BUILDINGS. Francesco Biasioli Politecnico di Torino, Italy

CONCRETE FOR ENERGY EFFICIENT AND COMFORTABLE BUILDINGS Francesco Biasioli Politecnico di Torino, Italy Mats Öberg NCC Construction Sweden AB, Sweden SUMMARY A heavy material such as concrete is capable

Some key aspects to consider ventilative cooling in energy performance regulations

Some key aspects to consider ventilative cooling in energy performance regulations François Rémi Carrié, ICEE Valérie Leprince, PLEIAQ Maria Kapsalaki, INIVE International Workshop on summer comfort technologies

Construction simulations with inside and outside insulation of temperature and vapor

Construction simulations with inside and outside insulation of temperature and vapor 1 Research goal To separate the controlled indoor climate from the fluctuating outdoor temperature and reduce energy

Investigation of Multilayered Phase-Change- Material Modeling in ESP-R

Purdue University Purdue e-pubs International High Performance Buildings Conference School of Mechanical Engineering 10 Investigation of Multilayered Phase-Change- Material Modeling in ESP-R Fabio Almeida

MODELLING COUPLED HEAT AND AIR FLOW: PING-PONG VS ONIONS

MODELLING COUPLED HEAT AND AIR FLOW: PING-PONG VS ONIONS Jan Hensen University of Strathclyde Energy Systems Research Unit 75 Montrose Street, GLASGOW G1 1XJ, Scotland Email: jan@esru.strath.ac.uk SYNOPSIS

The Influence of Insulation Styles on the Air Conditioning Load of Japanese Multi- Family Residences

The Influence of Insulation Styles on the Air Conditioning Load of Japanese Multi- Family Residences Yupeng Wang 1, and Hiroatsu Fukuda 2 1 Department of BCEE, Concordia University, Canada, Email: wangyupeng0628@gmail.com

THE EFFECT OF WINDOW POSITION AND WINDOW SIZE ON THE ENERGY DEMAND FOR HEATING, COOLING AND ELECTRIC LIGHTING. R.M.J. Bokel

THE EFFECT OF WINDOW POSITION AND WINDOW SIZE ON THE ENERGY DEMAND FOR HEATING, COOLING AND ELECTRIC LIGHTING R.M.J. Bokel Department of Architecture, Delft Technical University, Delft, The Netherlands,

Building envelope and heat capacity: re-discovering the thermal mass for winter energy saving

346 2nd PALENC Conference and 28th AIVC Conference on Building Low Energy Cooling and Building envelope and heat capacity: re-discovering the thermal mass for winter energy saving S. Ferrari Politecnico

THE BIG STAR: A genius insulation from jute fibre.

TWO STRONG PARTNERS: ecological buildings systems + Thermo Natur THE BIG STAR: A genius insulation from jute fibre. ADVANTAGES: Best summer heat protection Very attractive price Resource-friendly INSULATING

BUILDING ENERGY DEMAND AGGREGATION AND SIMULATION TOOLS A DANISH CASE STUDY

BUILDING ENERGY DEMAND AGGREGATION AND SIMULATION TOOLS A DANISH CASE STUDY P. Gianniou; A. Heller; C. Rode Department of Civil Engineering, Technical University of Denmark, Kgs. Lyngby ABSTRACT Nowadays,

COOLING AND HEATING OF BUILDINGS BY ACTIVATING THEIR THERMAL MASS WITH EMBEDDED HYDRONIC PIPE SYSTEMS -

pcoolingandheating COOLING AND HEATING OF BUILDINGS BY ACTIVATING THEIR THERMAL MASS WITH EMBEDDED HYDRONIC PIPE SYSTEMS - Bjarne W. Olesen, Ph.D. D. F. Liedelt "Velta" Summary Due to intensive use of

IMPROVING CALCULATIONS OF BUILDING ENERGY CONSUMPTION BASED ON TEN YEAR MEASURED DATA

IMPROVING CALCULATIONS OF BUILDING ENERGY CONSUMPTION BASED ON TEN YEAR MEASURED DATA Mihkel Kiviste, Ralf Lindberg, Virpi Leivo Tampere University of Technology mihkel.kiviste@tut.fi, ralf.lindberg@tut.fi,

Thermal properties of contemporary lightweight cavity bricks: a semi-scale experimental study

CTU Prague, Faculty of Civil Engineering Department of Materials Engineering and Chemistry Thermal properties of contemporary lightweight cavity bricks: a semi-scale experimental study Z. Pavlík, J. Fořt,

Carnegie Mellon University School of Architecture, Department of Mechanical Engineering Center for Building Performance and Diagnostics

Carnegie Mellon University School of Architecture, Department of Mechanical Engineering Center for Building Performance and Diagnostics A Presentation of Work in Progress 4 October 2006 in the Intelligent

Case study on residential building renovation and its impact on the energy use and thermal comfort

Case study on residential building renovation and its impact on the energy use and thermal comfort Hanne Kauko, Maria Justo Alonso, Ole Stavset and Ingrid Camilla Claussen SINTEF Energy Research Motivation

Proceedings: The Second International Conference on Building Energy and Environment 2012

Topic 11. Computer tools and experimental techniques for assessment of building energy and built environments Energy Performance Evaluation of New Residential Buildings with a Low- Temperature Heating

CFD SIMULATION OF SDHW STORAGE TANK WITH AND WITHOUT HEATER

International Journal of Advancements in Research & Technology, Volume 1, Issue2, July-2012 1 CFD SIMULATION OF SDHW STORAGE TANK WITH AND WITHOUT HEATER ABSTRACT (1) Mr. Mainak Bhaumik M.E. (Thermal Engg.)

BIPV modules replace. These advantages make BIPV one of the fastest growing segments of the photovoltaic industry [3]. PV specialists and innovative d

COMPARISON OF DIFFERENT TYPE OF CONFIGURATIONS FOR PHOTOVOLTAIC FAÇADE IN COMPOSITE CLIMATIC ZONE OF INDIA (NEW DELHI) Himanshu Gupta, Sumit Sharma, Sanjay Mathur, Jyotirmay Mathur Malaviya National Institute

Residential HVAC Load Sizing Training October 14, 2015. David Kaiser Green Code Plan Reviewer

Residential HVAC Load Sizing Training October 14, 2015 David Kaiser Green Code Plan Reviewer DCRA - Green Building Division Regulations of green codes including: Green Building Act Green Construction Code

Schedule Method Summary Sheet

Schedule Method Summary Sheet Address: House/Flat/Unit.: Street: Suburb: Climate Zone: Climate Zone 2 te: all Wellington Regions are Climate Zone 2) Glazing Provisions : see guidance notes for commentary

Adapting to Change: New Thinking on Comfort Natural ventilation in UK schools: design options for passive cooling Steven Firth* and Malcolm Cook

Proceedings of Conference: Adapting to Change: New Thinking on Comfort Cumberland Lodge, Windsor, UK, 9-11 April 2010. London: Network for Comfort and Energy Use in Buildings, http://nceub.org.uk Natural

Frost Damage of Roof Tiles in Relatively Warm Areas in Japan

Frost Damage of Roof Tiles in Relatively Warm Areas in Japan Influence of Surface Finish on Water Penetration Chiemi IBA Hokkaido Research Organization, Japan Shuichi HOKOI Kyoto University, Japan INTRODUCTION

PROTOCOL FOR BUILDING ENERGY ANALYSIS SOFTWARE For Class 3, 5, 6, 7, 8 and 9 buildings

PROTOCOL FOR BUILDING ENERGY ANALYSIS SOFTWARE For Class 3, 5, 6, 7, 8 and 9 buildings Version 2006.1 AUSTRALIAN BUILDING CODES BOARD JANUARY 2006 TABLE OF CONTENTS Foreword 1. Scope 2. Purpose and context

Sistema de Etiquetagem Energética de Produtos (SEEP) Energy Labeling System for Products

Sistema de Etiquetagem Energética de Produtos (SEEP) Energy Labeling System for Products 10 reasons for an energy labeling system (1/2) The buildings sector is responsible for a considerable share of final

Computational modelling and experimental verification of the effective thermal conductivity of hollow bricks

Advanced Computational Methods and Experiments in Heat Transfer XII 293 Computational modelling and experimental verification of the effective thermal conductivity of hollow bricks J. Kočí, J. Maděra,

Demand controlled ventilation A case study for existing Swedish multifamily buildings

Energy and Buildings 36 (2004) 1029 1034 Demand controlled ventilation A case study for existing Swedish multifamily buildings Vitalijus Pavlovas Department of Building Technology, Building Services Engineering,

3-D Modeller Rendered Visualisations

Recognised energy Dynamic Simulation Modelling (DSM) software DesignBuilder is a user interface to the EnergyPlus DSM. EnergyPlus builds on the most popular features and capabilities of BLAST and DOE-2

Performance Estimation of Water Thermal Energy Storage Tank by Using Simplified Simulation

Performance Estimation of Water Thermal Energy Storage Tank by Using Simplified Simulation M. Kubota, K. Sagara, T. Yamanaka, H. Kotani Division of Global Architecture, Graduate School of Engineering,

Models and Methods in Applied Sciences

Energy consumption and energy saving in Malaysian office buildings S.Sadrzadehrafiei, K.Sopian S.Mat, C.Lim Solar Energy Research Institute University Kebangsaan Malaysia 43600, Bangi, Malaysia s.sadr.r@gmail.com,

Energy Efficient Building Design College of Architecture Illinois Institute of Technology, Chicago. Ceiling/Airspace

HEAT GAINS and LOSSES : ROOFS and WALLS Wall Roof Ts To Ts To Ti Ceiling/Airspace Ti Roof and wall are analyzed in the same way. In winter the heat loss is simple transmission based on the inside and outside

Test Report No. C926LPEN

Institut für Solartechnik Hochschule für Technik Rapperswil Oberseestrasse 10, CH 8640 Rapperswil Tel +41 55 222 48 21, Fax +41 55 222 48 44 www.solarenergy.ch Ordered by: AMK-Collectra AG Bahnweg Nord

Moisture Content in Insulated Basement Walls

Moisture Content in Insulated Basement Walls Peter Blom,PhD, SINTEF Building and Infrastructure; peter.blom@sintef.no, www.sintef.no/byggforsk Sverre B. Holøs M.Sc. SINTEF Building and Infrastructure;

Windows and glazed area technologies and materials in Europe. Bertrand Cazes

Windows and glazed area technologies and materials in Europe Bertrand Cazes IEA - Building Envelope Technologies and Policies Workshop 17 Nov 2011 About Glass for Europe 4 member companies and 1associate:

Coupling Forced Convection in Air Gaps with Heat and Moisture Transfer inside Constructions

Coupling Forced Convection in Air Gaps with Heat and Moisture Transfer inside Constructions M. Bianchi Janetti 1, F. Ochs 1 and R. Pfluger 1 1 University of Innsbruck, Unit for Energy Efficient Buildings,

Delivering on innovation and market uptake. Best-in-cases of nzeb. Ramon Pascual Bucharest May 8th, 2015

www.zebra2020.eu Delivering on innovation and market uptake. Best-in-cases of nzeb Ramon Pascual Bucharest May 8th, 2015 Outline nzeb Database Best in cases of nzeb Climates in Europe Preliminary results

Passive Houses: Principles and Projects 7 February Climate zone North. Nonresidential. For 1-2 family houses with electric resistance heating:

Passive houses: Principles and Projects 1. Background and definitions 2. Description of passive row houses in Lindås / Gothenburg 3. Results from measurements 4. Results from simulations - Important parameters

1/7 2009/11/14 上 午 11:10 Manage this Assignment: Chapter 16 Due: 12:00am on Saturday, July 3, 2010 Note: You will receive no credit for late submissions. To learn more, read your instructor's Grading Policy

PRINCIPLES OF ENERGY EFFICIENT HOUSE DESIGN

PRINCIPLES OF ENERGY EFFICIENT HOUSE DESIGN David Baetge B Ec, Dip ME, Grad IE(Aust), P Eng Thermal Performance Assessor B: (03) 5962 6410 M: 0417 319 830 W: www.postbeam.com.au E: david@postbeam.com.au

Energy audit in Finland

Energy audit in Finland NorTech Oulu Lauri Mikkonen Energy Audit in Finland An energy audit tells about the energy efficiency and total energy consumption in a building, including all consumed heating,

The Influence Of Window Type And Orientation On Energy-Saving In Buildings Application To A Single Family Dwelling

The Influence Of Window Type And Orientation On Energy-Saving In Buildings Application To A Single Family Dwelling Urbikain M. K., Mvuama M. C., García Gáfaro C. and Sala Lizarraga J. M. The University

HEAT LOAD AND SOLAR GAIN PREDICTION FOR SOLID WALL DWELLINGS RETROFITTED WITH TRIPLE VACUUM GLAZING FOR SELECTED WINDOW TO WALL AREA RATIOS

HEAT LOAD AND SOLAR GAIN PREDICTION FOR SOLID WALL DWELLINGS RETROFITTED WITH TRIPLE VACUUM GLAZING FOR SELECTED WINDOW TO WALL AREA RATIOS Saim Memon Philip C. Eames Centre for Renewable Energy Systems

EFA PSBP. Natural Ventilation Strategy. Introduction. 1.1 Relevant legislation. 1.1.1 The Building Regulations 2010

EFA PSBP Natural Ventilation Strategy Introduction The Baseline Designs Project will provide scheme design details for a number of Primary and Secondary School Exemplars. For the purposes of setting a

Benchmarking the effect of weather data upon energy estimation of UK homes

Benchmarking the effect of weather data upon energy estimation of UK homes Gavin Murphy, John Allison, John Counsell Department of Mechanical and Aerospace Engineering, University of Strathclyde, Glasgow.

Test Report No. C908LPEN

Institut für Solartechnik Hochschule für Technik Rapperswil Oberseestrasse 10, CH 8640 Rapperswil Tel +41 55 222 48 21, Fax +41 55 222 48 44 www.solarenergy.ch Ordered by: Changzhou He Jia Solar Energy

IMPACT OF INSULATION ON BUILDING ENERGY CONSUMPTION. Jong-Jin Kim and Jin Woo Moon TCAUP, University of Michigan, Ann Arbor, USA

Eleventh International IBPSA Conference Glasgow, Scotland July 27-3, 29 IMPACT OF INSULATION ON BUILDING ENERGY CONSUMPTION Jong-Jin Kim and Jin Woo Moon TCAUP, University of, Ann Arbor, USA ABSTRACT The

Heating and cooling. Insulation. Quick facts on insulation:

Heating and cooling Heating and cooling your home can be one of the biggest users of energy. Efficency in this area can bring great savings. Heating and cooling depend on many contributing factors. The

White Paper Nest Learning Thermostat Efficiency Simulation for Ireland. Nest Labs September 2014

White Paper Nest Learning Thermostat Efficiency Simulation for Ireland Nest Labs September 2014 Introduction This white paper gives an overview of potential energy savings using the Nest Learning Thermostat

Research Project F 2071. W. Richter. Manual of thermal comfort of Summer cooling mode

Research Project F 2071 W. Richter Manual of thermal comfort of Summer cooling mode Dortmund/Berlin/Dresden 2007 This publication is a summary of the final report of a project Development of a manual on

DESIGN OF NATURAL VENTILATION WITH CFD CHAPTER SEVEN. Qingyan Chen. difficult to understand and model, even for simple

CHAPTER SEVEN L. Glicksman and J. Lin (eds), Sustainable Urban Housing in China, 116-123 2006 Springer. Printed in the Netherlands. DESIGN OF NATURAL VENTILATION WITH CFD Qingyan Chen INTRODUCTION As the

Aalborg Universitet Two-Pipe Chilled Beam System for Both Cooling and Heating of Office Buildings General rights Take down policy

Aalborg Universitet Two-Pipe Chilled Beam System for Both Cooling and Heating of Office Buildings Afshari, Alireza; Gordnorouzi, Rouzbeh; Hultmark, Göran; Bergsøe, Niels Christian Published in: Proceedings

ENERGY AND THERMAL ANALYSIS OF GLAZED OFFICE BUILDINGS USING A DYNAMIC ENERGY SIMULATION TOOL. Harris Poirazis 1, Åke Blomsterberg 1

Ninth International IBPSA Conference Montréal, Canada August 15-18, 2005 ENERGY AND THERMAL ANALYSIS OF GLAZED OFFICE BUILDINGS USING A DYNAMIC ENERGY SIMULATION TOOL Harris Poirazis 1, Åke Blomsterberg

Test Report No. C1319LPEN

Institut für Solartechnik Hochschule für Technik Rapperswil Oberseestrasse 10, CH 8640 Rapperswil Tel +41 55 222 48 21, Fax +41 55 222 48 44 www.solarenergy.ch Ordered by: Thermics S.r.l. Via dell'olmo

Improving thermal insulation of concrete sandwich panel buildings

Improving thermal insulation of concrete sandwich panel buildings Jørgen Munch-Andersen Danish Building Research Institute, Aalborg University LCUBE conference, Vienna 17-18 April 2007 Outline A general

NEW CEILING MODULE DS-W1 WAVE : SUBSTANTIALLY HIGHER CAPACITY AND ENERGY EFFICIENCY

NEW CEILING MODULE DS-W1 WAVE : SUBSTANTIALLY HIGHER CAPACITY AND ENERGY EFFICIENCY With the groundbreaking new heating and cooling module DS-W1 Wave, compared to conventional radiant solutions, the heating

New Thermal Architecture For Future Green Data Centres

New Thermal Architecture For Future Green Data Centres S. Le Masson, D. Nörtershäuser France Télécom R&D 2, Av Pierre Marzin 22300 Lannion FRANCE stephane.lemasson@orange-ftgroup.com ; david.nortershauser@orange-ftgroup.com,

Thermal loads inside buildings with phase change materials: Experimental results

Available online at www.sciencedirect.com Energy Procedia 30 (2012 ) 342 349 SHC 2012 Thermal loads inside buildings with phase change materials: Experimental results Lidia Navarro a, Alvaro de Garcia

Heat capacity in relation to the Danish building regulations

Heat capacity in relation to the Danish building regulations Lars Olsen, MSc, PhD, Danish Technological Institute, Department of Building Technology; lars.olsen@teknologisk.dk KEYWORDS: Storage of heat,

Heating of large agricultural and industrial buildings

Agronomy Research 12(1), 237 244, 2014 Heating of large agricultural and industrial buildings M. Zajicek 1,* and P. Kic 2 1 Institute of Information Theory and Automation, The Academy of Science of The

The Importance of Building Criteria on Cooling Energy Demand of a Low Cost Residential House: Thailand Case Study

The Importance of Building Criteria on Cooling Energy Demand of a Low Cost Residential House: Thailand Case Study WARAPORN RATTANONGPHISAT 1,2,*, FEDERICO M. BUTERA 2, R.S. ADHIKARI 2 AND CHALERMPORN YOOPRATETH

IES <Virtual Environment> Tutorial. Apache Sim (Version 6.0)

IES Tutorial Apache Sim (Version 6.0) Introduction This tutorial will begin by showing you how to use the Building Template Manager (BTM) to create thermal and construction data for

GROUND COOLING OF VENTILATION AIR FOR ENERGY EFFICIENT HOUSE IN MALAYSIA: A CASE STUDY OF THE COOLTEK HOUSE

Conference on Sustainable Building South East Asia, -7 November 27, Malaysia GROUND COOLING OF VENTILATION AIR FOR ENERGY EFFICIENT HOUSE IN MALAYSIA: A CASE STUDY OF THE COOLTEK HOUSE G. REIMANN IEN Consultants,

THERMAL LOSSES Thermal Losses Calculations

Calculations -1- THERMAL LOSSES Thermal Losses Calculations Employer : 4M SA Project Location : ASHRAE Office Room : Example from ASHRAE 2013 Handbook - Fundamentals : Chapter 18, Single Room Example Peak