1 CISSP Exam Notes - Physical Security 1 CISSP Exam Notes - Physical Security 1. Introduction 1.1 Physical security addresses the physical protection of the resources of an organization, which include people, data, facilities, equipment, systems, etc. It concerns with people safety, how people can physically enter an environment and how the environmental issues affect equipment and systems. People safety always takes precedence over the other security factors. 1.2 Physical security is the first line of defense. 1.3 Major sources of physical security threats are: Weather, e.g. temperature, humidity, water, flood, wind, snow, lightening, etc. Fire and Chemical, e.g. explosion, smoke, toxic material, industrial pollution, etc. Earth movement, e.g. earthquake, volcano, slide, etc. Object movement, e.g. building collapse, falling object, car, truck, plane, etc. Energy, e.g. electricity, magnetism, radio wave anomalies, etc. Equipment, e.g. mechanical or electronic component failure, etc. Organism, e.g. virus, bacteria, animal, insect, etc. Human, e.g. strike, war, sabotage, etc. 1.4 There are three major types of control mechanisms for physical security: Administrative controls, e.g. facility selection, facility construction and management, personnel control, evacuation procedure, system shutdown procedure, fire suppression procedure, handling procedures for other exceptions such as hardware failure, bomb threats, etc. Physical controls, e.g. facility construction material, key and lock, access card and reader, fence, lighting, etc. Technical controls, e.g. physical access control and monitoring system, intrusion detection and alarm system, fire detection and suppression system, uninterrupted power supply, heating / ventilation / air conditioning system (HVAC), disk mirroring, data backup, etc. 1.5 Some physical security controls are required by laws, e.g. fire exit door, fire alarm, etc.
2 CISSP Exam Notes - Physical Security 2 2. Facility Requirement 2.1 Factors that should be considered when selecting a site are: Visibility, e.g. surrounding terrain, markings and signs, etc. Local considerations, e.g. crime rate, adjacent neighbors, proximity to police and fire station, etc. Transportation, e.g. road access and traffic condition, proximity to airport and train station, etc. Natural threats, e.g. likelihood of flood, earthquake, or other natural threats. Depending on the needs of a business, some of the above concerns may be more important than the others. 2.2 A data center should be located: Not on the top floor (for fire consideration). Not in the basement (for flooding consideration). In the core of a building (for providing protection from natural disasters or bomb attacks). Not close to a public area (for security consideration). 2.3 When designing and building a facility, the following items should be considered: Wall - fire rating (level of fire protection and combustibility), load (the maximum weight it can hold), floor to ceiling barrier, reinforcement for secured area. Partition considerations similar to those of wall, plus the requirement of extension above drop ceiling (if there is no extension, an intruder can lift the ceiling panels and climb above the partition). Door fire rating (should be equal to that of the surrounding walls), emergency marking, directional opening, resistance from being forced open, intrusion detection alarm, fail-soft vs fail-safe lock (i.e. lock that is unlocked or locked in a power outage), placement of doors. Window characteristics of windows material (opaque, translucent, transparent, shatterproof, bulletproof), intrusion detection alarm, placement of windows. Ceiling fire rating, load, waterproof (preventing water leakage from the upper floor), drop ceiling. Floor fire rating, load, raised floor, electrical grounding (for raised floor), nonconducting material. Heating, ventilation, and air conditioning (HVAC) independent power source, positive air pressure (i.e. air will flow out of a room when the door is open, which can avoid contamination of the room), protected intake vents to prevent tampering, monitoring of environmental condition, emergency power off, placement of HVAC
3 CISSP Exam Notes - Physical Security 3 system. Power supplies backup power supply, clean power supply, circuit breaker, access to power distribution panels, placement of power sockets. Liquid and gas line shutoff valve, positive flow (i.e. liquid or gas should flow out of a building, not in), leakage sensor, placement of liquid and gas lines. Fire detection and suppression fire or smoke detector and alarm, sprinkler, gas discharge system, placement of detectors and sprinkler heads. Emergency lighting essential power supply and battery for emergency lighting. 2.4 In general, a wall should have 1-hour fireproof rating. For data center or room which stores paper document, magnetic media, etc., the walls should have a minimum of 2-hour fireproof rating. 3. Perimeter Security 3.1 Perimeter security controls are used to prevent unauthorized access to a facility. They deal with access control, auditing and monitoring; intrusion detection and response. 3.2 The perimeter security requirements when a facility is in operation should be different from those when the facility is closed. Access Control and Auditing 3.3 Physical access control mechanisms include: Lock and key. Access card and reader. Fence. Lighting. Doorway and Man-trap. 3.4 Lock and key is the most inexpensive physical access control mechanism. It is a deterrent and delaying device to intruders. There are several types of locks as follows: Preset lock Typical door lock, which needs to be replaced if the key needs to be changed. Programmable lock or Cipher lock Lock with key pad which requires a combination of keys to open the lock, or lock with reader which requires an access card to open the lock. It may have special options such as: Hostage alarm (support a key combination to trigger an alarm).
4 CISSP Exam Notes - Physical Security 4 Master-keying (support key combinations to change the access code and configure the functions of the lock). Key-override (support key combinations to override the usual procedures). Device lock (for locking a device rather than for perimeter security): Slot lock secure a device to a stationary component (e.g. steel cable with lock). Cable trap secure a peripheral by locking its cable to a stationary component. Power switch lock lock the on/off power switch of a device (e.g. key-switch). 3.5 A fail-soft lock is unlocked in a power interruption. A fail-safe (or fail-secure) lock is locked in a power interruption. 3.6 Access card and reader can also be used as an access control mechanism (details can be found in Chapter 5). 3.7 Fence is another physical access control mechanism. Fences of different heights can serve different purposes: 3 4 feet deter casual trespassers. 6 7 feet deter general intruders. 8 feet with strands of barbed wire (slant at a 45 o angle) deter more determined intruders. 3.8 Perimeter intrusion and detection assessment system (PIDAS) is a fencing system with mesh wire and passive cable vibration sensors that can detect if an intruder is approaching and damaging the fence. However, it may generate many false alarms. 3.9 Bollards are small and round concrete pillars that are constructed and placed around a building to protect it from being damaged by someone running a vehicle into the side of the building Lighting (e.g. streetlight, floodlight and searchlight) is a good deterrent for unauthorized access. It can also provide safety for personnel. The National Institute of Standards and Technology (NIST) standard requires critical areas to be illuminated 8 feet in height with 2-foot candle power Doors to secured areas should have the following characteristics: Have similar appearance as the other doors to avoid catching the attention of intruders. Be self-closing and have no hold-open feature. Trigger alarms if they are forcibly opened or have been held open for a long period
5 CISSP Exam Notes - Physical Security 5 of time (door delay trigger). Use fail-secure locks, if necessary A man-trap is an area with double doors. There is a security guard or another mechanism to identify and authenticate an individual before opening the second door. This control can solve the piggybacking problem of access control (one following another closely through a door) Visitor access to restricted areas requires special security controls such as visitor registration and escort An audit trail should be maintained for every entrance of a restricted area. It can be used for auditing whether the access controls are properly enforced, and for incident investigation after an incident happens. It should contain the following information for every access attempt: Timestamp of the access attempt. User name. Result of the access attempt (successful or unsuccessful). Departure time of the user For mobile devices, laptops, or similar equipment that cannot be protected by the perimeter security controls, other security measures (e.g. device lock and data encryption) and user responsibilities become more important. Access Monitoring and Intrusion Detection 3.16 Physical access monitoring controls include patrol force, security guards and dogs Patrol force / security guard is a good deterrent to intrusion and can provide flexible security and safety response, but it has the following drawbacks: It is expensive. The reliability of security guards is an issue. Pre-employment screening and other background checking are required. Human is subject to social engineering. Training against social engineering is required Dogs are very effective in detecting intruders and other exceptions because they have good sight, hearing and smelling capabilities. Moreover, they are loyal, intelligent, and can be trained to recognize specific smells, e.g. smoke.
6 CISSP Exam Notes - Physical Security Technical access monitoring controls include: Dry contact switch uses metallic foil tape as a contact detector to detect whether a door or window is opened. Electro-mechanical detection system detects a change or break in a circuit. It can be used as a contact detector to detect whether a door or window is opened. Vibration detection system detects movement on walls, ceiling, floors, etc., by vibration. Pressure mat detects whether there is someone stepping on the mat. Visual recording device, e.g. camera and Closed Circuit TV (CCTV), records the activities taking place in a particular area. It should be used together with security guards to detect for anomalies. Photoelectric or photometric detection system emits a beam of light and monitors the beam to detect for motion and break-in. Wave pattern motion detector generates microwave or ultrasonic wave, and monitors the emitted wave to detect for motion. Passive infrared detection system detects for changes of heat wave generated by an intruder. Audio or Acoustical-seismic detection system listens for changes in noise level. Proximity detector or capacitance detector emits magnetic field and monitors the field to detect for any interruption. It is especially useful for protecting specific objects There are several types of alarm systems: Local system The alarm system only rings locally. Central station system Alarms (and CCTV) are monitored by a central station. The central station should be located within 10-minute travel time from the customer site. Proprietary system Similar to a central station system except that the monitoring facilities are owned and operated by the customer. Auxiliary system The alarm system rings local fire station and/or police station. Many central station systems have this feature Other issues related to intrusion detection and alarm systems are: An intrusion detection system may generate a lot of false alarms. For simplicity, different detectors (e.g. intrusion, fire, water, etc.) should be connected to a central alarm system rather than using multiple alarm systems. An alarm system should have emergency backup power supply to prevent intruders from disabling the system by cutting the normal power supply.
7 CISSP Exam Notes - Physical Security 7 An alarm system and the signal transmission medium should be monitored to detect for tampering. An alarm should be audible for at least 400 feet. An alarm requires a security guard to respond to locally. 4. Fire Protection Combustion Elements and Fire Types 4.1 Combustion elements which can sustain a fire are: Fuel, e.g. wood, paper, wiring, etc. (can be suppressed by CO 2 or Soda acid). Oxygen (can be suppressed by CO 2 or Soda acid). Temperature (can be reduced by water). Chemical (can be suppressed by Halon, which interferes with the chemical reaction). 4.2 There are four types of fire: Class Description Element of fire Suppression method A Common Miscellaneous, e.g. wood, Water, Soda acid combustibles paper, etc. B Liquid Petroleum products, Halon, CO 2, Soda acid coolants, etc. C Electrical Electrical equipment, wires, Halon, CO 2 etc. D Combustible metal Magnesium, sodium, etc. Dry powder 4.3 The flash point is the lowest temperature at which a Class B fire will continue to burn. Fire Detection 4.4 There are several types of fire detectors: Heat detector, which is based on a temperature threshold or the rising rate of temperature. Flame detector, which detects infra-red energy or pulse of flame (expensive but fast response). Smoke or Combustion particle detector, which emits a light beam and uses a photoelectric device to detect if the beam is obstructed. 4.5 Fire detectors and alarms should be installed with the following considerations: Fire detectors should be installed above ceiling, below raised floor (where wires can
8 CISSP Exam Notes - Physical Security 8 start an electrical fire), and in air vents (where smoke spreads). A fire alarm system should be configured to dial-up to a fire station and police station automatically. If a fire alarm will trigger automatic system shutdown, there should be a warning before the shutdown, and there should be some methods to override the shutdown. There should be some manual methods to trigger a fire alarm. Fire Suppression 4.6 A heating, ventilation, and air conditioning (HVAC) system has to be stopped automatically (e.g. by connecting it to the fire alarm system) when there is a fire because it can supply oxygen to the fire and spread smoke to the other areas. 4.7 A portable fire extinguisher should be used with the following considerations: It should have marking which indicates the type of fire it is designed for. Most portable fire extinguishers are filled with CO 2 or Soda acid. It should be placed within 50 feet of electrical equipment or at an exit. It should be easily reached and can be operated by an average-sized person. It should be inspected by licensed personnel regularly, e.g. quarterly. 4.8 A gas discharge system uses pressurized gas, e.g. CO 2 or Halon, to extinguish a fire. It is recommended for unmanned computer facilities, as the gas will not damage computer equipment, but may be dangerous to people. In a manned area, a gas discharge system should have built-in delay (after the fire alarm is triggered) before releasing gas, so that people have enough time to evacuate. 4.9 CO 2 is colorless, odorless and can cause suffocation. It is more suitable for unattended facilities Halon is harmless to people in small quantity. It should be used with 5% concentration. If the concentration is above 10%, it can be dangerous to people. It can also deplete ozone. In an extremely hot fire (> 900 o C), it will even degrade into toxic chemicals. Because of these problems, it is no longer manufactured since 1994 by international agreement. Extinguishers using Halon are not allowed to be refilled. However, it is not necessary to replace them immediately Halon 1211 is a liquid agent used mainly in portable extinguishers. Halon 1301 is a gas agent used mainly in flooding systems. Halon 1301 requires sophisticated pressurization.
9 CISSP Exam Notes - Physical Security FM-200 is a common replacement for Halon. FM-200 should be used with 7% concentration. Other replacements for Halon include Argon, Inergen, CEA-410, FE-13 and NAF-S-III A water sprinkler system is an inexpensive fire suppression mechanism. There are four main types of water sprinkler systems. They are: 1. Wet pipe system (or Closed head system) All the pipes are filled with water. When the temperature increases above a certain threshold, the links melt and water is released from the sprinkler heads. Water in the pipes may freeze in cold area, which may break the pipes. 2. Dry pipe system All the pipes are filled with air under pressure, and water is held back by valves. If a fire is detected, water will fill the pipes and then begin to sprinkle. During the time delay when water is filling the pipes, someone can shut down the sprinkler system, if necessary (e.g. for false alarm). It is suitable for cold climate. It does not react as fast as the wet pipe system. 3. Pre-action system Water is not held in the pipes in normal situation. When the temperature exceeds a certain threshold, water is released into the pipes, but is not yet released from the sprinkler heads until the links melt (combine the wet pipe system and dry pipe systems). It is designed for equipment that is costly such that water damage should be avoided in a small fire (leaving it to hand-held fire extinguisher). It is suitable for data processing environment. 4. Deluge system It is similar to the dry pipe system except that all the sprinkler heads are opened, so that a larger volume of water can be released over a large area in a short period of time. It is not suitable for data processing environment A water sprinkler system should be used with the following considerations: Water can increase the fire intensity in an electrical fire. Therefore, electrical power should be shut down automatically (e.g. by connecting it to the fire alarm system) before water is discharged from the sprinkler heads. Each sprinkler head should be activated individually to avoid wide-area water damage.
10 CISSP Exam Notes - Physical Security Power Protection 5.1 Power protection controls include: Uninterrupted Power Supply (UPS) to protect against a short duration power failure. There are two types of UPS: Online UPS It is in continual use because the primary power source goes through it to the equipment. It uses AC line voltage to charge a bank of batteries. When the primary power source fails, an inverter in the UPS will change DC of the batteries into AC. Standby UPS It has sensors to detect for power failures. If there is a power failure, the load will be switched to the UPS. It stays inactive before a power failure, and takes more time than online UPS to provide power when the primary source fails. Backup power source to protect against a long duration power failure, e.g. motor generator, another electrical substation, etc. Voltage regulator and line conditioner to protect against unstable power supply. Proper grounding for all electrical devices to protect against short circuit and static electricity, e.g. by using 3-prong outlets. Cable shielding to avoid interference. Power line monitor to detect for changes in frequency and voltage amplitude. Emergency power off (EPO) switch to shut down the power quickly when required. Electrical cables should be placed away from powerful electrical motors and lighting to avoid electromagnetic interference. Electrical cables should be placed away from powerful electrical cables and fluorescent lighting to avoid radio frequency interference. 5.2 UPS has several attributes: Electrical load it can support (measured in kva). Length of time it can support. Speed of providing power when there is a power failure. Physical space it occupies. 5.3 UPS is designed for protection against a short duration power outage, or for providing enough time for system administrators to shut down the systems and equipment orderly. Backup power source such as motor generator is designed for protection against a long duration power outage.
11 CISSP Exam Notes - Physical Security UPS and backup power source should be tested periodically. 5.5 Clean power refers to stable power with no voltage fluctuation or interference. It is necessary for power-sensitive equipment. 5.6 Interference or noise is a random disturbance of power. There are two types of interference: Electromagnetic interference (EMI) created by the charge difference between the 3 electrical wires (hot, neutral and ground). induced by motors, lightning, etc. Radio frequency interference (RFI) created by the components of an electrical system, and electrical cables. created by fluorescent lighting, truck ignition, etc. 5.7 There are several types of electrical voltage fluctuations: Excess power Spike for momentary high, Surge for prolonged high. Power degradation Sag for momentary low, Brownout for prolonged low. Power loss Fault for momentary outage, Blackout for prolonged outage. 6. General Environmental Protection 6.1 A HVAC system is a control system which governs heating, ventilation and air conditioning. It can be used to control the temperature, humidity and contamination (e.g. dust, dirt, smoke, gas, etc.) of a facility. 6.2 The temperature of a data center should be maintained between o C or o F ( o C = 5 / 9 x ( o F 32) ). If the temperature is too low, it may cause mechanisms to slow down. If the temperature is too high, it may cause equipment damage. The temperature damaging points of different products are as follows: Magnetic media 38 o C or 100 o F Computer hardware 80 o C or 175 o F Paper products 175 o C or 350 o F 6.3 The relative humidity of a data center should be maintained between 40 60%. If the humidity is too low, there may be excessive static electricity. If the humidity is too high, there may be condensation and corrosion. The humidity can be monitored by a hygrometer.
12 CISSP Exam Notes - Physical Security To avoid contamination and to maintain air quality, a data center should use a closedloop re-circulating air conditioning system and maintain positive air pressure inside the center (i.e. when the door is open, air will not flow in the room because of the higher pressure inside). 6.5 Liquid and gas lines must have shut-off valves and leakage sensors. The lines should maintain positive flow (i.e. liquid or gas should flow out instead of flow in a building). 6.6 Static electricity can be prevented by using anti-static floor, anti-static carpet (or not use carpet) and anti-static band. Proper humidity and grounding are also required. 7. Equipment Failure Protection 7.1 There are several types of controls for ensuring system availability: Hardware maintenance, with service level agreements (SLAs) with the maintenance service suppliers. Hardware redundancy, e.g. RAID disk, clustering, spare equipment. Regular backup of data and systems (Details can be found in Chapter 9). Alternate site or Disaster Recovery (DR) site (Details can be found in Chapter 10). 7.2 There are two important concepts when determining the requirement of controls for system availability: Mean-Time-Between-Failure (MTBF) expected time a device can function before failure. Mean-Time-To-Repair (MTTR) expected time required to repair a device. 7.3 Availability of disk storage can be increased by: Disk mirroring or shadowing Real-time duplication of data on a mirror disk. Disk duplexing Disk mirroring plus redundant disk controller. Redundant Array of Inexpensive Disks (RAID). 7.4 Redundant Array of Inexpensive Disks (RAID) makes use of redundant physical hard disks to increase the availability of a logical disk. There are several levels of RAID. The common RAID levels are listed below: Level 0 Stripping, i.e. a large logical disk which has data being divided and written over several physical disks. It can improve the logical disk performance, but has no redundancy. Failure of one physical disk will make the whole logical disk fails.
13 CISSP Exam Notes - Physical Security 13 Level 1 Disk mirroring, i.e. all data on a physical disk are duplicated to a mirror disk, and all modifications are made to the both disks simultaneously. Level 2 Stripping plus hamming code parity at bit level for redundancy (32 disks for storage and 7 disks for parity). This level is seldom used in the real world. Level 3 Byte level stripping plus parity (N data disks and 1 parity disk). Level 4 Block level stripping plus parity (N data disks and 1 parity disk). Level 5 Block level stripping plus interleaved parity, i.e. parity information is interleaved across all physical disks (N+1 disks). The logical disk performance is better than that of Levels 3 and 4 because of the distribution of parity information. It is the most widely used RAID level. Level 6 Block level stripping plus two sets of parity (N+2 disks). A logical disk can operate without data loss even if at most two physical disks failed. (For Levels 1-5, a logical disk can operate without data loss if at most one physical disk failed.) Level 10 Level 1 + Level 0, i.e. stripping across multiple RAID-1 disk pairs. Level 01 Level 0 + Level 1, i.e. 2 x RAID-0 disk groups, each disk group is a mirror of the other. Level 15 Level 1 + Level 5, i.e. stripping with interleaved parity across multiple RAID-1 disk pairs. Level 51 Level 5 + Level 1, i.e. 2 x RAID-5 disk groups, each disk group is a mirror of the other. 7.5 Most RAID systems support hot swapping disks, i.e. replacement of a failed hard disk and reconstruction of the contents of the failed disk onto a replacement disk while the system is running. 7.6 The RAID Advisory Board introduced the concept of Extended Data Availability and Protection (EDAP) in 1997, which is a classification system for the resilience of an entire storage system rather than just a disk-based storage as in the RAID classification. The classification system contains the following classes: FRDS (failure-resistant disk system): 1. Protection against data loss and loss of access due to disk failure. 2. Ability to reconstruct the failed disk contents onto a replacement disk. 3. Protection against data loss due to the failure of a system component. 4. Active component monitoring and failure indication. FRDS+: 5. Features Hot swapping. 7. Protection against data loss due to cache, power and other environmental
14 CISSP Exam Notes - Physical Security 14 failures. FTDS (failure-tolerant disk system): 8. Features Protection against loss of access due to device channel and controller failure. FTDS+: 10. Features Protection against loss of access due to bus and power failure, and component replacement. FTDS++: 12. Features Protection against data loss and loss of access due to multiple disk failures. DTDS (disaster-tolerant disk system): 14. Features Protection against data loss due to complete failure of one zone (distance between two zones > 1 km). DTDS+: 16. Features Protection against data loss due to complete failure of one zone (distance between two zones > 10 km). 7.7 A Storage Area Network (SAN) is composed of storage systems and servers connected by switching fabric, such that multiple servers can share the same storage systems. Redundancy and fault tolerance can be built into the switching fabric to increase the availability of access to the storage systems. 7.8 Fault tolerance means that a system can detect if there is a fault and can correct it or work around it automatically. 7.9 Clustering is a fault tolerant server technology. A group of servers working together as a logical unit to provide load balancing, redundancy and fail-over functions. If any one server fails, the other servers will pick up the load of the failed server.
15 CISSP Exam Notes 15 Table of Contents of CISSP Exam Notes CHAPTER 1. INTRODUCTION COMMON BODY OF KNOWLEDGE (CBK) CERTIFICATION AND RE-CERTIFICATION...1 CHAPTER 2. SECURITY MANAGEMENT PRACTICES SECURITY MANAGEMENT SECURITY PRINCIPLES AND DEFINITIONS RISK MANAGEMENT DATA CLASSIFICATION SECURITY POLICIES, STANDARDS, GUIDELINES, AND PROCEDURES EMPLOYMENT POLICIES AND PRACTICES...12 CHAPTER 3. SECURITY ARCHITECTURE & MODELS COMPUTER ARCHITECTURE OPERATING SYSTEM ARCHITECTURE SECURITY ARCHITECTURE DEFINITIONS SECURITY MODELS SECURITY EVALUATION CERTIFICATION AND ACCREDITATION...33 CHAPTER 4. PHYSICAL SECURITY INTRODUCTION FACILITY REQUIREMENT PERIMETER SECURITY FIRE PROTECTION POWER PROTECTION GENERAL ENVIRONMENTAL PROTECTION EQUIPMENT FAILURE PROTECTION...46 CHAPTER 5. ACCESS CONTROL SYSTEMS & METHODOLOGY INTRODUCTION IDENTIFICATION AUTHENTICATION AUTHORIZATION ACCOUNTABILITY ACCESS CONTROL MODELS...60
16 CISSP Exam Notes ACCESS CONTROL AND MONITORING MECHANISMS THREATS AND COUNTERMEASURES...67 CHAPTER 6. TELECOMMUNICATIONS & NETWORK SECURITY NETWORKING BASICS LOCAL AREA NETWORK (LAN) TECHNOLOGIES METROPOLITAN AREA NETWORK (MAN) AND WIDE AREA NETWORK (WAN) TECHNOLOGIES WIRELESS TECHNOLOGIES NETWORK DEVICES NETWORK SERVICES...99 CHAPTER 7. CRYPTOGRAPHY INTRODUCTION ENCRYPTION ALGORITHM BASICS SYMMETRIC ENCRYPTION ASYMMETRIC ENCRYPTION MESSAGE AUTHENTICATION PUBLIC KEY INFRASTRUCTURE (PKI) KEY MANAGEMENT CRYPTOGRAPHY APPLICATIONS ATTACK METHODS TO CRYPTOGRAPHY CHAPTER 8. APPLICATIONS & SYSTEMS DEVELOPMENT SECURITY INTRODUCTION SYSTEM DEVELOPMENT LIFE CYCLE AND SOFTWARE PROCESS MANAGEMENT APPLICATION DEVELOPMENT TECHNOLOGIES DATABASE AND DATA WAREHOUSING THREATS, MALICIOUS CODE AND ATTACK METHODS CHAPTER 9. OPERATIONS SECURITY INTRODUCTION ROLES AND RESPONSIBILITIES BACKUP AND RECOVERY OTHER OPERATION CONTROLS THREATS AND COUNTERMEASURES CHAPTER 10. BUSINESS CONTINUITY PLANNING & DISASTER RECOVERY PLANNING INTRODUCTION BUSINESS CONTINUITY PLAN (BCP) DISASTER RECOVERY PLAN (DRP)
17 CISSP Exam Notes 17 CHAPTER 11. LAW, INVESTIGATIONS & ETHICS LAWS RELATED TO COMPUTER CRIME COMPUTER FRAUD AND ABUSE INCIDENT HANDLING AND EVIDENCE CONTROL ETHICAL CONDUCT APPENDIX BRITISH STANDARD 7799 (BS7799) USEFUL WEBSITES COMMONLY USED WELL-KNOWN TCP AND UDP PORTS INDEX...186
18 CISSP Exam Notes 18 CISSP Exam Notes All you need to pass the exam Copyright 2003 by the KP Lab Limited. All rights reserved. No part of this publication may be reproduced or distributed in any form or by any means, or stored in a database or retrieval system, without the prior written permission of the publisher. ISBN Publisher KP Lab Limited Author K. Wan Web Site About the Author K. Wan, MSc., CISSP, CCNP, CCSE, MCSE, MCDBA, SCSA, SCNA, SCJP, has ten years experience in system and security administration on various computing platforms. He is currently an IT infrastructure and security manager working in Hong Kong. IT Certification Examination Study Guides published by KP Lab: 1. CISSP Exam Notes ISBN: Free Chapter: Complete Book ($16.80): 2. CCNA Exam Notes ISBN: Free Chapter: Complete Book ($9.74):
Security+ Guide to Network Security Fundamentals, Fourth Edition Chapter 13 Business Continuity Objectives Define environmental controls Describe the components of redundancy planning List disaster recovery
Physical Security Requirements Marcus Bendtsen Institutionen för Datavetenskap (IDA) Avdelningen för Databas- och Informationsteknik (ADIT) Physical Security Requirements Protect against physical threats:
Page 1 of 10 Scope Crime Central Station Burglary Alarm Systems This criteria is intended to provide Loss Control Representatives with specific guidelines and information for evaluating central station
9.1 USE SECURITY AREAS TO PROTECT FACILITIES 1 GOAL Do you use physical methods to prevent unauthorized access to your organization s information and premises? 2 GOAL Do you use physical methods to prevent
MARULENG LOCAL MUNICIPALITY Data Centre Physical Access and Environmental Control Policy Draft: Data Centre Access Control and Environmental Policy Page 1 Version Control Version Date Author(s) Details
LI_M_POPO PROVINCIAL GOVERNMENT :;:ED.JBl-C ()F SO"';-H AFR;IC. ':.,. DEPARTMENT OF CO-OPERATIVE GOVERNANCE, HUMAN SETTLEMENTS & TRADITIONAL AFFAIRS REVIEWED ICT DATA CENTRE PHYSICAL ACCESS AND ENVIROMENTAL
JT Rue Des Pres Data Centre Facility Product Description JT s Data Centre Hosting Service provides a secure computer room environment with protected and backup power, security and bandwidth. Data Centre
2. Physical Security Cargo handling and storage facilities in domestic and foreign locations must have physical barriers and deterrents that guard against unauthorized access. Where applicable, there must
Data Center Presentation The NetSource Datacenter. Agenda General Layout of Data Center Policies and Procedures Designed to Latest Standards High Performance High Reliability High Security Design Details
Data Center Infrastructure & Managed Services Outline The 360 Technology Center Solutions Data Center is located in Lombard, IL, USA. We are 20 minutes outside of downtown Chicago. The 360TCS staff consists
Guide to Computer Forensics and Investigations, Second Edition Chapter 3 The Investigator s Office and Laboratory Objectives Understand computer forensics lab certification requirements Determine the physical
SECURITY VULNERABILITY CHECKLIST FOR ACADEMIC AND SMALL CHEMICAL LABORATORY FACILITIES by the American Chemical Society, Committee on Chemical Safety, Safe Practices Subcommittee Introduction Terrorism
ARE YOU READY FOR A DISASTER? THE ROAD TO PHYSICAL SECURITY Dr. David A. Cook Stephen F. Austin State University firstname.lastname@example.org 1 Page 1 Critical Aspects of Security Physical Security Personnel Security
Understanding Alarm Systems A false alarm occurs when an alarm signal designed to elicit an immediate emergency Law Enforcement, Fire, or Medical response is activated, when in fact no emergency exists.
BEST PRACTICES STANDARDS FOR SCHOOLS UNDER CONSTRUCTION OR BEING PLANNED FOR CONSTRUCTION I. Site Layout A. School buildings shall be provided with a securable perimeter. A securable perimeter means that
IBM Twin Data Center Complex Ehningen Peter John IBM BS email@example.com Overview Profile IBM owned facility 6447 m² IT-Space Infrastructure concurrent maintainable (Tier Level 3) Feed-ins of Power
Alarm and Detection/Suppression Fire Safety American Fire Technologies To provide special hazard services world wide to the industrial market through the integration of components and services Clean Agent
Information Technology General Controls Review (ITGC) Audit Program Date Prepared: 2012 Internal Audit Work Plan Objective: IT General Controls (ITGC) address the overall operation and activities of the
Oracle Maps Cloud Service Enterprise Hosting and Delivery Policies Effective Date: October 1, 2015 Version 1.0 Unless otherwise stated, these Oracle Maps Cloud Service Enterprise Hosting and Delivery Policies
Version: Modified By: Date: Approved By: Date: 1.0 Michael Hawkins October 29, 2013 Dan Bowden November 2013 Rule 4-004L Payment Card Industry (PCI) Physical Security (proposed) 01.1 Purpose The purpose
'Helping our customers stay in business by reducing risk' NZI Risk Solutions TM About NZI Risk Solutions NZI has extensive experience in providing expert risk management advice to help our commercial customers
Physical Security Types of Threats Human Intrusion Attackers looking to perform some sort of damage or obtain useful information Natural Disasters* Fire Flood Earthquake/Seismic Vibrations Power Outages/Fluctuations
JUNE 1, 2012 SalesNOW Security Policy v.1.4 2012-06-01 v.1.4 2012-06-01 1 Overview Interchange Solutions Inc. (Interchange) is the proud maker of SalesNOW. Interchange understands that your trust in us
JT First Tower Lane Data Centre Facility Product Description JT s Data Centre Hosting Service provides a secure computer room enviroment with protected incoming power supplies, state-of-the-art security
Home Security Inspection This document sets forth conclusions and recommendations following a Crime Prevention Through Environmental Design inspection performed by the Thunderbolt Police Department. The
Las Vegas Datacenter Overview Product Overview and Data Sheet Product Data Sheet Maintaining a Software as a Service (SaaS) environment with market leading availability and security is something that Active
OPERATIONAL CAPABILITY TECHNOLOGY QUESTIONNAIRE Please provide all relevant documents responsive to the information requests listed within each area below. In addition to the specific documents requested,
. Facility Criteria (RFP).0 Location Characteristics Criteria Requirements 1 Ownership and Management: Please identify the owner(s) and managers of the property and indicate if there is on-site management.
CAMERAS & ALARMS Closed Circuit Television (CCTV) / SMART Home Structured Wiring & Systems Commercial and Residential Alarm Systems / Central Monitoring Integrated Access Control Systems (Proximity Cards,
Physical Security Paul Troncone CS 996 NSTISSI 4011 Building Construction Alarms Access Controls Information Systems Centers Personnel Security Tamper Resistance Goals of Physical Security Safeguard personnel
Network Design Yiannos Mylonas Physical Topologies There are two parts to the topology definition: the physical topology, which is the actual layout of the wire (media), and the logical topology, which
Course: Information Security Management in e-governance Day 2 Session 3: Physical and Environmental Security Agenda Introduction to physical and environmental infrastructure elements needed for supporting
Learning Outcomes Physical Security Information Security Dr Hans Georg Schaathun After this week, students should be able to identify threats and useful controls in the physical environment of an information
SMOKE DETECTOR INSTALLATION PROGRAM The Burlington Ordinance Perspective The National Fire Alarm Code, NFPA 72, sets the minimum requirements of performance, selection, use and location of automatic detection
Facility XXXX Site Security Survey Date: 10/9-10/10/02 (A) Perimeter Security DELAY/DETER Site Boundary None of the critical facilities have protective Fence (Height and Construction) fences. Outriggers
internet + intellectual property + intelligence We thank you for the opportunity to work with you regarding your colocation needs in Hong Kong, China. We can colocate standard rack-mountable servers or
TABLE OF Contents List of Illustrations................................. IX Preface........................................... XV Why You Should Read This Book Burglars Kill Every Security System Can Be
Availability and Disaster Recovery: Basic Principles by Chuck Petch, WVS Senior Technical Writer At first glance availability and recovery may seem like opposites. Availability involves designing computer
PHYSCIAL SECURITY SURVEY CHECKLIST PERIMETER BARRIERS TRANSIT FACILITIES Does a fence or other type physical barrier define the perimeter of the facility? (1) Specify type and height of physical barrier
Department of the Interior Security Control Standard Physical and Environmental Protection April 2011 Version: 1.1 Signature Approval Page Designated Official Bernard J. Mazer, Department of the Interior,
internet + intellectual property + intelligence We thank you for the opportunity to work with you regarding your colocation needs in Melbourne,. We can colocate standard rack-mountable servers or other
Exterior Grounds Commercial or Business Security Survey Is there a fence around the property or a clear definition of Territoriality? If there is a fence, is it tall enough and maintained in good repair?
BURGLAR ALARM SYSTEMS BURGLAR ALARM SYSTEMS BURGLAR ALARM SYSTEM EURO ALARM WIRELESS BURGLAR ALARM SYSTEM OASIS BURGLAR ALARM SYSTEM EURO ALARM Six zones with the following connection capabilities: One
Wireless peripherals EYE-02 GSM Security Camera Application note File name: EYE-02 Wireless peripherals 1/12 1 INTRODUCTION The application note describes possibilities of using camera EYE-02 with wireless
SWAP EXECUTION FACILITY OPERATIONAL CAPABILITY TECHNOLOGY QUESTIONNAIRE Please provide all relevant documents responsive to the information requests listed within each area below. In addition to the specific
Integration of Alarm Systems Ing. Jan Valouch Tomas Bata University in Zlin, Faculty of Applied Informatics, Department of Security Engineering, Zlín, Czech Republic firstname.lastname@example.org Abstract Integrated
Fire Safety Log Book Company... Address........ Responsible Person. Competent Person. Date Started For Additional Information: Safety Management (UK) Ltd Holme Suite, Clawthorpe Hall Business Centre, Burton
Nuclear Plant Security Systems Course Description Gary W Castleberry, PE This course will introduce the student into the design of security systems for commercial nuclear power plants. An overview of plant
AT&T Internet Data Center Site Specification Chicago Area (Lisle, IL) Site Biography Market Area: Chicago, IL Location: Lisle, IL 60532 Address: 4513 Western Avenue CLLI,POP, NPA/NXX Code: LSLEILAA, EQLAILAA
REPORT Proposals for Surge Protection and Ventilation BELFAST HEALTH AND SOCIAL CARE TRUST ROYAL GROUP OF HOSPITALS GROSVENOR ROAD BELFAST BT12 6BA Rev. 01 6th September 2013 Table of Contents 1.0 Ventilation
TEMPERATURE SENSOR This sensor measures temperature in degrees Celsius or Fahrenheit. It works with all SensorHawk base units (SensorHawk-2, SensorHawk-8 and SensorHawk8/20) as well as the SecurityHawk-8
Page 1 of 5 CBD-233. Fire Alarm and Detection Systems Originally published August 1984. R.H.L. McEwen Fire alarm systems are normally required by building codes. In the case of new buildings, this is usually
DESIGNATED CONTRACT MARKET OPERATIONAL CAPABILITY TECHNOLOGY QUESTIONNAIRE Please provide all relevant documents responsive to the information requests listed within each area below. In addition to the
CISSP Common Body of Knowledge Review: Physical (Environmental) Security Domain Version: 5.10 CISSP Common Body of Knowledge Review by Alfred Ouyang is licensed under the Creative Commons Attribution-NonCommercial-ShareAlike
TYPICAL FIRE SAFETY INSPECTION VIOLATIONS The following is a list of typical violations often found by inspectors and a generic solution. You can use this list to improve the safety of your facility, to
Dennis Fire Department Fire Prevention Mark Dellner Fire Chief FIRE SAFETY INSPECTION GUIDELINES FOR COMMERCIAL PROPERTIES (MA Fire Prevention Regulations 527 CMR, MGL Chapter 148) FIRE PREVENTION CHECKLIST-
Perimeter security system T-REX Moscow, 2011 Table of content 1. Introduction... 3 2. Main features of the T-REX system... 3 3. Structure of the system... 5 4. SL-6000 system sensors... 6 5. Signal processing
How to Solve the Most Persistent Problem in Perimeter Security Systems Duane Thompson General Manager of Fiber SenSys Carrondo, Antonio Commercial Manager, Teleprinta Perimeter Security Challenging!! More
Requirements for Hydrogen Storage and Use I. INTRODUCTION Fire and Life-Safety Group (FLS) The following is a summary of the fire and building code requirements for the storage and use of hydrogen. These
AIMS is Malaysia and South East Asia s leading carrier neutral data centre operator and managed services provider. We provide international class data storage and ancillary services, augmented by an unrivaled
AT&T Internet Data Center Site Specification - Phoenix Area (Mesa, AZ) Site Biography Market Area: Phoenix, Mesa, Tempe, Chandler, Scottsdale, AZ Location: Mesa, AZ 85201 Address: 1301 University Blvd.
Overview NetSource is a Chicago area (Naperville) hosting company that owns and operates its own world class datacenter. The initial datacenter buildout was put into operation in 2007 and expanded in 2013.
HMO Information Sheet No 1 FIRE DETECTION AND ALARM SYSTEMS 1. Introduction When a property is in multiple occupation, the risk of fire breaking out is greater than in an ordinary single family home. Some
BCE Security Solutions Restricted Attachment 1 Toronto Public Library Disaster Recovery recommended safeguards and controls Final Prepared by: Bell Security Solutions Inc. Professional Services 333 Preston
GSM Alarm System User Manual For a better understanding of this product, please read this user manual thoroughly before using it. Quick Guider After getting this alarm system, you need to do the following
Cloud Computing Chapter 10 Disaster Recovery and Business Continuity and the Cloud Learning Objectives Define and describe business continuity. Define and describe disaster recovery. Describe the benefits
Page 1 SPECIAL APPLICATIONS The protection of microelectronics clean rooms using aspirating smoke detection systems requires special consideration. The physical configuration of the room(s) and the direction
User s Guide Security Systems D220 Table of Contents About This User s Guide... 3 Introduction... 3 Security System Basics... 4 Controlled Points... 5 24-Hour Points... 6 Keypad Keys... 6 Keypad Lights...
EULESS FIRE DEPARTMENT FIRE MARSHAL S OFFICE INFORMATION LINE: Revised 2/12 Fire Chief Wes Rhodes Fire Marshal Paul Smith EFD-FMO 3-2 2009 International Fire & Building Code as Amended NFPA Standards Adopted
ELECTRICAL EMERGENCY SYSTEM PLAN REVIEW What to Look for during Plan Review OVERVIEW OF CODE REQUIREMENTS First determine the type of emergency power system; is the system designed for Emergency or Legally
AT&T Internet Data Center Site Specification San Diego Koll (San Diego, CA) Site Biography Market Area: San Diego, CA Location: San Diego, CA 92121 Address: 5732 Pacific Center Blvd CLLI,POP, NPA/NXX Code:
Commercial Fire Alarm Systems How can a Fire Alarm system help protect your business from the threat of fire? How do Fire and Smoke Alarms actually work, from the different types of controls to positioning
A Health and Safety Guideline for Your Workplace What is static electricity? What causes it? How is it hazardous? And, most importantly, how can it be controlled? All of these questions will be answered
Intruder Alarm System GSM & PSTN Wireless and Wired Touch Model 2013-01 V1.0.0 Statment This equipment must be installed and used in strict accordance with the instructions given in this user documentation.
FIRE PREVENTION INSPECTION CHECKLIST For Class A Occupancy (For Assembly Buildings, Bars, Restaurants, Gyms, Churches, Arenas, Theatres or wherever people gather) Name Of Occupancy Date Physical Address
PLAN REVIEW GUIDE FOR FIRE ALARM PROJECT NAME: PERMIT # PROJECT ADDRESS: CONTACT PERSON: PHONE Fire alarm system installation information shall be provided on the appropriate architectural and electrical
DC-8706K Auto Dial Alarm System User Guide Basic Contents: 1x the host unit; 1x wireless door (window) magnet; 1x wireless infrared detector; 2x remote control; 1x siren; 1x phone core; 1x AC to DC power
EXHIBIT A SCOPE OF WORK 1. (Contractor) shall provide fire alarm system maintenance/repair/testing services as described herein to the California Department of Veterans Affairs (hereinafter CDVA, CalVet,
St. John s University Fire Safety Plan Founder s Village Townhouses Page 1 St. John s University Fire Safety Plan Part 1-Building Information Section Founder s Village Townhouses 8000 Utopia Parkway Jamaica