1 Document code: MN67507_ENG Revision Page 1 of 25 User Manual Revision English Modbus TCP Slave / Modbus Master - Converter (New Order Codes: HD67507-A1 HD67507-B2) (Old Order Codes: HD67507 HD67507M) for Website information: HD67507-A1 HD67507-B2 for Price information: Benefits and Main Features: INDEX: Very easy to configure Low Cost 32mm Rail DIN mount Wide supply input range Galvanic Isolation of RS485 Page Industrial temperature range: UPDATED DOCUMENTATION 2 REVISION -40 C / +85 C LIST (-40 F / +185 F) 2 WARNING 2 TRADEMARKS 2 INDEX 3 WARRANTIES AND TECHNICAL SUPPORT 4 For others products, see also the following links: RS232 / RS485 / USB / Ethernet (RS232 / RS485 - Converter) (USB / RS485 - Converter) (RS485 / RS232 / Ethernet - Converter) CAN / CANopen / Modbus / Modbus TCP (CANopen / Modbus Master - Converter) (CANopen / Modbus Slave - Converter) (CAN / Modbus Master - Converter) (CAN / Modbus Slave - Converter) RETURN POLICY 4 (CAN / Modbus TCP Master Converter) PRODUCTS AND RELATED (CAN DOCUMENTS / Modbus TCP Slave 4 Converter) CHARACTERISTICS 5 Modbus CONNECTION RTU Slave / Modbus SCHEME TCP Master - Converter 5 USE OF COMPOSITOR SW NEW PROJECT / OPEN PROJECT 7 Do you have an your customer protocol? GENERAL PARAMETER 7 ROUTING 8 Do you NATTING need to choose a device? do you want help? 8 TRANSLATE TABLE 9
2 INDEX: Page INDEX 2 UPDATED DOCUMENTATION 2 REVISION LIST 2 WARNING 2 TRADEMARKS 2 SECURITY ALERT 3 EXAMPLES OF CONNECTION 4 CONNECTION SCHEME 5 CHARACTERISTICS 7 POWER SUPPLY 8 FUNCTION MODES 9 LEDS 10 ETHERNET 11 RS RS USE OF COMPOSITOR SW NEW PROJECT / OPEN PROJECT 13 GENERAL PARAMETER 14 PING DEVICE 15 OPERATION MODE 16 TRANSLATE TABLE 17 UPDATE VIA SERIAL 19 UPDATE VIA UDP 20 MECHANICAL DIMENSIONS 23 ORDER CODE 23 ACCESSORIES 23 DISCLAIMER 24 OTHER REGULATIONS AND STANDARDS 24 WARRANTIES AND TECHNICAL SUPPORT 25 RETURN POLICY 25 PRODUCTS AND RELATED DOCUMENTS 25 Document code: MN67507_ENG Revision Page 2 of 25 UPDATED DOCUMENTATION: Dear customer, we thank you for your attention and we remind you that you need to check that the following document is: Updated Related to the product you own To obtain the most recently updated document, note the document code that appears at the top right-hand corner of each page of this document. With this Document Code go to web page and search for the corresponding code on the page. Click on the proper Document Code and download the updates. To obtain the updated documentation for the product that you own, note the Document Code (Abbreviated written "Doc. Code" on the label on the product) and download the updated from our web site REVISION LIST: Revision Date Author Chapter Description /07/2009 Ml All Revision /05/2010 Dp All Revision /06/2011 DP All Revision /09/2012 Fl All Software changed (v1.800) /12/2012 Fl All Revision /02/2013 Nt All Added new chapters /06/2013 Fl All Revision WARNING: ADFweb.com reserves the right to change information in this manual about our product without warning. ADFweb.com is not responsible for any error this manual may contain. TRADEMARKS: All trademarks mentioned in this document belong to their respective owners.
3 Document code: MN67507_ENG Revision Page 3 of 25 EXAMPLES OF CONNECTION:
4 Document code: MN67507_ENG Revision Page 4 of 25 SECURITY ALERT: GENERAL INFORMATION To ensure safe operation, the device must be operated according to the instructions in the manual. When using the device are required for each individual application, legal and safety regulation. The same applies also when using accessories. INTENDED USE Machines and systems must be designed so the faulty conditions do not lead to a dangerous situation for the operator (i.e. independent limit switches, mechanical interlocks, etc.). QUALIFIED PERSONNEL The device can be used only by qualified personnel, strictly in accordance with the specifications. Qualified personnel are persons who are familiar with the installation, assembly, commissioning and operation of this equipment and who have appropriate qualifications for their job. RESIDUAL RISKS The device is state of the art and is safe. The instrument can represent a potential hazard if they are inappropriately installed and operated by personnel untrained. These instructions refer to residual risks with the following symbol: This symbol indicates that non-observance of the safety instructions is danger for people to serious injury or death and / or the possibility of damage. CE CONFORMITY The declaration is made by us. You can send an to or give us a call if you need it.
5 Document code: MN67507_ENG Revision Page 5 of 25 CONNECTION SCHEME: Figure 1a: Connection Scheme for HD67507-A1, HD67507
6 Document code: MN67507_ENG Revision Page 6 of 25 Figure 1b: Connection Scheme for HD67507-B2, HD67507M
7 Document code: MN67507_ENG Revision Page 7 of 25 CHARACTERISTICS: The Modbus TCP Slave / Modbus Master Converter allows the following characteristics: Opto-isolated RS485; Choice possibility between RS232 or RS485 on Modbus RTU; Ethernet 10Base-T / 100Base-T, autosensing for Modbus TCP ; Mountable on 35mm Rail DIN; Temperature range -40 C / +85 C; EMS EN This device is able to manage a maximum of ten simultaneous connections from Ethernet side. To configure the Converter, use the available software that runs with Windows, called SW It is downloadable on the site and its operation is described in this document. It can be used in two operative ways: routing and natting. In the Routing Mode the command Modbus is forwarded on the serial line using the same requested addresses. In the Natting Mode the device addresses and data are altered through a translation table of the addresses.
8 Document code: MN67507_ENG Revision Page 8 of 25 POWER SUPPLY: The devices can be powered at 8 19V AC and 8 35V DC. The consumption depends to the code of the device. For more details see the two tables below. VAC VDC Vmin Vmax Vmin Vmax 8V 19V 8V 35V Consumption at 24V DC: Device Consumption [W/VA] HD67507-A1 4 HD67507-B2 5 Warning: Not reverse the polarity power HD67507-A1 HD67507-B2
9 Document code: MN67507_ENG Revision Page 9 of 25 FUNCTION MODES: The devices has got two functions mode depending of the position Jumper1 : The first, without Jumper1 (factory setting), is used for the normal working of the device; The second, with Jumper1, is used for upload the Project/Firmware into the device. For the operations to follow for the updating, see UPDATE DEVICE section. According to the functioning mode, the LEDs will have specifics functions, see LEDS section.
10 Document code: MN67507_ENG Revision Page 10 of 25 LEDS: The devices has got four LEDs that are used to give information of the functioning status. The various meanings of the LEDs are described in the table below. LED Normal Mode Boot Mode 1: RS485 communication (green) 2: Ethernet Link (green) Change state when receive a Modbus frame ON: Ethernet cable connected OFF: Ethernet cable disconnected Blinks quickly: Boot state Blinks very slowly (~0.5Hz): update in progress ON: Ethernet cable connected OFF: Ethernet cable disconnected 3: Device State (green) Blinks slowly (~1Hz) 4: Not used (green) OFF Blinks quickly: Boot state Blinks very slowly (~0.5Hz): update in progress Blinks quickly: Boot state Blinks very slowly (~0.5Hz): update in progress
11 Document code: MN67507_ENG Revision Page 11 of 25 ETHERNET: The Ethernet connection must be made using Connector3 of HD67507-A1/HD67507-B2 with at least a Category 5E cable. The maximum length of the cable should not exceed 100m. The cable has to conform to the T568 norms relative to connections in cat.5 up to 100 Mbps. To connect the device to an Hub/Switch is recommended the use of a straight cable, to connect the device to a PC/PLC/other is recommended the use of a cross cable. RS232: The connection from RS232 socket to a serial port (example one from a personal computer), must be made with a Null Modem cable (a serial cable where the pins 2 and 3 are crossed). It is recommended that the RS232C Cable not exceed 15 meters. The serial port is used for programming the device and for Modbus communication.
12 Document code: MN67507_ENG Revision Page 12 of 25 RS485: For terminate the RS485 line with a 220Ω resistor it is necessary to insert the Jumper2 like in figure. The maximum length of the cable should be 1200m (4000 feet). Here some codes of cables: Belden: p/n x 28AWG stranded twisted pairs conductor + foil shield + braid shield; Belden p/n x 24AWG stranded twisted pairs conductor + foil shield + braid shield; Tasker: p/n C521-1x 24AWG twisted pair conductor + foil shield + braid shield; Tasker: p/n C522-2x 24AWG twisted pairs conductor + foil shield + braid shield.
13 Document code: MN67507_ENG Revision Page 13 of 25 USE OF COMPOSITOR SW67507: To configure the Modbus TCP Slave / Morbus Master - Converter, use the available software that runs with Windows, called SW It is downloadable on the site and its operation is described in this document. (This manual is referenced to the last version of the software present on our web site). The software works with MSWindows (MS 2000, XP, Vista, Seven, 8; 32/64bit). When launching the SW67507 the right window appears (Fig. 2). Figure 2: Main window for SW67507 NEW PROJECT / OPEN PROJECT: The New Project button creates the folder which contains the entire device configuration. A device configuration can also be imported or exported: To clone the configurations of a Programmable Modbus TCP Slave / Morbus Master - Converter in order to configure another device in the same manner, it is necessary to maintain the folder and all its contents; To clone a project in order to obtain a different version of the project, it is sufficient to duplicate the project folder with another name and open the new folder with the button Open Project.
14 Document code: MN67507_ENG Revision Page 14 of 25 GENERAL PARAMETER: This section defines the fundamental communication parameters of two buses, Modbus TCP and Modbus RTU. By pressing the General Parameter button from the main window for SW67507 (Fig. 2) the window General Parameter appears (Fig. 3). The section Operation Mode defines the operation of the Converter in Routing Mode or NAT Mode (see the description at page 15). The means for the fields of MODBUS TCP are: In the field IP Address insert the IP address that you want to give to the slave Modbus TCP; In the field Subnet Mask insert the Subnet Mask; In field Gateway insert the Defualt Gateway IP address for use the Converter in WAN or Internet. For enable this feature is necessary to check the Gateway option. In the field Port insert the number of port; Checking Enable UDP Port field it is possible to do a Broadcast request. This request must be made at Port ($FADF) with these six byte of data: $53, $45, $41, $52, $43, $48. Each device in response sends a total of 10 Bytes. These bytes are four for the IP and the other for the MAC address (Example of response: 0xC0, 0xA8, 0x01, 0x2A, 0x11, 0x22, 0x33, 0x44, 0x55, 0x58. So the IP is: ; and the MAC Address: ). Figure 3: General Parameter window If the field Enable Special Command is checked, it is possible to send a no-modbus request through the gateway. i.e. a TCP frame with the first two characters 0x55 and 0xAA is sent in the Modbus RTU line as is. If you don t want to send the first two bytes (0x55, 0xAA) in the RTU line it is possible to check the field Cancel the first two bytes. If the field Fast StartUp (only 100Mb/s) is checked, the Converter take less time to go online. This command can use only if the gateway is used in a 100Mb/s network; If the field No TCP frame on RTU Timeout is checked the Converter don t sends back the reply on TCP (error response) if the Slave RTU interrogated has not replied.
15 Document code: MN67507_ENG Revision Page 15 of 25 The means for the fields of MODBUS RTU are: If the field RS232 is checked the serial line in use is the RS232, otherwise is the RS485 ; In the field Baud rate the velocity of the Modbus RTU is defined; In the field Parity the Modbus RTU parity is defined; Timeout is the maximum time that the device attends for the answer from the Slave interrogated; In the field RS485 Stop bits the number of Stop-Bit of Modbus RTU is defined; If the field Enable delay from last receive is checked the Converter, before send another Modbus RTU request, waits the time written in the field below (expressed in ms). PING DEVICE: If it is necessary to do a Ping on the net, before pressing the Ping Device button insert a value in the field on the right and then press the button. To use this feature in Vista and 7 you have to open the software with Administrator right. Note: In order to do this, the Converter must be in Normal Mode.
16 Document code: MN67507_ENG Revision Page 16 of 25 OPERATION MODE: ROUTING: A few characteristics of the Modbus RTU package have been modified in the standard of the Modbus TCP protocol. Two bytes of the final CRC were eliminated (no longer necessary for the information to reach its already corrected destination). The first byte of the slave identification was changed, leaving the one that is called PDU. A frame denominated as MBAP header with dimensions of 7 bytes was added to the head of the PDU. It is composed by the following: Word transaction identifier (recopied from the slave in the response phase); Word protocol identifier (0=Modbus protocol); Word length (number of successive bytes); Byte unit identifier (used for the routing operation). By using the last byte of the MBAP header, it is possible to carry out the routing from a requested Modbus TCP toward a serial line using the address from the slave which is specified by the byte unit identifier. Example: A requested Modbus TCP made in the device as the address for the holding register address $2000, which is MBAP unit identifier has the value of 2. It will be followed by the request on the serial for the device with the address 2 at the word $2000. After the request is made, the RTU will respond. The master TCP will be given the same response which will be reconstructed according to the specifications of the Modbus TCP. If the RTU slave responds with an exception, that exception code will be transmitted again to the TCP master. If the RTU slave does not respond in the estimated time defined by the Timeout parameter, an exception response will be given: error code $0B. NATTING: When using the operation mode, Natting, the requested data will be processed through a table of translations of the Modbus network addresses.
17 Document code: MN67507_ENG Revision Page 17 of 25 TRANSLATE TABLE: Within the section Translate Table you can define the variables that can be read or written by the TCP bus on the RTU bus when the device is in NAT mode. By pressing the Translate Table button from the main window for SW67507 (Fig. 2) the window Set Translate Table appears (Fig. 4). Figure 4: Set Translate Table window The data of the columns have the following meanings: In the field Data Type insert the type of data that is being considered; In the field Address TCP insert the virtual address of the present data in a device in the TCP Modbus; In the field Address Device RTU insert the address of the device on the RTU Modbus that contains the data; In the field Address RTU insert the address of the data on the RTU device; In the field N Point insert the number of consecutive data that you want to configure. For example, you create Address TCP=1000, Address RTU=100 and N point = 5, the following gets set-up automatically: addresses TCP 1001, 1002, 1003, 1004 and the variables RTU 101, 102, 103, 104; In the field Mnemonic you can insert a brief description.
18 Document code: MN67507_ENG Revision Page 18 of 25 Example 1: If you want, from TCP network, write a data it the RTU network on the device at: Address 5; Through Gateway WORD 100 (Address RTU); Address TCP In the above scenario: Specify the type of data between: Coil Status (bit in read write); Input Status (bit in read); Holding Register (word in read and write); Input Register (word in read). From the side of the MODBUS TCP: Address of data to read. From the side of the MODBUS RTU: Address of the device to interrogate; Address of data to read on device. Note: If the RTU slave responds with an exception, that exception code will be transmitted to the TCP Master. If the RTU slave does not respond within the estimated time defined by the Timeout parameter, an exception response will be given on TCP side: error code $0B.
19 Document code: MN67507_ENG Revision Page 19 of 25 UPDATE VIA SERIAL: By pressing the Update Via Serial button it is possible to load the created Configuration into the device, and also the Firmware if is necessary, using the RS232 port. In order to load the parameters or update the firmware in the device, follow these instructions: Turn off the Device; Connect the RS232 Null Modem Cable form your PC to the Converter; Insert the Boot Jumper (see FUNCTION MODES section); Select the COM port and press the Connect button; Turn on the device; Check the Device State Led. It must blink quickly (see LEDS section); Press the Next button; Select which operations you want to do. Press the Execute update firmware button to start the upload; When all the operations are OK turn off the device; Remove the Boot jumper; Disconnect the RS232 Cable; Turn on the device. At this point the configuration/firmware on the device is correctly updated. Figure 5: Update Device windows
20 Document code: MN67507_ENG Revision Page 20 of 25 UPDATE VIA UDP: By pressing the Update Via UDP button it is possible to load the created Configuration into the device, and also the Firmware if is necessary, using the Ethernet port. If you don t know the actual IP address of the device you have to use this procedure: Turn off the Device; Insert the Boot Jumper (see FUNCTION MODES section); Insert the IP ; Turn on the device; Press the Ping button, must appear Device Found! ; Press the Next button; Select which operations you want to do; Press the Execute update firmware button to start the upload; When all the operations are OK turn off the Device; Remove the Boot jumper; Turn on the device. At this point the configuration/firmware on the device is correctly updated. Figure 6: Update device windows
21 Document code: MN67507_ENG Revision Page 21 of 25 If you know the actual IP address of the device you have to use this procedure: Turn on the Device with the Ethernet cable inserted; Insert the actual IP of the Gateway; Press the Ping button, must appear Device Found! ; Press the Next button; Select which operations you want to do; Press the Execute update firmware button to start the upload; When all the operations are OK the device automatically goes at Normal Mode. At this point the configuration/firmware on the device is correctly update. Note: When you install a new version of the software it is better if the first time you do the update of the Firmware in the HD67507-A1 or HD67507-B2 device. Note: When you receive the device, for the first time, you have to update also the Firmware in the HD67507-A1 or HD67507-B2 device.
22 Document code: MN67507_ENG Revision Page 22 of 25 Warning: If the Fig. 7 appears when you try to do the Update before require assistance try these points: Check if the serial COM port selected is the correct one; Check if the serial cable is connected between the PC and the device; Try to repeat the operations for the updating; If you are using a USB RS232 converter try with a native COM port or change the converter; Try to repeat the operations for the updating; Try with another PC; Try to restart the PC; If you are using the program inside a Virtual Machine, try to use in the main Operating System; If you are using Windows Seven or Vista, make sure that you have the administrator privileges; In case you have to programming more than one device, using the "TCP Figure 7: Protection windows Update", you have to cancel the ARP table every time you connect a new device on Ethernet. For do this you have to launch the "Command Prompt" and write the command "arp -d". Pay attention that with Windows Vista, Seven, 8 you have to launch the "Command Prompt" with Administrator Privileges. Take attention at Firewall lock. In the case of HD67507-A1 or HD67507-B2 you have to use the software SW67507 : Note: The "Update via UDP" can be used only with Hardware HD67507-A1 or HD67507-B2, and only with Software version from 1.800; The "Update via TCP" can be used only with Hardware HD67507 or HD67507M, and only with Software version up to 1.400; The "Update via Serial" can be used with all hardware, and with all Software versions.
23 Document code: MN67507_ENG Revision Page 23 of 25 MECHANICAL DIMENSIONS: Figure 8: Mechanical dimensions scheme for HD67507-A1 (and Old Model HD67507) ORDER CODES: Figure 9: Mechanical dimensions scheme for HD67507-B2 (and Old Model HD67507M) Order Code: HD67507-A1 - Modbus TCP Slave / Modbus RTU Master - Converter ( Housing type: A, Terminal Blocks Connectors ) Order Code: HD67507-B2 - Modbus TCP Slave / Modbus RTU Master - Converter ( Housing type: B, Terminal Blocks Connectors ) ACCESSORIES: Order Code: AC Null Modem Cable Fem/Fem DSub 9 Pin 1,5 m Order Code: AC Null Modem Cable Fem/Fem DSub 9 Pin 5 m Order Code: AC Rail DIN - Power Supply 220/240V AC 50/60Hz 12 V AC Order Code: AC Rail DIN - Power Supply 110V AC 50/60Hz 12 V AC
24 Document code: MN67507_ENG Revision Page 24 of 25 DISCLAIMER All technical content within this document can be modified without notice. The content of the document content is a recurring audit. For losses due to fire, earthquake, third party access or other accidents, or intentional or accidental abuse, misuse, or use under abnormal conditions repairs are charged to the user. ADFweb.com S.r.l. will not be liable for accidental loss of use or inability to use this product, such as loss of business income. ADFweb.com S.r.l. shall not be liable for consequences of improper use. OTHER REGULATIONS AND STANDARDS WEEE INFORMATION Disposal of old electrical and electronic equipment (as in the European Union and other European countries with separate collection systems). This symbol on the product or on its packaging indicates that this product may not be treated as household rubbish. Instead, it should be taken to an applicable collection point for the recycling of electrical and electronic equipment. If the product is disposed correctly, you will help prevent potential negative environmental factors and human health, which could otherwise be caused by inappropriate disposal. The recycling of materials will help to conserve natural resources. For more information about recycling this product, please contact your local city office, your household waste disposal service or the shop where you purchased the product. RESTRICTION OF HAZARDOUS SUBSTANCES DIRECTIVE The device respects the 2002/95/EC Directive on the restriction of the use of certain hazardous substances in electrical and electronic equipment (commonly referred to as Restriction of Hazardous Substances Directive or RoHS). CE MARKING The product conforms with the essential requirements of the applicable EC directives.
25 Document code: MN67507_ENG Revision Page 25 of 25 WARRANTIES AND TECHNICAL SUPPORT: For fast and easy technical support for your ADFweb.com SRL products, consult our internet support at Otherwise contact us at the address RETURN POLICY: If while using your product you have any problem and you wish to exchange or repair it, please do the following: 1) Obtain a Product Return Number (PRN) from our internet support at Together with the request, you need to provide detailed information about the problem. 2) Send the product to the address provided with the PRN, having prepaid the shipping costs (shipment costs billed to us will not be accepted). If the product is within the warranty of twelve months, it will be repaired or exchanged and returned within three weeks. If the product is no longer under warranty, you will receive a repair estimate. PRODUCTS AND RELATED DOCUMENTS: Part Description URL HD67118 Converter RS232 to RS485 Isolated HD67119 Converter USB 2.0 to RS485 Isolated HD67507 Gateway Modbus TCP Server to RTU Master HD67510 Gateway Modbus TCP Client to RTU Slave
Document code: MN67221F_ENG Revision 2.002 Page 1 of 19 User Manual Revision 2.002 English CAN / Optic Fiber Repeater Extender bus line (With filter data configurable) (Order Code: HD67221F - HD67221FS)
Document code: MN67513_ENG Revision 1.002 Page 1 of 15 User Manual Revision 1.002 English Gateway / Adapter CAN to Ethernet (Order Code: HD67513 HD67513M) HD67513 for Website HD67513 information: www.adfweb.com?product=hd67513
Document code: MN67595_ENG Revision 1.012 Pagina 1 di 27 User Manual Revision 1.012 English EtherNet/IP / CAN - Converter (Order Code: HD67595-A1) for Website information: www.adfweb.com?product=hd67595
Document code: MN67648_ENG Revision 2.011 Page 1 of 38 User Manual Revision 2.011 English Ethernet / Serial - Converter ( Order Code: HD67648-A1-232 for Serial on RS232) ( Order Code: HD67648-A1-485 for
Document code: MN67302_ENG Revision 1.001 Page 1 of 35 User Manual Revision 1.001 English GSM I/O and Alarms Modem for Website information: www.adfweb.com?product=hd67302 for Price information: www.adfweb.com?price=hd67302-b2-02
Document code: MN67316_ENG Revision 1.013 Page 1 of 41 User Manual Revision 1.012 English CAN Analyzer Hardware and Software (Order Codes: HD67316-U-D1 HD67316-E-A1) for Website information: www.adfweb.com?product=hd67316
TCP/IP MODULE CA-ETHR-A INSTALLATION MANUAL w w w. c d v g r o u p. c o m CA-ETHR-A: TCP/IP Module Installation Manual Page Table of Contents Introduction...5 Hardware Components... 6 Technical Specifications...
BIT COMMANDER Serial RS232 / RS485 to Ethernet Converter (Part US2000A) Copyrights U.S. Converters 1 Contents Overview and Features... 3 Functions..5 TCP Server Mode... 5 Httpd Client Mode.5 TCP Auto mode....6
IntesisBox KNX TCP master Gateway for integration of TCP slave devices into KNX control systems. Integrate any TCP slave device into KNX. KNX TCP slave EIB Bus IntesisBox Ethernet slave LinkBoxEIB Configuration
70072-0104-14 TECHNICAL 06/2009 Modbus and ION Technology Modicon Modbus is a communications protocol widely used in process control industries such as manufacturing. PowerLogic ION meters are compatible
KRAMER ELECTRONICS LTD. USER GUIDE Ethernet Configuration Guide (Lantronix) P/N: 2900-300321 Rev 6 Contents 1 Connecting to the Kramer Device via the Ethernet Port 1 1.1 Connecting the Ethernet Port Directly
User Manual EtherUSB USB Ethernet Access Point for PDA V 2.0 Clarinet Systems, Inc. Clarinet Systems, Inc. http://www.clarinetsys.com Page 1 Publication Revision No. Control Table Rev. No. Date Contents
This Quick Start Guide is designed to familiarize the user with the connection and configuration of the DTS-305 DIN rail mounted single / 3 phase power & energy meter with RS-485 or TCP communications.
Broadband Router ESG-103 User s Guide FCC Warning This equipment has been tested and found to comply with the limits for Class A & Class B digital device, pursuant to Part 15 of the FCC rules. These limits
User Manual Protocol Converter PC-E, Serial to Ethernet (RS232/485 Modbus RTU to Modbus TCP/IP) UMPCEA Rev 1.0, 05/2007 COPYRIGHT NOTICE This manual is a publication of Brainchild Electronics Co... Ltd.
RS232 Serial TO Ethernet convert Module USR-TCP232-T Hard Version: V2.0 Doc Version: V1.1 2011-08-16 Jinan USR Technology Co., Ltd. works on LAN and WAN and wireless for MCU to Ethernet Solutions, Ethernet,
xepi 2 Diagnostic Unit and Configuration Interface Doc. Version 4.0 Installation Guide English Dear Customer, This "Installation Guide" will help you to install the hardware. If you have any further questions,
ENET-710 ENET-710 - Ethernet Module JAN / 06 ENET-710 FOUNDATION E N E T 7 1 0 ME smar www.smar.com Specifications and information are subject to change without notice. Up-to-date address information is
1 INTRODUCTION This document describes the procedure to upgrade LTMR. Limitation: this package and procedure describe only the upgrade of the LTMR firmware for all network versions (Modbus, Profibus, DeviceNet,
Setup Manual and Programming Reference Stanford Research Systems Revision 1.05 (11/2010) Certification Stanford Research Systems certifies that this product met its published specifications at the time
User Manual EtherUSB USB Ethernet Access Point for PDA V 1.6 Page 1 Publication Revision No. Control Table Rev. No. Date Contents 1.6 8/22/07 Support connection of multiple WM5.0 devices 1.5 6/18/07 Support
EMBEDDED ACCESS CONTROL Hardware Installation Guide Lenel goentry Hardware Installation Guide, product version 1.00. This guide is item number DOC- ENHW-ENU, revision 1.003, April 2009 Copyright 2009 Lenel
WEB log LIGHT+ 20 BASIC 100 PRO unlimited Device connection plans Version 20160425* Copyright Copyright for this manual remains with the manufacturer. No part of this manual may be reproduced or edited,
IP Sensor and Watchdog IPSW2210 Manual Relay Output Power input 12VDC adapter LED Indicators 1 wire 2 Dry Output Green : Power Yellow: Link temperature & humidity contact inputs LED indicator sensor input
Network/Floating License Installation Instructions Installation steps: On the Windows PC that will act as License Manager (SERVER): 1. Install HASP Run-time environment, SERVER 2. Plug in the red USB hardware
User s Guide NPD4747-01 EN Contents Contents Copyright and Trademarks Safety Instructions Important Safety Instructions... 4 Cautions and Notes... 4 Getting to Know Your Network Interface Panel Package
IntesisBox ModBus Server - KNX Gateway for integration of KNX equipment into Modbus (RTU and TCP) control systems. Integrate KNX based lighting control into your SCADA, BMS, PLC "talking" Modbus. Master
UPS Network Interface Quick InstallationGuide Version 1.1 March 1999 COPYRIGHT Copyright 1999 RINGDALE UK Limited. All rights reserved. No part of this publication may be reproduced, transmitted, transcribed,
Special Note Connection Problems and Handling Methods (CS203 / CS468 / CS469) Sometimes user cannot find the RFID device after installing the CSL Demo App and the RFID reader is connected. If user cannot
Installation Instructions Universal Serial Bus (USB) to DH-485 Interface Converter Catalog Number 1747-UIC Contents Overview..................................................3 Computer and Operating System
Sense +V Tx Rx LAN LINK Over ARCNET KBaud BACnet Rx BACnet Tx Archive Valid Port S Tx Port S Rx Low Battery Network- Enhanced Access Default MSTP PTP = Download Required on Rnet and Port S IP Address IP
One Port Serial Server Users Manual Model ESP901, ESP901E Documentation Number: ESP901-2303 International Headquarters B&B Electronics Mfg. Co. Inc. 707 Dayton Road -- P.O. Box 1040 -- Ottawa, IL 61350
IntesisBox Server Fidelio IP Gateway for integration of Micros Fidelio Ho management system into (RTU and TCP) enabled control systems. Integrate your Micros Fidelio Ho management system into your master
the following parts are needed to test the unit: Arduino UNO R3 Arduino Wifi shield And reciever 5V adapter Connecting wifi module on shield: Make sure the wifi unit is connected the following way on the
EMG Ethernet Modbus Gateway User Manual Rev 2.2 07/2010 CONTENTS 1. Introduction 1.1. General Features 1.2 Installing the Drivers 2. Configuration 2.1 Main Device Parameters 2.1.1 RS485 Serial Communication
User manual Compact Web PLC WP240 series IEC-line update: 09-01-2014 IEC-line by OVERDIGIT overdigit.com 1. General description The WP240 device is a PLC, programmable in IEC61131-3 language using CoDeSys
Data Bulletin 1210DB0002R3/05 03/2005 LaVergne, TN, USA Communications Wiring for POWERLINK G3 Systems Class 1210 Retain for future use. ABOUT THIS BULLETIN This data bulletin describes the proper wiring
CNC File Transfer Box The CNC File Transfer connects a serial CNC device to the network so files can be easily transferred from a computer to the CNC equipment. Any computer on the network can transfer
Xbox LIVE Vision Thanks for choosing the Xbox LIVE Vision camera. Xbox LIVE Vision adds video to your Xbox 360 system and games, including: Video chat and picture messages. Photo snapshots. Family Settings
Quick Operation Guide DAB, DAB + und DMB USB Digital Receiver Albrecht DR 403. 1 Note Thank you for purchasing the DAB/ DMB receiver. This Quick Guide is to guide you to the software installation of the
Wireless Router Setup Manual NETGEAR, Inc. 4500 Great America Parkway Santa Clara, CA 95054 USA 208-10082-02 2006-04 2006 by NETGEAR, Inc. All rights reserved. Trademarks NETGEAR is a trademark of Netgear,
Modbus and ION Technology Modicon Modbus is a communications protocol widely used in process control industries such as manufacturing. ACCESS meters are compatible with Modbus networks as both slaves and
Prestige 324 Intelligent Broadband Sharing Gateway Version 3.60 January 2003 Quick Start Guide 1 Introducing the Prestige The Prestige is a broadband sharing gateway with a built-in four-port 10/100 Mbps
Prestige 324 Intelligent Broadband Sharing Gateway Version V3.61(JF.0) May 2004 Quick Start Guide 1 1 Introducing the Prestige The Prestige is a broadband sharing gateway with a built-in four-port 10/100
MODEL ATC-2004 TCP/IP TO RS-232/422/485 CONVERTER User s Manual 1.1 Introduction The ATC-2004 is a 4 Port RS232/RS485 to TCP/IP converter integrated with a robust system and network management features
FOR MORE INFORMATION 125 8880 or from a non-telstra phone 13 2200 and say pre-paid telstra.com/ppmbb visit a telstra store or partner getting to know your telstra pre-paid 4G WI-FI (760S) LET S GET THIS
MAX T1/E1 TM VoIP Gateway Quick Start Guide Version 1.0 Contents INTRODUCTION 1 Hardware Needed Software Needed 1 1 NET2PHONE MAX SET UP Hardware Set Up Software Set Up Set Up Internet Protocol (IP) Address
Page 1 of 16 TITLE: Category: EDGE FX Network configuration GERBER EDGE Document Number: 4280 Supplied by: Gerber Service Last Modified: April 14, 2011 Summary: In order to connect an EDGE FX to your PC
GSC/VRC IP Converter Installation and Operation Manual Table of Contents Introduction... 2 Compatibility... 2 Remote Control Hardware... 2 PC Software... 2 Unpacking... 2 Front Panel Indicators... 3 Hardware
NETGEAR, Inc. 4500 Great America Parkway Santa Clara, CA 95054 USA 208-10060-01 2006-03-17 2006 by NETGEAR, Inc. All rights reserved. Trademarks NETGEAR is a trademark of Netgear, Inc. Microsoft, Windows,
ethernet table of contents ethernet connection The printer's built-in ethernet feature allows you to connect the printer directly to an ethernet network without the need for an external print server. For
RIGtalk Revision 5 Owner s Manual 2012 www.westmountainradio.com 1020 Spring City Drive Waukesha, WI 53186 262-522-6503 firstname.lastname@example.org 2012 West Mountain Radio, All rights reserved. All trademarks
32 Transferring Projects and Data This Chapter explains how to transfer GP-Pro EX project files to the GP and how to transfer the project files stored on the GP to your PC. Please start by reading 32.1
PLC training panel (Twido version) User manual Name School of Trades Produced by: GJR October 2012 Colour leaves: 9 BW leaves: 2 Cover colour: White Cover image: G.J.Rogerson Acknowledgments: Much of the
Application Note: Connecting to a 2500 Series Processor using PLC Workshop This application note will describe a step by step process for the three ways to connect to a 2500-CXXX with PLC Workshop. The
For Use with L-GAGE LH Series Sensors Features Converts an LH Network to the 485-RTU protocol Supports baud rates up to 230,400 baud Supports LH Networks with up to 32 sensors Model Protocol Conversion
RN-XV-RD2 Evaluation Board 2012 Roving Networks. All rights reserved. -1.01Version 1.0 9/28/2012 USER MANUAL OVERVIEW This document describes the hardware and software setup for Roving Networks RN-XV-RD2