3 American Fire Technologies To provide special hazard services world wide to the industrial market through the integration of components and services
4 Clean Agent What are our goals today? How does a Clean Agent extinguish a fire Types of Clean Agents systems Halon? Design Considerations of a Clean Agent System System Components Sequence of Operation
5 How Does a Clean Agent System Work? Most clean agent s work by chemically extinguishing a fire at the molecular level. In order to extinguish a fire, the agent decomposes. When a Clean Agent decomposes, toxic gases are released. (Does not apply to inert gasses: CO2, Inergen) To avoid high levels of decomposed gasses, systems are designed for quick discharges (UL requires <10 seconds).
6 How Does a Clean Agent System Work? (cont) Agent Storage Agent is a liquid, stored in cylinders, pressurized with N2. Agent is super pressurized with N2 to a pressure of 360 psi. Agent is distributed to discharge nozzles, drilled to allow a specific flow rate. Discharge nozzles are located in the room area and below under floors. Cylinders are furnished with low-pressure switches to monitor agent pressure.
7 How Does a Clean Agent System Work? (cont) Halon HFC s Inert Gas Oxygen Depletion Primary Heat Absorption Secondary Primary Reaction Interruption Primary Secondary Chemical Reaction Heat Oxygen Fuel
8 How Does a Clean Agent System Work? (cont) Physical Heat absorption - remove heat faster than generated Reduces flame temperature below that necessary to maintain combustion Chemical Interruption of chemical chain reactions of combustion process by halogenated atoms (Fl, Cl, Br)
9 Physical Properties Property Halon 1301 FE-25 HFC-227ea Novec Inergin Chemical Formula CF3Br CHF2CF3 CF3CHFCF3 Molecular Weight Boiling Point -72º F -55º F 3º F 120º F Vapor Pressure 200 psi 195 psi 66 psi 5.87 psi 2175 ODP GWP Zero Ozone Depletion Potential (ODP) Very low Global Warming Potential (GWP) GWP is calculated of a 100 year time horizon and represents mass of CO2 equivalent to emission of one unit of this compound
10 Different Types of Fire Suppression Systems FM-200 (HFC-227ea) CF3CHFCF3 Most common agent used. Works by chemically inhibiting fire propagation. Poor flow characteristics. Supports 12 nozzles max
11 Different Types of Fire Suppression Systems (cont) Novec 1230 (Sapphire) CF3CF2C(o)CF(CF3)2 Fairly new agent. Works the same as FM-200. Short after life in the atmosphere (days). Poor flow characteristics. Pressurized with Nitrogen
12 Different Types of Fire Suppression Systems (cont) Ecaro 25 (Dupont FE-25) CHF2CF3 Closest to replacing Halon 1301 Works by removing O2 at the molecular level. Superior flow characteristics. Required 25% less agent than FM-200. Most economical of Clean Agents. No pressurization concerns No venting required Support 30 to 40 Nozzles
13 Different Types of Fire Suppression Systems (cont) Inergen (Argonite. Same as Inergen without any CO2) Inert gas (52% nitrogen, 40% argon, and 8% carbon dioxide) Lowers the oxygen in the room to a level that won t support a fire, but still enough oxygen to breath. Design is critical. Must vent room due to pressure build up. Doesn t leak from the room because of low density. Economical to recharge (Hard to find recharge locations).
14 Different Types of Fire Suppression Systems (cont) Water Mist (Micro Mist) Non-Chemical. Micron size water droplets. Best used for generator rooms or areas with high leakage. Very economical to recharge.
15 Different Types of Fire Suppression Systems (cont) CO2 (Carbon Dioxide) Not classified as a Clean Agent. Can be lethal to humans. Operates by removing the oxygen from the air. Good for non-occupied hazards.
16 United States Position - Halon Montreal Protocol - ban on Halon production - 12/31/93 No current restrictions on use of reclaimed or recycled Halon No current restrictions on existing installed systems Halon market value decreasing
17 Halon Retrofit Objectives Maintain an equivalent level of protection Utilize the existing Halon 1301 piping network Minimize business interruption Environmentally preferred Realize the most cost effective solutio Is Green important?
18 Halon Replacement No reason to remove Halon, but difficult to recharge if dumps FM200/Ecaro/Inert Gases/Green Gases Ecaro best one for one replacement.
19 Define Hazard System Design Determine volume of area(s) (L X W X H). Areas may include room, under-floor, and above ceiling.
20 Agent/Quantity Determine which agent to use. Try to use the same agent/mfg that is currently used in the facility. Determine quantity of agent to use.
22 Systems Design Automatic and Manual Operation Smoke Detectors are used for automatic operation Manual release stations are used for manual operation. System Alarms Alarm bells Horn strobes Strobes
23 Releasing Panels System controls Systems Design Main Control Panel ( UL9th Must be listed to release specific) Operates on 24 volts DC from a 120-volt AC input power source. Contains batteries for DC back up. Monitors and controls all input and output circuits. Includes replays for connections to building alarm panels and remote monitoring
24 Discharge Nozzles Systems Design Determine quantity and location for nozzles. Limit nozzles to a maximum flow of 20lbs./second. Locate nozzles in each protected area (Room/U/Floor). Try to locate nozzles away from exit doors.
25 Main Control Panel System Components Is Conventional or Intelligent. Used to monitor and control input and output devices. Supplies power to the field devices. Supervises field wiring INPUTS Opens, Grounds OUTPUTS Opens, Grounds, shorts Displays alarms and troubles. Contains timers for time delays for agent release.
26 System Components (cont) Ionization Smoke Detector Detects 1-2 micron particle size. Should be used in room areas only (airflow issues)
27 System Components (cont) Photoelectric Smoke Detector Detects visible particles (4+ microns) (Visible) Good for under floor areas. Normally not as sensitive as an ionization detector.
28 System Components (cont) Heat (Thermal Detector) Operates when temperature reaches set point. Not good for early warning detection Best suited for harsh areas (Smokey/Dirty).
29 System Components (cont) Air Sampling System Detects Sub-micron size particles. Good for ultra early warning of a fire condition. Detects Thermal degradation of the item. Allows you to be Pro-Active to alarms. You can find the source of the problem before needing the suppression system. Fairly expensive, but could save the cost of a systems recharge.
30 System Components (cont) Manual Release Station Used to manually discharge the system. Instant release, bypassing any time delays. Normally located near exit doors. Code requires every system to have a manual release.
31 System Components (cont) Abort Station Used to bypass a pending discharge. Located next to the manual release station. Must be depressed (operated) in order to bypass a discharge. Must be operated prior to a system release.
32 System Components (cont) Alarm Devices Alarm Bells. Used for 1 st detection zone alarms. Used for Air sampling system alarms.
33 System Components (cont) Horn Strobes Can be used for 1 st / 2 nd / Discharge alarms Normally are pulsed to indicate type of alarm. Slow pulse 1 st zone alarm Fast pulse 2 nd zone alarm (pre-discharge Steady Discharge alarm.
34 System Components (cont) Strobe Lights Normally used to indicate a system discharge. Located outside exit doors. Attached to a horn inside the hazard area, a strobe indicates a general alarm condition.
35 System Components (cont) Agent Storage Cylinders Used to store Clean Agent. Is supplied with pressure gauges and lowpressure switches. Are supplied with valves or bursting disc. Solenoids used to actuate valves. Actuators used for bursting disc type.
36 System Components (cont) Discharge nozzles. Used for distribution of agent. Located in protected areas. Sidewall and center room type. Maximum flow rate of 200 lbs (20 lbs. second)
37 Actuators System Components (cont) GCA (Compressed Gas Actuator). Triggered by small charge. Requires special handling. Used on cylinders with rupture disc. Solenoid Activated by applying voltage to coil. Used on cylinders with valves. Can also be used on N2 (Nitrogen Actuators)
38 System Components (cont) Special Detection Systems Early Warning Fire Alarms (VESDA/SAFE) Used for very early warning of a fire. Monitors particle size of.01 micron (Invisible) Works by taking air samples in the room and counting the particulate. Allow personnel to be pro-active in finding a potential fire hazard and eliminating the need to use the suppression system.
39 EARLY WARNING SMOKE DETECTOR Particles of Combustion are Found in Air Samples Control Panel Indicates Pre/Alarm Condition Control Bar Graph Indicates Level of Particle Count Control Panel Alarm Level Contacts Operate Alarm Bells in Ground Floor Area Are Activated
40 Detection Devices Determine quantity of smoke detectors. Use a spacing of 250 sq. ft. per detector. In room areas use a combination of ionization and photoelectric smoke detectors. In under-floor spaces, only use photoelectric smoke detectors. Located a manual release and abort station at the primary room exits. Normally, these are installed inside the hazard area. Locate audible and visual devices in the room so all personnel can hear/see the alarms. Locate discharge strobes outside of the main exit doors.
41 Sequence of Operation Single Smoke Detector In Alarm Control Panel Indicates Alarm Condition Control Panel Alarm Contacts Operate Control Panel Displays Device and Location of Alarm L.E.D. On Smoke Detector Illuminates Steady On Alarm Horn in Hazard Area Starts a Slow Pulse Signal Alarm Strobe in Hazard Area is Activated
42 Sequence of Operation (cont) Two Smoke Detectors in Alarm (Same Hazard Area) Control Panel Displays Device and Location of Alarm L.E.D. on Smoke Detector Illuminates Steady On Alarm Horn in Hazard Area Changes to a Fast Pulse Signal Control Panel Pre-Discharge Delay Timer is Activated Equipment Shutdown Contacts Are Activated
43 Note: Sequence of Operation (cont) At the end of 30 seconds, the system is discharged into the hazard area. If the abort station is operated prior to the 30- time delay, the system will not discharge. The abort is a Dead Man type, and must be continually depressed in order to bypass a discharge. Releasing the abort station will cause the time delay to restart.
44 Sequence of Operation (cont) System Discharge Control Panel Displays System Has Released Discharge Strobe Outside Exit Door is Activated Alarm Horn in Hazard Area Changes to a Steady Tone Discharge Strobe Outside of Exit Door is Activated Shutdown Relays are Energized
45 Sequence of Operation (cont) System Alarms and Troubles Control Panel will Display Either Alarm or Trouble Control Panel will Display Cause of the Alarm or Trouble Control Panel Sonalert Will Sound
46 Note: Sequence of Operation (cont) Depressing Acknowledge button on front panel can silence the control panel sounder. Alarm devices in the field can be silenced by depressing the Alarm Silence button on front panel. Depressing Reset button will return panel to Normal condition.
47 Sequence of Operation (cont) FIRE ALARM Operation of Any Smoke Detector or Fire Alarm Pull Station Control Panel Indicates Alarm Condition Control Panel Alarm Contacts Operate Control Panel Displays Device and Location of Alarm L.E.D. on Smoke Detector Illuminates Steady On Alarm Horns in Hazard Area Starts a Pulse Signal Shutdown Contacts Operate
48 Sequence of Operation (cont) NOTE: Depressing Alarm Silence button on control panel door will silence alarm bells. Depressing Reset button will reset panel to normal condition.
49 Clean Agent The End Thanks For Taking The Time To See This!! We Hope This Will Help
50 Questions? Leave me your card/ or me if you would like additional information on any of the additional detail
SECTION 1 - GENERAL CONDITIONS I. SCOPE: This specification outlines the requirements for a Total Flood Clean Agent Fire Suppression System with automatic detection and control. The work described in this
E2-E3: ELECTRICAL CHAPTER-13 FIRE PROTECTION SYSTEM- EVOLVING TRENDS AND APPLICABILITY TO DATA CENTRE BSNL, India For Internal Circulation Only Page: 1 Fire Protection System- Evolving Trends & Applicability
NYC SUB-SYSTEMS INSTALLATION & SERVICE REQUIREMENTS OF THE FDNY Presented by: James Goerl Metro Protection Systems, Inc. firstname.lastname@example.org Agenda Introduction & Learning Objectives History
SECTION 1 - GENERAL CONDITIONS I. SCOPE: This specification outlines the requirements for a Fike Micromist Water Mist Fire Suppression System with a Cheetah Xi addressable detection and control system.
Amerex CPS FM-200 Waterless Pre-engineered Fire Suppression System A Simple Solution An Affordable Approach An Industry Innovation I N T R O D U C T I O N A SIMPLE SOLUTION. AN AFFORDABLE How many days
EXHIBIT A SCOPE OF WORK 1. (Contractor) shall provide fire alarm system maintenance/repair/testing services as described herein to the California Department of Veterans Affairs (hereinafter CDVA, CalVet,
Hypoxic Air Ventilation Fire Prevention Systems Prevenex Hypoxic Air Ventilation (HAV) Using ordinary air to save lives and property Prevenex uses ordinary air with a reduced oxygen content SAFE. No nitrogen
Standard Message Library ALERT AL1 AL2 AL3 AL4 AL5 AL6 AL7 AL8 This is a fire alert. This is a fire alert. Await further instructions. Await further instructions. There is an emergency. Await further instructions.
PART 1 -- GENERAL 1.1 WORK OF THIS SECTION SECTION 16720 - City of San Diego, CWP Guidelines A. The WORK of this Section includes providing manual and automatic fire alarm and smoke detection systems meeting
May 18, 2015 DCSS (DCL) Data Center Fire Suppression Procedures Summary: This document is intended for personnel who have access to the data center in DCL. The objective is to provide an awareness of the
Conventional Fire Detection and Extinguishant Control System Specification Page 1 of 9 Scope Furnish a complete 24VDC Conventional, electrically supervised, combined fire detection and extinguishant release
Using your LED Plus keypad System 238 System 2316 System 238i System 2316i Part Number 5-051-372-00 Rev B Thank you for purchasing this C&K alarm system Your system is one of the most powerful and advanced
internet + intellectual property + intelligence We thank you for the opportunity to work with you regarding your colocation needs in Melbourne,. We can colocate standard rack-mountable servers or other
Manual for Fire Suppression & Methane Detection System Fogmaker North America Post address: 150 Gordon Dr Exton, PA 19341 Delivery address: 150 Gordon Dr Exton, PA 19341 Tel: 610-265-3610 Fax: 610-265-8327
Page 1 of 5 CBD-233. Fire Alarm and Detection Systems Originally published August 1984. R.H.L. McEwen Fire alarm systems are normally required by building codes. In the case of new buildings, this is usually
ENGINEERING SPECIFICATIONS FOR CO2 EXTINGUISHING AGENT PRE-ENGINEERED FIRE SUPPRESSION SYSTEMS SECTION 1 GENERAL SPECIFICATIONS I. SCOPE This specification outlines the requirements for a pre-engineered
FIRST ALERT INSTRUCTION MANUAL FOR FA 270 KEYPADS SECURITY SYSTEM Page 0 Table of Contents Introduction 1 System Basics.. 1 Burglary Protection.. 1 Fire Protection.. 1 Security Codes. 1 Zones and Partitions
PLAN REVIEW GUIDE FOR FIRE ALARM PROJECT NAME: PERMIT # PROJECT ADDRESS: CONTACT PERSON: PHONE Fire alarm system installation information shall be provided on the appropriate architectural and electrical
Technologies Gas extinguishing systems MX 1230 Fire Extinguishing Systems Fighting Fire using 3M Novec 1230 ire protection Efficient and compact MX 1230 fire extinguishing systems fight fires using Novec
How intelligent must an extinguishing solution be to keep fire virtual? Intelligent means: fire protection from Siemens. Sinorix intelligent extinguishing solutions. Answers for infrastructure. Sinorix
fire extinguishing systems Extinguishing technique is a colourless, odourless and electrical non-conductive gas. In systems the is mixed with a special identifiable odour. The extinguishing effect of is
TAMARAC FIRE RESCUE INSTRUCTIONS FOR FIRE ALARM PRE-SUBMITTAL CHECKLIST In order to provide a comprehensive plan review in a timely manner, and to insure the design and installation of fire alarm systems
For Data Center and Control Room Applications Nearly zero wetting No costly clean up or equipment replacement Sustainable design Quick system recharge, minimal downtime No need for assurance of tight room
QUADSCAN II SERIES 7400 ONE TO FOUR CHANNEL RECEIVER QUADSCAN II SERIES 7400 ONE TO FOUR CHANNEL RECEIVER Centralizes Monitoring and Alarming for Gas Transmitters and Fire Detectors. The QuadScan II receiver
SECURITY SYSTEM NOTES Installing/Service Company For Service Call Central Station Duress Code FUNCTION CODES Function Code Controls Function This system is is not partitioned. EMERGENCY ACTIVATION KEYS
TECHNICAL SPECIFICATIONS Page 1 of 10 FIRE DETECTION AND ALARM SYSTEM Scope Furnish a complete 24V DC conventional, electrically supervised, zone annunciated, fire detection and alarm system as specified
DESCRIPTION MODEL 5010 DUAL CHANNEL SMOKE/FIRE DETECTION MODULE DESCRIPTION The SST Model 5010 Two Channel Smoke/Fire Detection Module provides two independent detection input channels for the NOVA-5000
DATA CENTER FIRE PROTECTION DATA CENTER FIRE PROTECTION The following is a summary of a few key fire protection, detection, and suppression technologies used by Minimax Fire Solutions in data centers and
VISTA-128FBP VISTA-250FBP Commercial Fire and Burglary Partitioned Security Systems with Scheduling User Guide K0377V2 7/09 Rev. C 2 TABLE OF CONTENTS SYSTEM OVERVIEW... 5 General... 5 A Partitioned System...
PART 1 - GENERAL FIRE DETECTION/INERGEN SUPPRESSION SYSTEM ENGINEERING SPECIFICATIONS 1.01 DESCRIPTION OF WORK: A. Design and installation of an engineered fire detection and INERGEN total flooding, gaseous
GENERAL INFORMATION Chemetron High Pressure Carbon Dioxide fire extinguishing systems provide protection for a variety of industrial applications. High Pressure CO systems consist of four basic components
Fire Protection Options for Data Centres Mark L. Robin, PhD DuPont Chemicals & Fluoroproducts email@example.com Introduction Modern data centres are characterized by spaces filled with ever-increasing
NetworX NX-6V2 LED Keypad User Manual POWER Light is on when AC power is present; flashes to indicate a low battery condition. ARMED Light is on when armed; off when disarmed; flashes to indicate a previous
TABLE OF CONTENTS...Glossary of terms...2...code Pad Diagram...3 Understanding the Code Pad lights...4 Code Pad tones...5 Fully arming the system On MODE...6 Fully arming the system - Quick Arm MODE...6
SYSTEM ABORT PUSH AND HOLD COIL SUPERVISION MODULE (2 AMP) 2081-9046 RED INSTALLATION INSTRUCTIONS 574-437 REV YEL NAC+ MAINTAIN 1/4" SEPARATION BETWEEN POW ER LIMITED (RED/) AND NONPOWER S LIMITED (YEL/)
Installation and user manual for the FX range of fire panels 1, 2, 4 and 8 zone panels Contents Panel installation 3 Panel connections 3 Wiring connection drawings 4 Panel facilities 6 Installation check
User s Guide Security Systems D220 Table of Contents About This User s Guide... 3 Introduction... 3 Security System Basics... 4 Controlled Points... 5 24-Hour Points... 6 Keypad Keys... 6 Keypad Lights...
May 18, 2015 DCSS (ACB) Data Center Fire Suppression Procedures Purpose: This document is intended for all individuals who have access to the data center at 1011 West Springfield Avenue, Advanced Computation
Guardian Fire Safety Solutions FIRE RISK CONTROL IN WELDING FUME EXTRACTION SYSTEMS Guardian Fire Safety Solutions FIRE RISK CONTROL IN WELDING FUME EXTRACTION SYSTEMS DO YOU CONTROL THE RISK OF FIRE AT
What is Fire? The Combustion a Chemical Chain Reaction Between Oxygen and a Combustible Material Under the Development of Heat / Energy Smoke Gasses Fire Parametres Energy Heat UV Radiation IR Radiation
C E A S E F I R E S WIRELESS FIRE ALARMS Wireless Fire Alarm System A dangerous enemy Smoke generated by fire has long been recognised as a threat to human life. It contains toxic chemicals and travels
How to determine the amount of inert gas needed for total flooding fire- extinguishing systems Introduction Total flooding is a fire extinguishing technique in which the Oxygen (O 2 ) level in a room is
Ammonia Detection System Codes and Design Specifications December 28, 2015 Revision 5 920 N Trade Winds Pkwy Columbia, MO 65201 Ammonia detection system codes and design specifications Following is a discussion
RPC Safety System Blue Sheet Certification Test Procedure procedure name PHENIX Procedure No. PP-126.96.36.199-10 Revision: A Date: _1/29/2007 Hand Processed Changes HPC No. Date Page Nos. Initials Approvals
USER MANUAL SECURIT 800L+ CONTROL PANEL COMPANY PROFILE IntelliSense have been successfully making security products for over 20 years and lead the security industry throughout the world with many innovative
SECTION 908 EMERGENCY ALARM SYSTEMS 908.1 Group H occupancies. Emergency alarms for the detection and notification of an emergency condition in Group H occupancies shall be provided as required in Chapter
Contact ID Event Definition Codes EVENT ALARMS Medical Alarms -100 100 Medical Zone 101 Personal Emergency Zone 102 Fail to report in Zone Fire Alarms -110 110 Fire Zone 111 Smoke Zone 112 Combustion Zone
Recommended Practice for Installation of Transit Vehicle Fire Protection Systems Approved October 25, 2007 APTA Fire Safety Working Group Approved May 3, 2008 APTA Bus Safety Committee Approved October
FIRE SAFETY Fire Fire is a rapid chemical reaction of oxidant with fuel accompanied by the release of energy, indicated by incandescence or flame. Chain Reaction Oxidiser Heat Fire Tetrahedron Fuel Combustion
SUBFLOOR PROTECTION CO 2 DESIGN GUIDE The Subfloor Application Profile (AP 006) provides guidance on fire protection requirements for spaces beneath raised floors. In the event of a fire, the Fike Carbon
SECTION 16721 FIRE ALARM AND DETECTION SYSTEM PART 1 - GENERAL 1.1 RELATED DOCUMENTS: A. Drawings and general provisions of Contract, including General and Supplementary Conditions and Division-1 Specification
FUNDAMENTALS OF FIRE ALARM SYSTEMS 72 33 FIRE ALARM SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. 1. PROTECTED PROPERTY
SECTION 16721 PART 1 - GENERAL 1.1 SECTION INCLUDES A. Fire Alarm Control Panels B. Manual Fire Alarm Stations C. Automatic Smoke D. Fire Alarm Notification Appliances E. Auxiliary Fire Alarm Equipment
1. GENERAL 1.1. Related Documents: 1.2. Scope: 1.1.1. The general provisions of the Contract, including General and Supplementary Conditions and General Requirements apply to the work specified in this
FIRE ALARM SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. 1. Protected Property Information Name of property: Description
DS7060 User Guide Copyright 1996-97 Detection Systems, Inc. User Guide for the DS7060 Control/Communicator Copyright 1996-97 Detection Systems, Inc. Detection Systems, Inc., 130 Perinton Parkway, Fairport,
Service Requirements Fire protection equipment requires care and maintenance at scheduled intervals to assure it will operate properly and safely when needed. Only personnel who are trained and qualified
Fire Extinguisher Training Course Overview What is Fire? Classes of Fire 3 A s Types of Fire Extinguishers Use of a Fire Extinguisher Summary What is Fire? Fire is a self-sustaining, chemical chain reaction
For Data Center and Control Room Applications Nearly zero wetting No costly clean up or equipment replacement Sustainable design Quick system recharge, minimal downtime No need for assurance of tight room
Providing Quality and Professional Training Since 1984 FIRE SAFETY AND PREVENTION PROFESSIONAL IN ELECTRICAL POWER PLANT Date: 20 July 2015 31 July 2015 Course ID: ADDS097/2015 Duration: 12 Days Fee US
SECURITY SYSTEM NOTES Installing/Service Company For Service Call Installation Date / / Central Station Duress Code EMERGENCY ACTIVATION KEYS (check if enabled) Fire Auxiliary Emergency Police PROGRAMMED
ESPRIT BURGLAR ALARM CONTROL PANEL Welcome to the world of ESPRIT technology. Your Esprit control panel has been designed with ease of use and simplicity in mind. We ve developed a highly advanced technology
Page 1 of 8 1. DESCRIPTION The Viking VFR400 is a microprocessor based multi-hazard releasing control panel for use on preaction, deluge, Surefire and Firecycle multicycle sprinkler systems, MX-1230 Fire
S-World.com CLEAN AGENT IRE PROTECTION OR COMPUTER ROOMS By Mark L. Robin Mark L. Robin, Ph.D., is Technical Services Consultant for Specialty luorochemicals with DuPont luoroproducts and has over 20 years
SECTION 13850 DETECTION AND ALARM PART 1 GENERAL 1.01 SUMMARY A. Section Includes 1. Control Panel 2 Associated Equipment B. Products Installed But Not Supplied Under This Section 1. Section 16140 - Wiring
EXTINGUISHER TRAINING 29 CFR 1910.157 Objectives Understand basic firefighting concepts: R.A.C.E. P.A.S.S. Know what to do if you find a fire Be able to correctly and safely select and use a fire extinguisher
SMOKE DETECTOR INSTALLATION PROGRAM The Burlington Ordinance Perspective The National Fire Alarm Code, NFPA 72, sets the minimum requirements of performance, selection, use and location of automatic detection
Fire Alarm System Plans Submittal Guidelines For New and Existing Systems SCOPE The Temecula Fire Prevention Bureau (TFPB) has established the following requirements for the submittal of all fire alarms,
Not all fires are the same, and they are classified according to the type of fuel that is burning. If you use the wrong type of fire extinguisher on the wrong class of fire, you can, in fact, make matters
R.P. SCHIFILITI ASSOCIATES, INC. P.O. Box 297 Reading, Massachusetts 01867-0497 USA 781.944.9300 Fax / Data 781.942.7500 Telephone Sample Fire Alarm System Calculations 1. A fire alarm manufacturer specifies
PDHonline Course M110A (4 PDH) Introduction to Fire Protection Systems Instructor: Lawrence J. Marchetti, P.E. 2012 PDH Online PDH Center 5272 Meadow Estates Drive Fairfax, VA 22030-6658 Phone & Fax: 703-988-0088
HSC505-R Home Security Controller - User Manual Release R1a Pi HSC505 and Pi HSC505R Home Security Controller User s Information Guide R1A Page 1 QD Dynamics (Pty) Ltd reserves the right to make changes
MONITOR ISM / AFx Multi-Tenant Security System User Guide V.3 Multi-Tenant Security System User Guide Welcome New Users! There are two types of suite security keypads. Follow the instructions in the proceeding