1 Document code: MN67225_ENG Revision Page 1 of 30 User Manual Revision English NMEA 2000 / Modbus TCP Slave - Converter (Order Code: HD67225-A1, HD67225-B2) for Website information: for Price information: Benefits and Main Features: Very easy to configure Low cost 32mm Rail DIN mount Wide supply input range Temperature range: -40 C/+85 C (-40 F/+185 F) For others Gateways / Bridges: NMEA2000 to Modbus See also the following links: (Modbus RTU) CANopen to Modbus See also the following links: (Modbus RTU Master) (Modbus RTU Slave) (Modbus TCP Master) (Modbus TCP Slave) For others Gateways / Bridges: For CAN bus 2.0A and/or CAN bus 2.0B to Modbus See also the following links: (Modbus RTU Slave) (Modbus RTU Master) (Modbus TCP Slave) (Modbus TCP Master) Do you have an your customer protocol? See the following links: Do you need to choose a device? do you want help? Ask it to the following link: User Manual
2 Pagina 2 di 30 User Manual NMEA2000 / Modbus TCP Slave INDEX: Document code: MN67225_ENG Revision Page 2 of 30 UPDATED DOCUMENTATION: Page INDEX 2 UPDATED DOCUMENTATION 2 REVISION LIST 2 WARNING 2 TRADEMARKS 2 SECURITY ALERT 3 EXAMPLE OF CONNECTION 4 CONNECTION SCHEME 5 CHARACTERISTICS 7 CONFIGURATION 7 POWER SUPPLY 8 FUNCTION MODES 9 LEDS 10 ETHERNET 11 NMEA USE OF COMPOSITOR SW NEW PROJECT / OPEN PROJECT 14 SOFTWARE OPTIONS 15 SET COMMUNICATION 16 RECEIVE NMEA DEFINE RECEIVE NMEA TRANSMIT NMEA DEFINE TRANSMIT NMEA UPDATE DEVICE VIA SERIAL 24 UPDATE DEVICE VIA UDP 25 MECHANICAL DIMENSIONS 27 ORDER CODE 28 ACCESSORIES 28 DISCLAIMER 29 OTHER REGULATIONS AND STANDARDS 29 WARRANTIES AND TECHNICAL SUPPORT 30 RETURN POLICY 30 Dear customer, we thank you for your attention and we remind you that you need to check that the following document is: Updated Related to the product you own To obtain the most recently updated document, note the document code that appears at the top right-hand corner of each page of this document. With this Document Code go to web page and search for the corresponding code on the page. Click on the proper Document Code and download the updates. REVISION LIST: Revision Date Author Chapter Description /07/2010 Dp All First release version /02/2013 Nt All Added new chapters /08/2015 Ff All New hardware version WARNING: ADFweb.com reserves the right to change information in this manual about our product without warning. ADFweb.com is not responsible for any error this manual may contain. TRADEMARKS: All trademarks mentioned in this document belong to their respective owners.
3 Document code: MN67225_ENG Revision Page 3 of 30 SECURITY ALERT: GENERAL INFORMATION To ensure safe operation, the device must be operated according to the instructions in the manual. When using the device are required for each individual application, legal and safety regulation. The same applies also when using accessories. INTENDED USE Machines and systems must be designed so the faulty conditions do not lead to a dangerous situation for the operator (i.e. independent limit switches, mechanical interlocks, etc.). QUALIFIED PERSONNEL The device can be used only by qualified personnel, strictly in accordance with the specifications. Qualified personnel are persons who are familiar with the installation, assembly, commissioning and operation of this equipment and who have appropriate qualifications for their job. RESIDUAL RISKS The device is state of the art and is safe. The instrument can represent a potential hazard if they are inappropriately installed and operated by personnel untrained. These instructions refer to residual risks with the following symbol: This symbol indicates that non-observance of the safety instructions is danger for people to serious injury or death and / or the possibility of damage. CE CONFORMITY The declaration is made by us. You can send an to or give us a call if you need it.
4 Document code: MN67225_ENG Revision Page 4 of 30 EXAMPLES OF CONNECTION:
5 Document code: MN67225_ENG Revision Page 5 of 30 CONNECTION SCHEME: Figure 1a: Connection scheme for HD67225-A1
6 Document code: MN67225_ENG Revision Page 6 of 30 Figure 1b: Connection scheme for HD67225-B2
7 Document code: MN67225_ENG Revision Page 7 of 30 CHARACTERISTICS: The NMEA 2000 / Modbus TCP Slave Converter allows the following characteristics: two-directional information between networks NMEA 2000 and Modbus; electrical isolation between two Buses; to read NMEA 2000 frame from Modbus word; to write NMEA 2000 frame from Modbus word; Mountable on Rail DIN; Temperature range from -40 C to +85 C. This device is able to manage a maximum of four simultaneous connections at Modbus TCP side. CONFIGURATION: You need Compositor SW67225 software on your PC in order to perform the following: Define the parameter of NMEA 2000; Define the parameter of Modbus TCP; Define which NMEA 2000 frames are read by the Modbus; Define which NMEA 2000 frames are write by the Modbus.
8 Document code: MN67225_ENG Revision Page 8 of 30 POWER SUPPLY: The devices can be powered at 8 24V AC and 12 35V DC. For more details see the two tables below. VAC VDC Vmin Vmax Vmin Vmax 8V 24V 12V 35V Consumption at 24V DC: Device Consumption [W/VA] HD67225-A1 3.5 HD67225-B2 3.5 Caution: Not reverse the polarity power HD67225-A1 HD67225-B2
9 Document code: MN67225_ENG Revision Page 9 of 30 FUNCTION MODES: The device has got two function modes depending on the position of the Dip2 of Dip-Switch A : The first, with Dip2 of Dip-Switch A at OFF position, is used for the normal working of the device. The second, with Dip2 of Dip-Switch A at ON position, is used for uploading the Project and/or Firmware. For the operations to follow for the updating, see UPDATE DEVICE section. According to the functioning mode, the LEDs will have specific functions, see LEDS section. Warning: Dip1 of Dip-Switch A must be at ON position to work even if the Ethernet cable is not inserted.
10 Document code: MN67225_ENG Revision Page 10 of 30 LEDS: The devices has got four (five for HD67225-B2) LEDs that are used to give information of the functioning status. The various meanings of the LEDs are described in the table below. LED Normal Mode Boot Mode 1: NMEA Communication (green) 2: Ethernet Link (green) 3: Modbus Communication (green) Blinks when configured NMEA frames are received ON: Ethernet cable connected OFF: Ethernet cable disconnected Blinks when Modbus TCP requests are received Blinks quickly: Boot state Blinks very slowly (~0.5Hz): update in progress ON: Ethernet cable connected OFF: Ethernet cable disconnected Blinks quickly: Boot state Blinks very slowly (~0.5Hz): update in progress 4: Device State (yellow) Blinks slowly (~1Hz) Blinks quickly: Boot state Blinks very slowly (~0.5Hz): update in progress 5: Not used (yellow) (Present only on HD67225-B2) OFF Blinks quickly: Boot state Blinks very slowly (~0.5Hz): update in progress
11 Document code: MN67225_ENG Revision Page 11 of 30 ETHERNET: The Ethernet connection must be made using Connector5 of HD67225-A1/HD67225-B2 with at least a Category 5E cable. The maximum length of the cable should not exceed 100m. The cable has to conform to the T568 norms relative to connections in cat.5 up to 100 Mbps. To connect the device to a Hub/Switch the use of a straight cable is recommended. To connect the device to a PC/PLC/other the use of a cross cable is recommended.
12 Document code: MN67225_ENG Revision Page 12 of 30 NMEA 2000: For terminating the NMEA 2000 line with a 120Ω resistor it is necessary that the Dip1 of Dip-Switch C is at ON position. Cable characteristics: DC parameter: Impedance 70 Ohm/m AC parameters: Impedance 120 Ohm/m Delay 5 ns/m Length Baud Rate [bps] Length MAX [m] 10 K K K K K K K K K 25
13 Document code: MN67225_ENG Revision Page 13 of 30 USE OF COMPOSITOR SW67225: To configure the Converter, use the available software that runs with Windows called SW It is downloadable on the site and its operation is described in this document. (This manual is referenced to the last version of the software present on our web site). The software works with MSWindows (XP, Vista, Seven, 8, 10; 32/64bit). When launching the SW67225, the window below appears (Fig. 2). Note: It is necessary to have installed.net Framework 4. Figure 2: Main window for SW67225
14 Document code: MN67225_ENG Revision Page 14 of 30 NEW CONFIGURATION / OPEN CONFIGURATION: The New Configuration button creates the folder which contains the entire device s configuration. A device s configuration can also be imported or exported: To clone the configurations of a programmable NMEA 2000 / Modbus TCP Slave - Converter in order to configure another device in the same manner, it is necessary to maintain the folder and all its contents; To clone a project in order to obtain a different version of the project, it is sufficient to duplicate the project folder with another name and open the new folder with the button Open Configuration.
15 Document code: MN67225_ENG Revision Page 15 of 30 SOFTWARE OPTIONS: By pressing the Settings ( ) button there is the possibility to change the language of the software and check the updatings for the compositor. In the section Language it is possible to change the language of the software. In the section Connection Options, it is possible to check if there are some updatings of the software compositor in ADFweb.com website. Checking the option Check Software Update at Start of Program, the SW67225 check automatically if there are updatings when it is launched.
16 Document code: MN67225_ENG Revision Page 16 of 30 SET COMMUNICATION: This section defines the fundamental communication parameters of two Buses, NMEA 2000 and Modbus TCP. By pressing the Set Communication button from the main window for SW67225 (Fig. 2) the window Set communication appears (Fig. 3). This window is divided in two sections, one for configure the NMEA 2000 and the other for the Modbus TCP Slave. In the section Select Device it is possible to select the type of converter used: Device till April 2014 (with Jumper); Device from May 2014 (with Dip-Switches). I The means for the fields for the NMEA 2000 are: In the field Baud Rate the baudrate of the NMEA 2000 is defined; In the field TimeOut the timeout of the data is defined. If this time is elapsed the value of the data of the NMEA 2000 frame become 0. If the Cancel Data field is checked in the Receive NMEA 2000 window; If the field Enable Peer to Peer is checked, the Source Address of the PGNs received by the converter is masked (only if a single NMEA device is connected); In the field Device ID NMEA 2000 the ID of the converter is defined (only if Device from May 2014 (with Dip-Switches) is selected); Figure 3: Set Communication window
17 User Manual NMEA2000 / Modbus TCP Slave Document code: MN67225_ENG Revision Page 17 of 30 If the field Filter FECA (ms) is checked when the FECA PGN arrives the gateway puts the values in Standby. If the time, expressed in milliseconds and written at the right side of Filter FECA, is elapsed and there aren t arrived the frames of Transport Protocol the gateway put the data of FECA into Modbus Registers. Otherwise if the Transport Protocol arrives before the time is elapsed the gateway put his data into Modbus Registers discarding the data of FECA. When this field is checked the values aren t updated when the FECA frame arrive but there is an offset of xx ms. You can use this function if there is only one NMEA 2000 device in the network; If the field Send frame every (ms) is checked the gateway sends cyclically the NMEA 2000 frames defined in Transmit NMEA section with the specific delay defined. Otherwise a frame is sent in NMEA 2000 when a modbus register is written into the gateway (only if Device till April 2014 (with Jumper) is selected). The means for the fields for Modbus TCP Slave are: In the field IP Address, insert the IP address that you want to give to slave Modbus; In the field SubNet Mask insert the SubNet Mask; In the field Gateway, insert the default gateway that you want to use. This feature can be enabled or disabled pressing the Check Box field. This feature is used for going out of the net; In the field Port insert the number of the port; If the field Fast StartUp is checked, the gateway take less time to go online. This command can use only if the gateway is used in a 100Mb/s network (only if Device till April 2014 (with Jumper) is set); If the field Enable write NMEA on request is checked, the field Write NMEA 2000 frame in Transmit NMEA 2000 frame info is enabled. If this field is not checked, the device send a NMEA 2000 frame for every written register. Otherwise it is possible to select when to send the NMEA 2000 frame (only if Device till April 2014 (with Jumper) is selected).
18 Document code: MN67225_ENG Revision Page 18 of 30 RECEIVE NMEA 2000: By pressing the Receive NMEA 2000 button from the main window for SW67225 (Fig. 2) the window Receive CAN Frames Definition appears (Fig. 4). In this section, it is possible to define the CAN frames that the converter will receive from CAN network. If Device till April 2014 (with Jumper) is set in the section Set Communication, the window appears like below: Figure 4a: Receive NMEA 2000 Frames window In the field PGN insert the PGN of the NMEA 2000 frame; In the field Source Address insert the Source Address of the NMEA 2000 frame; If the field Transport Protocol is checked the frame uses Transport Protocol functions; If the field Fast Packet is checked the frame uses Fast Packet functions; In the field Start Byte insert the byte which you would start read, this field is enable only when the field Transport Protocol is checked; In the field Num Bytes insert the number of byte you would read, for example your Start Byte is 20 an Num Bytes is 10, you can read the byte from 20 to 30; If the field Cancel Data is checked, after the timeout defined in the Set Communication window the value of the data of the NMEA 2000 frame become 0xFF ; In the field Mnemonic a description of the frame is defined.
19 Document code: MN67225_ENG Revision Page 19 of 30 If Device from May 2014 (with Dip-Switches) is set in the section Set Communication, the window appears like below: Figure 4b: Receive NMEA 2000 Frames window In the field PGN insert the PGN of the NMEA 2000 frame; In the field Source Address insert the Source Address of the NMEA 2000 frame; If the field Transport Protocol is checked the frame uses Transport Protocol functions; If the field Fast Packet is checked the frame uses Fast Packet functions; In the field Start Byte insert the byte which you would start read, this field is enable only when the field Transport Protocol is checked; In the field Num Bytes insert the number of byte you would read, for example your Start Byte is 20 an Num Bytes is 10, you can read the byte from 20 to 30; If the field Cancel Data is checked, after the timeout defined in the Set Communication window the value of the data of the NMEA 2000 frame become 0xFF ; If the field On Request is checked, the converter send the request frame to the related PGN in order to receive the frame with the data; In the field Time (ms) is possible to insert the interval used to send the frame On Request ; In the field Mnemonic a description of the frame is defined.
20 Document code: MN67225_ENG Revision Page 20 of 30 DEFINE NMEA 2000: By pressing the Define COB button near Receive NMEA 2000 from the main window for SW67225 (Fig. 2) the window Define Modbus Registers for Receive NMEA 2000 Frames appears (Fig. 5): For example: In the field List of Receive CAN Frames there is the list of NMEA 2000 frames that you inserted in Receive NMEA 2000 Section In the field List of Modbus Registers there are the Modbus words. In the field Create/Modify a Modbus Register you can define the index of the Modbus register and the bytes of the can frame that you map in. Click on the frame, insert the valid address in the field Index of Modbus Register, select the byte position (Byte 1 in High Modbus byte and Byte 3 in Low Modbus byte), click the Create button, in the field List of Modbus Registers appears the new Modbus register created with the data that it contains. Figure 5: Define NMEA 2000 window
21 Document code: MN67225_ENG Revision Page 21 of 30 TRANSMIT NMEA 2000: By pressing the Transmit NMEA 2000 button from the main window of SW67225 the window Transmit NMEA 2000 Frames Definition appears (Fig. 6): in this section, it is possible to define the CAN frames that the converter will send to the CAN network. If Device till April 2014 (with Jumper) is set in the section Set Communication, the window appears like below: Figure 6a: Transmit CAN Frame Definition window In the field Priority insert the priority of the frame, in NMEA 2000 protocol is a number among 0,1,2,3,4,5,6,7. The number 0 is the highest priority and 7 is the lowest; In the field PGN insert the PGN of the data you would to write from modbus to NMEA 2000 (in the NMEA 2000 protocol the PGN is an identifier); In the field Source Address you insert the ID of device that sends the frame; If the field Transport Protocol is checked the frame uses Transport Protocol functions; If the field Fast Packet is checked the frame uses Fast Packet functions; In the field Max Byte insert the maximum number of bytes that the PGN will have (only if Transport Protocol is enabled); In the field N Byte Address insert the Modbus register where the number of bytes of the PGN is written. It must be smaller than Max Byte field; In the field Mnemonic the description for the frame is defined.
22 Document code: MN67225_ENG Revision Page 22 of 30 If Device from May 2014 (with Dip-Switches) is set in the section Set Communication, the window appears like below: Figure 6b: Transmit CAN Frame Definition window In the field Priority insert the priority of the frame, in NMEA 2000 protocol is a number among 0,1,2,3,4,5,6,7. The number 0 is the highest priority and 7 is the lowest; In the field PGN insert the PGN of the data you would to write from modbus to NMEA 2000 (in the NMEA 2000 protocol the PGN is an identifier); In the field Source Address you insert the ID of device that send the frame; If the field Transport Protocol is checked the frame uses Transport Protocol functions; If the field Fast Packet is checked the frame uses Fast Packet functions; In the field Max Byte insert the maximum number of bytes that the PGN will have (only if Transport Protocol is enabled); In the field N Byte Address insert the Modbus register where the number of bytes of the PGN is written. It must be smaller than Max Byte field; If the field On Request is checked, the frame is sent when the converter receives the On Request command; If the field Data Change is checked, the frame is sent when the data changes; If the field On Timer is checked, the frame is send cyclically; In the field Time (ms) insert the interval used to send the frame with the option On Timer ; In the field Mnemonic the description for the frame is defined.
23 Document code: MN67225_ENG Revision Page 23 of 30 DEFINE NMEA 2000: By pressing the Define NMEA 2000 button, near Transmit NMEA 2000 from the main window of SW67225 (Fig. 2) the window Define Modbus Registers for Transmit NMEA 2000 appears (Fig. 7). The meaning of the fields of the table are: In the field List of Transmit NMEA 2000 Frames there is the list of frames NMEA 2000 who you inserted in Transmit NMEA 2000 Section; In the field List of Modbus Registers there is the list of Modbus registers you have defined for the selected NMEA 2000 frame; In the field Index of Modbus Register insert a value for the Modbus register; In the field Selecet the Byte to put in the High Part of Modbus Register select which byte of the NMEA 2000 frame you want to save in the high part of Modbus register; In the field Selecet the Byte to put in the Low Part of Modbus Register select which byte of the NMEA 2000 frame you want to save in the low part of Modbus register; In the field Send NMEA 2000 frame on Modbus Write is possible to decide if the NMEA 2000 frame is sent when the related Modbus register is written by the Modbus master. For example: Figure 7: Define NMEA 2000 window Select one of the J1939 frames you have defined, insert a valid address in the field Index of Modbus Register, select the byte position (Byte 1 in high MODBUS byte and Byte 2 in low MODBUS byte), press the Create button. In the field List of Modbus Registers appears the modbus register you have defined.
24 Document code: MN67225_ENG Revision Page 24 of 30 UPDATE VIA SERIAL (only if Device till April 2014 (with Jumper) is set): By pressing the Update Device button it is possible to load the created Configuration into the device, and also the Firmware if is necessary, using the RS232 port. In order to load the parameters or update the firmware in the device, follow these instructions: Turn off the Device; Connect the RS232 Null Modem cable form your PC to the Converter; Put Dip2 of Dip-Switch A in ON position; Select the COM port and press the Connect button; Turn on the device; Check the Device state Led. It must blink quickly (see LEDS section); Press the Next button; Select which operations you want to do. Press the Execute update firmware button to start the upload; When all the operations are OK turn off the device; Put Dip2 of Dip-Switch A in OFF position; Disconnect the RS232 cable; Turn on the device. At this point the configuration/firmware on the device is correctly updated. Figure 8a: Update Device windows
25 Document code: MN67225_ENG Revision Page 25 of 30 UPDATE VIA UDP: By pressing the Update Device button, it is possible to load the created Configuration into the device; and also the Firmware, if necessary. This by using the Ethernet port. If you don t know the actual IP address of the device you have to use this procedure: Turn off the Device; Put Dip2 of Dip-Switch A in ON position; Turn on the device Connect the Ethernet cable; Insert the IP ; Press the Ping button, Device Found! must appear ; Press the Next button; Select which operations you want to do; Press the Execute update firmware button to start the upload; When all the operations are OK turn off the Device; Put Dip2 of Dip-Switch A in OFF position; Turn on the device. At this point the configuration/firmware on the device is correctly updated. If you know the actual IP address of the device, you have to use this procedure: Turn on the Device with the Ethernet cable inserted; Insert the actual IP of the Converter; Press the Ping button, must appear Device Found! ; Press the Next button; Select which operations you want to do; Press the Execute update firmware button to start the upload; When all the operations are OK the device automatically goes at Normal Mode. Figure 8b: Update device windows
26 Document code: MN67225_ENG Revision Page 26 of 30 Note: When you install a new version of the software, if it is the first time it is better you do the update of the Firmware in the HD A1 or HD67225-B2 device. Note: When you receive the device, for the first time, you also have to update the Firmware in the HD67225-A1 or HD67225-B2 device. Warning: If Fig. 9 appears when you try to do the Update try these points before seeking assistance: Check if the serial COM port selected is the correct one; Check if the serial cable is connected between the PC and the device; Try to repeat the operations for the updating; If you are using a USBRS232 converter try with a native COM port or change the converter; Try to repeat the operations for the updating; Try with another PC; Try to restart the PC; Check the LAN settings; Check the Wi-Fi settings; If you are using the program inside a Virtual Machine, try to use in the main Operating System; If you are using Windows Seven, Vista and 8 make sure that you have the administrator privileges; In case you have to program more than one device, using the "UDP Update", you have to cancel the ARP table every time you connect a new device on Ethernet. For do this you have to launch the "Command Prompt" and write the command "arp -d". Pay attention that with Windows Vista, Seven, 8 you have to launch the "Command Prompt" with Figure Administrator 9: Protection Rights; window Pay attention at Firewall lock. In the case of HD67225-A1 or HD67225-B2 you have to use the software SW67225 :
27 Document code: MN67225_ENG Revision Page 27 of 30 MECHANICAL DIMENSIONS: Figure 10a: Mechanical dimensions scheme for HD67225-A1 Figure 10b: Mechanical dimensions scheme for HD67225-B2
28 Document code: MN67225_ENG Revision Page 28 of 30 ORDERING INFORMATIONS: The ordering part number is formed by a valid combination of the following: HD67225 x x Connectors Type 1: Removable 5mm Screw Terminal 2: Fixed 5mm Screw Terminal Enclosure Type A: 1M, 35mm DIN Rail mounting B: 4M, 35mm DIN Rail mounting Device Family HD67225: NMEA 2000 / Modbus TCP slave - Converter Order Code: HD67225-A1 - NMEA 2000 / Modbus TCP slave - Converter Order Code: HD67225-B2 - NMEA 2000 / Modbus TCP slave - Converter ACCESSORIES: Order Code: AC mm Rail DIN - Power Supply 220/240V AC 50/60Hz 12 V AC Order Code: AC mm Rail DIN - Power Supply 110V AC 50/60Hz 12 V AC
29 Document code: MN67225_ENG Revision Page 29 of 30 DISCLAIMER: All technical content within this document can be modified without notice. The content of the document is a under continual renewal. For losses due to fire, earthquake, third party access or other accidents, or intentional or accidental abuse, misuse, or use under abnormal conditions repairs are charged to the user. ADFweb.com S.r.l. will not be liable for accidental loss of use or inability to use this product, such as loss of business income. ADFweb.com S.r.l. shall not be liable for consequences of improper use. OTHER REGULATIONS AND STANDARDS: WEEE INFORMATION Disposal of old electrical and electronic equipment (as in the European Union and other European countries with separate collection systems). This symbol on the product or on its packaging indicates that this product may not be treated as household rubbish. Instead, it should be taken to an applicable collection point for the recycling of electrical and electronic equipment. If the product is disposed correctly, you will help prevent potential negative environmental factors and impact of human health, which could otherwise be caused by inappropriate disposal. The recycling of materials will help to conserve natural resources. For more information about recycling this product, please contact your local city office, your household waste disposal service or the shop where you purchased the product. RESTRICTION OF HAZARDOUS SUBSTANCES DIRECTIVE The device respects the 2002/95/EC Directive on the restriction of the use of certain hazardous substances in electrical and electronic equipment (commonly referred to as Restriction of Hazardous Substances Directive or RoHS). CE MARKING The product conforms with the essential requirements of the applicable EC directives.
30 Document code: MN67225_ENG Revision Page 30 of 30 WARRANTIES AND TECHNICAL SUPPORT: For fast and easy technical support for your ADFweb.com SRL products, consult our internet support at Otherwise contact us at the address RETURN POLICY: If while using your product you have any problem and you wish to exchange or repair it, please do the following: Obtain a Product Return Number (PRN) from our internet support at Together with the request, you need to provide detailed information about the problem. Send the product to the address provided with the PRN, having prepaid the shipping costs (shipment costs billed to us will not be accepted). If the product is within the warranty of twelve months, it will be repaired or exchanged and returned within three weeks. If the product is no longer under warranty, you will receive a repair estimate. ADFweb.com S.r.l. Via Strada Nuova, 17 IT Mareno di Piave TREVISO (Italy) Phone Fax
Document code: MN67595_ENG Revision 1.012 Pagina 1 di 27 User Manual Revision 1.012 English EtherNet/IP / CAN - Converter (Order Code: HD67595-A1) for Website information: www.adfweb.com?product=hd67595
Document code: MN67221F_ENG Revision 2.002 Page 1 of 19 User Manual Revision 2.002 English CAN / Optic Fiber Repeater Extender bus line (With filter data configurable) (Order Code: HD67221F - HD67221FS)
Document code: MN67648_ENG Revision 2.011 Page 1 of 38 User Manual Revision 2.011 English Ethernet / Serial - Converter ( Order Code: HD67648-A1-232 for Serial on RS232) ( Order Code: HD67648-A1-485 for
Document code: MN67513_ENG Revision 1.002 Page 1 of 15 User Manual Revision 1.002 English Gateway / Adapter CAN to Ethernet (Order Code: HD67513 HD67513M) HD67513 for Website HD67513 information: www.adfweb.com?product=hd67513
Document code: MN67302_ENG Revision 1.001 Page 1 of 35 User Manual Revision 1.001 English GSM I/O and Alarms Modem for Website information: www.adfweb.com?product=hd67302 for Price information: www.adfweb.com?price=hd67302-b2-02
Document code: MN67316_ENG Revision 1.013 Page 1 of 41 User Manual Revision 1.012 English CAN Analyzer Hardware and Software (Order Codes: HD67316-U-D1 HD67316-E-A1) for Website information: www.adfweb.com?product=hd67316
BIT COMMANDER Serial RS232 / RS485 to Ethernet Converter (Part US2000A) Copyrights U.S. Converters 1 Contents Overview and Features... 3 Functions..5 TCP Server Mode... 5 Httpd Client Mode.5 TCP Auto mode....6
TCP/IP MODULE CA-ETHR-A INSTALLATION MANUAL w w w. c d v g r o u p. c o m CA-ETHR-A: TCP/IP Module Installation Manual Page Table of Contents Introduction...5 Hardware Components... 6 Technical Specifications...
Setup Manual and Programming Reference Stanford Research Systems Revision 1.05 (11/2010) Certification Stanford Research Systems certifies that this product met its published specifications at the time
IP Sensor and Watchdog IPSW2210 Manual Relay Output Power input 12VDC adapter LED Indicators 1 wire 2 Dry Output Green : Power Yellow: Link temperature & humidity contact inputs LED indicator sensor input
This Quick Start Guide is designed to familiarize the user with the connection and configuration of the DTS-305 DIN rail mounted single / 3 phase power & energy meter with RS-485 or TCP communications.
IntesisBox KNX TCP master Gateway for integration of TCP slave devices into KNX control systems. Integrate any TCP slave device into KNX. KNX TCP slave EIB Bus IntesisBox Ethernet slave LinkBoxEIB Configuration
xepi 2 Diagnostic Unit and Configuration Interface Doc. Version 4.0 Installation Guide English Dear Customer, This "Installation Guide" will help you to install the hardware. If you have any further questions,
RS232 Serial TO Ethernet convert Module USR-TCP232-T Hard Version: V2.0 Doc Version: V1.1 2011-08-16 Jinan USR Technology Co., Ltd. works on LAN and WAN and wireless for MCU to Ethernet Solutions, Ethernet,
GSC/VRC IP Converter Installation and Operation Manual Table of Contents Introduction... 2 Compatibility... 2 Remote Control Hardware... 2 PC Software... 2 Unpacking... 2 Front Panel Indicators... 3 Hardware
IntesisBox ModBus Server - KNX Gateway for integration of KNX equipment into Modbus (RTU and TCP) control systems. Integrate KNX based lighting control into your SCADA, BMS, PLC "talking" Modbus. Master
1 INTRODUCTION This document describes the procedure to upgrade LTMR. Limitation: this package and procedure describe only the upgrade of the LTMR firmware for all network versions (Modbus, Profibus, DeviceNet,
User Manual Protocol Converter PC-E, Serial to Ethernet (RS232/485 Modbus RTU to Modbus TCP/IP) UMPCEA Rev 1.0, 05/2007 COPYRIGHT NOTICE This manual is a publication of Brainchild Electronics Co... Ltd.
For Use with L-GAGE LH Series Sensors Features Converts an LH Network to the 485-RTU protocol Supports baud rates up to 230,400 baud Supports LH Networks with up to 32 sensors Model Protocol Conversion
User Manual EtherUSB USB Ethernet Access Point for PDA V 2.0 Clarinet Systems, Inc. Clarinet Systems, Inc. http://www.clarinetsys.com Page 1 Publication Revision No. Control Table Rev. No. Date Contents
70072-0104-14 TECHNICAL 06/2009 Modbus and ION Technology Modicon Modbus is a communications protocol widely used in process control industries such as manufacturing. PowerLogic ION meters are compatible
Special Note Connection Problems and Handling Methods (CS203 / CS468 / CS469) Sometimes user cannot find the RFID device after installing the CSL Demo App and the RFID reader is connected. If user cannot
User manual Compact Web PLC WP240 series IEC-line update: 09-01-2014 IEC-line by OVERDIGIT overdigit.com 1. General description The WP240 device is a PLC, programmable in IEC61131-3 language using CoDeSys
User s Guide NPD4747-01 EN Contents Contents Copyright and Trademarks Safety Instructions Important Safety Instructions... 4 Cautions and Notes... 4 Getting to Know Your Network Interface Panel Package
User Manual EtherUSB USB Ethernet Access Point for PDA V 1.6 Page 1 Publication Revision No. Control Table Rev. No. Date Contents 1.6 8/22/07 Support connection of multiple WM5.0 devices 1.5 6/18/07 Support
ENET-710 ENET-710 - Ethernet Module JAN / 06 ENET-710 FOUNDATION E N E T 7 1 0 ME smar www.smar.com Specifications and information are subject to change without notice. Up-to-date address information is
LHC Gas Systems 28 th February, 2007 Schneider OS-Loader usage via Ethernet or USB. Jacques ROCHEZ - IT/CO/FE Abstract This document is a guideline on how to configure correctly a PC for the use of the
Broadband Router ESG-103 User s Guide FCC Warning This equipment has been tested and found to comply with the limits for Class A & Class B digital device, pursuant to Part 15 of the FCC rules. These limits
SolarEdge RS485 Expansion Kit Installation Guide Version 1.0 Disclaimers Disclaimers Important Notice Copyright SolarEdge Inc. All rights reserved. No part of this document may be reproduced, stored in
Installation Instructions Universal Serial Bus (USB) to DH-485 Interface Converter Catalog Number 1747-UIC Contents Overview..................................................3 Computer and Operating System
About This Guide 3 About This Guide This user guide is intended for Photovoltaic (PV) system owners, installers, technicians, maintainers, administrators and integrators who are authorized to configure
IntesisBox Server Fidelio IP Gateway for integration of Micros Fidelio Ho management system into (RTU and TCP) enabled control systems. Integrate your Micros Fidelio Ho management system into your master
One Port Serial Server Users Manual Model ESP901, ESP901E Documentation Number: ESP901-2303 International Headquarters B&B Electronics Mfg. Co. Inc. 707 Dayton Road -- P.O. Box 1040 -- Ottawa, IL 61350
KRAMER ELECTRONICS LTD. USER GUIDE Ethernet Configuration Guide (Lantronix) P/N: 2900-300321 Rev 6 Contents 1 Connecting to the Kramer Device via the Ethernet Port 1 1.1 Connecting the Ethernet Port Directly
Kvaser Mini PCI Express User s Guide Copyright 2013-2014 Kvaser AB, Mölndal, Sweden http://www.kvaser.com Printed Sunday 28 th September, 2014 We believe that the information contained herein was accurate
HDTV Anywhere USER MANUAL 3 20672/ 20140710 HDTV Anywhere ALL RIGHTS RESERVED MARMITEK 2 MARMITEK SAFETY WARNINGS To prevent short circuits, this product should only be used inside and only in dry spaces.
Keep it Simple Timing Support... 1 Introduction... 2 Turn On and Go... 3 Start Clock for Orienteering... 3 Pre Start Clock for Orienteering... 3 Real Time / Finish Clock... 3 Timer Clock... 4 Configuring
Sense +V Tx Rx LAN LINK Over ARCNET KBaud BACnet Rx BACnet Tx Archive Valid Port S Tx Port S Rx Low Battery Network- Enhanced Access Default MSTP PTP = Download Required on Rnet and Port S IP Address IP
VFS24/32HDIP Public Display IP Monitor User Manual 2 Contents Before You Begin...4 Side Panel Control buttons...6 Connections...7 OSD Function...7 LCD monitor Mounting Guide...9 Getting started... 10 Power
Application Note: Connecting to a 2500 Series Processor using PLC Workshop This application note will describe a step by step process for the three ways to connect to a 2500-CXXX with PLC Workshop. The
Required information Job Aid Pre-Installation Information S8500 Media Server This job aid provides the information, hardware requirements, and computer hardware and software specifications necessary for
Xbox LIVE Vision Thanks for choosing the Xbox LIVE Vision camera. Xbox LIVE Vision adds video to your Xbox 360 system and games, including: Video chat and picture messages. Photo snapshots. Family Settings
Programming Flash Microcontrollers through the Controller Area Network (CAN) Interface Application te Programming Flash Microcontrollers through the Controller Area Network (CAN) Interface Abstract This
GW-7552 PRIFIBUS/MODBUS GATEWAY Quick Start User Guide 1. Introduction This manual introduces the GW-7552's basic setting and operating quickly, the user can refer to the user manual in the ICP DAS companion
Sollae Systems Co., LTD. ezvsp ver 1.4a Chapter 1 Overview 1.1 Introduction ezvsp is the Windows application support virtual serial port which converts a data on Serial port to Ethernet without modification
IntesisBox Server SAMSUNG Air Conditioners Gateway for monitoring and control of Samsung Air Conditioning Systems from any master device TCP or RTU (BMS, PLC, SCADA, HMI, TouchPanel ) Master TCP Master
RN-XV-RD2 Evaluation Board 2012 Roving Networks. All rights reserved. -1.01Version 1.0 9/28/2012 USER MANUAL OVERVIEW This document describes the hardware and software setup for Roving Networks RN-XV-RD2
Industrial 1 Port RS232/422/485 to Dual Ethernet Serial Device Server NETRS232485 *actual product may vary from photos DE: Bedienungsanleitung - de.startech.com FR: Guide de l'utilisateur - fr.startech.com
NETRS2321E NETRS2321EEU NETRS2321EGB Instruction Manual Serial Over IP Ethernet Device Server 1 Port RS-232/422/485 Serial over IP Ethernet Device Server Manual Revision:10/13/2010 For the most up-to-date
Crow Limited Warranty (Crow) warrants this product to be free from defects in materials and workmanship under normal use and service for a period of one year from the last day of the week and year whose
User Manual Welcome Unleash Your Phone For assistance with installation or troubleshooting common problems, please refer to this User Manual or Quick Installation Guide. Please visit www.vonage.com/vta
CNC File Transfer Box The CNC File Transfer connects a serial CNC device to the network so files can be easily transferred from a computer to the CNC equipment. Any computer on the network can transfer
User's Guide 99 Washington Street Melrose, MA 02176 Phone 781-665-1400 Toll Free 1-800-517-8431 Visit us at www.testequipmentdepot.com Back to the Extech 407780 Product Page Integrating Sound Level Datalogger
WiFly Evaluation Kit 2012 Roving Networks. All rights reserved. Version 1.32r 10/9/2012 USER MANUAL OVERVIEW This document describes the hardware and software setup for Roving Networks evaluation kits,
Type code Ident no. 1545065 Number of channels 2 Dimensions (W x L x H) 108 x 145 x 77.5 mm CoDeSys-programmable acc. to IEC 61131-3 Cable max. 50 m between interface and read/write head 10/100 Mbps Male
CU-111 APRIL 11, 2013 Paragon Explorer Lite Communication Software For Fireye Paragon Scanners using Windows XP DESCRIPTION Paragon Explorer Lite, is the basic PC based configuration tool for Paragon model
AXIS 205 Quick Installation Guide Page 1 of 6 AXIS 205 Network Camera Quick Installation Guide Focus Ring Status Indicator (surrounding the focus ring) Serial number Network Indicator Control Button Power