1 Valve Sizing Te chnic al Bulletin Scope Valve size often is described by the nominal size of the end connections, but a more important measure is the flow that the valve can provide. And determining flow through a valve can be simple. This technical bulletin shows how flow can be estimated well enough to select a valve size easily, and without complicated calculations. Included are the principles of flow calculations, some basic formulas, and the effects of specific gravity and temperature. Also given are six simple graphs for estimating the flow of water or air through valves and other components and examples of how to use them. Sizing Valves The graphs cover most ordinary industrial applications from the smallest metering valves to large ball valves, at system pressures up to 000 psig and 0 bar. The water formulas and graphs apply to ordinary liquids and not to liquids that are boiling or flashing into vapors, to slurries (mixtures of solids and liquids), or to very viscous liquids. The air formulas and graphs apply to gases that closely follow the ideal gas laws, in which pressure, temperature, and volume are proportional. They do not apply to gases or vapors that are near the pressure and temperature at which they liquefy, such as a cryogenic nitrogen or oxygen. For convenience, the air flow graphs show gauge pressures, whereas the formulas use absolute pressure (gauge pressure plus one atmosphere). All the graphs are based on formulas adapted from ISA S75.01, Flow Equations for Sizing Control Valves. 1 Flow Calculation Principles The principles of flow calculations are illustrated by the common orifice flow meter (Fig. 1). We need to know only the size and shape of the orifice, the diameter of the pipe, and the fluid density. With that information, we can calculate the flow rate for any value of pressure drop across the orifice (the difference between inlet and outlet pressures). For a valve, we also need to know the pressure drop and the fluid density. But in addition to the dimensions of pipe diameter and orifice size, we need to know all the valve passage dimensions and all the changes in size and direction of flow through the valve. However, rather than doing complex calculations, we use the valve flow coefficient, which combines the effects of all the flow restrictions in the valve into a single number (Fig. 2). Pipe diameter Orifice diameter Pressure drop Orifice shape Fluid density Fig. 1. The flow rate through a fixed orifice can be calculated from the meter dimensions of pipe diameter and orifice size and shape. Pressure drop Safe Product Selection When selecting a product, the total system design must be considered to ensure safe, trouble-free performance. Function, material compatibility, adequate ratings, proper installation, operation, and maintenance are the responsibilities of the system designer and user. Pipe diameter Size changes Valve passage size Fluid density Direction changes Fig. 2. Calculating the flow rate through a valve is much more complex. The valve flow coefficient (C v ) takes into account all the dimensions and other factors including size and direction changes that affect fluid flow.
2 2 Valve Sizing Fig. 3. Valve manufacturers determine flow coefficients by testing the valve with water using a standard ISA test method. p 1 p p 2 Flow meter Test valve Flow control valve Flow control valve Standard distances from test valve Minimum lengths of straight pipe Valve manufacturers determine the valve flow coefficient by testing the valve with water at several flow rates, using a standard test method 2 developed by the Instrument Society of America for control valves and now used widely for all valves. Flow tests are done in a straight piping system of the same size as the valve, so that the effects of fittings and piping size changes are not included (Fig. 3). Liquid Flow Because liquids are incompressible fluids, their flow rate depends only on the difference between the inlet and outlet pressures (Dp, pressure drop). The flow is the same whether the system pressure is low or high, so long as the difference between the inlet and outlet pressures is the same. This equation shows the relationship: Symbols Used in Flow Equations q = N 1 C v p G f C v = flow coefficient q = flow rate p 1 = inlet pressure p 2 = outlet pressure Dp = pressure drop (p 1 p 2 ) G f = liquid specific gravity (water = 1.0) G g = gas specific gravity (air = 1.0) N 1, N 2 = constants for units T 1 = absolute upstream temperature: K = C R = F + 4 Note: p 1 and p 2 are absolute pressures for gas flow. The water flow graphs (pages 6 and 7) show water flow as a function of pressure drop for a range of C v values. Gas Flow p = p 1 p 2 p 1 p 2 C v Gas flow calculations are slightly more complex, because gases are compressible fluids whose density changes with pressure. In addition, there are two conditions that must be considered low pressure drop flow and high pressure drop flow. G f q
3 p 2 < 1/2p 1 q Valve Sizing 3 Low and High Pressure Drop Gas Flow The basic orifice meter illustrates the difference between high and low pressure drop flow conditions. In low pressure drop flow when outlet pressure (p 2 ) is greater than half of inlet pressure (p 1 ) outlet pressure restricts flow through the orifice: as outlet pressure decreases, flow increases, and so does the velocity of the gas leaving the orifice. When outlet pressure decreases to half of inlet pressure, the gas leaves the orifice at the velocity of sound. The gas cannot exceed the velocity of sound and therefore this becomes the maximum flow rate. The maximum flow rate is also known as choked flow or critical flow. Any further decrease in outlet pressure does not increase flow, even if the outlet pressure is reduced to zero. Consequently, high pressure drop flow only depends on inlet pressure and not outlet pressure. Low pressure drop p 1 p 2 Maximum flow p 1 p 2 Sonic flow High pressure drop p 1 p 2 q p 2 > 1/2p 1 p 2 = 1/2p 1 q This equation applies when there is low pressure drop flow outlet pressure (p 2 ) is greater than one half of inlet pressure (p 1 ): 2 p q = N 2 C v p 1 (1 ) 3p 1 p p 1 G g T 1 p 2 > 1/2p 1 pressure does not increase the flow because the gas has reached sonic velocity at the orifice, and it cannot break that sound barrier. The equation for high pressure drop flow is simpler because it depends only on inlet pressure and temperature, valve flow coefficient, and specific gravity of the gas: q = N 2 C v p 1 1 G g T 1 G g T 1 p 1 p 2 q p 2 < 1/2p 1 The low pressure drop air flow graphs (pages 8 and 9) show low pressure drop air flow for a valve with a C v of 1.0, given as a function of inlet pressure (p 1 ) for a range of pressure drop (Dp) values. When outlet pressure (p 2 ) is less than half of inlet pressure (p 1 ) high pressure drop any further decrease in outlet C v G g T 1 p 1 p 2 The high pressure drop air flow graphs (pages and 11) show high pressure drop air flow as a function of inlet pressure for a range of flow coefficients. C v q
4 4 Valve Sizing + Fig. 4. For most common liquids, the effect of specific gravity on flow is less than %. Also, most high-density liquids such as concentrated acids and bases usually are diluted in water and consequently the specific gravity of the mixtures is much closer to that of water than to that of the pure liquid. Percent change Change in specific gravity Change in flow rate Ether Alcohol Oils Nitric acid Sulfuric acid + Fig. 5. For common gases, the specific gravity of the gas changes flow by less than % from that of air. And just as with liquids, gases with exceptionally high or low densities often are mixed with a carrier gas such as nitrogen, so that the specific gravity of the mixture is close to that of air. Percent change + 0 Change in specific gravity Change in flow rate 1 Hydrogen Natural gas Oxygen Argon Carbon dioxide Effects of Specific Gravity The flow equations include the variables G f and G g liquid specific gravity and gas specific gravity which are the density of the fluid compared to the density of water (for liquids) or air (for gases). However, specific gravity is not accounted for in the graphs, so a correction factor must be applied, which includes the square root of G. Taking the square root reduces the effect and brings the value much closer to that of water or air, 1.0. For example, the specific gravity of sulfuric acid is % higher than that of water, yet it changes flow by just 34 %. The specific gravity of ether is 26 % lower than that of water, yet it changes flow by only 14 %. Figure 4 shows how the significance of specific gravity on liquid flow is diminished by taking its square root. Only if the specific gravity of the liquid is very low or very high will the flow change by more than % from that of water. The effect of specific gravity on gases is similar. For example, the specific gravity of hydrogen is 93 % lower than that of air, but it changes flow by just 74 %. Carbon dioxide has a specific gravity 53 % higher than that of air, yet it changes flow by only 24 %. Only gases with very low or very high specific gravity change the flow by more than % from that of air. Figure 5 shows how the effect of specific gravity on gas flow is reduced by use of the square root. Effects of Temperature Temperature usually is ignored in liquid flow calculations because its effect is too small. Temperature has a greater effect on gas flow calculations, because gas volume expands with higher temperature and
5 Valve Sizing 5 Temperature, C Percent change 0 Change in flow rate Fig. 6. Many systems operate in the range F ( C) to +212 F (+ C). Within this range, temperature changes affect flow by little more than % Temperature, F Numerical Constants for Flow Equations Constant contracts with lower temperature. But similar to specific gravity temperature affects flow by only a square-root factor. For systems that operate between F ( C) and +212 F (+ C), the correction factor is only +12 to 11 %. Figure 6 shows the effect of temperature on volumetric flow over a broad range of temperatures. The plus-or-minus % range covers the usual operating temperatures of most common applications. Other Services Units Used in Equations N q p T 1 N U.S. gal/min psia Imperial gal/min psia L/min bar L/min kg/cm 2 N std ft 3 /min psia R 69 std L/min bar K 6816 std L/min kg/cm 2 K As noted above, this technical bulletin covers valve sizing for many common applications and services. What about viscous liquids, slurries, or boiling and flashing liquids? Suppose vapors, steam, and liquefied gases are used? How are valves sized for these other services? Such applications are beyond the scope of this document, but the ISA standards S75.01 and S75.02 contain a complete set of formulas for sizing valves that will be used in a variety of special services, along with a description of flow capacity test principles and procedures. These and other ISA publications are listed in the references. Also, most standard engineering handbooks have sections on fluid mechanics. Several of these are given in the references, as well. Cited References 1. ISA S75.01, Flow Equations for Sizing Control Valves, Standards and Recommended Practices for Instrumentation and Control, th ed., Vol. 2, ISA S75.02, Control Valve Capacity Test Procedure, Standards and Recommended Practices for Instrumentation and Control, th ed., Vol. 2, Other References L. Driskell, Control-Valve Selection and Sizing, ISA, J.W. Hutchinson, ISA Handbook of Control Valves, 2nd ed., ISA, Chemical Engineers Handbook, 4th ed., Robert H. Perry, Cecil H. Chilton, and Sidney D. Kirkpatrick, Ed., McGraw-Hill, New York. Instrument Engineers Handbook, revised ed., Béla G. Lipták and Kriszta Venczel, Ed., Chilton, Radnor, PA. Piping Handbook, 5th ed., Reno C. King, Ed., McGraw-Hill, New York. Standard Handbook for Mechanical Engineers, 7th ed., Theodore Baumeister and Lionel S. Marks, Ed., McGraw-Hill, New York.
6 6 Valve Sizing Water Flow U.S. Units Water flow, U.S. gallons per minute C v = Pressure Drop, psi Flow, U.S. gal/min Example: Enter the vertical scale with the pressure drop across the valve (Dp = psi). Read across to the desired flow rate (q = 4 U.S. gal/min). The diagonal line is the desired C v value (C v = 0.).
7 Water Flow Metric Units Water flow, liters per minute Valve Sizing C v = Pressure Drop, bar Flow, L/min Example: Enter the vertical scale with the pressure drop across the valve (Dp = bar). Read across to the desired flow rate (q = 0.2 L/min). The diagonal line is the desired C v value (C v = ).
8 8 Valve Sizing Low Pressure Drop Air Flow U.S. Units Low pressure air drop flow, standard cubic feet per minute psi 0 psi 0 psi 0 psi 0 25 psi 0 Inlet Pressure, psig 0 0 p = 5 psi psi High pressure drop flow Flow, std ft 3 /min Example: Enter the vertical scale with the inlet pressure at the valve (p 1 = 0 psig). Read across to the diagonal line for the pressure drop across the valve (Dp = 25 psi). Read down to the horizontal scale for the flow rate through a valve with a C v of 1.0 (q = 65 std ft 3 /min). Multiply that flow rate by the valve C v to determine the actual flow rate.
9 Low Pressure Drop Air Flow Metric Units Low pressure air drop flow, standard liters per minute Valve Sizing bar bar 5 bar 2.5 bar 1.0 bar 0. bar Inlet Pressure, bar p = bar High pressure drop flow Flow, std L/min Example: Enter the vertical scale with the inlet pressure at the valve (p 1 = bar). Read across to the diagonal line for the pressure drop across the valve (Dp = 1 bar). Read down to the horizontal scale for the flow rate through a valve with a C v of 1.0 (q = 00 std L/min). Multiply that flow rate by the valve C v to determine the actual flow rate.
10 Valve Sizing High Pressure Drop Air Flow U.S. Units High pressure drop air flow, standard cubic feet per minute C v C= v Inlet Pressure, psig Flow, std ft 3 /min Example: Enter the vertical scale with the inlet pressure at the valve (p 1 = 0 psig). Read across to the desired flow rate (q = std ft 3 /min). The diagonal line is the desired C v value (C v = 0.).
11 Valve Sizing 11 High Pressure Drop Air Flow Metric Units High pressure drop air flow, standard liters per minute 0 C v = Inlet Pressure, bar Flow, std L/min Example: Enter the vertical scale with the inlet pressure at the valve (p 1 = bar). Read across to the desired flow rate (q = 00 std L/min). The diagonal line is the desired C v value (C v = 1.0).
12 Safe Product Selection When selecting a product, the total system design must be considered to ensure safe, trouble-free performance. Function, material compatibility, adequate ratings, proper installation, operation, and maintenance are the responsibilities of the system designer and user. Swagelok TM Swagelok Company 1994, 1995, 00, 02 Swagelok Company December 07, R4 MS E
BASIC UNDERSTANDING OF FLOW CALCULATIONS AND ESTIMATES MAKES SIZING VALVES SIMPLER Valve size often is described by the nominal size of the end connections but a more important measure is the flow that
CHOOSING THE CORRECT REGULATOR HOW TO SIZE A PRESSURE REGULATOR In order to choose the correct regulator the following information is needed: - Function: Pressure reducing or backpressure control? - Pressure:
www.swagelok.com Pressure-educing egulator low Curves Technical Bulletin Scope Selecting a regulator for an application first requires review of its performance capabilities and their alignment with the
Technical Bulletin TB8102 Rupture Disc Sizing The objective of this bulletin is to provide detailed guidance for sizing rupture discs using standard methodologies found in ASME Section VIII Div. 1, API
Engineering Information For PDC Butterfly Valves Valve Sizing: Cv sizing is the most widely used method for valve sizing, today. By using the Cv method, the proper valve size can be accurately determined
46 Extending Flow Data EXTRAPOLATION 1. Specific Gravity Other Gases To convert air flow from chart to another gas flow. Flow (gas) = Flow (air) / S.G. (gas) To obtain flow rate for helium when air flow
Valve Pressure Loss & Flow The valve coefficient, Cv, is a number which represents the capability of a valve (or any flow component) to flow a fluid. The larger the Cv, the larger the flow at a given pressure
Flow Curves and Calculations Technical Information debul2007x012 Flow Curves Tescom flow charts are the graphic representation of test results which show the change in outlet pressure (P 2 ) with a varying
MR98 Series Backpressure Regulators, Relief and Differential Relief Valves May 2016 P1753 Type MR98H P1757 TYPE MR98L Figure 1. Typical MR98 Series Backpressure Regulators, Relief and Differential Relief
Self Study Physical Science Refresher Table of Contents 1. Three phases of matter: Solids, Liquids and Gases 2. The effect of heat and pressure on the phases of matter a) expanding and contracting 3. Changing
EQUATIONS OF STATE FOR GASES Questions A gas enters a reactor at a rate of 255 SCMH. What does that mean? An orifice meter mounted in a process gas line indicates a flow rate of 24 ft 3 /min. The gas temperature
The Connection Bulletin for Forged Steel Flow Control Valves CB 15 Flow Control Division Forged Steel Flow Control Valves GRADUATED DIAL AND INDICATOR FULLY GUIDED V-PORT THROTTLING DISC AND INTEGRAL HARD
Steam Tables What They Are How to Use Them The heat quantities and temperature/ pressure relationships referred to in this Handbook are taken from the Properties of Saturated Steam table. Definitions of
18.104.22.168 520-I-01/03 Question 1: Is this a correct interpretation of Section 22.214.171.124.3 in that the backpressure was specified to not exceed the allowable overpressure? Question 2: If my interpretation of
Section 000 Bulletin 00 Issued 5/87 Replaces /8 JET PUMP TECHNICAL DATA pumping liquids This technical bulletin includes general information about Penberthy Jet Pumps plus specific details for selecting
Description Air Eliminators and Combination Air Eliminator Strainers are designed to provide separation, elimination and prevention of air in piping systems for a variety of installations and conditions.
Flow Through the Regulator The SCUBA tank regulator arrangement can be idealized with the diagram shown below. This idealization is useful for computing pressures and gas flow rates through the system.
APPENDIX A (IFGS) SIZING AND CAPACITIES OF GAS PIPING (This appendix is informative and is not part of the code.) A.1 General. To determine the size of piping used in a gas piping system, the following
Determining Energy Requirements - & Gas Heating & Gas Heating and gas heating applications can be divided into two conditions, air or gas at normal atmospheric pressure and air or gas under low to high
Safetygram 46 A practical guide to restrictive flow orifices Restrictive flow orifices (RFOs) installed in cylinder valve outlets provide a significant safety benefit for users of hazardous gases, especially
CONTENT Chapter Description Page I Purpose of Control Valve II Type and Main Components of Control Valve 3 III Power 5 IV. Pressure Drop Across Control Valve 7 V. Symbols and Units 10 VI. Unit Conversion
BP Lower 48 Onshore Operations Safety Manual Page 4.19 1 Chapter 19 Purging Air from Piping and Vessels in Hydrocarbon Service I. General Requirements A. After motor vehicle accidents and underground excavation
7.2.2 Changing State 43 minutes 56 marks Page 1 of 17 Q1. Air is a gas at room temperature. The chemical formulae below show some of the substances in the air. Ar CO 2 H 2 O N 2 Ne O 2 (a) Put these formulae
Self-operated Pressure Regulators for special applications Type 235-11 Pressure Regulator Pressure build-up regulator Valve opens when the upstream pressure drops Pressure reducing valve Valve closes when
CHAPTER 12 Gases and the Kinetic-Molecular Theory 1 Gases vs. Liquids & Solids Gases Weak interactions between molecules Molecules move rapidly Fast diffusion rates Low densities Easy to compress Liquids
Pump Formulas Imperial and Pressure to Head H = head, ft P = pressure, psi H = head, m P = pressure, bar Mass Flow to Volumetric Flow ṁ = mass flow, lbm/h ρ = fluid density, lbm/ft 3 ṁ = mass flow, kg/h
Units and Dimensions Basic properties such as length, mass, time and temperature that can be measured are called dimensions. Any quantity that can be measured has a value and a unit associated with it.
1301 Series High-Pressure Regulators Bulletin 71.1:1301 December 2013 P10 Figure 1. Type 1301F Regulator Features Durable Stainless Steel Diaphragm For high-outlet pressure applications. Spare Valve Disk
DIN 2403 Identification of pipelines according to the fluid conveyed. Marking of pipes according to fluid transported 1 Field of application This standard specifies the colours for the identification of
Understanding Centrifugal Compressor Performance in a Connected Process System Scott Golden, Scott A. Fulton and Daryl W. Hanson Process Consulting Services Inc., Houston, Texas Wet gas compressor capacity
CALIFORNIA RESIDENTIAL CODE MATRIX ADOPTION TABLE APPENDIX A SIZING AND CAPACITIES OF GAS PIPING (Matrix Adoption Tables are non-regulatory, intended only as an aid to the user. See Chapter 1 for state
Chapter 11 Gas sensors need to be calibrated and periodically checked to ensure sensor accuracy and system integrity. It is important to install stationary sensors in locations where the calibration can
The below article deals with the link between the demand side and the supply side and deals with how to get the treated compressed air to the points of use at the right rate of flow and at the right pressure.
(IFGS) SIZING AND CAPACITIES OF GAS PIPING (Not Adopted by the State of Oregon) (This appendix is informative and is not part of the code. This appendix is an excerpt from the 2006 International Fuel Gas
comp_02 A CO 2 cartridge is used to propel a small rocket cart. Compressed CO 2, stored at a pressure of 41.2 MPa (abs) and a temperature of 20 C, is expanded through a smoothly contoured converging nozzle
SAMPLE PROBLEMS FOR TEST No. 1 ANSWERS AND SOLUTIONS TO SELECTED ODD-NUMBERED PROBLEMS 1.5 The attractive force of gravity for objects near the earth s surface increases as you get closer to the center
Aeration Air & Digester Gas Flow Metering Using Thermal Mass Technology HWEA 2011 Conference Craig S. Johnson Presentation Overview Introduction Aeration Air & Digester gas challenges Gas flow metering
Section 3.1 Properties of Matter In your textbook, read about physical properties and chemical properties of matter. Use each of the terms below just once to complete the passage. chemical mass physical
Sizing Pressure Regulators & Control Valves ( ( Sizing the Pressure Regulators Sizing of regulators is usually made on the basis of Cg valve and KG sizing coefficients. Flow rates at fully open position
Gas B34 Series Regulator Commercial and Industrial Regulator Applications Appropriate for many commercial and industrial uses such as gas engines, burners, furnaces and boilers. The rapid response of the
Lecture T1 Transient Mass Transfer Up to now, we have considered either processes applied to closed systems or processes involving steady-state flows. In this lecture we turn our attention to transient
Technical Note 1001 Metronics Inc. Generating Calibration Gas Standards with Dynacal Permeation Devices Permeation devices provide an excellent method of producing known gas concentrations in the PPM and
APPENDIX A CONTROL VALVE TESTING PROCEDURES AND EQUATIONS FOR LIQUID FLOWS Section A.1. Flow Coefficients Definition The flow coefficient or pressure loss coefficient is used to relate the pressure loss
116eering. Engineering. Engineering. Engineering. Engineerin Engineering Information SPECIFYING SPRAY NOZZLES Spray nozzles have three basic functions: meter flow distribute liquid break up a liquid stream
ModuMath Basic Math Basic Math 1.1 - Naming Whole Numbers 1) Read whole numbers. 2) Write whole numbers in words. 3) Change whole numbers stated in words into decimal numeral form. 4) Write numerals in
ADVANCED LEAK TEST METHODS Before new technologies were available to directly measure very small leaks, most leak measurements were done indirectly. Direct mass leak flow measurement has many advantages.
Applied Fluid Mechanics 1. The Nature of Fluid and the Study of Fluid Mechanics 2. Viscosity of Fluid 3. Pressure Measurement 4. Forces Due to Static Fluid 5. Buoyancy and Stability 6. Flow of Fluid and
T-41 Tutorial 6 GASES Before working with gases some definitions are needed: PRESSURE: atmospheres or mm Hg; 1 atm = 760 mm Hg TEMPERATURE: Kelvin, K, which is o C + 273 STP: Standard Temperature and Pressure:
Steam System Best Practices Condensate System Piping Summary The best method for improving steam system energy efficiency, reducing chemical costs, and reducing make-up water costs is to return the maximum
TOM WHEATLEY Piston Check Valves Designed to safely prevent backflow, preventing damage to pumps and compressors Table of Contents TOM WHEATLEY PISTON CHECK VALVES Features... 1 How to Order... Dimensions...
Lecture no. 7 1.6 PRESSURE Pressures, like temperatures, can be expressed by either absolute or relative scales. Pressure is defined as "normal force per unit area." Figure 1.5 shows a cylinder of water.
EXERCISE 139, Page 303 CHAPTER 5 IDEAL GAS LAWS 1. The pressure of a mass of gas is increased from 150 kpa to 750 kpa at constant temperature. Determine the final volume of the gas, if its initial volume
Gas Law Problems Abbreviations Conversions atm - atmosphere K = C + 273 mmhg - millimeters of mercury 1 cm 3 (cubic centimeter) = 1 ml (milliliter) torr - another name for mmhg 1 dm 3 (cubic decimeter)
Differential Relations for Fluid Flow In this approach, we apply our four basic conservation laws to an infinitesimally small control volume. The differential approach provides point by point details of
Refrigeration Service Engineers Society 1666 Rand Road Des Plaines, Illinois 60016 UNDERSTANDING REFRIGERANT TABLES INTRODUCTION A Mollier diagram is a graphical representation of the properties of a refrigerant,
5. The Kinetic Theory of Gases Introduction and Summary Previously the ideal gas law was discussed from an experimental point of view. The relationship between pressure, density, and temperature was later
Course Mathematical Tools and Unit Conversion Used in Thermodynamic Problem Solving 1 Basic Algebra Computations 1st degree equations - =0 Collect numerical values on one side and unknown to the otherside
1 Fluid Mechanics Fluid Statics [3-1] Dr. Mohammad N. Almasri Fluid Pressure Fluid pressure is the normal force exerted by the fluid per unit area at some location within the fluid Fluid pressure has the
Pressure and Controls Pressure Reducing Armstrong pressure reducing valves (PRVs) and temperature regulators help you manage steam, air and liquid systems safely and efficiently. And assure uninterrupted
501:440-13 User s Manual Laminar Flow Elements 10920 Madison Avenue Cleveland, Ohio 44102 Tel: 216.281.1100 email:email@example.com Web:www.meriam.com 1 TABLE OF CONTENTS Subject Page Introduction... 3
Introduction: Booster Pump and Ejector Nozzle Selection Hydro Instruments offers a standard nozzle for each of our ejectors. However, we also offer alternate nozzle choices for each ejector. Each nozzle
c h i l l e r G l o s s a ry of Te rm s A p p r o a c h Temperature difference between the leaving fluid and the evaporating refrigerant ARI Standard Conditions 54 F. water inlet; 44 F. water out; 35 F.
www.swagelok.com Proportional Relief Valves R Series Liquid or gas service Set pressures from 10 to psig (0.7 to 413 bar) 1/4 and 1/2 in. and 6 to 12 mm end connections 2 Proportional Relief Valves Spring
FLUID FLOW Introduction Fluid flow is an important part of many processes, including transporting materials from one point to another, mixing of materials, and chemical reactions. In this experiment, you
Vacuum Applications Vacuum regulators and breakers are widely used in process plants. Conventional regulators and relief valves might be suitable for service if applied correctly. This section provides
Piping Hydraulic Line Design and Sizing Software KLM Technology Group Practical Engineering Guidelines for Processing Plant Solutions #03-12 Block Aronia, Jalan Sri Perkasa 2 Taman Tampoi Utama 81200 Johor
A cart full of water travels horizontally on a frictionless track with initial velocity v. As shown in the diagram, in the back wall of the cart there is a small opening near the bottom of the wall that
Application of the Orifice Meter for Accurate Gas Flow Measurement page 1 DANIEL MEASUREMENT AND CONTROL WHITE PAPER Application of the Orifice Meter for Accurate Gas Flow Measurement www.daniel.com Summary
Name: Sunday, October 14, 2007 Test 1: Introduction to Chemistry 1. Two substances, A and Z, are to be identified. Substance A can not be broken down by a chemical change. Substance Z can be broken down
Fluid & Gas Properties FLUID DENSITY Density is the ratio of mass to volume. In English, units density is expressed in pounds mass/cubic foot (lbm/ft 3 ). The symbol for density is ρ. Density is usually
CHAPTER 4 GAS PIPING INSTALLATIONS SECTION 40 GENERAL 40. Scope. This chapter shall govern the design, installation, modification and maintenance of piping systems. The applicability of this code to piping
Technical Publication Flow Meter Selection for Improved Gas Flow Measurements: Comparison of Differential Pressure and Thermal Dispersion Technologies Art Womack, Sr. Applications Engineer Fluid Components
Deaerator White Paper for use with Industrial/Commercial and Institutional Boilers ABMA. representing the best of the boiler industry Page 1 of 7 Deaerator White Paper for use with Industrial/Commercial
CONTENTS STEAM PIPING........................................................... 3 WATER PIPING........................................................... 3 NATURAL GAS PIPING.....................................................
Working Math Formulas, Units, Conversions This presentation has been adapted from Math for Subsurface Operators given at the North Carolina Subsurface Operator School Math will be used to Determine a flow
Unit-7 Thermodynamics Introduction: The term Thermo means heat and dynamics means flow or movement.. So thermodynamics is concerned with the flow of heat. The different forms of the energy are interconvertible
WEEK 1 Engineering Calculations Processes Process Variables 2.1 Units and Dimensions Units and dimensions are important in science and engineering A measured quantity has a numerical value and a unit (ex:
Fluids and Solids: Fundamentals We normally recognize three states of matter: solid; liquid and gas. However, liquid and gas are both fluids: in contrast to solids they lack the ability to resist deformation.
Applied Fluid Mechanics 1. The Nature of Fluid and the Study of Fluid Mechanics 2. Viscosity of Fluid 3. Pressure Measurement 4. Forces Due to Static Fluid 5. Buoyancy and Stability 7. General Energy Equation