2 What is a fire alarm system? Per the defini+on in NFPA 72 A system or por+on of a combina+on system that consists of components and circuits arranged to monitor and annunciate the status of fire alarm or supervisory signal- ini+a+ng devices and to ini+ate the appropriate response to those signals
3 Basic Components of a Fire Alarm System Control Panel Communica+ons Ini+a+ng Devices No+fica+on Appliances
4 Control Panel/Communicator A component of the ﬁre alarm system that receives signals from ini+a+ng devices and processes these signals to determine the ﬁre alarm output func+ons
5 Communica+ons DACS Digital Alarm Communica+ons Systems POTS (Plain Old Telephone System) Loop Start with line seizure from the point of demarca+on prior to sending it to the home or business. Cable Company Service assuming you have no CODEC, Voice Compression or back up power issues. One Way/Two Way Radio Mesh Radio and GSM IP Communicators with UL lis+ngs Sole Path Communicators with UL Lis+ngs
6 2010 Edi+on Na+onal Fire Alarm and Signaling Code NFPA Housecleaning Efforts Recently removed transmission methods AcBve MulBplex McCulloh Directly Connected Non- Coded Systems Private Microwave Radio Systems
8 Ini+a+ng Devices A system component that originates transmission of a change- of- state condi+on
13 Types Of Sprinkler Systems Wet Pipe: Since water is always present in the pipes supplying the sprinkler heads, these types of sprinkler system are quick to react upon the opera+on of a sprinkler head in a fire scenario. These are the most common systems and are used in buildings where there is no risk of freezing. Wet systems are required for mul+- storey or high- rise buildings and for life safety systems for UK standards. Dry pipe: The pipes are filled with air under pressure at all +mes and the water is held back by the control valve outside of the protected area. Should a sprinkler head open in a fire scenario, the drop in air pressure opens the valve and water flows into the pipe work and onto the fire. Dry pipe systems are used where wet or alternate systems cannot be used. Alternate: Alternate systems have the pipes full of water for the summer period, then subsequently drained down and filled with air for the winter. This is typically for buildings that are not heated, e.g. underground car parks.
14 Sprinkler System Devices Water Flow Valve Tamper
15 Sprinkler Heads
16 No+fica+on Appliances A fire alarm system component such as a bell, horn, speaker, light, or text display that provides audible, tac+le, or visible outputs, or any combina+on thereof
17 Examples of No+fica+on Appliances
18 Horn/Strobe Strobe- Ceiling Mount)
19 Speaker Bell
20 Fire Alarm Requirements
21 Interna+onal Building Code In Pennsylvania, Ohio, and many other states, the Interna+onal Building Code (IBC) is the model building code for the state. Each building, based on it s use, is assigned a Use and Occupancy Code The Use and Occupancy Code then determines if a fire alarm system is required. Fire alarm systems may also be required by other authori+es, such as insurance companies
22 NFPA 72 The Na+onal Fire Alarm Code Once it is determined that a fire alarm system will be installed, NFPA 72 then tells us how to install the system
23 NFPA 70 The Na+onal Electric Code Once it is determined that a fire alarm is required by the IBC, and has been designed per NFPA 72, the Na+onal Electric Code (NEC) tells us how to wire the system
24 Underwriter s Laboratories (UL)
25 What is UL? UL is a global independent safety science company with more than a century of exper+se innova+ng safety solu+ons from the public adop+on of electricity to new breakthroughs in sustainability, renewable energy and nanotechnology. Dedicated to promo+ng safe living and working environments, UL helps safeguard people, products and places in important ways, facilita+ng trade and providing peace of mind.
26 Huh? Basically, UL is a company that has developed standards on how products should operate safely. Manufacturers send their products to UL to be tested by UL to UL standards. If the product passes the tests, the manufacturer can place the UL mark on the product.
27 What about fire alarms and UL? Fire alarm service companies and monitoring centers apply to UL to become listed companies UL inves+gates the company and ensures the company understands and can comply with applicable standards UL audits listed companies once per year to ensure the company is maintaining compliance
28 Authori+es Having Jurisdic+on (AHJ) will require a UL cer+ficate on a system The UL Cer+ficate is the UL mark for fire alarm systems The UL cer+ficate on a fire alarm system ensures the AHJ that the system was designed, installed, tested and maintained properly One of the main reasons an AHJ will require a UL cer+ficate is to reduce false alarms
29 Factory Mutual (FM) FM basically provides the same service as UL. At one +me, when a property was insured by Factory Mutual insurance, they required the fire alarm system to be FM approved.
30 Commercial Fire Alarm Monitoring and Dispatching Requirements Fire Alarm system alarm transmissions require immediate dispatch of the fire department (unless otherwise required)
31 UL Runner Response Runner response is required on all UL Listed/FM Placard fire alarm systems. Central Sta+on is responsible for the dispatch of Runners in accordance with procedures based on NFPA 72 aaer normal business hours. During normal business hours, Customer Care/Service is responsible. Runner Service is defined as a service performed at the protected premises, including resebng and silencing of all equipment transmibng fire alarm or supervisory signals to an off- premises loca+on. A UL Runner is a person (other than the required number of operators on duty at central, supervising, or runner sta+ons) available for prompt dispatching, when necessary, to the protected premises. A Runner shall not be required if there will not be a fire department or customer representa+ve on- site.
32 Fire Alarm Response Dispatch runner or technician to the protected premises within 1 hour of receipt of a signal if the equipment needs to be manually reset by the prime contractor. A runner/technician response may be waived by the fire department or other Authority Having Jurisdic+on (AHJ). The customer may not call off a runner response. A runner/technician is not required if the signal results from a prearranged test. If a runner/technician is required, they must arrive within 1 hour of the signal being received.
33 Supervisory Signal Response Dispatch a runner or maintenance person to arrive within 1 hour of the signal being received to inves+gate. Central sta+on must dispatch a runner/maintenance person to the protected premises if a supervisory signal is received, even if the signal has reset. A runner/technician is not required if the signal results from a prearranged test. In addi+on, a runner would not be required if a prearranged procedure is in place with the subscriber on the handling of supervisory signal and the subscriber is able to reset the supervisory signal. If the subscriber is unable to reset the supervisory signal, a runner/technician must s+ll arrive within 1 hour of receipt of the signal. Supervisory alarms are defined as alarms received from sprinkler system supervisory appliances. These include, but are not limited to, valve tampers switches, low air pressure/temperature switches, fire pump supervision, tank level/temperature switches. Addi+onally, when duct detectors are configured not to provide fire alarm response, they shall be considered a supervisory signal
34 Trouble Signal Response Dispatch personnel to arrive within 4 hours to ini+ate maintenance, if necessary. This is interpreted to mean the central sta+on must dispatch a technician to the protected premises if a trouble signal is received. If a reset signal to the trouble signal is received before the technician arrives, the technician would not have to respond. The customer should be no+fied of the reset signal and asked if they s+ll require runner response. Trouble signals also include such signals as AC power loss, badery trouble, phone line trouble, failure to test, and other related control panel problem signals. If the trouble is due to a known cause that would not be able to be repaired by the technician, runner response is not required (i.e. AC power to the building is off due to storm damage).
35 AddiBonal Runner Requirements The UL Runner should complete a Select Security Service Ticket and clearly mark the +cket as a UL Runner so that the customer is charged accordingly. This +cket is for the reset only. If addi+onal work or services are required at the site, the UL Runner should contact the primary on- call Technician.
36 AddiBonal Fire Alarm Requirements No Select Security personnel shall place a fire alarm system or any part of a fire alarm system on test without first inves+ga+ng the cause of the problem on- site. Select Security personnel may place a fire alarm system or a part of a fire alarm system on test at the request of the customer. If it is determined that a fire alarm system or any part of a fire alarm system will be placed on test, the reason for the system being on test and the person placing the system on test shall be documented in the account history on the central sta+on soaware. If it is determined that a fire alarm system or any part of a fire alarm system will be placed on test for a period of more than 8 hours, the Authority Having Jurisdic+on shall be no+fied. The person who was no+fied and the person that made the no+fica+on shall be documented in the account history on the central sta+on soaware. No Select Security personnel shall disconnect a device on a fire alarm system for a period of more than 8 hours. If a device must be disconnected for a period of more than 8 hours, the Authority Having Jurisdic+on shall be no+fied. The person who was no+fied and the person that made the no+fica+on shall be documented in the account history on the central sta+on soaware. Addi+onally, an out of service tag shall be placed on any device that is disconnected and at the fire alarm annunciator.
37 Fire Alarm Inspec+ons Fire alarm inspec+ons shall be conducted per the requirements of the current version of NFPA 72 and contract documents. The fire alarm inspec+ons will consist of the following:
38 Quarterly Inspec+ons: 1. The technician shall opera+onally test the fire alarm control panel. The fire alarm control panel shall be tested to verify correct receipt of alarm, supervisory and trouble signals, opera+on of no+fica+on appliance and auxiliary func+on outputs, circuit supervision and AC power loss. 2. Fire alarm panel baderies shall be inspected for corrosion or leakage and tested under full load with the primary power disconnected. The badery charging circuit shall be tested to ensure correct voltage output to the baderies. 3. The digital alarm communicator shall be opera+onally tested to ensure receipt of the correct signal to the central sta+on within 90 seconds of going off- hook. The digital alarm communicator shall be tested to ensure line seizure, line failure detec+on, and the ability to transmit line failure within 4 minutes of detec+ng the line fault.
39 4. The sprinkler alarm and supervisory ini+a+ng devices shall be func+onally tested per NFPA 72 standards and manufacturer s instruc+ons. Sprinkler alarm and supervisory ini+a+ng devices include but are not limited to waterflow switches, high/low pressure switches, valve tamper switches and room temperature switches. 5. Waterflow switches shall be tested by flowing water through the inspectors test valve. Ini+a+on of the waterflow alarm signal shall occur within 90 seconds of opening the inspectors test valve. 6. High/low pressure switches shall be operated and verified that receipt of the signal occurs when the required pressure is increased or decreased a maximum of 10 psi. 7. Valve tamper switches shall be operated and verified that receipt of signal occurs within the first two revolu+ons of the hand wheel. 8. Room temperature switches shall be operated and verified that receipt if signal occurs when the room temperature decreases to 40 F.
40 Annual Func+onal Inspec+ons: 1. The technician shall opera+onally test the fire alarm control panel. The fire alarm control panel shall be tested to verify correct receipt of alarm, supervisory and trouble signals, opera+on of no+fica+on appliance and auxiliary func+on outputs, circuit supervision and AC power loss. 2. Fire alarm panel baderies shall be inspected for corrosion or leakage and tested under full load with the primary power disconnected. The badery charging circuit shall be tested to ensure correct voltage output to the baderies. 3. The digital alarm communicator shall be opera+onally tested to ensure receipt of the correct signal to the central sta+on within 90 seconds of going off- hook. The digital alarm communicator shall be tested to ensure line seizure, line failure detec+on, and the ability to transmit line failure within 4 minutes of detec+ng the line fault. 4. Alternate communica+on methods and devices shall be tested per the current revision of NFPA72 and the manufacturer s instruc+ons
41 5. The alarm and supervisory ini+a+ng devices shall be func+onally tested per NFPA 72 standards and manufacturer s instruc+ons. Alarm and supervisory ini+a+ng devices include but are not limited to system spot type smoke detectors, heat detectors, duct detectors, projected beam smoke detectors, manual pull sta+ons, waterflow switches, high/low pressure switches, valve tamper switches and room temperature switches. 6. System spot type smoke detectors shall be tested in place to ensure smoke entry into the sensing chamber and an alarm response. 7. Restorable heat detectors shall be tested with a heat source. Non- restorable heat detectors shall be tested electrically and mechanically. 8. Duct detectors shall be tested to ensure that the device will sample the airstream.
42 9. Projected beam smoke detectors shall be tested per the manufacturer s recommenda+ons. 10. Manual pull sta+ons shall be operated. 11. Waterflow switches shall be tested by flowing water through the inspectors test valve. Ini+a+on of the waterflow alarm signal shall occur within 90 seconds of opening the inspectors test valve. 12. High/low pressure switches shall be operated and verified that receipt of the signal occurs when the required pressure is increased or decreased a maximum of 10 psi. 13. Valve tamper switches shall be operated and verified that receipt of signal occurs within the first two revolu+ons of the hand wheel. 14. Room temperature switches shall be operated and verified that receipt if signal occurs when the room temperature decreases to 40 F.
43 15. The alarm no+fica+on appliances shall be func+onally tested. Alarm no+fica+on appliances shall include but are not limited to bells, horns, horn/strobes, and strobes. 16. Audible no+fica+on appliances shall be tested to ensure proper sound pressure and verified that the sound is dis+nguishable from other audible devices. 17. Visual no+fica+on appliances shall be tested to ensure that the light flashes and has the proper intensity.
44 Semi- Annual Visual Inspec+ons: 1. The fire alarm control panel and annunciators shall be visually inspected to ensure they are secure and accessible. 2. Fire alarm ini+a+ng devices and no+fica+on appliances shall be visually inspected to ensure there are no changes that affect equipment performance
45 What s required to be red?
46 Per NFPA 72, the fire alarm disconnec+ng means (circuit breaker) must be red. Per the IBC, manual pull sta+ons must be red
Student Manual Module 4, Lesson 12 Fire Alarm Systems Performance Objectives At the conclusion of this lesson, you will be able to: Identify the components and functions of a fire alarm system and determine
Phone System Owner Phone System Engineered by: of Record Drawings: of System Manuals: of Test Reports: System Installer 1. GENERAL INFORMATION Phone Delaware License No: Certificate Holder No. System Supplier
FUNDAMENTALS OF FIRE ALARM SYSTEMS 72 33 FIRE ALARM SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. 1. PROTECTED PROPERTY
FIRE ALARM SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. 1. Protected Property Information Name of property: Description
INSTRUCTIONS FOR BUILDINGS WITH FIRE PROTECTION EQUIPMENT FIRE EXTINGUISHERS,SPRINKLER SYSTEMS AND FIRE ALARMS Attachment #1 Inspection of Fire Extinguishers Fire Extinguishers must be tested according
EXHIBIT A SCOPE OF WORK 1. (Contractor) shall provide fire alarm system maintenance/repair/testing services as described herein to the California Department of Veterans Affairs (hereinafter CDVA, CalVet,
Polk School District Specifications for the New Fire Alarm in the Existing Building Eastside Elementary School FIRE ALARM SYSTEM 1.01 SUBMITTALS A. Shop drawings shall be submitted as follows: 1. Manufacturer's
Fire Alarm System Monitoring - CAN/ULC-S561-03 Brian McBain ULC Regulatory Services May 4, 2011 Copyright 1995-2007 Underwriters' Laboratories of Canada. All rights reserved. No portion of this material
PART 1 -- GENERAL 1.1 WORK OF THIS SECTION SECTION 16720 - City of San Diego, CWP Guidelines A. The WORK of this Section includes providing manual and automatic fire alarm and smoke detection systems meeting
Fundamentals of Fire Alarm Systems Sponsored by UL SFPE Austin/San Antonio Chapter San Marcos, Texas 7 January 2015 Agenda Introduction and Administration Historical Context of Today s NFPA 72 Fire Alarm
CHANGES IN NFPA 72 NATIONAL FIRE ALARM CODE 1999 2002 Three new chapters were added. What was chapter 1 in 1999 was reorganized into chapters 1 (Fundamentals), 2 (Referenced Publications), and 3 (Definitions).
City of Bettendorf Fire Alarm System Requirements Section 907 of the 2009 Edition of the International Fire Code (IFC) and Section 10-7-3 of the Municipal Code provide fire alarm requirements. IFC Section
1. GENERAL 1.1. Related Documents: 1.2. Scope: 1.1.1. The general provisions of the Contract, including General and Supplementary Conditions and General Requirements apply to the work specified in this
The Evolution of Requirements for Supervising Station Alarm Systems Fire Marshal s Association of Colorado January 18, 2013 Warren Olsen, CFPS CBCO FSCI email@example.com 1 Disclaimer: The comments
SECTION 16721 PART 1 - GENERAL 1.1 SECTION INCLUDES A. Fire Alarm Control Panels B. Manual Fire Alarm Stations C. Automatic Smoke D. Fire Alarm Notification Appliances E. Auxiliary Fire Alarm Equipment
Fire Alarm System Plans Review Checklist Property location Date of Review 1. Is application completed in entirety? 2. Are the plans review fee submitted with the application? 3. Does floor plan include
FOAM SYSTEM SPECIFICATION WET PIPE AFFF SPRINKLER SYSTEM The sprinkler system shall be a closed-head wet pipe AFFF foam water sprinkler system designed to provide adequately proportioned foam water solution
1.0 General 1.1 Scope This specifications covers the minimum requirements for the inspection, testing, and maintenance of the existing Notifier fire alarm systems at Bergen Community College (BCC) campus
City of Mercer Island Development Services Group Fire Code Review and Inspection 9611 SE 36 th Street Mercer Island, WA 98040-3732 PHONE (206) 275-7605 FAX (206) 275-7726 www.mercergov.org Commercial Fire
Page 1 January 2, 2009 INSPECTION AND TESTING OF FIRE ALARM SYSTEMS Introduction Early warning plays a key role in a healthcare facility s ability to safely evacuate its residents during a fire emergency.
FIRE ALARM APPLICATION ENUMCLAW FIRE DEPARTMENT 1330 Wells St, Enumclaw, WA 98022 Phone: 360-825-5544 Fax: 360-825-9442 COMMUNITY DEVELOPMENT, BUILDING DEPARTMENT 1309 Myrtle Ave Enumclaw WA 98022 Phone:
Rancho Cucamonga Fire Protection District Prevention Bureau Standard Title: Fire Alarm and Monitoring Systems Standard # 9-3 Effective: May 2002 Number of Pages: 7 Revised: January 2014 INTENT The intent
NATIONAL FIRE ALARM CODE (NFPA-72) Fire Alarm System Testing Six Reasons To Test & Inspect Your Fire Alarm Systems Regularly: Lives are at stake! Your fire alarm system will only operate properly if it
R.P. SCHIFILITI ASSOCIATES, INC. P.O. Box 297 Reading, Massachusetts 01867-0497 USA 781.944.9300 Fax / Data 781.942.7500 Telephone Understanding Supervision of Fire Protection Systems by Robert P. Schifiliti,
Fire Prevention Coffee Break Training November 2015 Agenda Changes in the Pire Prevention Bureau FM Lund Tags FM Lund System priorities for the FD FM Lund Transmission Technologies- Phelan Questions and
FireSeeker Fire Alarm Control Panel Model FS-250 Programming Manual P/N 315-049403-1 Siemens Building Technologies Fire Safety Table Of Contents Introduction...1 The Access levels...1 User Level...1 Maintenance
Telluride Fire Protection District Fire Alarm Systems Policy Version 03/2007 FIRE ALARM SYSTEMS POLICY TELLURIDE FIRE PROTECTION DISTRICT TABLE OF CONTENTS FIRE ALARM PROTECTION POLICY PLAN REVIEW SUBMITTAL
TAMARAC FIRE RESCUE INSTRUCTIONS FOR FIRE ALARM PRE-SUBMITTAL CHECKLIST In order to provide a comprehensive plan review in a timely manner, and to insure the design and installation of fire alarm systems
GAP.126.96.36.199 A Publication of Global Asset Protection Services LLC NATIONAL FIRE ALARM AND SIGNALING CODE INTRODUCTION National Fire Protection Association (NFPA) documents describe a level of fire protection
Office of the Fire Marshal 1.0 PERMITS FIRE ALARM SYSTEMS PERMIT APPLICATION, PLAN SUBMITTAL, DESIGN, INSTALLATION AND INSPECTION REQUIREMENTS Effective Date: January, 2011 1.1 To acquire an installation
Building Name/Location: Installing Company: Observation By: Date: Time: 1 Building Occupants, Authorities and Alarm Monitoring Co Have Been Notified 2 FACP Manufacturer and Panel is Approved for NCSU Campus
FIRE ALARM AND EMERGENCY COMMUNICATION SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. It shall be permitted to modify this
STATEMENT OF WORK FOR FIRE ALARM SYSTEM TESTING & MAINTENANCE Project No. SAQMMA-07-C0060 ***OUAGA, BURKINA FASO*** CONTENTS: 1.0 Introduction 2.0 Objectives 3.0 General Requirements 4.0 Specific Requirements
SPECIFICATIONS FOR THE INSTALLATION OF FIRE ALARM SYSTEMS, SPRINKLER SYSTEMS, AND MASTER BOXES IN THE POQUONNOCK BRIDGE FIRE DISTRICT The purpose of these specifications is to insure that there are minimum
Fire Alarm and Detection Systems And Central Station Monitoring Plan Submittal Guidelines Red Oak Fire Rescue Office of the Fire Marshal 547 N. Methodist Red Oak, TX 75154 Phone: 469-218-7713 Fax: 468-218-7719
Fire Alarm System Plans Submittal Guidelines For New and Existing Systems SCOPE The Temecula Fire Prevention Bureau (TFPB) has established the following requirements for the submittal of all fire alarms,
Issued 2006/08/01 Section 13852 Multiplex Fire Alarm System Page 1 of 10 PART 1 GENERAL 1.1 RELATED WORK.1 Section 01330 Submittal Procedures..2 Section 01780 Closeout Procedures..3 Section 01810 Commissioning..4
KNOXVILLE, TENNESSEE SECTION 28 31 11 PAGE 1 PART 1 - GENERAL 1.01 DESCRIPTION OF WORK SECTION 28 31 11 A. Extent of fire alarm and detection system work shall be as described in this specification, as
SECTION 16721 FIRE DETECTION AND ALARM SYSTEM PART 1 - GENERAL 1.01 DESCRIPTION A. This section of the specifications includes the furnishing, installation, and connection of the microprocessor-controlled
EULESS FIRE DEPARTMENT FIRE MARSHAL S OFFICE INFORMATION LINE: Revised 2/12 Fire Chief Wes Rhodes Fire Marshal Paul Smith EFD-FMO 3-2 2009 International Fire & Building Code as Amended NFPA Standards Adopted
Sprinkler and for the Building Official Randall Kovacs, P.Eng., CP, FEC Gage-Babcock & Associates, Ltd. Topics Coordinated System Testing 1 Wet Dry Pre-action Deluge Wet System: Pipes filled with water
Understanding Fire Alarm Requirements & Inspections Presented By Bill Conroy Technical Sales For Briscoe Protective Systems Inc Introduction Fire Alarm Requirements are structured through a system of codes.
CAN/ULC-S561-03 Installation and Services for Fire Signal Receiving Centres and Systems- Ottawa 2013 Alan Cavers, Engineering Manager Underwriters Laboratories of Canada Dec. 2013 Copyright 1995-2007 Underwriters'
Page 1 of 8 1. DESCRIPTION The Viking VFR400 is a microprocessor based multi-hazard releasing control panel for use on preaction, deluge, Surefire and Firecycle multicycle sprinkler systems, MX-1230 Fire
I. Introduction Inspection and Testing Program Fire Protection Equipment State of Minnesota Emergencies seldom give warning before they strike. Thus, it is essential that fire protection equipment be inspected,
GENERAL: 1. The objective of this guideline is to provide minimum standards for design and installation of fire alarm systems for the University of Missouri. 2. Fire alarm systems are Life Safety Systems
University Design Standard Fire Alarm Systems 1.0 Overview This document provides Virginia Tech s standards for the design and installation of fire alarm systems and equipment in new construction, retrofit
Page 1 of 10 FIRE ALARM /FIRE PROTECTION OUTAGE/IMPAIRMENT RESPONSE GUIDELINE SYSTEM TESTING 1. Testing of the Fire Alarm and Fire Protection Systems 1.1. The Building Engineer, Electrician, Plumber (or
CLARK COUNTY FIRE DEPARTMENT Fire Hazard & Prevention Services 575 E. Flamingo Road, Las Vegas, NV 89119 (702) 455-7316 FAX (702) 455-7347 105.8a-6.1 TITLE: FIRE ALARM SYSTEM REQUIREMENTS SCOPE: This guideline
City of Columbus Department of Building and Zoning Services Introduction This manual is designed to provide you, the contractor, owner or design professional with a step-by-step guide to our process, beginning
INSPECTION AND TESTING FORM SERVICE ORGANIZATION PROPERTY NAME (USER) DATE: 08-04-15 TIME: 8:00 Name: Siemens Industries Inc. Name: Kcvtcs Madisonville Tech, School Bldg. Address: 2700 Stanley Gault Pkwy
PLAN REVIEW GUIDE FOR FIRE ALARM PROJECT NAME: PERMIT # PROJECT ADDRESS: CONTACT PERSON: PHONE Fire alarm system installation information shall be provided on the appropriate architectural and electrical
SECTION 16721 FIRE ALARM AND DETECTION SYSTEM PART 1 - GENERAL 1.1 RELATED DOCUMENTS: A. Drawings and general provisions of Contract, including General and Supplementary Conditions and Division-1 Specification
OBOA 2009 Huntsville, ON Overview of ULC Standards Affecting Building Occupancy Alan Cavers Area Manager Fire & Security Systems Group Course Title: Rev Date Agenda Introduction to Underwriters Laboratories
CITY OF SPRING LAKE PARK Code Enforcement Department 1301 81 st Avenue NE Spring Lake Park MN 55432 Business Phone 763-784-6491 Fax 763-792-7257 INSPECTION, TESTING AND MAINTENANCE OF FIRE PROTECTION SYSTEMS
Approval Standard for Central Station Service for Fire Alarms and Protective Equipment Supervision Class Number 3011 April 1999 2002 FM Approvals LLC. All rights reserved. Foreword The FM Approvals certification
ORANGE COUNTY FIRE AUTHORITY Planning & Development Services Section 1 Fire Authority Road, Building A, Irvine, CA 92602 714-573-6100 www.ocfa.org New and Existing Fire Alarm & Signaling Systems Guideline
Winnipeg Fire Department Fire Prevention Branch Manitoba Fire Code Life-Safety Equipment Maintenance Requirements The Fire Prevention Branch of the Winnipeg Fire Department has prepared this document of
D7050/D7050TH EN Installation Instructions Multiplex Photoelectric Smoke Detectors D7050/D7050TH Installation Instructions.0 Description Notices These instructions cover the installation of the D7050/D7050TH
SECTION 13850 DETECTION AND ALARM PART 1 GENERAL 1.01 SUMMARY A. Section Includes 1. Control Panel 2 Associated Equipment B. Products Installed But Not Supplied Under This Section 1. Section 16140 - Wiring
FIRE DEPARTMENT CITY OF NEW YORK STUDY MATERIAL FOR THE CERTIFICATE OF FITNESS FOR SUPERVISION OF FIRE ALARM SYSTEMS AND OTHER RELATED SYSTEMS S-95 ALSO INCLUDED IN THIS BOOKLET YOU WILL FIND THE FOLLOWING:
SECTION 16720 FIRE ALARM AND DETECTION SYSTEMS PART 1 GENERAL 1.01 Reference A. Related Sections 1. Section 15300 Fire Protection 2. Section 15950 Controls 3. Division 16 Electrical 4. Division 14 - Conveying
Scope Provide a fire alarm system, or expand the existing system, as required by Code, the requirements in the Special Instructions to Designers (SID) of the Design Guidelines, and/or as noted in the Program
Amerex CPS FM-200 Waterless Pre-engineered Fire Suppression System A Simple Solution An Affordable Approach An Industry Innovation I N T R O D U C T I O N A SIMPLE SOLUTION. AN AFFORDABLE How many days
Page 1 of 5 CBD-233. Fire Alarm and Detection Systems Originally published August 1984. R.H.L. McEwen Fire alarm systems are normally required by building codes. In the case of new buildings, this is usually
BUILDING OWNERS - SERVICE RELATED ISSUES FOR FIRE ALARM SYSTEMS Owners have numerous responsibilities as it pertains to the maintenance and operation of a building s fire safety equipment. The liabilities
SMOKE DETECTOR INSTALLATION PROGRAM The Burlington Ordinance Perspective The National Fire Alarm Code, NFPA 72, sets the minimum requirements of performance, selection, use and location of automatic detection
P a g e 1 SECTION 04 (Doc.No.A/DBR 001) FIRE-FIGHTING DESIGN BRIEF REPORT P a g e 2 1.0 SCOPE 2.0 STANDARDS AND CODES 3.0 TYPES OF SYSTEM PROPOSED 4.0 FIRE HYDRANT SYSTEM 5.0 AUTOMATIC SPRINKLER SYSTEM
Fire Alarm System plan(s) MUST be reviewed and approved by the Belmont Fire Department prior to the start of construction. The design and any changes must be fully compliant with NFPA 1, NFPA 101, NFPA
PART 1 - GENERAL 1.01 WORK INCLUDED FIRE ALARM AND DETECTION SYSTEMS SECTION 16721 A. Provide a complete fully addressable, power limited, fire detection and evacuation system. The system shall be connected
SECTION 28 31 00 FIRE DETECTION AND ALARM GENERAL This section deals with the fire alarm system, including the control panel and integral equipment, wiring and circuitry, initiating devices, indicating
Fire Sprinkler Monitoring & Releasing Systems Training Manual Contents Foreword...3 Introduction...4 Glossary/Definitions...5 Symbols...10 Codes and Standards...13 Fire Alarm Signals...15 Types Of Sprinkler
PART 1 GENERAL 1.01 Scope of Standard A. This standard provides general requirements of The Sam Houston State University for fire pumps. This document is not intended to serve as a guide specification.