1 TRP-C31M MODBUS TCP to RTU/ASCII Gateway User s Manual Printed Feb Rev 1.0 Trycom Technology Co., Ltd 1F, No.2-11, Sihu street, Yingge Township, Taipei, Taiwan ROC Tel: , Fax: Web: Copyright Copyright Notice: The information in this manual is subject to change without prior notice in order to improve reliability, design and function and dosed not represent a commitment on the part of the manufacturer. No part of this manual may be reproduced, copied, or transmitted in any form without the prior written permission of manufacturer. Acknowledgment Products mentioned in this manual are mentioned for identification purpose only. Products manes appearing in this manual may or may not be registered trademarks or copyright of their respective companies.
2 1. Introduction. The TRP-C31M, MODBUS gateway allows the legacy MODBUS RTU/ASCII devices to operate on a MODBUS TCP network. It allows either MODBUS serial master or slave to communicate with MODBUS TCP s slave or master. When TRP-C31M function as MODBUS TCP masters to RTU/ASCII slaves : It allows multiple MODBUS TCP masters to communicate with a MODBUS serial network. the queries from different masters are pipelined and processed one by one. When TRP-C31M function as MODBUS RTU/ASCII master to MODBUS TCP slaves: it can connect up to 8 MODBUS TCP slaves. User can specify a UID range for each MODBUS TCP slave. TRP-C31M provides inactive timeout that allows user to specify a time period to disconnect TCP/IP connection to prevent one connection slot was occupied if there is no activity in the network., or prevent any another connection again. A friendly management software provides user an easy way of configuration over Ethernet. TRP-C31M can work at Loop back Mode, all data is sent back immediately. This feature makes the connection testing easy. The industry standard DIN rail and panel mount design enable user a fast and professional installation Features DIN rail or Panel mount. Supports 10/100 Mbps Ethernet. Supports RS-232, RS-422, and RS-485 serial interface. Supports LAN and WAN communications. Management access password protected. High speed up to 230.4Kbps Supports 8 MODBUS TCP master to 31 MODBUS RTU/ASCII slave (up to 31). Supports MODBUS RTU/ASCII master to MODBUS/TCP slave devices (up to 8). Provide inactive timeout for connection auto-recovery when power failures. Automatically generate exception when RTU/ASCII slave device does not response. Remote IP address filtering function to reject unwanted incoming connection source Specifications Output: 64K bytes. Input: 8K bytes. Serial Connection: DTE BD-9 male LAN: 10/100 Mbps Auto-detecting. RS-232: TX, RX, RTS, CTS, DTR, DSR, DCD, GND. RS-422: TX+, TX-, RX+, RX-, RTS+, RTS-, CTS+, CTS-, GND. RS-485: Data +, Data, GND. Data Rate: 110 bps to k bps. Parity: none, even, odd, mark, space. Data Bits: 5, 6, 7 or 8. Stop Bits: 1, 1.5 or 2. Protocol: TCP, IP, ARP, DHCP, Telnet, HTTP, UDP, ICMP.
3 Power Requirements: 9 ~15 VDC / 500 Ma. Operating Temperature: 0 to 60 C. Storage Temperature: -20 to 70 C Humidity: 10~ 90% Non-Condensing. Dimensions: 151mm x 77mm x 26mm. Weight: 377g. 2. Hardware Description 2-1.Panel Layout
4 2-2.Block Diagram 2-3. LED display PWR LED: System is ready. RX LED: Data receiving. TX LED: Data transmitting. 2-4.Reset Button The reset button can be found between the switch and terminal block. To reset the unit manually apply power, insert a small plastic tool, and press lightly depressing switch. Hold for 1 second and release. The Link and Run LED will go out and turn back on Dip Switches A double DIP switch allows the TRP-C31M to be entered into Console/Loop back/default/data Mode. When all these switches are moved into the ON position, thetrp-c31m enters Console Mode, allowing configuration of the TRP-C31M from a PC running a terminal program such as Hyper-terminal. When the TRP-C31M enters Console Mode, the Console Mode screen will appear in the Hyper-terminal program window. The serial port settings must be 8-N-1 at 9600 baud. When the DIP switches are switched to the ON OFF position, the TRP-C31M will work at Loop back Mode, all data is sent back immediately. When the DIP switches are switched to the OFF ON position, the TRP-C31M will revert to its factory
5 version firmware no matter what newer firmware has been upgraded. When all of the DIP switches are switched back to the OFF position, the TRP-C31M will enter Data Mode (RS232, RS422 or RS485). 3. Install TRP-C31M The following information is provided to give the user an understanding of how to connect the TRP-C31M to the LAN and serial device. A review of the switch settings and the functionality of the LED s are also provided. 3-1.Power Connection The TRP-C31M has a two pins terminal block and power jack. Power can apply from either terminal block or the power jack. It accepts 9VDC-15VDC 500mA power supply. When power is applied PWR LED will turn and flash every one second to indicate the system is up and ready. 3-2.Ethernet Connection A straight-through Ethernet cable can be used to connect the MODBUS gateway to an Ethernet hub, switch, or wall plate. A crossover Ethernet cable can be used to make a connection directly to the NIC (Network Interface Card) on a PC or laptop. 3-3.Serial Connection The TRP-C31M has one DB-9 male connector. The serial port is configured as a DTE (data terminal equipment) device just as PC s COM ports. Therefore a null modem cable is required to make a connection between a COM port on a PC to the TRP-C31M serial port. The cable to connect the TRP-C31M serial port to a DCE device must be straight-through. The TRP-C31M has one serial port. The port can be configured as a Console Mode connection or as RS232, RS422 or RS485 interface to the TRP-C31M (if all of the DIP switches are in the OFF position) using the TRP-C3XM software, via Telnet, or using the Web Server DB9 Pin Configuration Pin RS-232 RS-422 RS DCD RXD (-) 2 RXD RXD (+) 3 TXD TXD (+) D (+) 4 DTR TXD (-) D (-) 5 GND GND GND 6 DSR CTS (-) 7 RTS CTS (+) 8 CTS RTS (+) 9 RI RTS (-)
6 4.Serial Port Operational Modes Using the TRP-C3XM Manager software, the serial port of TRP-C31M can be set to Console Mode, Default Mode or Upgrade Mode. The serial port can be configured for RS-232, RS-422 or RS-485 operation. The TRP-C31M also can be set to Console Mode by placing all the DIP switches into the ON position Console Mode The console mode allows TRP-C31M access to the setup menu. This is the way to reconfigure the default settings for the application. A serial connection is made between a COM port on the PC and the serial port on TRP-C31M by using h a null modem cable. In console mode, the serial port defaults to an RS-232 interface. The serial port default settings are, Server name: TRP-C31M Serial number: Fixed Password: Blank DHCP: Disable IP address: Netmask: Gateway : MAC address: Fixed Version & Date: Current firmware version number and date Serial port Baud rate: 9600 Data/Stop bits: 8-1 Parity: None Flow control: None Serial port mode: RS232 MODBUS parameters Serial data format: RTU Character timeout: 10 ms Message timeout: 100ms Inactive timeout: 0 minute (Disabled) Maximum connection: 1 Gateway type: TCP Master to Serial Slave
7 TCP Master to Serial Slave Listening TCP port: TRP-C31M: 502 Use MBAP s UID: Enable Use specific:10 Generate Exception: Off Remote IP address/filter: TCP Slave to Serial master UID range: 1 to 8 Slaves IP address: Destination TCP port: 502 and must be set to VT100 emulation mode. The default settings are used when the first serial port is set to console mode regardless the actual configuration parameters are. See Chapter 9 for console usage details Upgrade Mode The newest firmware can be upgraded to TRP-C31M using the PC s serial port or the Virtual COM port. See Chapter 12 for upgrade details. 4-3.Default Mode When Default Mode is selected and the Gateway Properties are updated (saved), all configuration settings return to their default values. 4-4.RS-232 Mode The RS-232 supports 8 channels plus Signal Ground and is configured as DTE like a computer. Signals are single ended and referenced to Ground. To use handshaking, Flow Control must be set to RTS/CTS during Configuration. Refer to the next Pin out for connections.
8 4-5.RS-422 Mode The RS-422 mode supports 4 channels with full duplex operation for Receive, Transmit, RTS (Request to send) and CTS (Clear to Send). The data lines are in differential pairs. Ground provides a common mode reference. To use handshaking Flow Control must be set to RTS/CTS during configuration. Refer to the next pin out for connections. 4-6.RS-485 Mode The RS-485 mode supports the Transmit and Receive Channels using 2-wire half-duplex operation. The data lines are differential pair Ground provides a common mode reference. Refer to the Pin out table for connections. 5. TRP-C31M Software Installation Trycom TRP-C3XM is a manager software provides user an easy way of TRP-C31M configuration over Ethernet. User may find the software in Trycom support CD or download from Trycom web The configuration of TRP-C31M to meet your LAN and application
9 requirement is an easy process with the available setup menu in the TRP-C3XM manager software. So It is recommended the user install the TRP-C3XM software and do a search for all TRP-C31M on the network. When the searching process is completed, a window will list all the on-line devices, user may make them available for configuration. 5-1.New Installation The following procedures are for the TRP-C3XM Manager Software installation. Step1. Inserting the TRP-C31M support CD in the CD-ROM, it will automatically launch the InstallShield Wizard. To manually start the software installation, select the Start button on the desktop. At the Run command line type D:start.exe, then select OK. The D: is the drive letter for the CD Rom. The InstallShield Wizard window automatically displays to begin the setup procedure. Step2.Select Next when the TRP-C31M Setup window appears.
10 Step3.In the Choose Destination Location window, select Next to install the TRP-C3XM software in the default location, or select Browse to install into a user selected directory. The installation progress will be shown until complete. Step4. Select Finish when the InstallShield Wizard Complete screen appears. When the installation is complete the Install window closes allowing the user to access the Manager software in the program files. If loaded in the default location Go to Start/Programs/Modbus/TRP-C3XM manager to open. Connect the TRP-C31M to the LAN and apply power. The PWE LED will flash indicating power has been applied and communications begin; and the Link LED indicates an Ethernet connection has been made. 5-2.Updating an Existing Installation If an older version of the TRP-C3XM Manager software is already installed, the Modify, Repair or Remove the program window will appear when the installation process is initiated:
11 The recommended procedure is to remove all installed components first. Once the software has been removed, install the new software. 5-3.Using TRP-C3XM Manager Software The Manager software performs several functions: Searching on LAN TRP-C31M. Displaying and changing the configuration of TRP-C31M Installing virtual COM ports on a computer Displaying and configuring virtual COM ports Uninstalling virtual COM ports on a computer Upgrading the TRP-C31M firmware Monitoring Port Status Saving and Loading Configuration Files 5-4. Searching on LAN TRP-C31M Once the TRP-C31M is connected to the LAN the TRP-C3XM Manager software will be able to search all the on LAN TRP-C31M and display them in a window by name and IP address. Select TRP-C3XM Manager in the program file menu. If the default location was selected during the installation the program will be found under Start/Programs/Modbus. Select TRP-C3XM Manager. As soon as the TRP-C3XM Manager opens it will initiate Searching Server and after a few seconds the MODBUS gateway list will display all (TRP-C31M) MODBUS gateways on the local area network.
12 To manually initiate a searching, on the menu side bar double click the Searching Server button. The Search Setup box will appear. It provides two options for searching for servers on the network: Specify the IP address of the MODBUS gateway Search all reachable servers Enter the IP Address assigned to the desired MODBUS gateway or click Search all reachable servers, then OK. The Searching window is shown until all active MODBUS gateways on the LAN are listed in the MODBUS gateway List window Configuring Gateway Properties Highlight the MODBUS gateway in the list window and double click to open the Gateway Properties window. The Gateway Properties window is used to configure and store the Server configuration settings. Details for setting Properties are described in the next chapter. After configuring as needed, click Update to store the configuration in the server and click Yes to restart the server to make sure all settings are changed and conform to the desired application. 6. Gateway Properties
13 There are four ways to access the Gateway Properties and program, the TRP-C3XM manager Software, Console mode, Telnet or Web Server. Instructions on how to move around in the user interface and change settings pertains to the TRP-C3XM Manager software are similar in others. 6-1.Server Configuration Server Name The server name is user configurable. He default server name is TRP-C31M. It is recommended users assign different server name on each TRP-C31M if more than one TRP-C31M connected to the LAN. When the TRP-C3XM Manager software searches for servers on the LAN it will display the server name allowing the user to distinguish between TRP-C31Ms. Serial Number Each TRP-C31M has a unique serial number. This is locked and cannot be changed. Password Entering a password activates a security feature on the MODBUS gateway. Once a password is entered it will be required to access the menu and make changes.
14 Version & Date The currently loaded version of the firmware, and when it was released, are shown here. 6-2.Network configuration DHCP DHCP servers are a part of numerous LAN management systems. The DHCP field has two selections, Enable or Disable. Arrow to the desired selection and select enter. When enabled, TRP-C31M will send a DHCP request to the DHCP server, which will assign a dynamic IP address, Netmask, and gateway to the TRP-C31M. If a DHCP server is not available on the network the TRP-C31M will time out after 10 seconds and the default values will remain. When DHCP is enabled, the IP address, Netmask and Gateway fields become inaccessible and cannot be changed by the user. IP Address A static IP address can also be assigned in this section of the menu. A dynamic address assigned by the DHCP server may change if the TRP-C31M looses the Ethernet connection or power is removed. The host (client) communication software requests a connection to the specific IP address of the MODBUS gateway. If the DHCP reassigns a different IP address the software will
15 not be able to communicate with the hardware. It is recommended to use a static IP address. A static IP address is permanent and will not change unless changed in the menu. In most cases the network administrator establishes the static address to be used. Netmask The default LAN Netmask is configured for a Class C address. This maybe reconfigured by the user. Gateway The gateway IP address allows users to access the MODBUS gateway from outside of the LAN. MAC Address The MAC address is not adjustable. This is assigned in the factory. Every Ethernet device manufactured has it own unique MAC address. Link Status Link status automatically displays the type of Ethernet connection. It will either display 10 Base-T or 100Base-TX in full duplex or half duplex. This will depend on the LAN, switches, hubs used in the LAN topology. 6-3.Serial Interface Configuration
16 Serial Port This field indicates the number of the port for with MODBUS gateway properties are currently being displayed. Changing the number in this field will cause all the other fields to display the properties for the specified port. Note, however, that before changing ports, any change to properties must be updated (Saved), or the MODBUS gateway will not retain them. Baud Rate The serial port baud rate on the TRP-C31M must match the serial baud rate of the connected device unless using Virtual COM mode. In Virtual COM mode the application program can setup this parameter on the fly by sending normal COM command and TRP-C31M will set it on the fly as if TRP-C31M s serial port is one of PC s COM port. Data/Parity/Stop This setting will have to match the data format of the connected device unless using Virtual COM mode. In Virtual COM mode the application program can setup this parameter on the fly by sending normal COM command and TRP-C31M will set it on the fly as if TRP-C31M s serial port is one of PC s COM port. Flow Control The flow control setting must match the connected serial device unless using Virtual COM mode. In Virtual COM mode the application program can setup this parameter on the fly by sending normal COM command and TRP-C31M will set it on the fly as if TRP-C31M s serial port is one of PC s COM port. Serial Port Mode This allows configuration of the MODBUS gateway for the following modes of operation: RS232 When this mode is selected and the gateway is updated, the selected serial port will become a RS232 serial port on the gateway. RS422 When this mode is selected and the gateway is updated, the selected serial port will become a RS422 serial port on the gateway. RS485 When this mode is selected and the gateway is updated, the selected serial port will become a RS485 serial port on the gateway. Console When this mode is selected and the gateway is updated, a PC running a communication program such as Hyperterminal can communicate with the MODBUS gateway via the Console Mode serial port. Upgrade When this mode is selected and the gateway is updated, firmware can be uploaded into the MODBUS gateway via the Console Mode serial port or a virtual COM port mapped to the number of the Console Mode serial port.
17 Default When this mode is selected and the gateway is updated, it will revert the gateway to its default configuration. 6-4.MODBUS configuration
18 Serial Format Serial format define the data format on the serial interface where it is RTU or ASCII. The default setting is RTU. Character Timeout In the MODBUS RTU protocol, character timeout is used to signal the end of a message. If there is an improper timeout occurs during sending message time period, it will cause a CRC checksum error and the message will be discarded. To improve this situation, whenever TRP-C31M receives a byte from its serial port, it will check the data in its buffer and estimate the message length. Base on the message length TRP-C31M calculates CRC checksum. If the CRC checksum matches, we know that is the end of the message. Therefore even there is a timeout error with the message. TRP-C31M can correctly parse the message and convert the MODBUS RTU packet into MODBUS TCP packet. Message Timeout This parameter allows you to set the time during for TRP-C31M to wait for the response message. When message timeout occurs, TRP-C31M would response an exception to MODBUS master if generate exception is enabled. Inactive Timeout Inactive timeout allows TRP-C31M to tear down a TCP/IP connection when there is no activity for a period of time. In case there is a networks failure or power outage. All the TCP/IP connection resource would be occupied by previous connection that prevent from TRP-C31M to accept further incoming connection. Maximum Connection This parameter defines the number of TCP connection to the gateway in either MODBUS TCP master or slave mode. The maximum number of the connection is 8. When TRP-C31M is set as gateway of TCP master to serial slave, it can accept Polling/Query from up to 8 different TCP masters. Each query will handle in sequence since MODBUS serial interface can only handle one query at a time. All other queries will be queued until the previous query is finished or timeout. TRP-C31M can queue up to 8 queries. If there are more than 8 queries at one time, those queries will be discarded and eventually TCP master will get a timeout. Gateway Type This parameter defines what kind of MODBUS devices which TRP-C31M is connected to. There are two types of connection. MODBUS TCP master to MODBUS serial slave. MODBUS TCP slave to MODBUS serial master.
19 The default setting is MODBUS TCP master to MODBUS serial slave. Each serial port in TRP-C31M can be configured into different gateway type. Listening TCP port The default listening MODBUS TCP port number is 502. It is recommended to use port number larger than 1024, if use TCP port number other than 502. Since most of TCP port number under 1024 are used by particular protocol. Use MBAP s UID or Use Specific UID If this parameter is enabled, TRP-C31M will extract the UID in MBAP s header and convert the message into MODBUS serial format with the extracted UID. If this parameter is disabled, TRP-C31 sends the converted message to MODBUS serial slave device with UID defined in the Use Specific UID field. Generate exception When this parameter is enabled, TRP-C31M will generate exception message when slave device does not response to the query command or message timeout. Remote IP Address/filter This is a security feature that is activated when the IP address of the desired client is programmed into the remote IP Address setting of the menu. This tells the TRP-C31M to communicate with only the listed IP address and to filter out all other requests for connection. This feature is only enabled at gateway type TCP Master to Serial Slave. The default setting is It is recommended not to change this setting until the application has been tested and is communicating properly. At that point the address filtering feature of the TRP-C31M can be activated. UID Range TRP-C31M use UID range to map a query from a MODBUS serial master with an UID within this range to an IP address and a TCP port. This is only used when the gateway type is MODBUS TCP slave to MODBUS serial master. Slave IP Address and TCP port This is only used when the gateway type is MODBUS TCP slave to MODBUS serial master. TRP-C31M maps a message from MODBUS serial master to a MODBUS serial slave. 6-5.Update/Save Gateway Properties must be updated separately for each serial port. Updating varies slightly depending on which of the four configuration user interfaces are used. Updating the Gateway Properties in TRP-C3XM Manager Software
20 From the Gateway Properties screen, click the Update button to store the configuration settings for the currently selected port. The vcomui dialogue box will appear indicating you must restart the device before the new settings will take effect. Click Yes. Saving Configuration Data in Console Mode or Telnet Saving (updating) Gateway Properties is done from the Configuration screen. Access the Configuration screen by tabbing through the list of screens on the left side of the window and highlighting Configuration. There are four options shown on the right side of the Configuration screen: Save, Default, Running and Reset. Use Tab, Backspace, or arrow keys to move the cursor to the option position, then press Enter.
21 Save stores the configuration data to the MODBUS gateway flash memory and resets it. Default restores the configuration data to factory default settings. Running restores the configuration data to the last values stored in the flash memory. Reset re-boots the MODBUS gateway, making it available for a client connection. Web Server Interface The Web Server interface provides the same updating options as Console Mode and Telnet. These are located at the bottom of all three Web Server pages. If a field is changed, you must click Save before leaving that page or the changes will be ignored.
22 9 Using Console Mode The console mode allows user to access to the TRP-C31M setup menu. This is the only way to reconfigure the default settings for the application. A serial connection is made between a COM port on the PC and the TRP-C31M serial port A with a null modem cable. In console mode, the serial port defaults to an RS-232 interface. The TRP-C31M serial port default settings are, baud rate 9600, 8 data bits, no parity, and 1 stop bit. Hyper Terminal should be used for this type of setup. Hyper Terminal s serial settings are configured the same as the mentioned default settings of the TRP-C31M and must be set to VT100 emulation mode. The default settings are used only if they have not been changed 9-1 Console Mode Software Install STEP1. Select Hyper Terminal WINDOWS Utility Start ---Accessories---Communications --- Hyper Terminal STEP2.Select New Connection and Enter a name, click OK. STEP3. Enter the COM Port number that TRP-C31M connect using, click OK
23 STEP4. Press the Space bar the TRP-C31M firmware setting screen will show. You can set the TRP-C31M by Console mode. 10. Using Telnet Telnet can be used to configure the TRP-C31M Serial Server from any PC on the LAN. The Telnet window displays the same configuration information shown in Console Mode and allows server properties to be configured. See chapter 6 for details on Server Properties. Ensure the PC and TRP-C31M are connected to the LAN, and the serial server is in RS-232, RS-422 or RS-485 mode before you can telnet to it and access the configuration screens. From the Desktop, click Start, and then run. The Run dialogue box will open. Type in Telnet and the IP
24 address of the Serial Server which to be configured, click OK. STEP1. Select Start then Click RUN then key in the Telnet IP STEP2. Click the OK TRP-C31M firmware setting will show as following screen. You can set the TRP-C31M by Telnet mode.
25 11. Upgrade MODBUS gateway Firmware New firmware may be available at times on our web site and may be downloaded and flashed to the TRP-C31M currently in use. The user can upgrade using a direct connection to the TRP-C31M serial port or the Virtual COM port feature. 1. Download the new upgrade.hex file from and place in a folder. 2. Set TRP-C31M to upgrade mode. Ensure that the DIP switches on OFF position. 3. Connect a null modem cable between the PC and the TRP-C31M. When using the Virtual COM mode a cable is not required. 4. Open the TRP-C3XM Manager software and select the Firmware Upgrade button. 5. In the Serial Port selection options select the COM port number used to connect the PC to the TRP-C31M. If using the Virtual COM port select that number. 6. Select Browse, find the location of the firmware, select Open, and then select the upgrade button.
26 7. A serial menu will appear allowing the upgrade software to be setup the same as the TRP-C31M serial settings. The settings must match or the upgrade will fail. 8. A window showing the Upgrade progress will appear followed by a window indicating the Upgrade was successful. 9. TRP-C31M will reset itself to complete the upgrade process.
One Port Serial Server Users Manual Model ESP901, ESP901E Documentation Number: ESP901-2303 International Headquarters B&B Electronics Mfg. Co. Inc. 707 Dayton Road -- P.O. Box 1040 -- Ottawa, IL 61350
TCP/IP MODULE CA-ETHR-A INSTALLATION MANUAL w w w. c d v g r o u p. c o m CA-ETHR-A: TCP/IP Module Installation Manual Page Table of Contents Introduction...5 Hardware Components... 6 Technical Specifications...
IP Serial Server IPS-101 (1-port) IPS-102 (2-port) IPS-201 (1-port) IPS-202 (2-port) IPS-204 (4-port) User Manual V2.0 2009.03.09 Page: 1 / 62 Copyright This document contains proprietary information that
NPort DE-311 Hardware Installation Guide Fourth Edition, June 2008 www.moxa.com/product 2008 Moxa Inc., all rights reserved. Reproduction without permission is prohibited. NPort DE-311 Hardware Installation
LS-101 LAN to Serial Device server User s Manual Revision History Revision No Date Author Remarks 0.1 August 29, 2001 IDC Initial document INTRODUCTION Overview Almost all instruments and most industrial
BIT COMMANDER Serial RS232 / RS485 to Ethernet Converter (Part US2000A) Copyrights U.S. Converters 1 Contents Overview and Features... 3 Functions..5 TCP Server Mode... 5 Httpd Client Mode.5 TCP Auto mode....6
KRAMER ELECTRONICS LTD. USER GUIDE Ethernet Configuration Guide (Lantronix) P/N: 2900-300321 Rev 6 Contents 1 Connecting to the Kramer Device via the Ethernet Port 1 1.1 Connecting the Ethernet Port Directly
MODEL ATC-2000 TCP/IP TO RS-232/422/485 CONVERTER User s Manual 1.1 Introduction The ATC-2000 is a RS232/RS485 to TCP/IP converter integrated with a robust system and network management features designed
ENET-710 ENET-710 - Ethernet Module JAN / 06 ENET-710 FOUNDATION E N E T 7 1 0 ME smar www.smar.com Specifications and information are subject to change without notice. Up-to-date address information is
16-Port RS232 to USB2.0 High Speed Multi Serial Adapter (w/ Metal Case) Installation Guide 1. Introduction Thank you for purchasing this 16-Port RS232 to USB2.0 High Speed Multi Serial Adapter. It is an
EMG Ethernet Modbus Gateway User Manual Rev 2.2 07/2010 CONTENTS 1. Introduction 1.1. General Features 1.2 Installing the Drivers 2. Configuration 2.1 Main Device Parameters 2.1.1 RS485 Serial Communication
IP-COM-M IP-COMi-M IP-COM-M PoE IP-COMi-M PoE RS-232 RS-232/422/485 RS-232, Power over Ethernet RS-232/422/485, Power over Ethernet Edition: September 2012 The computer programs provided with the hardware
1 NPort 6110 Modbus/TCP to Serial Communication Gateway User s Manual Second Edition, November 2004 Moxa Technologies Co., Ltd. Tel: +886-2-8919-1230 Fax: +886-2-8919-1231 Web: www.moxa.com MOXA Technical
Serial over Ethernet Device Server User s Manual Second Edition, November 2005 SUNIX Co., Ltd. Tel : +886-2-8913-1987 Fax: +886-2-8913-1986 Http://www.sunix.com.tw email@example.com Serial over Ethernet
Setup Manual and Programming Reference Stanford Research Systems Revision 1.05 (11/2010) Certification Stanford Research Systems certifies that this product met its published specifications at the time
Tu Sitio de Automatización! LBNP16312 RS-232/485/422 serial device server User manual Summarize-----------------------------------------------------------------------------14-3 Package checklist---------------------------------------------------------------------14-3
How to setup a serial Bluetooth adapter Master Guide Nordfield.com Our serial Bluetooth adapters part UCBT232B and UCBT232EXA can be setup and paired using a Bluetooth management software called BlueSoleil
NETRS2321E NETRS2321EEU NETRS2321EGB Instruction Manual Serial Over IP Ethernet Device Server 1 Port RS-232/422/485 Serial over IP Ethernet Device Server Manual Revision:10/13/2010 For the most up-to-date
Operation Manual of EX-9132C-2 Serial to TCP/IP Converter Version 1.2.1 20th May 2013 Table of Contents 1. Introduction 3 Overview 4 Package Checklist 4 Block Diagram 5 Features 6 Product Specifications
Programming and Using the Courier V.Everything Modem for Remote Operation of DDF6000 1.0 Introduction A Technical Application Note from Doppler System July 5, 1999 Version 3.x of the DDF6000, running version
USER MANUAL GUIMGR Graphical User Interface Manager for FRM301/FRM401 Media Racks CTC Union Technologies Co., Ltd. Far Eastern Vienna Technology Center (Neihu Technology Park) 8F, No. 60 Zhouzi St. Neihu,
PURPOSE Verify that communication is established for the following products programming option (488.2 compliant, SCPI only): DCS - M9C & DCS M130, DLM M9E & DLM-M9G & DLM M130, DHP - M9D, P series, SG,
RS-232/422/485 to 10/100Base-TX Device Server / Managed Media Converter (IRF-633) User s Manual COPYRIGHT All rights reserved. No part of this publication may be reproduced, stored in a retrieval system,
MODEL ATC-2004 TCP/IP TO RS-232/422/485 CONVERTER User s Manual 1.1 Introduction The ATC-2004 is a 4 Port RS232/RS485 to TCP/IP converter integrated with a robust system and network management features
Broadband Router ESG-103 User s Guide FCC Warning This equipment has been tested and found to comply with the limits for Class A & Class B digital device, pursuant to Part 15 of the FCC rules. These limits
Prestige 324 Intelligent Broadband Sharing Gateway Version 3.60 January 2003 Quick Start Guide 1 Introducing the Prestige The Prestige is a broadband sharing gateway with a built-in four-port 10/100 Mbps
ICS-2 S15 Industrial RS-232/ RS-422/ RS-485 over Ethernet Media Converter Cost Effective Solution for RS-232 / RS-422 / RS-485 to Industrial Ethernet Application PLANET ICS-210x series Smart Media Converter
IntesisBox ModBus Server - KNX Gateway for integration of KNX equipment into Modbus (RTU and TCP) control systems. Integrate KNX based lighting control into your SCADA, BMS, PLC "talking" Modbus. Master
T3 Mux M13 Multiplexer User Manual [Type the abstract of the document here. The abstract is typically a short summary of the contents of the document. Type the abstract of the document here. The abstract
70072-0104-14 TECHNICAL 06/2009 Modbus and ION Technology Modicon Modbus is a communications protocol widely used in process control industries such as manufacturing. PowerLogic ION meters are compatible
isco Connecting Routers Back to Back Through the AUX P Table of Contents Connecting Routers Back to Back Through the AUX Ports...1 Introduction...1 Before You Begin...1 Conventions...1 Prerequisites...1
Prestige 324 Intelligent Broadband Sharing Gateway Version V3.61(JF.0) May 2004 Quick Start Guide 1 1 Introducing the Prestige The Prestige is a broadband sharing gateway with a built-in four-port 10/100
Configuration Gateway > WAN Page Gateway: LAN nat config Page Gateway: LAN dhcp server config Page Gateway LOG Page Preparing the Network Preparing the Computers for TCP/IP Networking Configuring TCP/IP
Prestige 650R-31/33 Read Me First Prestige Rear Panel Connections PORT DSL CONSOLE LAN 10/100M POWER Connect to a telephone jack using a telephone wire. CONNECTION Connect to a serial port (COM port) on
Chapter 10 Troubleshooting This chapter provides troubleshooting tips and information for your ProSafe Dual WAN Gigabit Firewall with SSL & IPsec VPN. After each problem description, instructions are provided
1 Port RS232 Serial over IP Device Server NETRS232 *actual product may vary from photos DE: Bedienungsanleitung - de.startech.com FR: Guide de l'utilisateur - fr.startech.com ES: Guía del usuario - es.startech.com
Application Note 2 Using the TCPDIAL & TCPPERM Commands to Connect Two TransPort router Serial Interfaces Over TCP/IP. Reverse Telnet or Serial Terminal Server MultiTX feature UK Support March 2014 1 Contents
Prestige 314 Read Me First Console WAN 10M PORT Prestige Rear Panel Connections CONNECTION Use an RS-232 console cable. Use the cable that came with your broadband modem. LAN 10/100M Port Number COMPUTER
RS232C < - > RS485 CONVERTER S MANUAL Model: LD15U INTRODUCTION Milestone s model LD-15U is a RS232 to RS 485 converter is designed for highspeed data transmission between computer system and or peripherals
Serial to Bluetooth Adapter Serial (RS-232) to Bluetooth Class 1 Adapter ICRS232BT1 Actual product may vary from photo FCC Compliance Statement This equipment has been tested and found to comply with the
GV-Data Capture V3 Series User's Manual Before attempting to connect or operate this product, please read these instructions carefully and save this manual for future use. 2006 GeoVision, Inc. All rights
Applications What are some of the applications for the Model 2120 Single Port Terminal Server? The Patton Single Port RS-232 Terminal Server provides the ability to bring virtually any RS-232 device onto
Print Date: 04.03.2010 Testing Serial Cards Instructions on How to Use HyperTerminal to Test Serial Ports... Brain Boxes Limited, Unit 3C, Wavertree Boulevard South, Wavertree Technology Park, Liverpool,
Using HyperTerminal with Agilent General Purpose Instruments Windows HyperTerminal can be used to program most General Purpose Instruments (not the 531xx series counters) using the RS-232 Serial Bus. Instrument
VSCOM USB PRO Series Industrial I/O Adapters 1.Introduction The VSCOM USB PRO Series Industrial I/O Adapters are advanced USB to Serial Adapters that connect to 1, 2, 4 or 8 RS-232/422/485 serial devices.
ProSafe Plus Switch Utility User Guide 350 East Plumeria Drive San Jose, CA 95134 USA December 2012 202-10524-05 NETGEAR, Inc. All rights reserved No part of this publication maybe reproduced, transmitted,
User Guide Modbus Communications for PanelView Terminals Introduction This document describes how to connect and configure communications for the Modbus versions of the PanelView terminals. This document
Monitoring For Business-Critical Continuity Liebert IntelliSlot Web Cards Firmware Upgrade Manual Liebert IntelliSlot Web Card, Liebert IntelliSlot Web Card-LB, Liebert IntelliSlot Web Card-LBDS, Liebert
Contents of Package: DG-102S VoIP Station Gateway Power adapter CD-ROM, including User s Manual Quick Install Guide Requirements: RS-232 Console Cable Two RJ-45 CAT-5 Straight-Through Cables For more information
Panduit Corp. 2010 TDP43ME NetPS PA26306A01 Rev. 01 11-2010 Network Printer Server Control Center for Ethernet Module NOTE: In the interest of higher quality and value, Panduit products are continually
UPS Network Interface Quick InstallationGuide Version 1.1 March 1999 COPYRIGHT Copyright 1999 RINGDALE UK Limited. All rights reserved. No part of this publication may be reproduced, transmitted, transcribed,
User Manual EtherUSB USB Ethernet Access Point for PDA V 2.0 Clarinet Systems, Inc. Clarinet Systems, Inc. http://www.clarinetsys.com Page 1 Publication Revision No. Control Table Rev. No. Date Contents
Products: EFA with EFA Scan, DVRM and DVMD with Realtime Monitor or Stream Explorer DVMD-B1 LAN / WAN Connection Of Instruments with Serial Interface By Using a Terminal Server Remote control of test and
2-Port RS232/422/485 Combo Serial to USB2.0 Adapter (w/ Metal Case and Screw Lock Mechanism) Installation Guide 1. Introduction Thank you for purchasing this 2-Port RS232/422/485 Combo Serial to USB Adapter.
ProSAFE 8-Port and 16-Port Gigabit Click Switch Model GSS108E and GSS116E User Manual March 2015 202-11520-01 350 East Plumeria Drive San Jose, CA 95134 USA Support Thank you for selecting NETGEAR products.
Serial-Ethernet Server User s Manual Version 1.3 IMPORTANT ANNOUNCEMENT The information contained in this document is the property of Aaxeon Technologies, LLC and is supplied for the sole purpose of the
CNC File Transfer Box The CNC File Transfer connects a serial CNC device to the network so files can be easily transferred from a computer to the CNC equipment. Any computer on the network can transfer
ETHERNET WEATHER STATION CONNECTIONS Application Note 33 With WeatherLink and a Device Server INTRODUCTION It is possible to substitute an Ethernet connection for the direct USB or serial connection that
Technical Note D64 0815 RS-232 COMMUNICATIONS RS-232 is an Electronics Industries Association (EIA) standard designed to aid in connecting equipment together for serial communications. The standard specifies
Linksys Gateway SPA2100-SU Manual Manuel de l'utilisateur Table of Contents Looking for Basic Setup Instructions?... 3 Most Recent Version of this Manual... 3 Advanced Setup Instructions... 4 Wiring Your
Hardware Installation and Configuration Guide Trademark Notices Comtrol, DeviceMaster, and PortVision are registered trademarks of Comtrol Corporation. Ethernet is a registered trademark of Digital Equipment
ZyWALL 5 Internet Security Appliance Quick Start Guide Version 3.62 (XD.0) May 2004 Introducing the ZyWALL The ZyWALL 5 is the ideal secure gateway for all data passing between the Internet and the LAN.
APPENDIX A This appendix provides the connector and pinout information you need for making or purchasing cables used with Cisco VG224 voice gateway. To order cables from Cisco, see the Obtaining Technical
GS_GSR_GCR_UserManual_App_E_MOXA_V01.doc / 17.08.2009 GeoSIG Ltd. Appendix E Page E-1 1. MOXA NPort Express TCP/IP to RS-232 server 1.1. General Explanations The NPort Express RS-232/422/485 Device server
DIRECT INTERNET DATA User s Guide Iridium Satellite LLC Rev. 2; June 15, 2001 DIRECT INTERNET DATA ------------------------------------------------------------------------------------- TABLE OF CONTENTS
32 Transferring Projects and Data This Chapter explains how to transfer GP-Pro EX project files to the GP and how to transfer the project files stored on the GP to your PC. Please start by reading 32.1
LHC Gas Systems 28 th February, 2007 Schneider OS-Loader usage via Ethernet or USB. Jacques ROCHEZ - IT/CO/FE Abstract This document is a guideline on how to configure correctly a PC for the use of the
7.7 Ethernet Communication (AFPX-COM5) 7.7.1 AFPX-COM5 Overview The communication cassette AFPX-COM5 has an Ethernet interface at the COM1 port and a 3-wire RS232C interface at the COM2 port. The Ethernet
NETGEAR, Inc. 4500 Great America Parkway Santa Clara, CA 95054 USA 208-10060-01 2006-03-17 2006 by NETGEAR, Inc. All rights reserved. Trademarks NETGEAR is a trademark of Netgear, Inc. Microsoft, Windows,
Quick Start Guide 2008 Copyright Lantronix is a trademark of Lantronix. All rights reserved. 900-447 Rev. B 7/08 QUICK START CONTENTS What s In the Box..........................................................2
www.prilink.com PRILINK PRI MANAGEMENT SSTEM INSTALLATION GUIDE PRI Management PRILINK PRI Management System Installation Guide Version 3.0, Rev. 12-01-24 Page 1 Table of Contents 1 HARDWARE INSTALLATION...
University of Jordan Faculty of Engineering & Technology Computer Engineering Department Computer Networks Laboratory 907528 Lab. 2 Network Devices & Packet Tracer Objectives 1. To become familiar with
Chapter 1 Installing the Gateway This chapter describes how to set up the wireless voice gateway on your Local Area Network (LAN), connect to the Internet, and perform basic configuration. For information
This document covers tasks associated with connecting a console port to a PC, and includes the following topics: Console (rollover) Cable and Adapters Making the physical connection Connecting using HyperTerminal
Cable Pinouts C This appendix lists the cables and connector pinout assignments for the cables used with the ERX-700 series and ERX-1400 series. Topic Page SRP I/O Module C-1 CT1 and CE1 I/O Modules C-4