# Figure. 1 - Split Phase 240/120V circuit (180 phase shift)

Save this PDF as:

Size: px
Start display at page:

## Transcription

1 This technical note describes the option of connecting the 60Hz XW Inverter/Charger to a three-phase source by using a transformer to convert the AC source to split-phase 240/120V. INTRODUCTION: Split-phase and three-phase systems Split-phase systems are commonly used in North America for residential and light commercial (up to 100KVA) installations. A split-phase (240/120V) power system, is a 3- wire, single-phase, mid-point neutral system, which consists of two 120V voltage sources connected out-of-phase by 180 with a neutral connection between them. The voltage between the two live conductors (L-L) is 240V, whereas the voltage between a live conductor and neutral (L-n) is 120V. Standard 120V lighting and small appliances are connected between a live wire and the neutral. Large appliances, such as cooking equipment, space heating, water pumps, clothes dryers, and air conditioners are connected across the two live conductors and operate at 240V, requiring less current and smaller conductors than would be needed if the appliances were designed for 120V operation. Since the current in each leg of a split-phase system is 180 out-of-phase, the neutral wire carries only the difference of current between the two lines, or zero current when loads on both legs are perfectly balanced (i.e. consuming equal amounts of power). Figure. 1 - Split Phase 240/120V circuit (180 phase shift) Because no individual conductor will be at more than 120V potential with respect to ground (earth), split-phase systems are considered safer than a 240V 2-wire system that has one leg (the neutral) earthed. In addition, it is more efficient as it requires smaller conductor size compared to a 2- wire 120V system with the same two loads connected in parallel.

2 Three-phase power systems are defined by having three equal AC voltages which are outof-phase by one third of a cycle (120 ). Three-phase power is the backbone of the electrical distribution system and is used to power both three-phase and single phase loads. There are two basic configurations for three-phase systems, Wye (Y) and Delta (Δ). Wye configuration is a 4-wire system with three live lines (commonly referred as phases) and a neutral point where all three phases are connected together. This configuration allows for two different supply voltages; phase-to-phase voltage (line voltage), and phase-toneutral voltage (phase voltage). Line voltage is 3 times the phase voltage, while line current and phase current are the same. Three-phase power is most commonly provided by the Utility companies in a Wye configuration. Delta configuration is a 3-wire system, which also consists of three live lines. There is no neutral wire in a Delta system and thus the line voltage is equal to the phase voltage. Line current, on the other hand, is 3 times the phase current. Delta configurations are primarily used to provide power to three-phase motor loads. Delta systems are sometimes corner grounded to protect for ground faults. Figure 2. Most Common three-phase transformers (120 phase shift)

3 THE XW INVERTER/CHARGER: Split phase design 60Hz XW Hybrid Inverter/Charger models are designed to be connected to split-phase (240/120V) AC sources, where the current from each leg (L1 and L2) is 180 out-of-phase. This ensures the neutral wire never receives more current than it was designed to handle as the current from each line cancels out, leaving only the difference current between the two lines. The XW Inverter/Chargers allow a maximum current imbalance of 75% between L1-n and L2-n. This equates to: XW6048 L-N: (6,000W x 0.75)/120V = 37.5 Amp XW4548 L-N: (4,500W x 0.75)/120V = 28.1 Amp XW4024 L-N: (4,000W x 0.75)/120V = 25.0 Amp Input power to the XW Inverter/Charger cannot be simply derived from a phase or line voltage of a three phase 208:120Y or 240VΔ AC source. Instead of cancelling each other as they would with a split-phase source, each 120 out-of-phase leg effectively creates a short circuit (limited by the impedance of the transformer and the wiring), which leads to very high currents flowing on the neutral line causing imminent failure of the inverter s AC relay board. To protect against this, the XW Inverter/Charger will sense if a non-symmetrical phase is present and will prevent the unit from connecting to the AC source. That is, the three-phase input source will not be qualified and the unit will stay in invert mode until a qualified splitphase source is present on either of the Inverter/Charger s two AC inputs terminals. 1 1 The original firmware released with the XW / (XW6048_v1.00_BN0011) did not check for this split-phase condition. All subsequent firmware versions do, including those for the XW4024 and XW4548 models.

4 THE XW INVERTER/CHARGER AND THREE-PHASE SOURCES: Use of a transformer All is not lost! A 60Hz XW Inverter/Charger can still be connected to a three-phase distribution system or three-phase generator by using a transformer to convert the AC input to the Inverter/Charger into split-phase 240/120VAC. The selection of the transformer depends on the size of the Inverter/Charger(s), and the AC source input voltage. There are 3 different inverter power levels to consider for single-unit configuration: 4.0kW (XW4024), 4.5kW (XW4548) or 6kW (XW6048). A larger transformer would be required in multi-unit configurations where more than 1 unit is connected together for increased power capacity. The largest XW inverter system consists of three XW6048 inverters for a total capacity of 18kW; however, for even larger systems where there are more than one 18kW load panels, two or more 18KW XW systems can be installed sharing the same AC input (grid or generator). Consider the total power of the XW system and size the transformer accordingly. Different types of transformers from different manufacturers can be found in the market that can convert from practically any common three-phase voltage (e.g. 208V, 277V, 380V, 416V) to split-phase 240/120V, and with power capacities available from 50VA to 750KVA. Two well known manufacturers of transformers are Mag-Tran and Hammond Power Solutions. The links to their web pages are below: EXAMPLE 1: Connecting an XW Hybrid Inverter/Charger to a 208:120Y distribution system through a 6KVA, 120V to split phase autotransformer. In this example, a 208:120Y distribution system is the primary AC input source to an XW / (p/n: ). A transformer is used to convert from 120V, the phase voltage of the three-phase system, to 240/120V split phase required by the XW Inverter/Charger. The transformer used is a Xantrex TX Autotransformer, TX6K (6KVA). See Figure 3. From the Utility Distribution panel, a single hot leg wire (Phase A, for example) and Neutral (N) wire are connected as input to the transformer s 120V L1 and Neutral wiring terminal, respectively. The ground wire is connected to the transformer s ground bar.

5 From the transformer s 240V output terminal, L1 and L2wires are connected to the input side of the AC1 Breaker (60Amp 2-pole breaker) in the XW-Power Distribution Panel (XW- PDP). The neutral (N) wire is connected to the neutral bar on the XW-PDP. The input to the XW-PDP is therefore 240V Line to Line, and 120V line to neutral. Figure 3. Connecting the XW Inverter/charger to a three-phase source through a 120V to 240/120V split phase autotransformer Note: Using a 120V to 240/120V transformer as described above may significantly imbalance the 208:120Y three-phase source. A better approach would be to use a 208V to 240/120V transformer to balance the load on two phases, as described in Example 2.

6 Example 2: Connecting an XW Hybrid Inverter/Charger to a 208:120Y distribution system through a 208V to split phase autotransformer. In this example, a 208:120Y distribution system is the primary AC input source to an XW / (p/n: ). A transformer is used to convert from 208V, the line voltage of the three-phase system, to 240/120V split-phase required by the XW Inverter/Charger. The sketch of the primary and secondary windings of a generic 6KVA, 208V to 120/240V transformer is used for this example. See figure 4. From the Utility Distribution panel, the line voltage wires (VAB, for example) are connected as input to the transformer s 208V L1 and L2 wiring terminal. The ground wire is connected to the transformer s ground bar. From the transformer s split-phase output terminal, L1 and L2wires are connected to the input side of the AC1 Breaker (60Amp 2-pole breaker) in the XW-PDP. The neutral (N) wire is connected to the neutral bar on the XW-PDP. The input to the XW-PDP is therefore 240VAC line-to-line, and 120V line-to-neutral. Figure 4. Connecting the XW Inverter/charger to a three-phase source through a 208 to split-phase transformer

### Single-Phase. Three-Phase

Three-Phase Transformers When more power is needed - three transformers can be tied together. This is called three-phase. Here s a simple way of comparing single-phase to threephase power. Single-Phase

### Three-Phase Electric Power Distribution for Computer Data Centers

Three-hase Electric ower Distribution for Computer Data Centers WHITE AER E901 Geist January 008 Summary This paper will describe the characteristics of three-phase power and outline the advantages of

### Three-phase AC circuits

Three-phase AC circuits This worksheet and all related files are licensed under the Creative Commons Attribution License, version 1.0. To view a copy of this license, visit http://creativecommons.org/licenses/by/1.0/,

### Current Transformer (CT) Selection Guide

Current Transformer (CT) Selection Guide Article ESA-1008D December 5, 2014 Contents 1 Introduction.............................................. 3 1.1 Extending CT leads.......................................

### Lecture Notes ELE A6

ecture Notes EE A6 Ramadan El-Shatshat Three Phase circuits 9/12/2006 EE A6 Three-phase Circuits 1 Three-phase Circuits 9/12/2006 EE A6 Three-phase Circuits 2 Advantages of Three-phase Circuits Smooth

### 3-Phase AC Calculations Revisited

AN110 Dataforth Corporation Page 1 of 6 DID YOU KNOW? Nikola Tesla (1856-1943) came to the United States in 1884 from Yugosiavia. He arrived during the battle of the currents between Thomas Edison, who

### Chapter 24. Three-Phase Voltage Generation

Chapter 24 Three-Phase Systems Three-Phase Voltage Generation Three-phase generators Three sets of windings and produce three ac voltages Windings are placed 120 apart Voltages are three identical sinusoidal

### 415V DISTRIBUTION FOR GREEN DATA CENTERS

White Paper: HMRP-WP001-A5 June 5, 2012 415V DISTRIBUTION FOR GREEN DATA CENTERS Prepared by: Anthony (Tony) Hoevenaars, P. Eng President and CEO Mirus International Inc. Copyright 2012 Mirus International

### (3 )Three Phase Alternating Voltage and Current

EEE 2015 EECTRCS (3) Monophase 1 Three phase Three phase electric power is a common method of alternating current electric power generation, transmission, and distribution. t is a type of polyphase system

### Three phase circuits

Three phase circuits THREE PHASE CIRCUITS THREE-PHASE ADVANTAGES 1. The horsepower rating of three-phase motors and the kva rating of three-phase transformers are 150% greater than single-phase motors

### 3. TYPES OF SERVICE AVAILABLE. 3.1 Scope

3. TYPES OF SERVICE AVAILABLE 3.1 Scope UI supplies 60 hertz, alternating current with different voltage and ampere ratings. Not all voltage and ampere ratings are available throughout the entire service

### DANGER! HIGH VOLTAGE HAZARD

WattNode Pulse kwh Transducer Connection Instructions For use with HOBO H21, H22, U30, UX90, and UX120 series data loggers, and HOBO data nodes Applies to these WattNode Pulse kwh Transducers: Onset Part

### Services. Three Phase Service

Services Primary Service vs Secondary Service Overhead vs Underground Common Service Types Three Phase Wye Closed Open Delta Corner Grounded Center Tapped Open Single Phase Three Phase Service Wye Delta

### Off-grid solar and backup power installations

Off-grid solar and backup power installations A World of Power Problems... Residential Backup Power Grid-Interactive 3-Phase Commercial Buildings with Backup Power Grid-Interactive Residential with Backup

### Server Technology, Inc.

Server Technology, Inc. Power Efficiency Gains by Deploying 415 VAC Power Distribution in North American Data Centers White Paper STI-100-008 2009-April-07 Headquarters Server Technology, Inc. 1040 Sandhill

### BALANCED THREE-PHASE CIRCUITS

BALANCED THREE-PHASE CIRCUITS The voltages in the three-phase power system are produced by a synchronous generator (Chapter 6). In a balanced system, each of the three instantaneous voltages have equal

### Short Circuit Current Calculations

Introduction Several sections of the National Electrical Code relate to proper overcurrent protection. Safe and reliable application of overcurrent protective devices based on these sections mandate that

Electrical Drawings - Table of Contents E1.0 Lighting Plan E1.1 Power Plan E2.0 Electrical Specifications E2.1 Electrical Specifications E3.0 Panel Schedule E3.1 Load Summary 1 2 1 Panel Schedule LP1

### HPS Universal. Single and Three Phase Potted. Buck-Boost Transformers. Buck-Boost Applications & Standard Specification... 80

Buck-Boost Transformers Single and Three Phase Potted Buck-Boost Transformers Buck-Boost Applications & Standard Specification... 80 Selecting Buck-Boost Transformers... 81 Single Phase Selection Tables...

### GUIDELINES FOR COMMERCIAL ELECTRIC SERVICE HOOKUP

GUIDELINES FOR COMMERCIAL ELECTRIC SERVICE HOOKUP 1 Steps to Commercial Service Pay the Design Deposit Commercial Buildings: Up to 1, sq ft = \$1,. 1, 5, sq ft = \$2,. Over 5, sq ft = \$3,. Commercial jobs

### Equipment: Power Supply, DAI, Variable resistance (8311), Variable inductance (8321)

Lab 4: 3-phase circuits. Objective: to study voltage-current relationships in 3-phase circuits; to learn to make delta and Y connections; to calculate and measure real, apparent, and reactive powers. Equipment:

### Module Title: Electrotechnology for Mech L7

CORK INSTITUTE OF TECHNOLOGY INSTITIÚID TEICNEOLAÍOCHTA CHORCAÍ Autumn Examinations 2012 Module Title: Electrotechnology for Mech L7 Module Code: ELEC7007 School: School of Mechanical, Electrical and Process

### TERMS AND CONDITIONS

Virginia Electric and Power Company TERMS AND CONDITIONS XXIV. GENERATOR INTERCONNECTION STANDARD Electric generator interconnection service includes only the ability to interconnect an electric generator

### BASIC NEC CODE RULES AND DESIGN PRACTICE

BASIC NEC CODE RULES AND DESIGN PRACTICE Wire Ampacity and Size Circuit Breaker Size 1. Maximum loading for any branch circuit is 80% of rating of circuit for ampacity of wire for any load. NEC 220-2,

### SECTION 26 09 13 - POWER MONITOR FOR ELECTRICAL, STEAM CONDENSATE, AND WATER PART I - GENERAL

SECTION 26 09 13 - POWER MONITOR FOR ELECTRICAL, STEAM CONDENSATE, AND WATER PART I - GENERAL 1.1 SUMMARY A. This section describes the requirements for the installation of Power Monitors and associated

### SP 4K/5K Efecto & SP 5K Brilliant Parallel Installation Guide 1. Introduction

SP 4K/5K Efecto & SP 5K Brilliant Parallel Installation Guide 1. Introduction This inverter can be used in parallel with two different operation modes. 1. Parallel operation in single phase with up to

### 4KVA/5KVA Parallel Installation Guide

4KVA/5KVA Parallel Installation Guide 1. Introduction This inverter can be used in parallel with two different operation modes. 1. Parallel operation in single phase with up to 4 units. The supported maximum

### 4.5 Transformer Connections

ELECTRIC POWER SYSTEMS IN COMMERCIAL BUILDINGS IEEE Std 241-1990 5) Flat Billing Ñ Certain applications involve service to the load of a Þxed characteristic. For such loads, the supplying utility may offer

### BGE Service Application Guidelines Residential Modification/Relocation Projects

BGE Service Application Guidelines Residential Modification/Relocation Projects To the Customer Following is important information to assist you in applying for BGE gas and/or electric modification or

### GENERATOR SELECTION. a. Three phase - 120/208V, 3 phase, 4W wye; 277/408, 3 phase, 4W wye; * 120/240V 3 phase, 4W Delta

GENERATOR SELECTION Generators must be sized to handle their load based on the continuous KW, kilowatt load, and KVA, kilovoltamp load, and the worst case starting load KW + KVA. They must be derated for

### FW-X240 AUTO TRANSFORMER Installation Manual

FW-X240 AUTO TRANSFORMER Installation Manual 1 FW-X240 Auto Transformer About OutBack Power Systems OutBack Power Systems is a leader in advanced energy conversion technology. Our products include true

### THREE PHASE CIRCUITS

THREE PHASE CIRCUITS A. PREPARATION 1. Three Phase Voltages and Systems 2. The Determination of Phase Sequence 3. Blondel's Theorem and Its Consequences 4. References B. EXPERIMENT 1. Equipment List 2.

### High-Efficiency AC Power Distribution for Data Centers

High-Efficiency AC Power Distribution for Data Centers White Paper 128 Revision 2 by Neil Rasmussen > Executive summary The use of 240 volt power distribution for data centers saves floor space, simplifies

### Proper Application of 415V Systems in North American Data Centers. A White Paper from the Experts in Business-Critical Continuity

Proper Application of 415V Systems in North American Data Centers A White Paper from the Experts in Business-Critical Continuity Introduction Increasing pressure to reduce operating expenses and be more

### Circuit breaker panel. Power supply for condensing unit. Power supply for furnace. Air handler (Furnace)

UNIT OBJECTIVES Describe the concept of year-round air conditioning List three typical year-round air conditioning system types List the five ways to condition the air Determine airflow for a cooling system

### Applying For New or Revised Electric Service

Applying For New or Revised Electric Service Dear Customer: ComEd is happy to assist you in initiating new or revised electric service to your location. Please complete, sign and return the attached service

### Battery Backup for Grid-Tied PV Systems

A presentation for solar industry professionals Presented by Doug Pratt, and SimpleRay Solar SMA Sunny Island System Large(!)Outback System But first, a moment of thanks for northern California growers

### Rotary Phase Converters

FACTS from Ronk Electrical Industries, Inc. Bulletin 11981 Rotary Phase Converters ROTOVERTER Pat. No. 3,670,238 ROTO-CON Pat. No. 4,158,225 What are the ROTO-CON and ROTOVERTER power converters? The ROTO-CON

### Application of Four-Pole Circuit Breakers within Data Centers

Application of Four-Pole Circuit Breakers within Data Centers December 2013/AT324 by Frank Waterer, Fellow Engineer, Schneider Electric Engineering Services Make the most of your energy SM Revision #1

### Simulation of Ungrounded Shipboard Power Systems in PSpice

Simulation of Ungrounded Shipboard Power Systems in PSpice Haibo Zhang IEEE Student Member Karen L.Butler IEEE Member Power System Automation Lab Electrical Engineering Department Texas A&M University

### Server Technology Intl.

Server Technology, Inc. 3-Phase Power in the Data Center White Paper STI-100-005 North America/ASIA EMEA Server Technology, Inc. Server Technology Intl. 1040 Sandhill Drive Sienna Court Reno, NV 89521

### Power System Harmonics

Pacific Gas and Electric Company Power System Harmonics What are power system harmonics? Ideally, voltage and current waveforms are perfect sinusoids. However, because of the increased popularity of electronic

### TRANSFORMERS. Unit 14 OBJECTIVES

Unit 14 TRANSFORMERS OBJECTIVES After studying this unit, the student will be able to state the purpose of a transformer. explain the principle of mutual induction. determine the output voltage of a transformer

### The Fundamentals of Three-Phase Power Measurements. Application Note

The Fundamentals of - Power Measurements pplication ote pplication ote 0 120 240 360 Figure 1. -phase voltage wavefm. Figure 2. -phase voltage vects. 100Ω 100Ω Figure 4. -phase supply, balanced load -

### Before You Start 1 Overview 2 Supported Devices 4 Public (User LAN) and Private (APC LAN) Networks 5. Initial Configuration Requirements 6

Contents Introduction 1 Before You Start 1 Overview 2 Supported Devices 4 Public (User LAN) and Private (APC LAN) Networks 5 Initial Configuration Requirements 6 Overview 6 Setup Wizard 7 Status, Alarm,

### CHAPTER 4 UTILITY SYSTEMS ELECTRICAL. Utility Systems Electrical. Main Panel

CHAPTER 4 UTILITY SYSTEMS ELECTRICAL Utility Systems Electrical The electrical supply to your home begins outside, where you will see either an overhead feed and piping down the side of your home or (if

### Effective: September 10, 2006 Vermont Attachment 1 to Rule 5.500 Public Service Board Page 1 of 6

Public Service Board Page 1 of 6 STANDARD APPLICATION FOR INTERCONNECTION OF GENERATION RESOURCES IN PARALLEL TO THE ELECTRIC SYSTEM OF: (Interconnecting Utility) Preamble and Instructions: An owner of

### Inverter technology. bulletin

Inverter technology application bulletin What is the inverter component? The inverter is an electronic power component that continuously varies the electricity supply frequency of an electric motor. The

### DOE FUNDAMENTALS HANDBOOK ELECTRICAL SCIENCE Volume 4 of 4

DOE-HDBK-1011/4-92 JUNE 1992 DOE FUNDAMENTALS HANDBOOK ELECTRICAL SCIENCE Volume 4 of 4 U.S. Department of Energy Washington, D.C. 20585 FSC-6910 Distribution Statement A. Approved for public release;

### Single-phase (220...240 V) voltage monitoring: Undervoltage Overvoltage Window mode (overvoltage + undervoltage) Voltage fault memory selectable

Features 70.11 70.31 70.41 Electronic voltage monitoring relays for single and three-phase applications Multifunctional types, providing the flexibility of monitoring Undervoltage, Overvoltage, Window

### AC Versus DC Power Distribution

AC Versus DC Power Distribution Issues to consider when comparing options for improving data center energy efficiency By Robert W. Johnson Chief Engineer, Platform Development and Intellectual Property,

### Specification guide no. 9 Active harmonic conditioner from 20 to 480 A

Active harmonic conditioner from 20 to 480 A Contents 1 - Installations concerned... 2 1.1 - New installations... 2 1.2 - Existing installations... 2 2 - General... 2 2.1 - Scope... 2 2.2 - Applicable

### Single and Three Phase Transformer Testing Using Static Motor Circuit Analysis Techniques

Single and Three Phase Transformer Testing Using Static Motor Circuit Analysis Techniques Howard W. Penrose, Ph.D On behalf of ALL-TEST Pro, LLC Old Saybrook, CT Introduction Field and shop testing of

### ISL Insulation monitoring devices Continuous monitoring of IT systems from photovoltaic to industrial applications.

ISL Insulation monitoring devices Continuous monitoring of IT systems from photovoltaic to industrial applications. Ensuring operational continuity To ensure the operational continuity of an electrical

### Figure 1 - Crydom 3RHP Three-phase Hybrid Solid State Contactor. Crydom Inc.

Crydom RHP Series 3 Phase Hybrid Solid State Contactor By Paul Bachman Fellow Engineer, Crydom, Inc. ABSTRACT Solid State Relays and Contactors (SSRs) have been available in one form or the other for over

### Understanding Power Factor and How it Affects Your Electric Bill. Presented by Scott Peele PE

Understanding Power Factor and How it Affects Your Electric Bill Presented by Scott Peele PE Understanding Power Factor Definitions kva, kvar, kw, Apparent Power vs. True Power Calculations Measurements

### Power measurement in balanced 3 phase circuits and power factor improvement. 1 Power in Single Phase Circuits. Experiment no 1

Experiment no 1 Power measurement in balanced 3 phase circuits and power factor improvement 1 Power in Single Phase Circuits Let v = m cos(ωt) = cos(ωt) is the voltage applied to a R-L circuit and i =

### > Executive summary. The Role of Isolation Transformers in Data Center UPS Systems. White Paper 98 Revision 0. Contents.

The Role of Isolation Transformers in Data Center UPS Systems White Paper 98 Revision 0 by Neil Rasmussen > Executive summary Most modern UPS systems do not include the internal s that were present in

### 21 st Century Facilities

Electrical Testing 21 st Century Facilities Facility Owners face tough challenges 24 X 7 reliability needed Non linear loads cause harmonics VFD Computers Switching transients disrupt operations Less customer

### INTRODUCTION. THREE PHASE SSRs DEFINED & DESCRIBED

pero 1 Three Phase Solid State Relays & Their Application in Three Phase Heating Circuits By Paul Bachman, Fellow Engineer, Dr. Oscar Montero, R&D Manager, and Doug Sherman, FSAE Manager, Crydom, Inc.

### Triplen Harmonics Mitigation 3 Phase Four-Wire Electrical Distribution System Using Wye- Zig-Zag Transformers

Journal Journal of of Emerging Emerging Trends Trends in in Engineering Engineering and and Applied Applied Sciences Sciences (JETEAS) (JETEAS) 1 1 (1): (1): 72-78 72-78 Scholarlink Research Institute

### Three-phase and single-phase voltage optimisation systems

Three-phase and single-phase voltage optimisation systems Save Electricity - Save Money - Save the Environment What is a VO4 voltage optimisation system? The premise behind voltage optimisation is simple.

### Gree Solar Hybrid Hi Wall Inverter Air Conditioner

Gree Solar Hybrid Hi Wall Inverter Air Conditioner Utilize the natural power of the sun to heat or cool your home. Find out more at www.greeonline.com Why Choose a Solar Hybrid Inverter? The new Gree Solar

### The generation and supply of electricity within the U.K is achieved through the use of a 3-phase system.

Three Phase Electricity Supplies and Systems The generation and supply of electricity within the U.K is achieved through the use of a 3-phase system. This consists of 3 separate phase conductors along

ALL ABOUT LOAD SERVICE APPLICATION HOW-TO QUICK GUIDE New or expanded electrical connections: Getting power when and where you need it. To expedite your electricity service request, FortisAlberta has published

### Three-Phase AC Power Circuits

Electricity and New Energy Three-Phase AC Power Circuits Student Manual 86360-F0 Order no.: 86360-00 Revision level: 10/2014 By the staff of Festo Didactic Festo Didactic Ltée/Ltd, Quebec, Canada 2010

### Electric Power in Airplane. Student: Maja Knezev Course ELEN 615, 31 st August 2006

Electric Power in Airplane Student: Maja Knezev Course ELEN 615, 31 st August 2006 Power sources on aircraft engine driven AC generators, auxiliary power units (APUs), external power and ram air turbines.

### COUNTY OF LOS ANGELES BUILDING AND SAFETY DIVISION ELECTRICAL CODE FEE SCHEDULE (Title 27 of the County of Los Angeles Code, Ord No.

COUNTY OF LOS ANGELES BUILDING AND SAFETY DIVISION ELECTRICAL CODE FEE SCHEDULE (Title 27 of the County of Los Angeles Code, Ord No. 2013-0049) Effective July 1, 2014, Electrical Permit Fees in the unincorporated

Radial Distribution Test Feeders Distribution System Analysis Subcommittee Report Abstract: Many computer programs are available for the analysis of radial distribution feeders. In 1992 a paper was published

### Introduction. Upon completion of Basics of Switchboards you should be able to: Explain the role of switchboards in a distribution system

Table of Contents Introduction... 2 Distribution Systems... 4 Switchboard Definition... 9 Switchboard Construction... 12 Service Entrance Equipment... 18 Service Section... 20 Switchboard Grounding...

### Alternating current three-phase circuits

Unit. C HEE-PHE CCU lternating current three-phase circuits Unit. C HEE-PHE CCU COE: hree-phase systems characteristics Generation of three-phase voltages hree-phase loads -Y and Y- transformation nstantaneous

### The reliability of the grid

Power topic #9019 Technical information from Cummins Power Generation Power system considerations for cell tower applications White Paper By Wissam Balshe, Group Leader, Sales Application Engineering Industry

### Power Distribution in Data Centers: STARLINE Track Busway, PX ipdus and Power IQ

Power Distribution in Data Centers: STARLINE Track Busway, PX ipdus and Power IQ 2011 Raritan Inc. Overview Data center managers are faced with increasingly challenging demands: supplying additional computing

### GUIDE TO NET ENERGY METERING. www.heco.com

GUIDE TO NET ENERGY METERING www.heco.com Welcome to Net Energy Metering As a Net Energy Metering (NEM) customer, you are helping Hawaii reach its clean energy goals. Your photovoltaic (PV) system should

### Unified requirements for systems with voltages above 1 kv up to 15 kv

(1991) (Rev.1 May 2001) (Rev.2 July 2003) (Rev.3 Feb 2015) Unified requirements for systems with voltages above 1 kv up to 15 kv 1. General 1.1 Field of application The following requirements apply to

### INDUSTRIAL AND COMMERCIAL SERVICE TRANSFORMER & METERING INSTALLATION SPECIFICATION

INDUSTRIAL AND COMMERCIAL SERVICE TRANSFORMER & METERING INSTALLATION SPECIFICATION February 2013 NOTE: If conflict exists between St. Thomas Energy s Conditions of Service and this document, the Conditions

### Chapter 12: Three Phase Circuits

Chapter 12: Three Phase Circuits 12.1 What Is a Three Phase Circuit? 12.2 Balance Three Phase Voltages 12.3 Balance Three Phase Y to Y Connection 12.4 Other Balance Three Phase Connections 12.5 Power in

### EEL303: Power Engineering I - Tutorial 4

1. Determine the voltage at the generating station and the efficiency of the following system (Figure 1): Both transformers have ratio of 2kV/11kV. The resistance on LV side of both Figure 1: transformers

### SECTION DVD01: VOLTAGE DROP/VOLTAGE FLICKER AND TRANSFORMER SIZING GUIDELINES

Issued 06-01-07 DESIGN Section DVD00 INFORMATION SECTION Page 1 of 1 INDEX SECTION DVD01: VOLTAGE DROP/VOLTAGE FLICKER AND TRANSFORMER INTRODUCTION... Page 2 LOAD ESTIMATING AND TRANSFORMER SIZING GUIDELINES...Page

### Extollo Communications. Home Electrical Wiring and Cross Phase Coupling Overview

Extollo Communications Home Electrical Wiring and Cross Phase Coupling Overview Table of Contents Introduction... 3 Electrical Wiring in the Typical North American Home... 3 Figure 1. Transformer for a

### I = V/r P = VI. I = P/V = 100 W / 6 V = 16.66 amps. What would happen if you use a 12-volt battery and a 12-volt light bulb to get 100 watts of power?

Volts, Amps and Ohms Measuring Electricity The three most basic units in electricity are voltage (V), current (I) and resistance (r). Voltage is measured in volts, current is measured in amps and resistance

### How Much Voltage Drop Is Acceptable?

How Much Voltage Drop Is Acceptable? Article supplied by Ideal The National Electrical Code (NEC) recommends that the combined voltage drop of the electrical system (branch circuit and feeders) not exceed

### 1 Introduction. 2 Two Phases. J.L. Kirtley Jr.

Massachusetts Institute of Technology Department of Electrical Engineering and Computer Science 6.061 Introduction to Power Systems Class otes Chapter 3 Polyphase etworks J.L. Kirtley Jr. 1 Introduction

### RISH EM 3490 DS Dual Source Energy Meter RISH EM 3490 DS. Application : Product Features:

Application : RISH Master 3490 DS measures important electrical parameters of Utility (in normal mode) & Generators (in Power back up) in three phase and single phase Network & replaces the multiple analog

### ELECTRIC WATER HEATER CREDIT

RESIDENTIAL, FARM AND SMALL COMMERCIAL ELECTRIC WATER HEATER CREDIT AVAILABILITY Available to any member of the REMC, located on its lines for general residential, farm, and small commercial use up to

### MODELING AND TESTING OF UNBALANCED LOADING AND VOLTAGE REGULATION. Prepared For: California Energy Commission Public Interest Energy Research Program

PIER FINAL PROJECT REPORT MODELING AND TESTING OF UNBALANCED LOADING AND VOLTAGE REGULATION Arnold Schwarzenegger Governor Prepared For: California Energy Commission Public Interest Energy Research Program

### CONTROLS DATA MANAGEMENT PROCESS AUTOMATION EUROCUBE. General purpose single phase thyristors and solid state relays Product data.

425 CONTROLS DATA MANAGEMENT PROCESS AUTOMATION EUROCUBE General purpose single phase thyristors and solid state relays Product data abc 425 EUROCUBE A complete range of low cost solid state relays and

### SURGE PROTECTIVE DEVICES

SURGE PROTECTIVE DEVICES 1. INTRODUCTION In order to ensure safety of people, protection of equipment and, to a certain extent, continuity of supply, insulation co-ordination aims at reducing the likelihood

### ATTACHMENT F. Electric Utility Contact Information Utility Name. For Office Use Only

ATTACHMENT F CATEGORY 2 GENERATOR INTERCONNECTION APPLICATION FOR ALL PROJECTS WITH AGGREGATE GENERATOR OUTPUT OF MORE THAN 20 KW BUT LESS THAN OR EQUAL TO 150 KW Also Serves as Application for Category

### BGE Service Application Guidelines Commercial & Industrial Projects

BGE Service Application Guidelines Commercial & Industrial Projects To the Customer Following is important information to assist you in applying for BGE gas and/or electric service and in completing the

### The Basics of Digital Multimeters

IDEAL INDUSTRIES INC. The Basics of Digital Multimeters A guide to help you understand the basic Features and Functions of a Digital Multimeter. Author: Patrick C Elliott Field Sales Engineer IDEAL Industries,

### TRANSFORMER: THREE PHASE

CONTENTS Transformer : Three Phase 1211 C H A P T E R 33 Learning Objectives Three-phase Transformers Three-phase Transformer Connections Star/Star or Y/Y Connection Delta-Delta or Connection Wye/Delta

### NATIONAL CERTIFICATE (VOCATIONAL)

NATIONAL CERTIFICATE (VOCATIONAL) SUBJECT GUIDELINES ELECTRICAL PRINCIPLES AND PRACTICE NQF Level 4 September 2007 ELECTRICAL PRINCIPLES AND PRACTICE LEVEL 4 CONTENTS INTRODUCTION 1 DURATION AND TUITION

National Renewable Energy Laboratory Innovation for Our Energy Future A national laboratory of the U.S. Department of Energy Office of Energy Efficiency & Renewable Energy Modeling and Testing of Unbalanced

### TECHNICAL DESCRIPTION OF THE DISTRIBUTION SUBSTATION REMOTE MONITORING SYSTEM

HELLENIC ELECTRICITY DISTRIBUTION NETWORK OPERATOR S.A. NOTICE OF CALL FOR TENDERS No ND-xxx PROJECT: Pilot Telemetering and Management System for the Electric Power Supply Demand by Residential and Small

### LTR Series Uninterruptible Power Systems 700 VA - 2.1 KVA. General Specification

08/17/12 Rev2 LTR Series General Specification 700 VA to 2.1 KVA 1.0 General LTR Series Uninterruptible Power Systems 700 VA - 2.1 KVA General Specification This specification describes the features and

### Current valve. for AC 24 V pulse/pause control of electrical loads up to 30 kw

4 937 DESIO Current valve for AC 24 V pulse/pause control of electrical loads up to 30 kw SEA45.1 Use The current valve is used for the control of electric heating elements in heating, ventilation and

Transfer Switch 30 Amps STS-30 Owner's Manual Please read this manual before operating your transfer switch Section 1 Introduction Function of a Transfer Switch In case of failure of the main AC power

### The Different Types of AC Power Connectors in North America

The Different Types of AC Power Connectors in North America White Paper 20 Revision 1 by James Spitaels > Executive summary A confusing array of AC power plugs and receptacles exist to deliver power to