# HYDRAULIC ANALYSIS OF PIPE LINED WITH MADISON S 100% SOLIDS STRUCTURAL POLYURETHANE COATINGS

Save this PDF as:

Size: px
Start display at page:

## Transcription

2 An example of the hidden costs is the pump efficiency, which is related to the water/wastewater flow efficiency. Because Madison s 100% solids structural polyurethanes have better abrasive resistance and is smoother than cement-mortar and other lining materials, the pump efficiency of pipes lined with Madison s polyurethane coatings is significantly higher than the case of other lining materials. This paper gives out detailed hydraulic and friction analysis of various pipes lined with Madison s 100% solids structural polyurethane coatings. 2. Fundaments of hydraulic analysis While conducting hydraulic analysis on pipes lined/coated with a coating, it is important to understand how water is going to flow through the piping and the loss associated with this flow. The primary loss of energy is due to the friction between the fluid and the pipe wall. The flow is converted to waste heat, drop in pressure in a pipeline is observed, and the energy is lost. Illustrations made by Dan Lundy 1 are very helpful to help one understand the basic terminology of hydraulic analysis. Consider Figure 1 below. With the pump "on" but the hydrant valve closed, the pump simply produces pressure with no flow. The pressure all along the horizontal pipe is 60 psi. This is the "shutoff head" for this pump. Figure 1. Shutoff head, courtesy of Dan Lundy 1 Consider then if the pump is "on" and the hydrant valve is open. As water flows through the pipe, valves and fittings, the interaction of the liquid with the pipe walls will produce turbulence and friction resistance, which results in the loss of energy or "head" (Figure 2). Water flowing through a closed pipe will experience irreversible loss of pressure or "headloss.

5 3. Friction and hydraulic headloss of pipes lined with Madison s 100% solids structural polyurethane coatings For any pipeline internal lining application, the lining must be able to withstand the constant flow of liquid and any particulates. Normal municipal pipeline velocities are in the range of 8 to 16 feet per second (2 to 4 meters per second) but these rates can increase in some cases to over 30 feet per second. The corrosion protection lining must be capable to withstand the constant abrasion caused by the passing water at the various velocities. Premature failure of the lining system can occur thereby exposing the steel substrate to the corrosion cycle. ASTM D4060 is a commonly used testing method for measuring the abrasion resistance of a coating system. The Taber Abrasion Test (ASTM D4060) rotates a sample under a specific weight against a grinding wheel for a defined number of revolutions. The samples are evaluated by measuring the weight of the sample before and after the abrasion. The resulting weight loss indicates the comparative ability of the lining to resist abrasion and wear. The lower the reported weight loss, the more abrasion resistant the lining. Table 1 summarizes the abrasion resistance testing results of a typical Madison s 100% solids structural polyurethane lining material, comparing with other solvent based or 100% solids epoxy linings as well as cement-mortar systems. The 100% solids polyurethane lining demonstrated superior abrasion resistance. This parallels what is already known in the industry that polyurethanes offer excellent abrasion resistance. The solvent based and 100% solids epoxy lining systems offered moderate abrasion resistance. The cement-mortar system samples illustrated the inherent nature of cement-based products to wear away at an accelerated rate in environments that are subject to fast velocities. However, with cementitious linings, the abrasion resistance can vary widely depending on the type and amount of aggregate. Table 1 Abrasion Resistance Results Product Type Solvent Amine Based Epoxy 100% Solids Epoxy Madison s 100% Solids Polyurethane Cement Mortar Average Weight Loss 122 mg loss 183 mg loss 50 mg loss 1500 mg loss For a pipe to have satisfactory flow characteristics, it initially must provide a high Hazen- Williams flow coefficient C factor and must be able to maintain a high flow coefficient through years of service. The capability of a lining system to maintain a high flow coefficient is correlated with its ability resisting to deterioration due to abrasion or other

6 physical/chemical attack. The higher resistances to deterioration, the better the capability can a lining have to maintain the high flow coefficient. Numerous flow tests have been conducted to demonstrate how well various pipe lining materials meet these requirements. The average value of C factor for new cementmortar lined pipes was found to be 144, although some tests reported values from 150 to 157. For older systems, the average value of C factor was found to be 140. As a result, it is commonly accepted by the pipe industry that a C factor of 140 for cement-mortar linings is a realistic and long-term value. 2 Tests have also been conducted and reported by third parties, including a world s leading pipe manufacturer, on the abrasion resistance and flow coefficient of pipes lined with Madison s 100% solids structural polyurethane coating systems 3. It showed that the Madison s linings will provide a tough abrasion resistant interior that will resist erosion from sand or grit particles being carried in suspension. Also the pipes and fittings lined with the Madison s polyurethane materials can produce and maintain a smooth interior of pipe surface to which most materials will not adhere, having a Hazen-Williams C factor of 150. For a specific set of conditions, such a Hazen-Williams C factor of 150 is approximately equal to a Manning n coefficient of Effluent line 4 mile steel pipeline Average speed of 10 ft/sec Temperature: 140 o F/60 o C. Lining: Madison s 100% solids rigid PU Production: 16,000 ft 2 /12hr shift Figure 4 A smooth and abrasion resistant interior pipe surface for high aggressive and high slow rate applications with a Madison s 100% solids structural polyurethane product Typical minimum specified dry film coating thickness of Madison s 100% solids structural polyurethane coatings for water/wastewater applications is given in Table 2, depending on the condition of substrate. In contrast, most other lining materials such as cement mortar, polyethylene, and/or 100% solids polyurea are applied at a much thicker dry film thickness than Madison s 100% solids structural polyurethane products, hence the actual inside diameter of the pipes lined with theses other materials is much smaller. The combination of high flow coefficient with a larger inside diameter provides

7 exceptionally high flow capacities of pipes lined with Madison s 100% solids structural polyurethane lining materials. Table 2 Typical minimum specified dry film coating thickness of Madison s 100% solids structural polyurethane linings for water/wastewater interior applications Substrate Type Madison s 100% solids structural polyurethane linings External Application Steel 25 mils (625 microns) normal 25 mils (625 microns) normal 50 mils (1250 microns) - slip bore Ductile iron 40 mils (1000 microns) 25 mils (625 microns) 50 mils (1250 microns) slip bore Reinforced concrete Pre-stressed concrete cylinder 60 mils (1500 microns) 40 mils (1000 microns) 25 mils (625 microns) 30 mils (750 microns) \$60,000 \$50,000 \$40,000 \$30,000 \$20,000 \$53,107 \$40,129 Cement mortar Polyurethane \$10,000 \$0 Pumping cost Figure 5 Significant annual pumping cost with a Madison s polyurethane lining vs. cement-mortar for a 30,000 ft normal 24 inch size pipe Figure 5 illustrates that significant pumping cost savings of about \$12, US dollars could be achieved by simply the use of a Madison s 100% solids rigid polyurethane lining rather than a cement-mortar lining for a 30,000 feet length 24 inch normal size

8 steel pipe. This saving is estimated assuming: 6,000 gpm design flow, 70% pumping efficiency, \$0.06 dollar KWH unit power cost, a 140 Hazen-Williams C factor for a 375 mils thick cement-mortar lining and 150 for a 25 mils thick polyurethane lining. This represents the total pumping cost savings of over \$648,900 dollars during the pipeline operation period of a 50-year design life (assuming zero inflation). Pipe manufacturers can also save money from the use of Madison s 100% solids rigid polyurethane lining. The estimation in Figure 5 assumes a 24 inch normal size of steel pipe. About 2.83% pipe material cost could be saved if a Madison s polyurethane lining rather than a cement-mortar lining is used. For the 30,000 feet length pipeline, it means a pipe material cost saving of \$68,000 US dollars assuming a unit cost of \$80 per feet of steel. Furthermore, the above estimation assumes that Madison s 100% solids rigid polyurethane performs equally as cement-mortar. However, both laboratory and field experience and testing results have proved that the polyurethane would outperform the cement-mortar. 4. Summary Madison s 100% solids structural polyurethanes have better abrasive resistance and is smoother than cement-mortar and other lining materials, the pump efficiency of pipes lined with Madison s polyurethane coatings would be significantly higher than the case of other lining materials. 1 Dan Lundy, Water & Environmental Technology, Course Notes, Clackamas Community College, Oregon City, Oregon, USA, DIPRA, Hydraulic Analysis of Ductile Iron Pipe, U.S. Pipe, Polyurethane Lined Ductile Iron Pipe and Fittings For Force Mains and Gravity Sewer Lines, 1993

### Strength and Durability for Life HYDRAULICS. Hydraulic Analysis of Ductile Iron Pipe

Strength and Durability for Life HYDRAULICS Hydraulic Analysis of Last Revised: August 2016 Head Loss Friction head loss or drop in pressure in a pipeline is an everyday concern for the water works engineer.

Linings Linings Along with technical and metallurgical advancement in piping materials, research on lining requirements for pipe and fittings has resulted in the development of linings to meet many different

### Module 9: Basics of Pumps and Hydraulics Instructor Guide

Module 9: Basics of Pumps and Hydraulics Instructor Guide Activities for Unit 1 Basic Hydraulics Activity 1.1: Convert 45 psi to feet of head. 45 psis x 1 ft. = 103.8 ft 0.433 psi Activity 1.2: Determine

### Water & Wastewater Coatings & Linings Environmentally Friendly Coatings Protection From Collection to Storage

Water & Wastewater Coatings & Linings Environmentally Friendly Coatings Protection From Collection to Storage Coatings - Linings - Fireproofing Collections & Transportation Manholes, Fittings, Penstocks,

### Avoiding Pump Wear in Centrifugal Pumps

Pump Wear Avoiding Pump Wear in Centrifugal Pumps Introduction: In the moment of starting a new pump, that pump is headed for a day when it will need repair even if the design and operation is correct.

### Pressure drop in pipes...

Pressure drop in pipes... PRESSURE DROP CALCULATIONS Pressure drop or head loss, occurs in all piping systems because of elevation changes, turbulence caused by abrupt changes in direction, and friction

### Applied Fluid Mechanics

Applied Fluid Mechanics 1. The Nature of Fluid and the Study of Fluid Mechanics 2. Viscosity of Fluid 3. Pressure Measurement 4. Forces Due to Static Fluid 5. Buoyancy and Stability 6. Flow of Fluid and

### Liquid Applied Internal Flow Coatings for Oil Transmission Lines

Liquid Applied Internal Flow Coatings for Oil Transmission Lines M R McDonnell E Wood Limited United Kingdom This paper will examine more closely the benefits to the Industry by lining Oil Pipelines. Introduction

### Module 3: Sewer Material Lecture 3: Sewer Material

Module 3: Sewer Material Lecture 3: Sewer Material [NPTEL, IIT Kharagpur, Prof. M.M.Ghangrekar, Department of Civil Engineering Page 1 3.0 SEWER MATERIAL 3.1 Important Factors Considered for Selecting

### CORROSION PROTECTION BY COATINGS FOR WATER AND WASTEWATER PIPELINES

Water and Wastewater Program West Virginia University, PA May 15, 2001 CORROSION PROTECTION BY COATINGS FOR WATER AND WASTEWATER PIPELINES Shiwei William Guan, Ph.D. Vice President, Research and Development

### Piping Systems. General considerations

SRAC Publication No. 373 May 2013 Revision PR VI Piping Systems J. David Bankston, Jr. and Fred Eugene Baker 1 A piping system allows the controlled movement of water from one location to another. It consists

### Waterproofing System for Wastewater Tanks in Petrochemical Industries and Refineries

Waterproofing System for Wastewater Tanks in Petrochemical Industries and Refineries Introduction Wastewater of petrochemical industries and refineries contains high amounts of emulsified aliphatic or

### Module 7: Hydraulic Design of Sewers and Storm Water Drains. Lecture 7 : Hydraulic Design of Sewers and Storm Water Drains

1 P age Module 7: Hydraulic Design of Sewers and Storm Water Drains Lecture 7 : Hydraulic Design of Sewers and Storm Water Drains 2 P age 7.1 General Consideration Generally, sewers are laid at steeper

### SYSTEMS ENGINEERING DATA FOR THERMOPLASTIC PIPING

SYSTEMS ENGINEERING DATA INTRODUCTION In the engineering of thermoplastic piping systems, it is necessary to have not only a working knowledge of piping design but also an awareness of a number of the

### Module 3 : Sewer Material. Lecture 3 : Sewer Material

1 P age Module 3 : Sewer Material Lecture 3 : Sewer Material 2 P age 3.1 Important Factors Considered for Selecting Material for Sewer Following factors should be considered before selecting material for

### Before H 2 Town of South Windsor, CT Evaluates Large Diameter Concrete Pipe

Before H 2 Town of South Windsor, CT Evaluates Large Diameter Concrete Pipe September 11, 2012 NEWEA Collection Systems Conference Presented by: Laurie L. Perkins, PE Dennis A. Dievert, PE C. Frederick

### Force Main Condition Assessment: New Technologies & Case Studies

Force Main Condition Assessment: New Technologies & Case Studies Andy Dettmer, Ph.D., P.E. CMOM Workshop August 19, 2014 2 1 Three takeaways 1. Most of your force mains are good 2. We can pinpoint the

### ADS, Inc. Drainage Handbook Hydraulics 3-1

ADS, Inc. Drainage Handbook Hydraulics 3-1 3-0 HYDRAULICS TABLE OF CONTENTS 3-1 Overview of Hydraulic Considerations... 3-2 3-2 Design Manning s Value... 3-2 3-3 Discharge Curves... 3-4 3-3 The Conveyance

### STANDARD SPECIFICATIONS SECTION 02512 CLEANING AND LINING WATER MAINS

STANDARD SPECIFICATIONS SECTION 02512 CLEANING AND LINING WATER MAINS PART 1 GENERAL 1.1 DESCRIPTION A. Section includes requirements for cleaning and lining existing cast iron and ductile iron water mains

### Theory, Application, and Sizing of Air Valves

Theory, Application, and Sizing of Air Valves VAL-MATIC VALVE AND MANUFACTURING CORP. 905 RIVERSIDE DRIVE, ELMHURST, IL 60126 TEL. (630) 941-7600 FAX. (630) 941-8042 www.valmatic.com 1 THEORY, APPLICATION,

### SIZING AND CAPACITIES OF GAS PIPING

APPENDIX A (IFGS) SIZING AND CAPACITIES OF GAS PIPING (This appendix is informative and is not part of the code.) A.1 General. To determine the size of piping used in a gas piping system, the following

### CHAPTER 8 WATER DISTRIBUTION SYSTEMS

CHAPTER 8 WATER DISTRIBUTION SYSTEMS Distribution system is a network of pipelines that distribute water to the consumers. They are designed to adequately satisfy the water requirement for a combination

### Relining of Water Mains with. Flexible High Pressure Pipelines. Raedlinger Primus Line, Inc. Ivan Zubiaga Executive Vice President 2014

Relining of Water Mains with Flexible High Pressure Pipelines Raedlinger Primus Line, Inc. Ivan Zubiaga Executive Vice President 2014 Aging water main infrastructure The American Society of Civil Engineers

### Pacific Pump and Power

Pacific Pump and Power 91-503 Nukuawa Street Kapolei, Hawaii 96707 Phone: (808) 672-8198 or (800) 975-5112 Fax: (866) 424-0953 Email: sales@pacificpumpandpower.com Web: www.pacificpumpandpower.com Pumps

### SECTION XXXXXX TECHNICAL SPECIFICATIONS FOR INSTALLATION OF PROTECTIVE COATINGS FOR MANHOLES, WETWELLS, AND OTHER SANITARY SEWER STRUCTURES

1.00 PART 1 GENERAL 1.01 SCOPE A. It is the intent of this contract to install a 100% solids epoxy monolithic coating to the walls, benches and inverts of all manholes and the specified surfaces of other

### Section Four: Linings and Coatings

Section Four: Linings and Coatings SPIRALWELD PIPE The majority of steel water pipe furnished today is specified to be provided with both an interior lining and an exterior coating. AMERICAN offers a wide

### Letty Arvide-Gomar, PE

Letty Arvide-Gomar, PE Outline DIP History and Applications Corrosion Issues Internal Cleaning Technologies Rehabilitation Options DIP History and Applications Corrosion Issues Internal Cleaning Technologies

### Water Supply. Simulation of Water Distribution Networks. Mohammad N. Almasri. Optimal Design of Water Distribution Networks Mohammad N.

Water Supply Simulation of Water Distribution Networks The Use of EPANET Mohammad N. Almasri 1 Introduction This presentation focuses on two issues: The simulation of water distribution networks (WDNs)

### Radiation Curable Components and Their use in Hard, Scratch Resistant Coating Applications

Radiation Curable Components and Their use in Hard, Scratch Resistant Coating Applications William Schaeffer Steven Tyson Indu Vappala Robert Kensicki Sartomer USA, LLC 502 Thomas Jones Way Exton, PA 19343

### WATER MEASUREMENT USING TWO INCH (50 mm) DRAIN TESTS

GAP.14.1.2.2 A Publication of Global Asset Protection Services LLC WATER MEASUREMENT USING TWO INCH (50 mm) DRAIN TESTS INTRODUCTION A hydrant or other large-volume flow test is necessary for proper water

### PRODUCT DATA SHEET DESCRIPTION:

DESCRIPTION: SP-9888 Pipe Lining is based on the latest Zero VOC Novolac Technology. The product cures to a highly cross-linked coating with excellent chemical, solvent and water immersion resistance.

### DEVELOPMENTS IN SPRAY APPLIED COATINGS FOR THE PROTECTION OF PROCESS VESSELS

DEVELOPMENTS IN SPRAY APPLIED COATINGS FOR THE PROTECTION OF PROCESS VESSELS Presented By : Mr. Ron Campbell Senior Vice President Belzona Asia Pacific NACE Jubail Meeting October 2009 Protective Coatings

### Pipe Flow-Friction Factor Calculations with Excel

Pipe Flow-Friction Factor Calculations with Excel Course No: C03-022 Credit: 3 PDH Harlan H. Bengtson, PhD, P.E. Continuing Education and Development, Inc. 9 Greyridge Farm Court Stony Point, NY 10980

### DIVISION OF WATER QUALITY CONSTRUCTION GRANTS & LOANS SECTION FAST TRACK AUDIT CHECKLIST

DIVISION OF WATER QUALITY CONSTRUCTION GRANTS & LOANS SECTION FAST TRACK AUDIT CHECKLIST CERTIFICATION 1. Did the engineer submit a certificate of completion utilizing the appropriate page of the issued

### Design Criteria & Service Goals

4.1 Design Life of Improvements The design life of a water system component is sometimes referred to as its useful life or service life. The selection of a design life is a matter of judgment based on

### Rehabilitation or Replacement? That Is The Question

Rehabilitation or Replacement? That Is The Question Chris L. Windley PE Greg Anderson, PE 94th Annual Conference November 18, 2014 Overview Project Background Existing Sewer Condition Flow Projections

### LIQUID FLOW PROVERS (Conventional) Class Number 252. Brendan S. Ryan Smith Meter Inc P.O. Box 4658 Corpus Christi, Texas 78404

LIQUID FLOW PROVERS (Conventional) Class Number 252 Brendan S. Ryan Smith Meter Inc P.O. Box 4658 Corpus Christi, Texas 78404 Introduction Flow meters need to be calibrated for accurate measurement! To

### TECHNICAL REQUIREMENTS AND SPECIFICATIONS

TECHNICAL REQUIREMENTS AND SPECIFICATIONS REHABILITATION OF CONCRETE AND MASONRY MANHOLES OR UNDERGROUND VAULTS WITH A PROTECTIVE COATING (As Provided by Raven Lining Systems) FOREWORD This specification

### Experiment (13): Flow channel

Introduction: An open channel is a duct in which the liquid flows with a free surface exposed to atmospheric pressure. Along the length of the duct, the pressure at the surface is therefore constant and

### Minor losses include head losses through/past hydrants, couplers, valves,

Lecture 10 Minor Losses & Pressure Requirements I. Minor Losses Minor (or fitting, or local ) hydraulic losses along pipes can often be estimated as a function of the velocity head of the water within

### Hydraulics Guide. Table 1: Conveyance Factors (English Units)... 7 Table 2: Conveyance Factors (Metric Units)... 8

Table of Contents 1.1 Index of Tables... 1 1. Index of Figures... 1 1.3 Overview of Hydraulic Considerations... 1.4 Discharge Curves... 1.5 Conveyance Method... 5 1.6 Flow Velocity Considerations... 9

### PROTECTO 401 CERAMIC EPOXY LINED DUCTILE IRON PIPE AND FITTINGS

CERAMIC EPOXY LINED DUCTILE IRON PIPE AND FITTINGS FOR FORCE MAINS, GRAVITY AND INDUSTRIAL SEWER LINES P 2 Table of Contents PROTECTO 401 3 Suggested Specification For PROTECTO 401 5 Procedures for Sealing

### hose-to-hose coupling pump-to-hose coupling

pipe_02 A homeowner plans to pump water from a stream in their backyard to water their lawn. A schematic of the pipe system is shown in the figure. 3 m 1 m inlet pipe-to-pump coupling stream re-entrant

### Demonstration of an Innovative Large-Diameter Sewer Rehabilitation Technology in Houston, Texas

North American Society for Trenchless Technology (NASTT) NASTT s 2014 No-Dig Show Orlando, Florida April 13-17, 2014 Paper TA-T3-03 Demonstration of an Innovative Large-Diameter Sewer Rehabilitation Technology

### Rehabilitation of an Aging Concrete Reservoir Adit Tower

Rehabilitation of an Aging Concrete Reservoir Adit Tower Raymond S. Tombaugh, Senior Coatings Consultant KTA-Tator, Inc. and Mongkol Mahavongtrakul, P.E. Corrosion Control Contract Manager San Francisco

### Pump Ratio and Performance Charts

Pump Ratio and Performance Charts Concept and Theory Training Table of Contents Introduction... 1 Overview... 1 How to use this Module... 2 Learning Objectives...2 Text...2 Charts, Illustrations...2 Progress

### DISTRIBUTION PIPING MATERIALS: BUILDING HYDRONIC SYSTEM MANAGEMENT. Jim Riley, Texas A&M University February 10, 2015

DISTRIBUTION PIPING MATERIALS: BUILDING HYDRONIC SYSTEM MANAGEMENT Jim Riley, Texas A&M University February 10, 2015 Piping at Texas A&M 2 History of Distribution Piping at Texas A&M Concrete reinforced

### Fire Pump Layout and Sizing. Victoria B. Valentine, P.E.

Fire Pump Layout and Sizing Victoria B. Valentine, P.E. Learning Outcomes Identify the appropriate sections of NFPA 20 that apply to sizing and layout of fire pumps. Identify the components of a fire pump

### POLYURETHANE LINING AND COATING ON PIPE RAW WATER

POLYURETHANE LINING AND COATING ON PIPE RAW WATER PART 1 -- GENERAL 1.1 THE REQUIREMENT A. The CONTRACTOR shall provide pipe coating, complete and in place, in accordance with the Contract Documents. 1.2

### Secondary Containment Comparison ATI Ultra COAT vs HDPE

When choosing a secondary containment system it must be chosen based on its ability to withstand long term contact with the natural elements (weather), whatever the tanks hold (unrefined oil, fuels, acids,

### Experimentation and Computational Fluid Dynamics Modelling of Roughness Effects in Flexible Pipelines

Experimentation and Computational Fluid Dynamics Modelling of Roughness Effects in Flexible Pipelines Sophie Yin Jeremy Leggoe School of Mechanical and Chemical Engineering Daniel Teng Paul Pickering CEED

### The AQUAFIN Approach to Concrete Repair

Concrete Repair Building Product Systems Waterproofing & Concrete Restoration Decorative Coatings Moisture Vapor Remediation & Flooring Injection Grouting The AQUAFIN Approach to Concrete Repair www.aquafin.net

### SANITARY SEWER SPECIFICATIONS

SANITARY SEWER SPECIFICATIONS OCTOBER 2003 HARVEST-MONROVIA WATER, SEWER, AND FIRE PROTECTION AUTHORITY SECTION 1.00 1.10 Purpose The purpose of this document is to assemble the sewer specifications, policies,

### Industrial Pipeline Integrity Management & Remote Polyurea Pipe Lining Systems.

Industrial Pipeline Integrity Management & Remote Polyurea Pipe Lining Systems. Aging pipeline infrastructure and industry s inability to evaluate and inspect has left many engineers and plant managers

### Determining Tube Size for Hydraulic Systems

Determining Size for Hydraulic Systems Use Tables U13 and U14 to determine recommended flow diameter for the required flow rate and type of line. The table is based on the following recommended flow velocities:

### Open Channel Diffusers

Open Channel Diffusers Application Information: Open channel diffusers are used to increase mixing and absorbance efficiency of a chemical solution into the process water. Specifically designed penetrations

### LECTURE 1: Review of pipe flow: Darcy-Weisbach, Manning, Hazen-Williams equations, Moody diagram

LECTURE 1: Review of pipe flow: Darcy-Weisbach, Manning, Hazen-Williams equations, Moody diagram 1.1. Important Definitions Pressure Pipe Flow: Refers to full water flow in closed conduits of circular

### CHAPTER II UNIFORM FLOW AND ITS FORMULAS MODULE 1. This experiment was designed to observe the characteristics of uniform flow in

CHAPTER II UNIFORM FLOW AND ITS FORMULAS MODULE 1 2.1 Introduction and Objective This experiment was designed to observe the characteristics of uniform flow in the teaching flume and to utilize the common

### Native InDesign 2890 SaniTite Brochure 1/8" 100 300 CMYK April 17, 07

Sanitary Sewer Pipe Tough pipe for a tough environment SaniTite Sanitary Sewer Pipe delivers the features that engineers, contractors and municipalities demand durability, performance, handling, toughness

### CENTRIFUGAL PUMP OVERVIEW Presented by Matt Prosoli Of Pumps Plus Inc.

CENTRIFUGAL PUMP OVERVIEW Presented by Matt Prosoli Of Pumps Plus Inc. 1 Centrifugal Pump- Definition Centrifugal Pump can be defined as a mechanical device used to transfer liquid of various types. As

### SECTION 15076 CEMENT-MORTAR LINED AND COATED STEEL PIPE

SECTION 15076 CEMENT-MORTAR LINED AND COATED (CML&C) STEEL PIPE PART 1 GENERAL 1.01 DESCRIPTION This section designates the requirements for steel pipe fabrication, test in shop, installation of steel

### Applied Fluid Mechanics

Applied Fluid Mechanics Sixth Edition Robert L. Mott University of Dayton PEARSON Prentkv Pearson Education International CHAPTER 1 THE NATURE OF FLUIDS AND THE STUDY OF FLUID MECHANICS 1.1 The Big Picture

### Hydraulics Laboratory Experiment Report

Hydraulics Laboratory Experiment Report Name: Ahmed Essam Mansour Section: "1", Monday 2-5 pm Title: Flow in open channel Date: 13 November-2006 Objectives: Calculate the Chezy and Manning coefficients

SECTION 08000 STORM DRAINAGE 08010 DESIGN A. Location B. Sizing TABLE OF CONTENTS 08020 MATERIALS A. Pipe Materials B. Structure Materials C. Installation D. Inlets and Outlets 08030 INSPECTIONS AND TESTING

### SIZING AND CAPACITIES OF GAS PIPING (Not Adopted by the State of Oregon)

(IFGS) SIZING AND CAPACITIES OF GAS PIPING (Not Adopted by the State of Oregon) (This appendix is informative and is not part of the code. This appendix is an excerpt from the 2006 International Fuel Gas

### 2.0 BASIC CONCEPTS OF OPEN CHANNEL FLOW MEASUREMENT

2.0 BASIC CONCEPTS OF OPEN CHANNEL FLOW MEASUREMENT Open channel flow is defined as flow in any channel where the liquid flows with a free surface. Open channel flow is not under pressure; gravity is the

### ASCE Pipelines 2011. Common Pitfalls in Hydraulic Design of Large Diameter Pipelines: Case Studies and Good Design Practice

961 ASCE Pipelines 2011 Common Pitfalls in Hydraulic Design of Large Diameter Pipelines: Case Studies and Good Design Practice David Bennett, P.E. 1 and Rebecca Glaser, E.I.T. 2 Freese and Nichols, Inc.,

### Wastewater Collection System Supplemental Design Standards for Capital Improvement Program Projects

Wastewater Collection System Supplemental Design Standards for Capital Improvement Program Projects March 2013 i Metropolitan Sewer District of Greater Cincinnati Wastewater Collection System Supplemental

### SECTION 3 SANITARY SEWER DESIGN

SECTION 3 SANITARY SEWER DESIGN 3.1 GENERAL DESIGN CRITERIA 3.1.1 Requirement for Sanitary Sewer 3.1.2 Design Approval 3.1.3 IEPA Permit Required 3.1.4 Differentiation Between Public and Private Sanitary

### Working Math Formulas, Units, Conversions

Working Math Formulas, Units, Conversions This presentation has been adapted from Math for Subsurface Operators given at the North Carolina Subsurface Operator School Math will be used to Determine a flow

### APPENDIX A FORMULAE AND SAMPLE CALCULATIONS

APPENDIX A FORMULAE AND SAMPLE CALCULATIONS Pipe Installation (Fused) The fused polyethylene (PE) pipe can be pulled by a cable attached to a pulling head fastened to the pipe. This prevents damage to

### SECTION 33 11 00.15 DUCTILE IRON PIPE AND FITTINGS

SECTION 33 11 00.15 DUCTILE IRON PIPE AND FITTINGS PART 1: GENERAL 1.01 COORDINATION OF WORK Connection to existing pipelines may require shutdown of AW facilities. Closely coordinate construction work

Green Thread Product Data Applications Dilute Acids Caustics Produced Water Industrial Waste Hot Water Condensate Return Materials and Construction All pipe manufactured by filament winding process using

### Appendix A: Acceptable pipe and fitting materials

Watercare Services Limited Water and Code of Practice Content from the NZS 4404:2010 Land development and subdivision infrastructure has been reproduced for use in the Infrastructure Design s Manual for

### High Density Polyethylene Liners for Rehabilitation of Corroded Pipelines

High Density Polyethylene Liners for Rehabilitation of Corroded Pipelines Jeff Schell General Manager United Pipeline Middle East, Inc. Introduction HDPE Liners A cost effective and environmentally beneficial

### Gasketed Sewer Pipe. Storm and Sanitary pipe for use with STI Gasketed Sewer Fittings.

Gasketed Sewer Pipe Storm and Sanitary pipe for use with STI Gasketed Sewer Fittings. Gasketed Sewer Pipe Installation Royal Municipal Solutions Gasketed Sewer Pipe weighs a fraction of the weight of traditional

### Friction Loss of Pulp Suspensions in Pipe

Friction Loss of Pulp Suspensions in Pipe I. INTRODUCTION In any stock piping system, the pump provides flow and develops hydraulic pressure (head) to overcome the differential in head between two points.

### SECTION 33 11 00.11 POLYVINYL CHLORIDE (PVC) PIPE

SECTION 33 11 00.11 POLYVINYL CHLORIDE (PVC) PIPE PART 1: GENERAL 1.01 SECTION INCLUDES PVC pressure pipe and fabricated fittings in nominal sizes 4-inches through 12-inches with cast iron pipe equivalent

### Open channel flow Basic principle

Open channel flow Basic principle INTRODUCTION Flow in rivers, irrigation canals, drainage ditches and aqueducts are some examples for open channel flow. These flows occur with a free surface and the pressure

### Fluid Dynamics Viscosity. Dave Foster Department of Chemical Engineering University of Rochester Email: dafoster@che

Fluid Dynamics Viscosity Dave Foster Department of Chemical Engineering University of Rochester Email: dafoster@che che.rochester.eduedu 1 Chemical Engineering What do Chemical Engineers Do? Manufacturing

### Pumps: Convert mechanical energy (often developed from electrical source) into hydraulic energy (position, pressure and kinetic energy).

HYDRAULIC MACHINES Used to convert between hydraulic and mechanical energies. Pumps: Convert mechanical energy (often developed from electrical source) into hydraulic energy (position, pressure and kinetic

### CHAPTER 3 STORM DRAINAGE SYSTEMS

CHAPTER 3 STORM DRAINAGE SYSTEMS 3.7 Storm Drains 3.7.1 Introduction After the tentative locations of inlets, drain pipes, and outfalls with tail-waters have been determined and the inlets sized, the next

### CHAPTER 2 HYDRAULICS OF SEWERS

CHAPTER 2 HYDRAULICS OF SEWERS SANITARY SEWERS The hydraulic design procedure for sewers requires: 1. Determination of Sewer System Type 2. Determination of Design Flow 3. Selection of Pipe Size 4. Determination

### Pacific Pump and Power

Pacific Pump and Power 91-503 Nukuawa Street Kapolei, Hawaii 96707 Phone: (808) 672-8198 or (800) 975-5112 Fax: (866) 424-0953 Email: sales@pacificpumpandpower.com Web: www.pacificpumpandpower.com Table

### In-Line Air Separators

Air Elimination & Control In-Line Air Separators The AC models of air separators deliver all the quality and performance you expect from Taco products. They are built to last with shell, heads and ANSI

### Chesapeake Section AWWA Symposium

PRESTRESSED CONCRETE CYLINDER PIPE (PCCP) Chesapeake Section AWWA Symposium HANSON PRESSURE PIPE Steve Smith January 16,2014 Interpace Projects with Problems INTERPACE 45 MILLION FEET 11,500 PROJECTS Slide

### Session: HDPE Pipe Test Rafael Ortega, Vice President, Lockwood, Andrews & Newnam

Session: HDPE Pipe Test Rafael Ortega, Vice President, Lockwood, Andrews & Newnam Education Master of Business Administration University of Houston, 1985 Bachelor of Science, Civil Engineering University

### SECTION 02630 STORM DRAINAGE SYSTEM

SECTION 02630 PART 1 - GENERAL 1.01 DESCRIPTION A. Section includes specifications for storm drainage systems including modifications and connections to existing storm drainage systems. 1.02 REFERENCE

### ME 305 Fluid Mechanics I. Part 8 Viscous Flow in Pipes and Ducts

ME 305 Fluid Mechanics I Part 8 Viscous Flow in Pipes and Ducts These presentations are prepared by Dr. Cüneyt Sert Mechanical Engineering Department Middle East Technical University Ankara, Turkey csert@metu.edu.tr

### Hydrant flow testing data provides important

feat40606.qxd 5/30/06 5:24 PM Page 44 The use of hydrant flow testing data to design automatic sprinkler systems has gotten easier thanks to new computer modeling software. By Dr. Sang H. Wong Hydrant

### NAPCA BULLETIN 18-99 APPLICATION PROCEDURES FOR CONCRETE WEIGHT COATING APPLIED BY THE COMPRESSION METHOD TO STEEL PIPE

NAPCA BULLETIN 18-99 APPLICATION PROCEDURES FOR CONCRETE WEIGHT COATING APPLIED BY THE COMPRESSION METHOD TO STEEL PIPE GENERAL a. These specifications may be used in whole or in part by any party without

### AIR RELEASE, CLEANOUT, AND SEWER MANHOLES

AIR RELEASE, CLEANOUT, AND SEWER MANHOLES **From Hartford IM BLDG(10) DESCRIPTION. This work shall consist of the construction of air release, cleanout, and sanitary sewer manholes; and the furnishing

### Water hammering in fire fighting installation

Water hammering in fire fighting installation Forward One of major problems raised in the fire fighting network installed at Pioneer company for pharmaceutical industry /Sulaymania was the high water hammering

### This will also provide you with the knowledge to insure long life for your Investment

CONDUIT PIPE DRYING This Presentation will guide you to why systems fail! This will also provide you with the knowledge to insure long life for your Investment Drainable and Dryable System Design Trough

### BRAKE SYSTEM DESIGN AND THEORY

RAKE SYSTEM DESIGN AND THEORY Aircraft brake systems perform multiple functions. They must be able to hold the aircraft back at full static engine run-up, provide adequate control during ground taxi operations,

### SIZING AND CAPACITIES OF GAS PIPING

CALIFORNIA RESIDENTIAL CODE MATRIX ADOPTION TABLE APPENDIX A SIZING AND CAPACITIES OF GAS PIPING (Matrix Adoption Tables are non-regulatory, intended only as an aid to the user. See Chapter 1 for state

### UNDERSTANDING GRAVITY-FLOW PIPELINES. Water Flow, Air Locks and Siphons

Livestock Watering Order No. 590.304-5 January 2006 UNDERSTANDING GRAVITY-FLOW PIPELINES Water Flow, Air Locks and Siphons This Factsheet discusses the problems and solutions of gravity flow pipe system

### TRICON STEEL-CON. System Specifications

TRICON STEEL-CON System Specifications Pipe Size Insulation Thickness Steel Conduit O.D. 1 1½ 6.63 2 1½ 8.63 3 2 10.75 4 2 10.75 6 2 14.00 8 2½ 16.00 10 2½ 18.00 12 2½ 20.00 Based on a minimum 3-6 burial