SinglePhase. ThreePhase


 Clyde Butler
 3 years ago
 Views:
Transcription
1
2 ThreePhase Transformers When more power is needed  three transformers can be tied together. This is called threephase. Here s a simple way of comparing singlephase to threephase power. SinglePhase ThreePhase Think of singlephase as one guy driving a stake into the ground; Threephase as three guys, working together, driving the same stake into the ground. 25
3 Generating ThreePhase Threephase power is delivered from a generator with three separate windings. These windings are equally spaced around a rotating cylinder (rotor) with each winding occupying onethird of the rotor circumference. Threephase generator windings are spaced 120 apart for a total of Because the three source voltages timed at three different intervals, they can be transmitted over just three conductors (rather than the six conductors needed to transmit three separate singlephase loads) A threephase system can produce 173% higher effective voltage than a singlephase system. This is very useful for higher power loads such as large motors. 26
4 We calculate the total voltage (of all three lines of a threephase transformer) by multiplying the voltage of each single winding (phase) by the square root of 3 (!3). The reason for this is the angles of each phase are always 120 apart By using this trigonomic formula (don t get scared) we can see where we derive the square root of three. sin = =!3 sin Wye Connection One way of tying three transformers together is in parallel (+ to +) and ( to ). This is called a Wye connection. Here s how a Wye connection is wired: Line Phase eutral 27
5 We call each of the singlephase transformer windings Phases.The combination (hooked together) of the three singlephase transformers ( ) is called the Line. We really only draw threephase from the Line side. Also, Line Amps on a Wye connected transformer equals Phase Amps. It would seem that current would not remain the same in a parallel circuit. But, three transformers wired in parallel are not like three resistors in parallel. Transformers produce, instead of consume voltages, so the opposite rules would would apply in this case. A more simplified representation of a Wye looks like this: A B C If we tie together three singlephase, olt, transformers in a Wye configuration our output voltage would look like this: 208 v 3Ø Why do we get 208 volts, threephase on the Line side ()? Just multiply olts times the square root of 3 (!3). Remember phase angles of three olt sources. olts x (!3) = 208 volts 28
6 We can also get 208 volts, singlephase on the Line side of this transformer by connecting (); "A" 208 v 1Ø "C" "B" As you see, we are connecting only two of the three singlephase transformers available. We still only get 208 volts (120 x!3) from this connection, and it is just singlephase. But, we have the capability of using two transformers ( A & B ) to help share the load. Also, we can use two other possible connections () and () to feed other 208 volt, singlephase loads. Guess what! Yes, it s even possible to get olts, singlephase out of the same transformer. "A" "C" "B" 1Ø Remember, we have the benefit of a neutral conductor and, by connecting () we can feed olt, singlephase loads. And, seeing that we are only using one singlephase transformer ( B ), that leaves two other possibilities ( ) and () for serving other olt circuits. What s also very useful is that we can balance three olt circuits on just one neutral. In other words, A 208/olt (Wye configured) transformer could supply olt, singlephase equipment (like fluorescent lights), 208 volt, singlephase 29
7 equipment (like range or oven), and 208 volt, threephase equipment (like heavy machinery). This is what makes threephase so great! Delta Connections Another way of tying three transformers together is in series (+ to ). This is called a Delta connection. Here s how a Delta connection is wired: Line Phase A more simplified representation of a Delta configuration looks like this: A B C 30
8 By connecting three (240 volt) singlephase transformers (Delta) we get 240 volts, threephase. We don t multiply by!3 because Line volts equals Phase volts on Delta transformers. It would seem that voltage, would not remain the same in a series type circuit. But, three transformers wired in series are not like three resistors in series. Transformers produce, (instead of consume) voltages, so the opposite rules would would apply in this case. 240 v 240 v 240 v 240 v 3Ø Connect () and you ll get 240 volts, singlephase. Connecting () or () will also give us 240 volts, singlephase. otice how three different 240 volt (1Ø) loads utilize three different transformers. 240 v 240 v 240 v 240 v 1Ø We can still get olts, (singlephase) out of a 240 volt Delta system, but it s going to take some additional work. We are going to have to centertap one of the 240 volt, singlephase transformers. It s customary to centertap transformer C... "C" 240 v, 1Ø, 1Ø 31
9 As you can see, we can get olts, (singlephase) from a Delta configuration () (). Unfortunately, all olt loads must be carried on transformer C. Types Of ThreePhase Transformers With the possibility of wiring both the primary and secondary of threephase transformers, there are four possible configurations: (1) Wye/Wye is commonly used for interior wiring systems. (2) Wye/Delta is used to stepdown utilities high line voltages. (3) Delta/Delta is often used for industrial applications. (4) Delta/Wye is popular for stepping down transmission lines to fourwire services when neutrals are needed. The most commonly used threephase transformer is a Delta/Wye configuration. It s used primarily for power distribution from utilities to residential and commercial services. 480 v 3Ø Primary 480 v 480 v 480 v Secondary 208 v 1Ø 208 v 3Ø 1Ø The given voltage designations for a Delta/Wye threephase transformer is: PrimaryLine/SecondaryLine/SecondaryPhase Or in this case: Delta/Wye (480/208/120) 32
10 PhaseToPhase Let s not forget that threephase is a product of three individual singlephase transformers. When calculating the PhaseToPhase relationship the same rules apply as any singlephase transformer. In other words, Our PhaseTo Phase voltage below is 480 to 120 which is a ratio of 4:1. Line Phase Phase Line "A" 480 v "A" "B" 480 v R A T I O "A" eutral "C" 480 v "A" We can also use the the same ladder chart we used for a typical singlephase transformer. Primary Phase Secondary Phase x VA R 480 A 120 T I O x Don t forget that this is just one of three singlephase transformers. There may be efficiency or power factor losses between the primary and secondary phases. But, we ll assume that this transformer is 100% efficient with no power factor loss so the Primary va will equal the Secondary Watts. 33
11 Calculate the Primary va, Primary Amps and Secondary Watts assuming that our Secondary Amps = 100. Primary Phase Secondary Phase x 480 VA R A T I O x Did you get 12,000 Primary va? Multiplying 12,000 by 3 (three transformers) will give us 36 kva (36,000 va). We ll call this our Line kva, which is the sum total of all threephases. In other words, our transformer rating is 36 kva. It s important to understand the difference between Phase and Line. Phase is the singlephase transformer relationship. Line is the result of the combination of all three transformers hooked together. LineToLine There are a few of rules we must remember. (1) Line Watts = Phase Watts x 3 (or) Phase Watts = Line Watts 3 (2) Delta Phase Volts = Delta Line Volts (3) Wye Phase Amps = Wye Line Amps Yes, we can use the ladder LineToLine on threephase transformers Check this out... Primary Secondary! 3 VA 36, ! 3 36, x! 3 x! 3 34
12 For example, knowing the values of Secondary Line Amps (100) and Secondary Line Volts (208) we would multiply going up the ladder to find Secondary Line Watts. In this case, because we are dealing with threephase, we ll multiply our answer by!3 (1.732). Here s what it looks like... Line Amps (100) x Line Volts (208) x!3 (1.732) = Line Watts (36,000) I know! You get 36, watts. The problem is that 208 volts (3Ø) is not exactly 208 volts. olts x = So we round up! Remember, whenever we see 3Ø, the square root of three!3 must be involved. On the Primary side. stepping down the ladder... Primary va (36,000) Primary Volts (480)!3 (1.732) = Primary Amps (43.3) The key to using the ladder in threephase is multiplying the answer by!3 going up the ladder, and divide the answer by!3 going down the ladder. Here s a chart that may be useful.!3 va e i x!3 delta line line volts=phase volts amps phase to phase va e i line phase!3 watts line phase 3 w e i volts line phase!3 wye line w e i line amps=phase amps!3 x!3 On the bottom of this chart are a few helpful tools: For the Delta side Amps... line amps phase amps x!3 For the Wye side Amps... line volts phase volts x!3 For the Watts... line watts phase watts x 3 Just cover the value you need to know. For example: line amps = phase amps x!3 (or) phase amps = line amps/!3 35
13 Here s one for you to try; Primary Secondary! 3 VA ! x! 3 x! 3 Delta/Delta A Delta/Delta connected transformer looks like this... Primary Secondary! 3 VA! 3 x! 3 x! 3 There are the rules we must remember. (1) Line Watts = Phase Watts x 3 (or) Phase Watts = Line Watts 3 (2) Delta Phase Volts = Delta Line Volts PhaseToPhase Although our transformer is connected Delta/Delta the PhaseToPhase situation has not changed. We still have three singlephase transformers. Let s do some calculations for a Delta/Delta 480/240/120 transformer. First we must find the Secondary Watts, then the Primary va and Primary Amps... 36
14 Primary Phase Secondary Phase x 480 VA R A T I O x Then, we can calculate the values for Line... Primary Secondary! 3 VA 480! 3 7, x! 3 x! 3 3Ø Transformer Size Chart FullLoad Current In Amps At The Line Voltages Listed Below kva Rating olts 240 volts 480 volts 600 volts 2400 volts 4160 volts kva = ( full load current x voltage x!3) 1,000 37
15 Wye Transformer Balancing We might have forgotten the real purpose of a threephase transformer which is to serve loads. Wye connected 208/olt secondaries can feed loads at three different levels: (1) 208 volts, 3Ø () (2) 208 volts, 1Ø () or () or () (3) olts, 1Ø () or () or () "A" "B" "C" A 208 volt (3Ø) load would be distributed on all three Phases... 1/3 on Phase A 1/3 on Phase B 1/3 on Phase C A 208 volt (1Ø) load would be distributed on two Phases... 1/2 on one Phase 1/2 on one Phase A olt (1Ø) load would be distributed on one Phase % on any one Phase For example, Let s balance the following loads Ø, 208 volt, Motor at 9,000 watts 31Ø, 208 volt, Ovens at 6,000 watts each 31Ø, olt, Light Circuits at 1,800 watts each 38
16 The 208 volt (3Ø) Motor can be distributed on all three Phases... Load Phase A Phase B Phase C Motor (3Ø) 3,000 w (1/3) 3,000 w (1/3) 3,000 w (1/3) The three 208 volt (1Ø) Ovens can be distributed on two Phases each... Load Phase A Phase B Phase C Oven (1Ø) 3,000 w (1/2) 3,000 w (1/2)  Oven (1Ø) 3,000 w (1/2) 3,000 w (1/2) Oven (1Ø) 3,000 w (1/2) 3,000 w (1/2) The three olt (1Ø) Light Circuits can be distributed on one Phases each... Load Phase A Phase B Phase C Light Ckt (1Ø) 1,800 w (100%)   Light Ckt (1Ø)  1,800 w (100%)  Light Ckt (1Ø)   1,800 w (100%) Totals 10,800 w 10,800 w 10,800 w So, our total demand is 32,400 watts (10,800 x 3). We re lucky, our loads balanced evenly, otherwise, we would have to multiply our largest Phase by three. Looks like we need a 45 kva (standard size) Wye/Wye or Delta/Wye connected transformer. Delta Transformer Balancing What if we had a Delta connected (240/) secondary Delta connected 240/olt secondaries can also feed loads at three different levels: (1) 240 volts, 3Ø () (2) 240 volts, 1Ø () or () or () (3) olts, 1Ø () or () A 240 volt (3Ø) load would be distributed on all three Phases... 1/3 on Phase A 1/3 on Phase B 1/3 on Phase C A 240 volt (1Ø) load would be distributed 100% on one Phase only... 39
17 100% on Phase A 100% on Phase B 100% on Phase C A olt (1Ø) load would be distributed on Phase C only % on Phase C only Let s balance the same loads on a Delta Ø, 208 volt, Motor at 9,000 watts 31Ø, 208 volt, Ovens at 6,000 watts each 31Ø, olt, Light Circuits at 1,800 watts each The 240 volt (3Ø) Motor can be distributed on all three Phases... Load Phase A Phase B Phase C Motor (3Ø) 3,000 w (1/3) 3,000 w (1/3) 3,000 w (1/3) The three 240 volt (1Ø) Ovens can be distributed on one Phase each... Load Phase A Phase B Phase C Oven (1Ø) 6,000 w (100%)   Oven (1Ø)  6,000 w (100%)  Oven (1Ø)   6,000 w (100%) The three olt (1Ø) Light Circuits can be distributed on Phase C only... Load Phase A Phase B Phase C Light Ckt (1Ø)   1,800 w (100%) Light Ckt (1Ø)   1,800 w (100%) Light Ckt (1Ø)   1,800 w (100%) Totals 9,000 w 9,000 w 14,400 w Poor old Phase C has to carry 1/3 of all threephase loads, 100% of any 240 volt (1Ø) loads that distributed on it, and 100% of all olt loads. Our total demand is 43,200 watts (14,400 x 3). This time we re not so lucky, our loads did not balanced evenly. But, we can still use a 45 kva (standard size) Wye/Delta or Delta/Delta connected transformer. 40
18 Open Delta One benefit of a Delta threephase configuration is that it can still work with just two singlephase transformers. An OpenDelta or Vconnected transformer can be used in a emergency or temporary situation.the only problem is that there is a power reduction to just 57.7% of full power. Primary Secondary A third singlephase transformer can be added later if needed. Or, if one original transformer should fail, it can be removed temporarily for repair. In this situation, partial service can be maintained temporarily. ThreePhase Transformer Sample Problem Problem: Calculate the threephase 480/208/olt transformer required to feed the following loads: one 10 hp, 208 volt, 3Ø Motor (11,096 w) three 3 kw, 208 volt, 1Ø Heaters three 1 kw, olt, 1Ø Light Banks Solution: Loads Balanced: Phase A Phase B Phase C 3Ø Motor (1/3 per phase) 3,699 w 3,699 w 3,699 w 1Ø Heaters (1/2 per phase) 1,500 w 1,500 w   1,500 w 1,500 w 1,500 w  1,500 w 1Ø Light Banks (100% per phase) 1,000 w ,000 w w 7,699 w 7,699 w 7,699 w 41
19 !3 va e i x!3 delta line line volts=phase volts amps phase to phase va e i line phase!3 watts line phase 3 w e i volts line phase!3 wye line w e i line amps=phase amps!3 x!3 Voltages: Primary Line = 480 volts Secondary Line = 208 volts Primary Phase = 480 volts Secondary Phase = olts Amps: Primary Line = 27.7 amps Secondary Line = 64 amps Primary Phase = 16 amps Secondary Phase = 64 amps Wattage: Primary Line = 23,096 watts Secondary Line = 23,096 watts Primary Phase = 7,699 watts Secondary Phase = 7,699 watts Use (25 kva) rated, 3Ø, 480/208/olt transformer. 42
20 Transformer Problems (1) The phase current of a fully loaded 36 kva, 208/olt, threephase transformer would be amps. (a) 300 (b) 175 (c) 100 (d) 75 (2) If ten single phase 208 volt, 5000 watt office machines were on the same transformer, the total current with all the machines operating would be amps. (a) 120 (b) 208 (c) 240 (d) 416 (3) With a threephase, deltawye transformer bank having a 480 volt primary and a 208/olt secondary, the line current of the secondary is 120 amps. The primary line current will be amps. (a) 480 (b) 208 (c) 52 (d) 30 (4) The voltage from either leg, excluding the hileg, to neutral of a threephase, deltadelta hileg transformer system with a secondary of 240/120 volts is volts. (a) 120 (b) 190 (c) 208 (d) 240 (5) If all the load on a threephase 480/208/olt transformer is singlephase olt, the size of the neutral on a 24 kva transformer would have a load current rating of amps. (a) 24 (b) 67 (c) 75 (d) 100 (6) If a threephase wattmeter reads 12,970 watts on a threephase 208/120 volt system and each ammeter reads 36 amps, the power factor would be. (a) 1 (b).96 (c).62 (d) none of these (7) With a threephase deltadelta, hileg transformer system, the primary is 480 volts, and the secondary is 240/olts, the turns ratio for the transformer is. (a) 2 to 1 (b) 4 to 1 (c) 1 to 4 (d) 1 to 2 43
21 (8) If three 115 volt, 1,800 watt lighting circuits and two 2 H.P. singlephase 115 volt pumps are balanced as closely as possible on a threewire 230 volt system. The conductor amp rating will be approximately amps. (a) 15 (b) 45 (c) 48 (d) 54 (9) The secondary load of a threephase 480/208/olt includes; 1 Motor (3 hp, 3Ø, 208 volt) 4 Heat Strips (2500 va, 3Ø, 208 volt) 1 Induction Heater (2000 va, 1Ø, 208 volt) 3 Light Banks (1500 va, 1Ø, olt) Calculate Primary Feeder? Secondary Phase Current? Transformer Size Required? (10) Determine the threephase transformer requirements based on the following loads: (voltages are 480/208/olts connected DeltaWye) 1 Motor (15 hp, 3Ø, 208 volt) 5 Water Heaters (2500 va, 1Ø, 208 volt) 2 Dryers (1500 va, 1Ø, 208 volt) 1 Cooktop (1600 va, 1Ø, 208 volt) 4 Light Circuits (3000 va, 1Ø, olt) Calculate Primary Feeder? Secondary Phase Current? Transformer Size Required (kva)? 44
Module 19 Units 13 ThreePhase Transformers
Module 19 Units 13 ThreePhase Transformers 1. What is the difference between a threephase transformer and a bank of singlephase transformers? Windings from all three phases are wound on the same core
More informationChapter 24. ThreePhase Voltage Generation
Chapter 24 ThreePhase Systems ThreePhase Voltage Generation Threephase generators Three sets of windings and produce three ac voltages Windings are placed 120 apart Voltages are three identical sinusoidal
More informationThreephase AC circuits
Threephase AC circuits This worksheet and all related files are licensed under the Creative Commons Attribution License, version 1.0. To view a copy of this license, visit http://creativecommons.org/licenses/by/1.0/,
More informationA fter studying this unit, you should be able to:
Unit 12 ThreePhase Circuits objectives A fter studying this unit, you should be able to: Discuss the differences between threephase and singlephase voltages. Discuss the characteristics of delta and
More informationTransformer Calculations
Transformer Calculations Transformers Transformers are one of the most basic yet practical devices used today. No matter where you are there is always a transformer nearby. They are used throughout alternatingcurrent
More informationFigure. 1  Split Phase 240/120V circuit (180 phase shift)
This technical note describes the option of connecting the 60Hz XW Inverter/Charger to a threephase source by using a transformer to convert the AC source to splitphase 240/120V. INTRODUCTION: Splitphase
More informationDefinition AC Power Distribution
COMMON AC POWER DISTRIBUTION CONFIGURATIONS The input voltage needed to power electronic equipment is provided by the manufacture in the product specifications. Matching this requirement to the facility
More informationChapter 5 TRANSFORMERS
Chapter 5 TRANSFORMERS Objective Understand the transformer nameplate Describe the basic construction features of a transformer. Explain the relationship between voltage, current, impedance, and power
More informationThree phase circuits
Three phase circuits THREE PHASE CIRCUITS THREEPHASE ADVANTAGES 1. The horsepower rating of threephase motors and the kva rating of threephase transformers are 150% greater than singlephase motors
More informationLecture Notes ELE A6
ecture Notes EE A6 Ramadan ElShatshat Three Phase circuits 9/12/2006 EE A6 Threephase Circuits 1 Threephase Circuits 9/12/2006 EE A6 Threephase Circuits 2 Advantages of Threephase Circuits Smooth
More informationBALANCED THREEPHASE CIRCUITS
BALANCED THREEPHASE CIRCUITS The voltages in the threephase power system are produced by a synchronous generator (Chapter 6). In a balanced system, each of the three instantaneous voltages have equal
More informationGENERATOR SELECTION. a. Three phase  120/208V, 3 phase, 4W wye; 277/408, 3 phase, 4W wye; * 120/240V 3 phase, 4W Delta
GENERATOR SELECTION Generators must be sized to handle their load based on the continuous KW, kilowatt load, and KVA, kilovoltamp load, and the worst case starting load KW + KVA. They must be derated for
More informationAlternating current threephase circuits
Unit. C HEEPHE CCU lternating current threephase circuits Unit. C HEEPHE CCU COE: hreephase systems characteristics Generation of threephase voltages hreephase loads Y and Y transformation nstantaneous
More informationUSE OF A SINGLE ELEMENT WATTMETER OR WATT TRANSDUCER ON A BALANCED THREEPHASE THREEWIRE LOAD WILL NOT WORK. HERE'S WHY.
USE OF A SINGLE ELEMENT WATTMETER OR WATT TRANSDUCER ON A BALANCED THREEPHASE THREEWIRE LOAD WILL NOT WORK. HERE'S WHY. INTRODUCTION Frequently customers wish to save money by monitoring a threephase,
More informationSeries and Parallel Circuits
Series and Parallel Circuits Components in a circuit can be connected in series or parallel. A series arrangement of components is where they are inline with each other, i.e. connected endtoend. A parallel
More informationEquipment: Power Supply, DAI, Variable resistance (8311), Variable inductance (8321)
Lab 4: 3phase circuits. Objective: to study voltagecurrent relationships in 3phase circuits; to learn to make delta and Y connections; to calculate and measure real, apparent, and reactive powers. Equipment:
More informationUnit 33 ThreePhase Motors
Unit 33 ThreePhase Motors Objectives: Discuss the operation of wound rotor motors. Discuss the operation of selsyn motors. Discuss the operation of synchronous motors. Determine the direction of rotation
More information3Phase AC Calculations Revisited
AN110 Dataforth Corporation Page 1 of 6 DID YOU KNOW? Nikola Tesla (18561943) came to the United States in 1884 from Yugosiavia. He arrived during the battle of the currents between Thomas Edison, who
More informationUnderstanding Power Factor and How it Affects Your Electric Bill. Presented by Scott Peele PE
Understanding Power Factor and How it Affects Your Electric Bill Presented by Scott Peele PE Understanding Power Factor Definitions kva, kvar, kw, Apparent Power vs. True Power Calculations Measurements
More informationGround Fault Protection
GE Energy Industrial Solutions Ground Fault Protection Digital Specification Program Latin America Ground Fault. I. Introduction In the electrical systems always exists the possibility of having shutdowns
More informationcodeissues APPLYING DEMAND FACTOR AND DIVERSITY FACTOR PER THE NEC By James Stallcup Sr., NEC/OSHA Consultant
By James Stallcup Sr., NEC/OSHA Consultant APPLYING DEMAND FACTOR AND DIVERSITY FACTOR PER THE NEC Don t be confused by these terms! There are two terms used in calculating loads in electrical systems
More informationApplication guide for power factor testing of power & distribution transformers
Application guide for power factor testing of power & distribution transformers Introduction The transformer is probably one of the most useful electrical devices ever invented. It can raise or lower the
More informationTransformer Basics Information Guide
Property of Motion Laboratories, Inc. Transformer Basics Information Guide 2014 Motion Laboratories, Inc. Created By: Jim Herrick / Michael Shaw Approved By: Peter Herrmann Page: 1 Transformer Definition
More informationThe generation and supply of electricity within the U.K is achieved through the use of a 3phase system.
Three Phase Electricity Supplies and Systems The generation and supply of electricity within the U.K is achieved through the use of a 3phase system. This consists of 3 separate phase conductors along
More informationSingle and Three Phase Transformer Testing Using Static Motor Circuit Analysis Techniques
Single and Three Phase Transformer Testing Using Static Motor Circuit Analysis Techniques Howard W. Penrose, Ph.D On behalf of ALLTEST Pro, LLC Old Saybrook, CT Introduction Field and shop testing of
More informationSeptember, Rectifier Duty Transformers
September, 2013 Rectifier Duty Transformers Transformers play an important role in industrial applications, especially in metallurgical plants and processes. Very high currents need to be supplied for
More informationThreePhase Electric Power Distribution for Computer Data Centers
Threehase Electric ower Distribution for Computer Data Centers WHITE AER E901 Geist January 008 Summary This paper will describe the characteristics of threephase power and outline the advantages of
More information1 Introduction. 2 The Symmetrical Component Transformation. J.L. Kirtley Jr.
Massachusetts Institute of Technology Department of Electrical Engineering and Computer Science 6.06 Introduction to Power Systems Class Notes Chapter 4 Introduction To Symmetrical Components J.L. Kirtley
More information(3 )Three Phase Alternating Voltage and Current
EEE 2015 EECTRCS (3) Monophase 1 Three phase Three phase electric power is a common method of alternating current electric power generation, transmission, and distribution. t is a type of polyphase system
More informationDelta and Wye 3phase circuits
Delta and Wye 3phase circuits This worksheet and all related files are licensed under the Creative Commons Attribution License, version 1.0. To view a copy of this license, visit http://creativecommons.org/licenses/by/1.0/,
More informationThe Fundamentals of ThreePhase Power Measurements. Application Note
The Fundamentals of  Power Measurements pplication ote pplication ote 0 120 240 360 Figure 1. phase voltage wavefm. Figure 2. phase voltage vects. 100Ω 100Ω Figure 4. phase supply, balanced load 
More informationModule Overview. This module presents the following topics: Principle of Operation Types of Transformers Operating Considerations and Limitations
Course Outline 1. Introduction to WECC 2. Fundamentals of Electricity 3. Power System Overview 4. Principles of Generation 5. Substation Overview 6. Transformers 7. Power Transmission 8. System Protection
More informationLecture 5: Transformers(continued)
Lecture 5: Transformers(continued) Equivalent circuit of a transformer Figure (1) shows an equivalent circuit of a transformer. R 1 and R 2 represent the resistances of the primary and secondary windings
More informationThree Phase Circuits. Three Phase Circuits
Three Phase Circuits 1 Three Phase Circuits Chater Objectives: Be familiar with different threehase configurations and how to analyze them. Know the difference between balanced and unbalanced circuits
More informationTechnical Reference. Introduction. Capstone MicroTurbine Electrical Installation
Capstone Capstone Turbine Corporation 21211 ordhoff Street Chatsworth CA 91311 USA Telephone: (818) 7345300 Facsimile: (818) 7345320 Website: www.microturbine.com Technical Reference Capstone MicroTurbine
More informationTRANSFORMER: THREE PHASE
CONTENTS Transformer : Three Phase 1211 C H A P T E R 33 Learning Objectives Threephase Transformers Threephase Transformer Connections Star/Star or Y/Y Connection DeltaDelta or Connection Wye/Delta
More informationInduction Motor (NoLoad Test) Induction Motor (Blocked Rotor Test) Example (NoLoad/Blocked Rotor Tests) The results of the noload and blocked rotor tests on a threephase, 60 hp, 2200 V, sixpole, 60
More informationIntroduction to Transformer Rated Meters
Introduction to Transformer Rated Meters Module 141 87 rd Annual Short Course and Conference Southeastern Electricity Metering Association November, 2012 Orlando, FL Larry Waters General Electric Company
More informationACCURACY OF POTENTIALTRANSFORMERS
8 VOLTAGE TRANSFORMERS Two types of voltage transformer are used for protectiverelaying purposes, as follows: (1) the "instrument potential transformer," hereafter to be called simply "potential transformer,"
More informationTransformer / Line Loss Calculations
70072015307 TECHNICAL NOVEMBER 2006 Transformer / Line Loss Calculations This document gives a brief overview of transformer loss and line loss calculations and describes how these calculations are implemented
More informationVoltage Drop (SinglePhase)
Voltage Drop (SinglePhase) To Find: To Find Voltage Drop Formula: 2 x K x L x I V.D. =  C.M. Variables: C.M. = Circular Mill Area (Chapter 9, Table 8) To Find Voltage Drop Percentage
More information615xx, 616xx, 617xxx, 646x, 64xx, 65xx Series Programmable AC source
Chroma Systems Solutions, Inc. AC Power Definitions 615xx, 616xx, 617xxx, 646x, 64xx, 65xx Series Programmable AC source Keywords: Peak, RMS, Phase, Inrush Current, Power Factor, Crest Factor, Apparent
More informationRule 5.500 Fast Track Analysis for National Life Insurance Co.
Rule 5.500 Fast Track Analysis for National Life Insurance Co. For a 500 kw Solar array to be located at 155 Northfield Street in Montpelier, Vermont Green Mountain Power Pam Allen Date: 5/31/13 SECTION
More informationOhm s Law. George Simon Ohm
Ohm s Law George Simon Ohm The law which governs most simple and many complex electrical phenomena is known as Ohm s Law. It is the most important law in electricity. In 1827, a German locksmith and mathematician
More information6/14/02 Chapter 2: Basic Electrical Power Fundamentals 1/6
Basic Electrical Power Fundamentals LOAD REFERENCE Kilowatts Kilovolt amps Power Factor PF Motors KW KVA USE NEC 430148 KW < KVA.6.95 and 430150 to find current for given HP Indancescant Lighting USE
More informationEffective: September 10, 2006 Vermont Attachment 1 to Rule 5.500 Public Service Board Page 1 of 6
Public Service Board Page 1 of 6 STANDARD APPLICATION FOR INTERCONNECTION OF GENERATION RESOURCES IN PARALLEL TO THE ELECTRIC SYSTEM OF: (Interconnecting Utility) Preamble and Instructions: An owner of
More informationPower System Harmonics
Pacific Gas and Electric Company Power System Harmonics What are power system harmonics? Ideally, voltage and current waveforms are perfect sinusoids. However, because of the increased popularity of electronic
More informationAC Generators. Basic Generator
AC Generators Basic Generator A basic generator consists of a magnetic field, an armature, slip rings, brushes and a resistive load. The magnetic field is usually an electromagnet. An armature is any number
More informationTHREE PHASE CIRCUITS
THREE PHASE CIRCUITS A. PREPARATION 1. Three Phase Voltages and Systems 2. The Determination of Phase Sequence 3. Blondel's Theorem and Its Consequences 4. References B. EXPERIMENT 1. Equipment List 2.
More information1 Introduction. 2 Two Phases. J.L. Kirtley Jr.
Massachusetts Institute of Technology Department of Electrical Engineering and Computer Science 6.061 Introduction to Power Systems Class otes Chapter 3 Polyphase etworks J.L. Kirtley Jr. 1 Introduction
More informationPrecertificati on V oltali!e Drop Calculations
7 Precertificati on V oltali!e Drop Calculations Rule 8102 governs the maximum amount of voltage drop for an electrical installation (this includes service, feeder and branch circuit conductors). Subrule
More informationLab 6: Transformers in parallel and 3phase transformers.
Lab 6: Transformers in parallel and 3phase transformers. Objective: to learn how to connect transformers in parallel; to determine the efficiency of parallel connected transformers; to connect transformers
More informationBasic Electrical Theory
Basic Electrical Theory Power Principles and Phase Angle PJM State & Member Training Dept. PJM 2014 10/24/2013 Objectives At the end of this presentation the learner will be able to; Identify the characteristics
More informationBuck and Boost Transformer
Buck and Boost Transformer Class 7414 CONTENTS Description Page Product Description.................................................. 2 Specifications.......................................................
More informationRadial Distribution Test Feeders
Radial Distribution Test Feeders Distribution System Analysis Subcommittee Report Abstract: Many computer programs are available for the analysis of radial distribution feeders. In 1992 a paper was published
More information2013 ElectriCities Electric Utility Webinar Series
2013 ElectriCities Electric Utility Webinar Series Sizing of Transformers Calculation of Loads Demand and Demand Factor Demand The value of electrical power required for a particular load. Expressed in
More informationTRANSFORMERS. Unit 14 OBJECTIVES
Unit 14 TRANSFORMERS OBJECTIVES After studying this unit, the student will be able to state the purpose of a transformer. explain the principle of mutual induction. determine the output voltage of a transformer
More information4.5 Transformer Connections
ELECTRIC POWER SYSTEMS IN COMMERCIAL BUILDINGS IEEE Std 2411990 5) Flat Billing Ñ Certain applications involve service to the load of a Þxed characteristic. For such loads, the supplying utility may offer
More information1. The type of service available at any particular location should be determined by inquiry at PG&E's local office.
Revised Cal. P.U.C. Sheet No. 11257E Cancelling Revised Cal. P.U.C. Sheet No. 6925E ELECTRIC RULE NO. 2 Sheet 1 A. GENERAL 1. The type of service available at any particular location should be determined
More information101 BASICS SERIES LEARNING MODULE 4: TRANSFORMERS. CutlerHammer
101 BASICS SERIES LEARNING MODULE 4: TRANSFORMERS CutlerHammer WELCOME Welcome to Module 4, which is about the transformer. In this module you will begin to appreciate how the topics discussed in previous
More informationSECTION 26 09 13  POWER MONITOR FOR ELECTRICAL, STEAM CONDENSATE, AND WATER PART I  GENERAL
SECTION 26 09 13  POWER MONITOR FOR ELECTRICAL, STEAM CONDENSATE, AND WATER PART I  GENERAL 1.1 SUMMARY A. This section describes the requirements for the installation of Power Monitors and associated
More informationRelease 1.1, January 2012
THREEPHASE TRANSFORMERS Release 1.1, January 2012 Har Hotzvim Industrial Park, 14 Hartom St., P.O.B. 45029, Jerusalem 91450, Israel Tel: 97225888222 Fax: 97225828875 Email: info@gamatronic.co.il
More informationChapter 3: Electricity
Chapter 3: Electricity Goals of Period 3 Section 3.1: To define electric charge, voltage, and energy Section 3.2: To define electricity as the flow of charge Section 3.3: To explain the generation electricity
More informationJEFFERSON ELECTRIC, INC. BuckBoost Transformer Application Manual
JEFFERSON ELECTRIC, INC. BuckBoost Transformer Application Manual Revised on February 15, 2012 Table of Contents I. Introduction... 2 II. Choosing the Proper Transformer... 2 III. Rapid Selector Charts...
More informationObjectives 316 CHAPTER 6 POWER
Objectives Explain the relationship between power, current, and voltage in electrical systems. Explain the relationship between power, current, and resistance in electrical systems. Calculate energy usage
More informationTRANSFORMER LOSS COMPENSATION FOR METERMEN PRESENTED BY: MICHAEL K. BEARDEN
TRANSFORMER LOSS COMPENSATION FOR METERMEN PRESENTED BY: MICHAEL K. BEARDEN WHAT are transformer losses? TRANSFORMER LOSS COMPENSATION THE WHAT, WHEN, WHO, WHERE AND HOW Transformer losses can be viewed
More informationWhat is a transformer and how does it work?
Why is a transformer needed? A control transformer is required to supply voltage to a load which requires significantly more current when initially energized than under normal steady state operating conditions.
More informationBuck  Boost Transformers
Buck  Boost Transformers Contents Buck  Boost Transformers  Terms & Definitions... 48 Buck  Boost Transformers  Sizing... 50 Quick Reference Chart  08, 0, 40 Volts Single & Three Phase... 5 Single
More informationMotor Protection Voltage Unbalance and SinglePhasing
Motor Protection Voltage Unbalance and SinglePhasing Cooper Bussmann contributes the following information, which is an excerpt from their 190page handbook SPD Selecting Protective Devices Based on the
More informationServices. Three Phase Service
Services Primary Service vs Secondary Service Overhead vs Underground Common Service Types Three Phase Wye Closed Open Delta Corner Grounded Center Tapped Open Single Phase Three Phase Service Wye Delta
More informationHPS Universal. Single and Three Phase Potted. BuckBoost Transformers. BuckBoost Applications & Standard Specification... 80
BuckBoost Transformers Single and Three Phase Potted BuckBoost Transformers BuckBoost Applications & Standard Specification... 80 Selecting BuckBoost Transformers... 81 Single Phase Selection Tables...
More informationElectrician s Math and Basic Electrical Formulas
UNIT 1 Electrician s Math and Basic Electrical Formulas INTRODUCTION TO UNIT 1 ELECTRICIAN S MATH AND BASIC ELECTRICAL FORMULAS In order to construct a building that will last into the future, a strong
More informationThreePhase AC Power Circuits
Electricity and New Energy ThreePhase AC Power Circuits Student Manual 86360F0 Order no.: 8636000 Revision level: 10/2014 By the staff of Festo Didactic Festo Didactic Ltée/Ltd, Quebec, Canada 2010
More informationINTRODUCTION. THREE PHASE SSRs DEFINED & DESCRIBED
pero 1 Three Phase Solid State Relays & Their Application in Three Phase Heating Circuits By Paul Bachman, Fellow Engineer, Dr. Oscar Montero, R&D Manager, and Doug Sherman, FSAE Manager, Crydom, Inc.
More informationELECTRONIC POWER SYSTEMS
ELECTRONIC POWER SYSTEMS TRADEOFFS BETWEEN SINGLEPHASE & THREEPHASE POWER WHITE PAPER: TW0057 1 Executive Summary Modern Electronic Systems are quite often powered from a threephase power source. While
More informationHow Does a Generator Work?
How Does a Generator Work? Clifford Power Systems is one of the largest full service generator providers in the United States. Our generator experts specialize in equipment, service, parts and rental of
More informationTHE PERUNIT SYSTEM. (2) The perunit values for various components lie within a narrow range regardless of the equipment rating.
THE PERUNIT SYSTEM An interconnected power system typically consists of many different voltage levels given a system containing several transformers and/or rotating machines. The perunit system simplifies
More informationModule Title: Electrotechnology for Mech L7
CORK INSTITUTE OF TECHNOLOGY INSTITIÚID TEICNEOLAÍOCHTA CHORCAÍ Autumn Examinations 2012 Module Title: Electrotechnology for Mech L7 Module Code: ELEC7007 School: School of Mechanical, Electrical and Process
More informationadjustment performs all the voltage limiting, the tapped Fig 1 SCR and Transformer transformer option lets you run with a higher power factor.
Silicon Controlled Rectifiers and Transformers in Power Control How transformers extend the capabilities of SCRs Arthur Holland, Holland Technical Skills The most common and economical arrangement of SCR
More informationIVE(TY) Department of Engineering Electrical Machines 1
Hour 8 slide 1 Introduction Transformer Transformer is a machine that has no moving parts but is able to transform alternating voltages and currents from high to low (stepup transformer ) and vice versa
More informationRotary Phase Converters
FACTS from Ronk Electrical Industries, Inc. Bulletin 11981 Rotary Phase Converters ROTOVERTER Pat. No. 3,670,238 ROTOCON Pat. No. 4,158,225 What are the ROTOCON and ROTOVERTER power converters? The ROTOCON
More informationQuestions. Question 1
Question 1 Questions Explain why transformers are used extensively in longdistance power distribution systems. What advantage do they lend to a power system? file 02213 Question 2 Are the transformers
More informationDISTRIBUTION SYSTEMS INDEX NOV 06 SECTION 2. Detroit...215 Ann Arbor...216 Mt. Clemens...217 Port Huron...218
DISTRIBUTION SYSTEMS INDEX NOV 06 SECTION 2 Kinds and Uses of Service... 211 and 212 Wye Network Area Maps Detroit...215 Ann Arbor...216 Mt. Clemens...217 Port Huron...218 Transformer Connections
More informationElectrical Power. How do you calculate electrical power? 14.3
. Name: Date: Electrical Power 14.3 How do you calculate electrical power? In this skill sheet you will review the relationship between electrical power and Ohm s law. As you work through the problems,
More informationElectrical Construction Technology
Job Ready Assessment Blueprint Electrical Construction Technology Test Code: 4130 / Version: 01 Copyright 2011. All Rights Reserved. General Assessment Information Electrical Construction Technology Blueprint
More informationShort Circuit Current Calculations
Introduction Several sections of the National Electrical Code relate to proper overcurrent protection. Safe and reliable application of overcurrent protective devices based on these sections mandate that
More informationPointToPoint Method Of ShortCircuit Calculation
PointToPoint Method Of ShortCircuit Calculation Calculation Of ShortCircuit Currents PointToPoint Method. Adequate interrupting rating and protection of electrical components are two essential aspects
More informationPower Transducer User s Guide
Power Transducer User s Guide Volume 1 Power Transducer User's Guide Volume 1 Applying Power Transducers Volume 1 Page I. Why Monitor Power?... 1 II. Beginning Definitions... 3 III. Basic Concepts of AC
More informationTransformer circuit calculations
Transformer circuit calculations This worksheet and all related files are licensed under the Creative Commons Attribution License, version 1.0. To view a copy of this license, visit http://creativecommons.org/licenses/by/1.0/,
More informationLoading Considerations When Paralleling Transformers
Application Guide 7400DB0701 02/2007 Nashville, TN, USA Loading Considerations When Paralleling Transformers Class 7400 Retain for future use. Introduction Principles of Paralleling This application guide
More information3. TYPES OF SERVICE AVAILABLE. 3.1 Scope
3. TYPES OF SERVICE AVAILABLE 3.1 Scope UI supplies 60 hertz, alternating current with different voltage and ampere ratings. Not all voltage and ampere ratings are available throughout the entire service
More informationDANGER! HIGH VOLTAGE HAZARD
WattNode Pulse kwh Transducer Connection Instructions For use with HOBO H21, H22, U30, UX90, and UX120 series data loggers, and HOBO data nodes Applies to these WattNode Pulse kwh Transducers: Onset Part
More informationTESLA Recorder Power Metering Setup Configuration for 3 and 2 Element Watt/VAR Metering
TESLA Recorder Power Metering Setup Configuration for 3 and 2 Element Watt/VAR Metering Introduction This application note will assist the user to set up 3phase metering to monitor Watt, VAR and VA power
More informationREVIEW QUESTIONS. A6 Test Preparation
A6 Test Preparation Note: The lessons, exercises and tests in this manual are great preparation for taking the ASE A6 (electrical) certification test. However, that s only for the topics we ve covered.
More informationCURRENT TRANSFORMERS INSTALLATION GUIDE
CURRENT TRANSFORMERS INSTALLATION GUIDE Information contained within this document is subject to change without notice and does not represent a commitment on the part of PRI Ltd or its agents. E&OE. Copyright
More informationElectric Motor Brake Horsepower Calculations
Electric Motor Brake Horsepower Calculations By Norm Christopherson These motor calculations are contained here as they apply to the changing conditions of the blower motor when pulley adjustments are
More informationPower measurement in balanced 3 phase circuits and power factor improvement. 1 Power in Single Phase Circuits. Experiment no 1
Experiment no 1 Power measurement in balanced 3 phase circuits and power factor improvement 1 Power in Single Phase Circuits Let v = m cos(ωt) = cos(ωt) is the voltage applied to a RL circuit and i =
More informationChapter 12: Three Phase Circuits
Chapter 12: Three Phase Circuits 12.1 What Is a Three Phase Circuit? 12.2 Balance Three Phase Voltages 12.3 Balance Three Phase Y to Y Connection 12.4 Other Balance Three Phase Connections 12.5 Power in
More informationS15Physics current and Circuit PRACTICE
Name: Class: Date: ID: A S5Physics current and Circuit PRACTICE Multiple Choice Identify the choice that best completes the statement or answers the question.. Three resistors, with values of 2.0, 4.0
More informationDirection of current flow. Heat produced in a resistor. Heat produced in a resistor. L 27 Electricity and Magnetism [4]
L 27 Electricity and Magnetism [4] simple electrical circuits direct current DC Alternating current (AC) vs direct current (DC) electric power distribution household electricity household wiring GFIC s
More information