4 Protection Systems HFC-227ea / FM200 / FE-227 FE-25 / ECARO-25 Novec 1230 Inergen / Argonite Halon Drop-in Systems High and Low Pressure CO 2 In-cabinet Foam HI-FOG Water Mist
5 Service Systems Experience Where and When It Counts Single Point Of Contact Service Effectiveness ISO Quality Standards Available Twenty-Four / Seven
6 Net Systems Next Generation: Inspection, Testing and Maintenance System Accurate Inspections Online Access to Reports Easy to Read Reports Standard Reporting Format
8 NetREPORT Accuracy Code Compliance Inspection Accountability Standard Reporting Format Reports and Document Management
9 NetSITE All Documentation Online Inspection Reports Proposals / Pricing Failure Trend Reports Invoices System Drawings Project Documentation Owner s Manuals
12 NFPA Edition 9 Technical Committees 300 committee members Report on Proposals 718 proposals Report on Comments 627 comments In my opinion, NFPA has the most improvements I have seen over the last three cycles of the Code development. We were able to include current research in almost every chapter of the Code. - Wayne D. Moore, P.E., FSFPE, CFPS, SET Chairman NFPA 72 Technical Correlating Committee
13 NFPA Edition Chapter Chapter Title 1 Administration 2 Reference Publications 3 Definitions 4 Fundamentals 5 Initiating Devices 6 Protected Premises Fire Alarm 7 Notification Appliances 8 Supervising Station 9 Public Fire Reporting 10 Inspection, Testing and Maintenance 11 Household Fire Warning
14 Chapter 4: Fundamentals Smoke Detector above FACP Modified the existing requirement NAC and Secondary (networked) panels also Exception: Fully sprinklered building 4.4.5* Protection of Fire Alarm System. In areas that are not continuously occupied, automatic smoke detection shall be provided at the location of each fire alarm control unit(s), notification appliance circuit power extenders, and supervising station transmitting equipment to provide notification of fire at that location. Exception No. 1: Where ambient conditions prohibit installation of automatic smoke detection, automatic heat detection shall be permitted. Exception No. 2: Fully sprinklered buildings shall not require protection in accordance with
15 Chapter 4: Fundamentals Record of Completion Document Kept at location of FACP Sample completed version in Annex (also ITM form) One copy of the record of completion, updated to reflect all system additions or modifications and maintained in a current condition at all times, shall be stored at the fire alarm control unit or other location approved by the authority having jurisdiction.
16 Chapter 4: Fundamentals Releasing Fire Alarm System Added a formal definition Brings clarity to suppression industry Releasing Fire Alarm System. A protected premises fire alarm system that is part of a fire suppression system and/or which provides control inputs to a fire suppression system related to the fire suppression systems sequence of operations and outputs for other signaling and notification.
17 Chapter 4: Fundamentals System Designer Qualifications Enforceable moved from Annex into body Removed specifics about NICET, IMSA, etc. (same intent) Notation on drawings The system designer shall be identified on the system design documents. Acceptable evidence of qualifications or certification shall be provided when requested by the authority having jurisdiction. Qualified personnel shall include, but not be limited to, one or more of the following: (1) Personnel who are factory trained and certified for fire alarm system design of the specific type and brand of system being designed (2)* Personnel who are certified by a nationally recognized fire alarm certification organization acceptable to the authority having jurisdiction (3) Personnel who are registered, licensed, or certified by a state or local authority
18 Chapter 4: Fundamentals System Installer Qualifications Enforceable moved from Annex into body Removed specifics about NICET, IMSA, etc. (same intent) Either qualified or supervised by qualified System Installer. Installation personnel shall be qualified or shall be supervised by persons who are qualified in the installation, inspection, and testing of fire alarm systems. Evidence of qualifications or certification shall be provided when requested by the authority having jurisdiction. Qualified personnel shall include, but not be limited to, one or more of the following: (1) Personnel who are factory trained and certified for fire alarm system installation of the specific type and brand of system being installed (2)* Personnel who are certified by a nationally recognized fire alarm certification organization acceptable to the authority having jurisdiction (3) Personnel who are registered, licensed, or certified by a state or local authority
19 Chapter 4: Fundamentals Remote Power Supply Location Record At main fire alarm control panel Allowed to be through LCD display accessed through menus Continue requirement for notation on As-Built drawings The location of any remotely located power supply shall be identified at the master control unit as well as on the record drawings. Identification on the control unit display shall be acceptable.
20 Chapter 5: Initiating Devices Fire Extinguisher Monitoring Device Added formal definition Fire Extinguisher Monitoring Device. A device connected to a control unit that monitors the fire extinguisher in accordance with the requirements of NFPA 10, Standard for Portable Fire Extinguishers. Panel must indicate 3 distinct signals 5.14 Fire Extinguisher Monitoring Device. A fire extinguisher monitoring device shall indicate those conditions for a specific fire extinguisher required by NFPA 10, Standard for Portable Fire Extinguishers, to a fire alarm control unit or other control unit.
21 Chapter 5: Initiating Devices Fire Extinguisher Monitoring Device Tested annually (Table (a.)) Added a test method Table (a.) Fire Extinguisher Monitoring Device/System. Communication between the device connecting the fire extinguisher monitoring device/system and the fire alarm control unit shall be tested to ensure proper signals are received at the FACU and remote annunciator(s) if applicable.
22 Chapter 5: Initiating Devices Video Image Smoke Detection Added formal definition VISD acronym * Video Image Smoke Detection (VISD). The principle of using automatic analysis of real-time video images to detect the presence of smoke. Equivalent to other forms of smoke detection UL test is the same Video Image Smoke Detection Video image smoke detection systems and all of the components thereof, including hardware and software, shall be listed for the purpose of smoke detection Systems shall be designed in accordance with the performancebased design requirements of Section 5.3.
23 Chapter 5: Initiating Devices Video Image Smoke Detection Okay to use in combination as security system * Video signals generated by cameras that are components of video image smoke detection systems shall be permitted to be transmitted to other systems for other uses only through output connections provided specifically for that purpose by the video system manufacturer. Secure the computer from unauthorized changes * All component controls and software shall be protected from unauthorized changes. All changes to the software or component settings shall be tested in accordance with Chapter 10.
24 Chapter 5: Initiating Devices Video Image Smoke Detection Inspect, Test and Maintain per Manufacturer for now Video Image Smoke and Flame Detectors. Video image smoke and flame detectors shall be inspected, tested, and maintained in accordance with the manufacturer's published instructions.
25 Chapter 5: Initiating Devices Beam ceiling smoke detector spacing Applies to Solid Joists or Beams on level ceilings Total replacement of current rules
26 30 ft. spacing Chapter 5: Initiating Devices Beam ceiling smoke detector spacing (1) For ceilings with beam depths of less than 10 percent of the ceiling height (0.1 H), smooth ceiling spacing shall be permitted. 30 ft. spacing Example 1: CH = 12 ft. 10% = 14.4 in. BH = 12 in. (< 10%)
27 30 ft. spacing Chapter 5: Initiating Devices Beam ceiling smoke detector spacing (2) For ceilings with beam depths equal to or greater than 10 percent of the ceiling height (0.1 H) and beam spacing equal to or greater than 40 percent of the ceiling height (0.4 H), spot-type detectors shall be located on the ceiling in each beam pocket. Every Pocket Example 2: CH = 10 ft. 10% = 12 in. 40% = 4 ft. BH = 12 in.(>10%) BS = 5 ft. (> 40%)
28 30 ft. spacing Chapter 5: Initiating Devices Beam ceiling smoke detector spacing (2) For ceilings with beam depths equal to or greater than 10 percent of the ceiling height (0.1 H) and beam spacing equal to or greater than 40 percent of the ceiling height (0.4 H), spot-type detectors shall be located on the ceiling in each beam pocket. 30 ft. spacing What if BS is less than 40%? Example 3: CH = 10 ft. 10% = 12 in. 40% = 4 ft. BH = 12 in. (>10%) BS = 3 ft. (< 40%)
29 Chapter 5: Initiating Devices Beam ceiling smoke detector spacing Waffle-type ceilings Reservoir volume spills into adjacent pockets causing comparable response to smooth ceilings (3)* For waffle or pan-type ceilings with beams or solid joists no greater than 600 mm (24 in.) deep and no greater than 3.66 m (12 ft) center-to-center spacing, the following shall be permitted: (a) Smooth ceiling spacing (b) Location of spot-type smoke detectors on ceilings or on the bottom of beams
30 30 ft. spacing Chapter 5: Initiating Devices Beam ceiling smoke detector spacing Waffle-type ceilings 30 ft. spacing If BH < 2 ft. BS < 12 ft. Bottom of beam OR Beam Pocket
31 < 15 ft. Chapter 5: Initiating Devices Beam ceiling smoke detector spacing Corridors (<15 ft. wide) with perpendicular beams Regardless of ceiling height or beam spacing (4)* For corridors 4.5 m (15 ft) in width or less having ceiling beams or solid joists perpendicular to the corridor length, the following shall be permitted: (a) Smooth ceiling spacing (b) Location of spot-type smoke detectors on ceilings, sidewalls, or the bottom of beams or solid joists 30 ft. spacing Beam Pocket OR Bottom of beam
32 Chapter 5: Initiating Devices Manual Fire Alarm Pull Stations Removed requirement to locate throughout the protected space (leave this to building codes) Requirements remain Unobstructed Conspicuous Accessible * Manual fire alarm boxes shall be located throughout the protected area so that they are conspicuous, unobstructed, and accessible.
33 Chapter 6: Protected Premises Releasing Disconnect Switch Existing requirements didn t change (2002 Edition) Fire alarm systems used for fire suppression releasing service shall be provided with a disconnect switch to allow the system to be tested without actuating the fire suppression systems Operation of a disconnect switch or a disable function shall cause a supervisory signal at the fire alarm control unit. Clarified requirement to be a physical device The disconnect shall be a physical switch and not be accomplished by using software.
34 Chapter 6: Protected Premises Circuit Classes and Styles Major revision to simplify eliminates confusion Only has circuit styles available in modern panels
35 Chapter 6: Protected Premises Circuit Classes and Styles Major revision to simplify eliminates confusion
36 Chapter 6: Protected Premises Circuit Classes and Styles Major revision to simplify eliminates confusion
37 Chapter 6: Protected Premises Combination Systems Many fire alarm panels also shared for non-fire alarm purposes (security, mass-notification, etc.) Clarifies how to do this without harming the priority of the Fire Alarm Functions and Required Features Combination Systems * Fire alarm systems shall be permitted to share components, equipment, circuitry, and installation wiring with non fire alarm systems Operation of non fire system function(s) originating within a connected non fire system shall not interfere with the required operation of the fire alarm system unless otherwise permitted by this Code. and many more requirements
38 Chapter 6: Protected Premises Notification Appliances in Exit Stairwells Exit Stairwells, Exit Passageways or Elevators No strobe lights Only speakers connected for manual paging * Notification Appliances in Exit Stair Enclosures, Exit Passageways, and Elevator Cars. Notification appliances shall not be required in exit stair enclosures, exit passageways, and elevator cars in accordance with through Visible signals shall not be required in exit stair enclosures and exit passageways Visible signals shall not be required in elevator cars The evacuation signal shall not be required to operate in exit stair enclosures and exit passageways The evacuation signal shall not be required to operate in elevator cars.
39 Chapter 6: Protected Premises Mass Notification Systems Several placeholder paragraphs changed to get it started in the code Annex E Expect combination systems concern of protecting the priority of fire alarm Fire Alarm and Mass Notification System Notification Outputs Occupant Notification. Fire alarm and mass notification systems provided for evacuation or relocation of occupants shall have one or more notification appliances listed for the purpose on each floor of the building and so located such that they have the characteristics described in Chapter 7 for public mode or private mode, as required.
40 Chapter 7: Notification Appliances Exit Marking Audible Notification Appliances Several paragraph changes to allow it to exist in code Added formal definition Exit Marking Audible Notification Appliance. An audible notification appliance that marks building exits and areas of refuge by the sense of hearing for the purpose of evacuation or relocation. Added entire new section of requirements Exit Marking Audible Notification Appliance Requirements. entire section added
41 Chapter 10: Testing and Maintenance Exit Marking Audible Notification Appliances Semi-Annual inspection frequency Annual testing frequency Test per manufacturers guidelines Table Exit Marking Audible Notification Appliance Tests shall be performed in accordance with manufacturer s published instructions.
42 Chapter 10: Testing and Maintenance Service Personnel Qualifications Removed specifics about NICET, IMSA, etc. (same intent) * Service Personnel Qualifications and Experience Service personnel shall be qualified and experienced in the inspection, testing, and maintenance of fire alarm systems. Qualified personnel shall include, but not be limited to, one or more of the following: (1)* Personnel who are factory trained and certified for fire alarm system service of the specific type and brand of system (2)* Personnel who are certified by a nationally recognized fire alarm certification organization acceptable to the authority having jurisdiction (3)* Personnel who are registered, licensed, or certified by a state or local authority (4) Personnel who are employed and qualified by an organization listed by a nationally recognized testing laboratory for the servicing of fire alarm systems
43 Chapter 10: Testing and Maintenance Site Specific Software Recordkeeping Copy stored on-site of system Non-rewritable, Non-volatile, Non-erasable Memory a.k.a. CD-ROM * For software-based systems, a copy of the site-specific software shall be provided to the owner or owner s designated representative. A copy of the software shall be stored in non-volatile non-erasable, non-rewritable memory and shall be stored on-site.
44 Chapter 10: Testing and Maintenance AHJ Notification of Acceptance Testing Only for initial acceptance testing (not inspections) Initial Acceptance Testing. All new systems shall be inspected and tested in accordance with the requirements of Chapter 10. The authority having jurisdiction shall be notified prior to the initial acceptance test.
45 Chapter 10: Testing and Maintenance Annual Frequency Definition Annex material to clarify Annual does not mean 1 time per calendar year Example: Jan 5, 2006 Dec. 20, 2007 Semi-Annual does not mean 1 time in 1 st half of calendar year and 1 time in 2 nd half of calendar year A It is suggested that the annual test be conducted in segments so that all devices are tested annually. The intent of is to prevent a test from being made at intervals exceeding those allowed by Table Annual tests should be made every 12 months; monthly tests should be made every 30 days, and so forth. For example, it is not acceptable to conduct an annual test in January of year one, and December of year two (23-month frequency) just because Table requires a test once each year.
46 Chapter 10: Testing and Maintenance Voice Intelligibility Testing Move from being a suggestion (footnote) to being a requirement Specific methods must be used ANSI S3.2 Subject-based method Instruments giving a common scale score See next page
47 Chapter 10: Testing and Maintenance Voice Intelligibility Testing Table (b.) Audible textual notification appliances (speakers and other appliances to convey voice messages) In locations where voice intelligibility is required, it shall be verified by one of the following methods: (1) Use of subject-based test methods as described in ANSI S3.2, Method for Measuring the Intelligibility of Speech Over Communications Systems (2) Use of methods and instruments that measure certain physical parameters and provide a common intelligibility scale score as described in IEC 60849, Sound systems for emergency purposes (3) Use of other methods acceptable to the authority having jurisdiction The use of test methods that provide a common intelligibility scale score shall be permitted for use in existing systems but shall not require revisions to systems that were designed prior to the 2002 edition of this Code.
TAMARAC FIRE RESCUE INSTRUCTIONS FOR FIRE ALARM PRE-SUBMITTAL CHECKLIST In order to provide a comprehensive plan review in a timely manner, and to insure the design and installation of fire alarm systems
CHANGES IN NFPA 72 NATIONAL FIRE ALARM CODE 1999 2002 Three new chapters were added. What was chapter 1 in 1999 was reorganized into chapters 1 (Fundamentals), 2 (Referenced Publications), and 3 (Definitions).
SUPPLEMENT 4 Life Safety Code Enabling References Editor s Note: Supplement 4 provides users of NFPA 72, National Fire Alarm and Signaling Code, with a summary of requirements from NFPA 101, Life Safety
Sam Docknevich, PSP, Security Service Portfolio Manager Are You Prepared? The impending impact of Code on Servicing Security Systems usa.siemens.com/infrastructure-cities Share current and upcoming standards
NFPA 72 Inspection and Testing Requirements for Fire Alarm Systems Presented by Brent Gooden, CET Specializing in Fire, Building, and Life Safety Disclaimer: The comments and opinions made during the presentation
Fire Alarm System Plans Submittal Guidelines For New and Existing Systems SCOPE The Temecula Fire Prevention Bureau (TFPB) has established the following requirements for the submittal of all fire alarms,
Student Manual Module 4, Lesson 12 Fire Alarm Systems Performance Objectives At the conclusion of this lesson, you will be able to: Identify the components and functions of a fire alarm system and determine
City of Bettendorf Fire Alarm System Requirements Section 907 of the 2009 Edition of the International Fire Code (IFC) and Section 10-7-3 of the Municipal Code provide fire alarm requirements. IFC Section
CLARK COUNTY FIRE DEPARTMENT Fire Hazard & Prevention Services 575 E. Flamingo Road, Las Vegas, NV 89119 (702) 455-7316 FAX (702) 455-7347 105.8a-6.1 TITLE: FIRE ALARM SYSTEM REQUIREMENTS SCOPE: This guideline
Office of the Fire Marshal 1.0 PERMITS FIRE ALARM SYSTEMS PERMIT APPLICATION, PLAN SUBMITTAL, DESIGN, INSTALLATION AND INSPECTION REQUIREMENTS Effective Date: January, 2011 1.1 To acquire an installation
North Collier Fire Control & Rescue District Greater Naples Fire Rescue District Immokalee Fire Control & Rescue District 2800 North Horseshoe Drive Naples, Florida 34104 SYSTEM REHABILITATION PLAN CHECKLIST
Page 1 January 2, 2009 INSPECTION AND TESTING OF FIRE ALARM SYSTEMS Introduction Early warning plays a key role in a healthcare facility s ability to safely evacuate its residents during a fire emergency.
Fire Alarm System Plan Review Checklist 2010 OFC and 2007 NFPA 72 This checklist is for jurisdictions that permit the use of the 2007 NFPA 72 in lieu of IFC s referenced 2002 NFPA 72. Date of Review: Permit
FUNDAMENTALS OF FIRE ALARM SYSTEMS 72 33 FIRE ALARM SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. 1. PROTECTED PROPERTY
FIRE ALARM SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. 1. Protected Property Information Name of property: Description
SPECIAL RESIDENCE (ASSISTED SELF-PRESERVATION) OCCUPANCIES (Adopted by the State of Oregon) SECTION SR101 GENERAL SR101.1 General. Group SR occupancies shall comply with the provisions of this appendix
1.0 General 1.1 Scope This specifications covers the minimum requirements for the inspection, testing, and maintenance of the existing Notifier fire alarm systems at Bergen Community College (BCC) campus
Rancho Cucamonga Fire Protection District Prevention Bureau Standard Title: Fire Alarm and Monitoring Systems Standard # 9-3 Effective: May 2002 Number of Pages: 7 Revised: January 2014 INTENT The intent
Fundamentals of Fire Alarm Systems Sponsored by UL SFPE Austin/San Antonio Chapter San Marcos, Texas 7 January 2015 Agenda Introduction and Administration Historical Context of Today s NFPA 72 Fire Alarm
ORANGE COUNTY FIRE AUTHORITY Planning & Development Services Section 1 Fire Authority Road, Building A, Irvine, CA 92602 714-573-6100 www.ocfa.org New and Existing Fire Alarm & Signaling Systems Guideline
Fire Alarm Fire Suppression Air Sampling Explosion Protection Local Regional National The Mission Critical Fire Protection Experts! Who is ORR Protection Systems? Largest privately owned safety company
INSPECTION, TESTING, AND MAINTENANCE OF FIRE ALARM AND OCCUPANT NOTIFICATION SYSTEMS William E. Koffel, P.E., FSFPE President Koffel Associates, Inc. www.koffel.com email@example.com Expertly Engineering
Phone System Owner Phone System Engineered by: of Record Drawings: of System Manuals: of Test Reports: System Installer 1. GENERAL INFORMATION Phone Delaware License No: Certificate Holder No. System Supplier
SECTION 16721 PART 1 - GENERAL 1.1 SECTION INCLUDES A. Fire Alarm Control Panels B. Manual Fire Alarm Stations C. Automatic Smoke D. Fire Alarm Notification Appliances E. Auxiliary Fire Alarm Equipment
PART 1 - GENERAL 1.01 WORK INCLUDED FIRE ALARM AND DETECTION SYSTEMS SECTION 16721 A. Provide a complete fully addressable, power limited, fire detection and evacuation system. The system shall be connected
PLAN REVIEW GUIDE FOR FIRE ALARM PROJECT NAME: PERMIT # PROJECT ADDRESS: CONTACT PERSON: PHONE Fire alarm system installation information shall be provided on the appropriate architectural and electrical
EULESS FIRE DEPARTMENT FIRE MARSHAL S OFFICE INFORMATION LINE: Revised 2/12 Fire Chief Wes Rhodes Fire Marshal Paul Smith EFD-FMO 3-2 2009 International Fire & Building Code as Amended NFPA Standards Adopted
Interfacing Elevators with Fire Alarm and Sprinklers IEEE Atlanta Chapter May 15, 2006 Brian K Fabel, PE Agenda Today s Codes NFPA, ASME, IBC/IFC Conflicts/Issues Tomorrow s Codes? Applicable Codes NFPA
TOWN OF BRIGHTON Office of the Fire Marshal 2300 Elmwood Avenue Rochester, New York 14618 (585) 784-5220 Office (585) 784-5207 Fax Inspection and Testing of Fire Protection Systems A fire protection system
University Design Standard Fire Alarm Systems 1.0 Overview This document provides Virginia Tech s standards for the design and installation of fire alarm systems and equipment in new construction, retrofit
EXHIBIT A SCOPE OF WORK 1. (Contractor) shall provide fire alarm system maintenance/repair/testing services as described herein to the California Department of Veterans Affairs (hereinafter CDVA, CalVet,
NFPA 72 188.8.131.52 184.108.40.206 False Alarm. Activation or reporting of an alarm for which no such alarm condition, fire or emergency actually exists. Additionally, False Alarm is the willful and knowing initiating
FIRE ALARM SYSTEMS INFORMATION PACKET Exeter Township Fire Department Office of the Fire Official 2010 1 TABLE OF CONTENTS PURPOSE, SCOPE, DEFINITIONS...3 GUIDELINES...3 I. INTRODUCTION...3 A. APPLICABLE
Alarm and Detection/Suppression Fire Safety American Fire Technologies To provide special hazard services world wide to the industrial market through the integration of components and services Clean Agent
Fire Alarm System Plans Review Checklist Property location Date of Review 1. Is application completed in entirety? 2. Are the plans review fee submitted with the application? 3. Does floor plan include
Scope Provide a fire alarm system, or expand the existing system, as required by Code, the requirements in the Special Instructions to Designers (SID) of the Design Guidelines, and/or as noted in the Program
P a g e 1 SECTION 04 (Doc.No.A/DBR 001) FIRE-FIGHTING DESIGN BRIEF REPORT P a g e 2 1.0 SCOPE 2.0 STANDARDS AND CODES 3.0 TYPES OF SYSTEM PROPOSED 4.0 FIRE HYDRANT SYSTEM 5.0 AUTOMATIC SPRINKLER SYSTEM
INSTRUCTIONS FOR BUILDINGS WITH FIRE PROTECTION EQUIPMENT FIRE EXTINGUISHERS,SPRINKLER SYSTEMS AND FIRE ALARMS Attachment #1 Inspection of Fire Extinguishers Fire Extinguishers must be tested according
General Safety & Health Standards Published by the Division of Building Safety In Cooperation with the Idaho Industrial Commission Local Fire Alarm 064. FIRE ALARM SYSTEMS 01. Scope 02. Definitions 03.
PART 1 -- GENERAL 1.1 WORK OF THIS SECTION SECTION 16720 - City of San Diego, CWP Guidelines A. The WORK of this Section includes providing manual and automatic fire alarm and smoke detection systems meeting
FireSeeker Fire Alarm Control Panel Model FS-250 Programming Manual P/N 315-049403-1 Siemens Building Technologies Fire Safety Table Of Contents Introduction...1 The Access levels...1 User Level...1 Maintenance
INSTRUCTIONS FOR BUILDINGS WITH FIRE PROTECTION EQUIPMENT FIRE EXTINGUISHERS,SPRINKLER SYSTEMS AND FIRE ALARMS Attachment #1 Inspection of Fire Extinguishers Fire Extinguishers must be tested according
Fire Alarm Systems Permit Packet City of Greer Fire Department Updated July 2004 If you have any questions or comments regarding the information contained within; or of you need assistance interpreting
SECTION 13850 (28 31 00) FIRE DETECTION AND ALARM SYSTEM ENGINEERING SPECIFICATION INTELLIGENT REPORTING FIRE DETECTION SYSTEM PART 1 GENERAL 1.1 DESCRIPTION A. This specification includes the furnishing,
1. GENERAL 1.1. Related Documents: 1.2. Scope: 1.1.1. The general provisions of the Contract, including General and Supplementary Conditions and General Requirements apply to the work specified in this
Understanding Fire Alarm Requirements & Inspections Presented By Bill Conroy Technical Sales For Briscoe Protective Systems Inc Introduction Fire Alarm Requirements are structured through a system of codes.
GAP.220.127.116.11 A Publication of Global Asset Protection Services LLC NATIONAL FIRE ALARM AND SIGNALING CODE INTRODUCTION National Fire Protection Association (NFPA) documents describe a level of fire protection
Telluride Fire Protection District Fire Alarm Systems Policy Version 03/2007 FIRE ALARM SYSTEMS POLICY TELLURIDE FIRE PROTECTION DISTRICT TABLE OF CONTENTS FIRE ALARM PROTECTION POLICY PLAN REVIEW SUBMITTAL
Page 1 of 5 CBD-233. Fire Alarm and Detection Systems Originally published August 1984. R.H.L. McEwen Fire alarm systems are normally required by building codes. In the case of new buildings, this is usually
The Evolution of Requirements for Supervising Station Alarm Systems Fire Marshal s Association of Colorado January 18, 2013 Warren Olsen, CFPS CBCO FSCI firstname.lastname@example.org 1 Disclaimer: The comments
CITY OF SPRING LAKE PARK Code Enforcement Department 1301 81 st Avenue NE Spring Lake Park MN 55432 Business Phone 763-784-6491 Fax 763-792-7257 INSPECTION, TESTING AND MAINTENANCE OF FIRE PROTECTION SYSTEMS
FIRE ALARM AND EMERGENCY COMMUNICATION SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. It shall be permitted to modify this
Fire Alarm and Detection Systems And Central Station Monitoring Plan Submittal Guidelines Red Oak Fire Rescue Office of the Fire Marshal 547 N. Methodist Red Oak, TX 75154 Phone: 469-218-7713 Fax: 468-218-7719
Fire Alarm System plan(s) MUST be reviewed and approved by the Belmont Fire Department prior to the start of construction. The design and any changes must be fully compliant with NFPA 1, NFPA 101, NFPA
UL LLC 333 Pfingsten Road, Northbrook, IL 60062-2096 Phone: (877) UL HELPS, Fax: (847) 407-1001 SN: Fire Alarm System Description Worksheet PROTECTED PROPERTY Name: Address: City: State: Zip Code: Representative
Lubbock Fire Marshal s Office 1601 Mac Davis Lane Lubbock, Texas 79401 806-775-2646 Fax 806-775-3508 email@example.com Fire Alarm Submittal Requirements and Acceptance Testing To all Registered
UL Code 864 9 th Edition An Overview of the Foremost Code Updates 9 th Edition of UL 864, ANSI/UL 864 Latest incarnation of a standard first published in 1948 Note that UL 864 is an ANSI standard. ANSI
CHAPTER 8 Village of Caledonia Alarm Systems Ordinance (2013-11 07/01/13) Section Title Number 5-8-1 Title 5-8-2 Declaration of Purpose 5-8-3 Definitions 5-8-4 Administrative Rules 5-8-5 Supervised Fire
FIRE ALARM AND EMERGENCY COMMUNICATION SYSTEM INSPECTION AND TESTING FORM To be completed by the system inspector or tester at the inspection or test. It shall be permitted to modify this form as needed
SOCIETY OF FIRE PROTECTION ENGINEERS (SFPE) NATIONAL SOCIETY OF PROFESSIONAL ENGINEERS (NSPE) NATIONAL INSTITUTE FOR CERTIFICATION IN ENGINEERING TECHNOLOGIES (NICET) POSITION STATEMENT THE ENGINEER AND
GENERAL: 1. The objective of this guideline is to provide minimum standards for design and installation of fire alarm systems for the University of Missouri. 2. Fire alarm systems are Life Safety Systems
LOUISVILLE FIRE PROTECTION DISTRICT 895 West Via Appia, Louisville, Colorado 80027 303-666-8809 Contractor s Checklist and Installation Guide TABLE OF CONTENTS Fire Protection Narrative........... 3 Fire
907.2.1.1 System initiation in Group A occupancies with an occupant load of 1,000 or more. Activation of the fire alarm in Group A occupancies with an occupant load of 1,000 or more shall initiate a signal
City of Mercer Island Development Services Group Fire Code Review and Inspection 9611 SE 36 th Street Mercer Island, WA 98040-3732 PHONE (206) 275-7605 FAX (206) 275-7726 www.mercergov.org Commercial Fire
2012 Ontario Building Code Changes Affecting Fire Alarm Systems CFAA Annual Technical Seminar May 31, 2013 Ken Baird VP Systems www.lrifire.com LRI 2010 Developments in Life Safety Introduction Code Development
PERMITS AND INSPECTIONS FIRE ALARM SYSTEM SUBMITTAL CHECKLIST AND APPLICATION 911 Assigned PROJECT LOCATION Subdivision: Lot: Blk: Sec: PROJECT New Construction Addition/Remodel Demolition Other: Number
FIRE ALARM APPLICATION ENUMCLAW FIRE DEPARTMENT 1330 Wells St, Enumclaw, WA 98022 Phone: 360-825-5544 Fax: 360-825-9442 COMMUNITY DEVELOPMENT, BUILDING DEPARTMENT 1309 Myrtle Ave Enumclaw WA 98022 Phone:
Fire Alarm Systems Certification The skills and knowledge listed under each task are suggestive of those involved in that task, but are not intended to constitute an exhaustive listing. 2.1 Submittal Preparation
FIRE ALARM AND EMERGENCY COMMUNICATION SYSTEM INSPECTION AND TESTING FORM To be completed by the system inspector or tester at the time of the inspection or test. It shall be permitted to modify this form
FIRE ALARM SYSTEM PLAN SUBMITTAL CHECKLIST All fire alarm system plan submittals must include this Fire Alarm System Plan Submittal Checklist. PLAN APPROVAL - No work shall be performed until plans are
DCD-0304 Identification # Rev. 9/08 County Date of Inspection NAME OF OPERATION BUILDING INSPECTORS INSPECTION FORM FOR CHILD CARE CENTERS ADDRESS TELEPHONE: CITY STATE ZIP BUILDING INSPECTORS CERTIFICATE
Office of the Fire Marshal 1.0 PERMITS FIRE ALARM SYSTEMS PERMIT APPLICATION, PLAN SUBMITTAL, DESIGN, INSTALLATION AND INSPECTION REQUIREMENTS Effective Date: January 2014 1.1 To acquire an installation
OBOA 2009 Huntsville, ON Overview of ULC Standards Affecting Building Occupancy Alan Cavers Area Manager Fire & Security Systems Group Course Title: Rev Date Agenda Introduction to Underwriters Laboratories
www.-fire.com R.P. SCHIFILITI ASSOCIATES, INC. P.O. Box 297 Reading, MA 01867-0497 USA 781.944.9300 Fax / Data 781.942.7500 Telephone Elevator Fire Safety: Elevator Recall and Elevator Power Shutdown Disclaimer:
Understanding Emergency Communication Systems, Risk Analysis, and Voice Intelligibility Jack Poole, PE, FSFPE May 5, 2015 Introduction Jack Poole, PE Graduate from Univ. of Md., BS in FPE Poole Fire Protection
BASIC FIRE ALARM TRAINING What is a fire alarm system? Per the defini+on in NFPA 72 A system or por+on of a combina+on system that consists of components and circuits arranged to monitor and annunciate
PARTICIPATION HOUSE 9 BUTTERNUT LANE, MARKHAM B 3 CASE STUDY RANDAL BROWN & ASSOCIATES ENGINEERING LTD. CONSULTING ENGINEERS LIFE SAFETY & FIRE PROTECTION 105 6 LANSING SQUARE TORONTO, ONTARIO PARTICIPATION
FMS FIRE ALARM SYSTEM DESIGN & INSTALLATION GUIDELINES 04-09-16 FIRE ALARM SYSTEM SUBMITTAL & CONSTRUCTION PROCESS 1. Fire alarm contractor to provide Owner with a full set of shop drawings, specifications,
Page 18 ABOUT CODE CORNER CCFS would like to remind you to check with your local Authority Having Jurisdiction (AHJ) for questions and opinions concerning your local Fire and Building Codes. The information
Mass Notification Systems: Design Challenges for the FPE Wayne D. Moore, P.E., FSFPE In the aftermath of September 11 th, and again in each of the military barracks and embassy bombings, school, college
NY Fire Safety Institute Presents the FDNY Coordinator of Fire Safety and Alarm Systems Homeless Shelters (Premise Related) Certificate of Fitness F-80 Definitions and Terminology Established 1995 Preparing