1 Risk Control Bulletin Water Damage Prevention A Property Protection Imperative Water is one of the most destructive agents when released into a building. Water erodes surfaces; causes rot and deterioration to building materials; creates an environment for mold growth; contributes to indoor air quality issues and damages building finishes. Most of the root causes of water damage are preventable. They can be managed and addressed with low to no cost strategies that any building owner can implement. Implementing a program to prevent water damage can pay additional benefits in improving occupant comfort, reducing air quality problems and safeguards your staff and visitors from injuries related to water damage. CNA knows that water damage is a leading cause of property related claims. Water damage issues occur more frequently than fires, thefts or vandalism. The cost of water damage claims continues to escalate as the cost of restoring finishes and replacing damaged building materials escalate. Often this cost is passed onto the policyholder in the form of deductibles for the smaller events. Simple steps to reduce the impact of water damage can pay dividends in the long run. Sources of Water Damage This guide will address three major areas of water damage exposure that every building faces. These three exposures are water use and transport systems, the building envelope and water from outside sources. We will examine the building systems that transport or use water as part of their normal function. Developing plans to address these systems and their water damage potential can improve your building system reliability and efficiency as well as protect your facility from a damaging water release. The building envelope, (walls, floors and ceiling and roof) are all designed to prevent water intrusion. Simple maintenance and inspection programs can help prevent water damage and damage to the building from water intrusion. The suggestions for protecting your building envelope will pay dividends in reduced damage, extended life of surfaces, possible warranty recoveries, and improved energy efficiencies. Water can come from outside sources or an unintended inside source. How you manage and respond to surface water, back up of sewers and drains and other flood hazards is a key risk control element for a property owner. CNA can suggest preventive and response plans that will help address this significant cause of damage. CNA has a team of risk control professionals who are available to help you with this or other risk control and risk management programs. You can also access risk control information, programs and services via our web site CNA Commercial Property and Casualty Insurance Provider Carrier Home Building Systems Freeze Protection All of your building systems that use water are subject to freeze damage. Additional guides presented at the conclusion of this bulletin can help you identify freeze exposures and take the necessary steps to prevent damage: Winter Freeze Precautions Preventing Sprinkler System Freeze-Ups Dry-Pipe Sprinkler Valve Heated Enclosure Leak Detection and Reporting Where there is a leak, there is a flood. You may have heard this phrase. It is very true. Small leaks that are not reported, investigated and repaired can lead to significant damage to your property. Does your property management program assign a high priority to investigating and correcting every leak reported? Do your tenants know that you will immediately respond to a leak to correct the problem? You should create awareness that you take water damage prevention seriously. Publicize your reporting process and make sure that leaks get immediate attention. Unreported leaks are leaks that can persist, create hidden damage, promote mold growth and cause unneeded damage to your property. : A low cost risk control procedure is to promptly investigate and correct any reported leak. This simple process can prevent significant damage to your property. It is not a costly program, but is one that will recover its costs very quickly. A very simple log, such as the one shown below, can be used to track reports, assignments and results. A review of this log should be part of the quarterly review. Leak Reported Date Assigned to Findings The information, examples and suggestions presented in this material have been developed from sources believed to be reliable, but they should not be construed as legal or other professional advice. CNA accepts no responsibility for the accuracy or completeness of this material and recommends the consultation with competent legal counsel and/or other professional advisors before applying this material in any particular factual situations. This material is for illustrative purposes and is not intended to constitute a contract. Please remember that only the relevant insurance policy can provide the actual terms, coverages, amounts, conditions and exclusions for an insured. All products and services may not be available in all states and may be subject to change without notice. CNA is a registered trademark of CNA Financial Corporation. Copyright 2013 CNA. All rights reserved.
2 Leak Response When you have a serious leak from piping, equipment, a roof or other building element, you don t have time to put together the tools and plan for a response. Most businesses have response plans for fires, medical emergencies and other critical events. You should treat water leaks and releases as a critical event for your property. Have a plan, have the equipment and know who to call for immediate assistance. : Do you have a valve list and shut off valves for your water system identified? Do you exercise these valves to be sure they can be used? Does your staff know the locations of the valves? This very simple, low cost action will limit the release of water from damaged plumbing system. This step alone can limit the extent of damage and reduce the loss you experience. Valve identification tags and labels are widely available. A very flexible system uses a high visibility, write-on tag that allows you to label the valve. The highly visible color you select will easily identify the valve for your staff. A sample Valve Identification Sheet is shown on the following page. You can identify, locate and document the key valves and their location using this type of sheet. Valve Identification Sheet Image of Valve Not being able to find a valve can lead to the water running for hours while you wait for someone to find the right valve. A simple program to identify, label and exercise valves can be a critical risk control effort and is a low cost, high return on investment. Valve Identification Plan: Your Key to Water Damage Control! The simple valve tag shown above can be the key to controlling water damage in your facility. Having an effective valve identification program is a low cost water damage prevention and reduction program. This program consists of four simple steps. 1. Identify the valve that controls water supply to specific equipment. 2. Apply a standard highly visible valve identification tag. 3. Exercise the valve to assure proper operation. 4. Advise your employees of the program, identification method, and how to operate the various types of valves. Description and Location Main incoming water valve is located in the mechanical room in the northwest corner of the building, red handle on far wall. : Do you have a leak response kit available? Mops, absorbent pads, wet dry vacuums, squeegees and wet floor warning signs should be immediately available. : Do you have an agreement with a water damage restoration firm? Have you authorized your staff to notify the outside resource when needed? Waiting until the next business day to start a clean-up can allow damage to spread and create a greater loss.
3 Having the proper resources and a plan to respond can be another low cost water damage prevention program. Sump Pumps Your sump pump is a critical piece of equipment. It may be all that stands between you and a flood. Do you pay attention to this critical item? Sump pumps are often taken for granted until they fail to operate. The consequences can be costly. Prevention is a function of preventive maintenance, planning for emergencies and having a reporting system to detect a failure before the flood occurs. Is your sump pump on a preventive maintenance program? Check the float switch, discharge the check valves and check the motor for proper operation in accordance with the manufacturer s recommended schedule and procedures. Do you need a back up power source? Adding a second pump with a battery back up or connecting your existing pump to emergency power is a low cost, high return undertaking. Many heavy storms can cause power interruptions. You may need your sump pump during the peaks of a heavy storm. Back up power is a prudent risk control action. How do you know the pump is not working? Having a high level water detector placed above the float level on the sump pump well will report a pump failure or a water flow that exceeds your pump capacity. Getting this alarm early will allow your water damage response plan to address and control the situation. Depending on the staffing at your facility this alarm can be a local signal or tied into an off premises monitored alarm system. Water Heaters Tank type water heaters create a significant water damage problem if they fail and release their contents into your building. With no excess flow control the damaged water heater will continue to leak until it is discovered and the water supply turned off. Many of these tanks fail due to age. The Building Owners and Managers Association (BOMA) estimates the life span of a tank type water heater at 15 years. You should consider planned replacements of this equipment if it is located in areas that would cause damage if they leak. When installing new equipment add a safety pan to catch leaks and pipe the pan to a drain. Water leak detection can be used to close the supply valve and limit the water leak size. Water heaters are an often forgotten plumbing fixture having a large role in many water damage events. HVAC Systems Your HVAC system is a key system to maintain a comfortable building. If not properly maintained this system can create significant water damage exposures. You should include the HVAC system as part of your water damage prevention efforts. Most HVAC systems create some discharge of condensate. This may be into a pan with a drain or may be piped to a small pump that sends the accumulated water to a drain. Identifying and maintaining these condensate pans and drains is an important control. Water accumulating in these pans can cause corrosion, leakage, and create odor problems. Roof mounted equipment should ideally have the condensate drain piped to a gutter or roof drain too. Maintaining your HVAC system can control humidity levels in your building. This can control the development of mold, odors and indoor air quality issues. Maintaining these systems pays benefits beyond water damage prevention. Identify all condensate drains and place on a preventive maintenance program to keep the drains clear, or maintain the small condensate pumps used to pump water to a drain. Water Reuse and Collection Systems An emerging water damage exposure for building owners is the use of gray water or rain water collection and reuse systems to reduce water consumption for irrigation purposes. This introduces new collection tanks and distribution piping to the plumbing system. As these systems collect water from unregulated sources, they are subject to overflow. Be sure your system has automatic diversion to drain excess water and level monitoring in case the diversion becomes clogged. This level control should be part of your inspection and testing program to assure they operate properly. The valves for this system should be part of your valve identification and location program. Automatic Shut Off Valves Your plumber can help you with a number of appliance-specific automatic shut off valves. These systems function on the basis of water detection and electronically controlled valves. These valves can help limit the spread of water from a damaged plumbing fixture. Valves are available that can be attached to the supply for specific appliance or devices or an entire building or section of a building. Consult with your plumbing contractor to select a valve and control system that suits your specific needs. The information, examples and suggestions presented in this material have been developed from sources believed to be reliable, but they should not be construed as legal or other professional advice. CNA accepts no responsibility for the accuracy or completeness of this material and recommends the consultation with competent legal counsel and/or other professional advisors before applying this material in any particular factual situations. This material is for illustrative purposes and is not intended to constitute a contract. Please remember that only the relevant insurance policy can provide the actual terms, coverages, amounts, conditions and exclusions for an insured. All products and services may not be available in all states and may be subject to change without notice. CNA is a registered trademark of CNA Financial Corporation. Copyright 2013 CNA. All rights reserved.
4 Evaluate and install automatic shut off valves where appropriate. You should incorporate water damage prevention into your facility inspection program. Adding water damage prevention to your other safety inspections such as fire extinguishers, emergency lights, etc., can reinforce the importance of this property risk control effort. It will also keep your staff aware of the items that are needed for a prompt response and recovery effort.
5 Valve Inspection Checklist Inspection Item Frequency Findings Indicate any signs of water leaks at this location. Review of leak reporting log. Identify all shut off valves. Is water shut off valve list current? Valve locations are labeled and accessible? Valves have been exercised? All staff/residents have been trained/informed on valve location and operation? Water damage response kit is stocked and available? Contact information for water damage restoration form is available? Sump pump maintenance current? Alternate power for sump pump? HVAC condensate pans and drains clean and maintained? HVAC system operating to control humidity? Have freeze precautions been taken? Any cold weather valves to be closed? Low temperature alarms tested? Are water heaters more than 15 years old? Are water heaters provided with a safety pan piped to a drain? Are there periodic inspections of water heaters, toilets, sinks, and appliance water hoses? Are sewer lines periodically inspected and cleaned? Are water reuse and collection systems provided with a safe overflow point? Is the automatic level control on water collection and reuse tanks tested regularly? Automatic shut off valve installed where appropriate? Annually Semi Annually Semi Annually Annually Fall and Winter Fall and Winter Fall and Winter Annually Annually Annually Annually Semi Annually The information, examples and suggestions presented in this material have been developed from sources believed to be reliable, but they should not be construed as legal or other professional advice. CNA accepts no responsibility for the accuracy or completeness of this material and recommends the consultation with competent legal counsel and/or other professional advisors before applying this material in any particular factual situations. This material is for illustrative purposes and is not intended to constitute a contract. Please remember that only the relevant insurance policy can provide the actual terms, coverages, amounts, conditions and exclusions for an insured. All products and services may not be available in all states and may be subject to change without notice. CNA is a registered trademark of CNA Financial Corporation. Copyright 2013 CNA. All rights reserved.
6 Building Envelope The first line of defense against water intrusion is the building envelope. This is a complex system of materials. Your building envelope has connections and joints that must work together to expand, contract and retain a watertight envelope. This system needs maintenance and inspections to be reliable. In most cases routine maintenance and inspection is a low to no-cost program that can extend the life of your building envelope and protect you from water leak damage. Roofing systems The roof on your building is a complex system of roof covering, flashing, metal work and sealants that together keep water out. Leaks in this system can deteriorate the insulation under the roof cover, cause rot and structural damage, create mold growth and damage surfaces inside the building. Severe problems with your roof can cause ponding and water retention that can lead to collapse. Snow loads that are not managed can also cause collapse. Identify areas of your building roof that are subject to unusual snow loads and plan for removal of the snow. Roof inspections are the key control to prevent water damage from roof leaks. Visual inspection, verifying roof drains are clear and looking for damage to flashing and edge details, is a no-cost program. You can supplement this program with regular inspections by a roofing maintenance provider. These firms can correct small deficiencies before they create bigger problems. These inspections may be required to support the warranty on your roof, so review any warranty documents for required inspection frequency and documentation. Another roof inspection service is aerial infrared which is a simple non-destructive inspection designed to find where moisture is penetrating your roof. It can pinpoint problem areas with exceptional accuracy to eliminate blind core testing and unnecessary roof replacements. This proven approach is highly accurate in detecting moisture at its earliest stages so issues can be addressed before there are visible signs, structural damage or business interruptions. By using this proactive predictive tool, a building owner or property manager can significantly extend the life of their roof while reducing overall maintenance expenditures. A Risk Assessment Roof Inspection Form can be found at the conclusion of this tool. Windows Windows require routine maintenance to keep them water tight. The most important item to inspect and maintain is the bead of caulk between the window and the structure. Failure of this simple bead of caulk can create water damage, potential for rot and mold development. Add window seals and caulk to your annual inspection and maintenance program. Windows can be damaged in storms and allow water entry. Modern building codes may require windows in coastal areas to have wind speed ratings and impact resistance. When replacing or updating window, consult the local building official to be sure you are providing your building with the most current level of protection. Utility and Mechanical Penetrations The building envelope has numerous points where vents, wires, pipes, and other mechanical and utility rated components penetrate the building envelope. These areas should be initially waterproofed, sealed and arranged to shed and repel water. They should also be part of your inspection and maintenance program to maintain the integrity of these penetrations. Every one of these openings is a potential leak and should be inspected and maintained to prevent that leak from occurring. Evaluate utility penetrations for water tight seals. Walls Exterior walls are designed to shed water. They are not designed to hold back standing water. A major source of water intrusion and damage can occur when landscaping, or grading of the exterior soils allow water to drain towards or stand against exterior walls. A routine visual inspection after a rain can easily detect areas where water is accumulating against your building walls. Changing the grade or adding a drain tile network to safely convey this water away is a low cost solution.
7 Look at exterior grade for water that runs toward your building. Change the grade or provide a safe drainage path. Look at the use of irrigation systems as well. Continued application of water against your exterior walls can lead to damage and water intrusion. If your irrigation system is wetting the building, you are wasting water and potentially damaging your building. The irrigation system should be adjusted to avoid this damage causing condition. Adjust irrigation system to prevent water from wetting the building. Building Envelope Self-Inspection Inspection Item Frequency Findings Have you completed a quarterly roof inspection? Are caulking and seals around windows in good condition? Any evidence of leaks around windows? Have all building penetrations been inspected and sealed as appropriate? Exterior walls showing evidence of water damage or accumulation? Does the irrigation system wet the building? Outside Sources of Water Semi Annually Back up of Sewers and Drains Semi Annually Semi Annually Spring / Startup Sewer back up can be addressed by inspection and maintenance to maintain existing systems. Clogged drains should be immediately identified and repaired or cleared. Inspection processes can include video inspection of lines and verifying their condition. If you have an identified exposure to sewer back up, the addition of a check valve in the affected line is also a consideration to prevent this type of exposure. Surface Water Surface water can be managed by proper grading and use of drain tile systems to divert water to a safe area. Changes in adjacent properties can impact your property by diverting water towards your property. Noting any changes in the amount or direction that water is taking on your site can help you identify surface water exposures. Proper maintenance of exterior drains in areas such as loading docks, outside stairwells and other areas should be included on a self inspection checklist. A clogged drain in these areas can create an immediate loss exposure for you. Flood Hazards If you are exposed to flooding from rivers, streams or other bodies of water, you can identify these hazards from flood hazard maps. Flood proofing strategies are available from FEMA to address these exposures. If you have this exposure, then working with an engineering / architectural firm to design a permanent flood proofing solution would be the best solution to this exposure. People are stunned to learn the extraordinary cost to repair damage arising from flood waters. The National Flood Insurance Program (NFIP) reports that one foot of water in a 1- story building causes content damage averaging 27 percent of the cost to replace. At 2 feet, the average cost is 52 percent. When flood waters are 8 or 12 feet deep, the average repair bill is 66 and 68 percent, respectively. Structural damage is also much greater than many people contemplate. A one foot flood can cause damage equivalent to 16 percent of the single story structure value. When the depth of flooding increases to 2 feet the damage is estimated at 29 percent of the structure value. When depths are 8 and 12 feet the percentages rise to 44 and 56 percent of the values (US Army Corps of Engineers Study). Flood hazards must be recognized, planned for and responded to in a prompt and efficient manner. You must have a plan to reduce the exposure and to safeguard your property from the rising waters. The FEMA web site provides advice in regard to flood preparation and mitigation. Go to CNA has a flood preparation checklist to help prepare your facility for a flood. This checklist can be used as the basis for preparing to reduce your loss exposure from a flood. The information, examples and suggestions presented in this material have been developed from sources believed to be reliable, but they should not be construed as legal or other professional advice. CNA accepts no responsibility for the accuracy or completeness of this material and recommends the consultation with competent legal counsel and/or other professional advisors before applying this material in any particular factual situations. This material is for illustrative purposes and is not intended to constitute a contract. Please remember that only the relevant insurance policy can provide the actual terms, coverages, amounts, conditions and exclusions for an insured. All products and services may not be available in all states and may be subject to change without notice. CNA is a registered trademark of CNA Financial Corporation. Copyright 2013 CNA. All rights reserved.
8 Recovering from a flood is not an easy process. Having a plan to evaluate, clean and dry mechanical equipment can help reduce the losses you incur. Use the guidance in the CNA publication, Before and After the Flood, to guide your recovery effort. Outside Sources of Water Inspection Inspection Item Frequency Findings Are materials stored at least 4 off the floor in areas subject to backup of sewers and drains? Have drains been Annually cleaned or have video inspection to identity potential clogs or obstructions? Any history of surface Semi Annually water intrusion? If so have exterior drains been provided or changes in slope provided to redirect water? Have you identified Annually the FEMA flood zone for your property? If in a flood hazard Annually area, do you have a flood response plan? Have you undertaken flood proofing of the building? Annually Builders Risk Projects A building under construction has unique exposures to water damage. The building is vulnerable as it is being enclosed and the process to install the water using appliances, fixtures and systems create exposures to leaks and unintended releases. The key to managing this exposure is having a water damage prevention plan for the job site. This plan should detail the proper reporting, response and mitigation steps to be taken in the event of a water damage event during construction or renovation work. Elements of your water damage prevention plan should include: Site development should include provisions to grade water away from the project. Accelerate permanent connections to storm water systems and retention areas to protect the job site from water accumulation. Initial foundation and footer work should include a documented inspection for water intrusion and immediate action to correct deficiencies. It is at this stage of the project that damaged or missing waterproofing will create an ongoing issue if not corrected. Use a third party inspector to verify that waterproofing systems installed in foundation and footers are properly applied and installed. As the building envelope is completed attention should be given to any leaks or water infiltration at windows, roofs or penetrations of the building envelope. These defects are often times easy to repair when they are exposed. The emergence of this issue after finishes are in place magnifies the repair cost and difficulty. As mechanical systems are installed consider a policy to shut off water at the end of every work day. This would limit the amount of water that could leak during unattended periods. Coordinate testing of plumbing and sprinkler systems with a low pressure air test to verify piping integrity. This simple step can identify potential problems before you apply high pressure water to test the systems. Develop a daily closing inspection for the project that includes water damage prevention and leak detection. If security officers are present, train them on water valve locations and operations. They can promptly detect and respond to a leak and prevent significant damage. Consider the use of water detection alarms for critical areas of the project - computer rooms, telephone exchanges, electrical vaults. These alarms are low cost and can be moved from job to job. Keep a water spill kit with absorbent socks or pigs available to contain and control a spill. Keeping the water on one level of the building will dramatically reduce your loss potential. Make water damage prevention a tool box topic for your site staff and subcontractors.
9 Risk Control Bulletin Winter Freeze-Up Precautions Too many businesses find themselves unprepared when normal winter weather suddenly turns extreme. During a severe cold spell, sprinkler or water pipes can freeze, burst, and produce devastating losses. Water damage from this type of incident, known as a freeze-up, can affect products in storage, paperwork, records, furniture, machinery, computers, and all types of electronic equipment. If the water leakage goes undetected for an extended period (over a weekend, for example), extensive flooding can result. Total costs often reach hundreds of thousands of dollars. In "deep-freeze" conditions, a broken window or an open door in an un-insulated or unheated area can let in enough cold to freeze nearby piping and start a catastrophic chain of events. Any equipment that contains or uses water, produces condensate, or depends on pneumatic controls is vulnerable to freezing. Other conditions that make your business susceptible to freeze-ups are heating systems that lack reserve capacity beyond their normal heating load, poor building insulation, and piping run out of doors. The following guidelines will help you plan for and implement preventive measures to better protect your business from the threat of freeze-ups. Before the Cold Sets In If at all possible, implement these measures in the fall, before the onset of cold weather. 1. Update your Emergency Response Program for winter emergencies to include appropriate response procedures for deep-freeze conditions. Appoint one or more members of the Emergency Response Team to monitor weather forecasts and initiate winter emergency procedures when appropriate. Develop procedures and priorities to be implemented when you lose heat and/or electricity. 2. Determine which processes are dependent upon continued building heat or electricity for safety (i.e., processes that are subject to solidification or runaway reactions) and need prompt attention. 3. Identify equipment, processes, and piping that contains or uses water or other liquid subject to freezing; they will need to be promptly and thoroughly drained if heat or electricity is lost. 5. Identify equipment that is vulnerable to freezing. Prepare the equipment for cold weather by: Draining and securing any idle equipment, Draining condensate frequently, Providing adequate heat or locating the equipment in a heated enclosure, and/or Protecting it with suitable anti-freeze. 6. Service the heating system before the heating season begins. Make sure adequate supplies of alternate fuels are on hand if the system is capable of dual firing. 7. Inspect and maintain the building shell to minimize unnecessary openings. Fix windows and doors so they close tightly. Caulk, insulate, and weather-strip as needed. Close and seal unneeded dampers, louvers, and vents. 8. Drain condensate from dry-pipe sprinkler system piping by opening the priming water level drain valve until the water in the riser has been expelled, and by using the auxiliary drains installed at system low points. If there are any trapped sections of branch line piping, it may be necessary to remove sprinklers and drain the water into a bucket. 9. Open any on-site fire hydrants and allow water to flow until it is flowing clear. This measure flushes any debris from the underground main and exercises the hydrant valve. Then slowly close the hydrant, making sure that it drains. Water can often be heard draining from the hydrant, and you will notice suction if you place a hand over the hydrant hose connection as the drainage occurs. During Cold Spells Monitor temperatures every few hours in vulnerable areas. Provide safe, portable heaters for vulnerable areas that might fall below 40 degrees. Provide heat or steam tracing for exterior piping that either contains liquids or needs to maintain constant temperatures. Use tarps to erect temporary windbreaks. For a permanent windbreak, consider planting evergreen trees and hedges upwind (prevailing winter wind direction) of vulnerable buildings and equipment. 4. Identify building areas that are unusually difficult to heat or that lose heat rapidly. Install ordinary thermometers to allow temperature monitoring during cold spells. The information, examples and suggestions presented in this material have been developed from sources believed to be reliable, but they should not be construed as legal or other professional advice. CNA accepts no responsibility for the accuracy or completeness of this material and recommends the consultation with competent legal counsel and/or other professional advisors before applying this material in any particular factual situations. This material is for illustrative purposes and is not intended to constitute a contract. Please remember that only the relevant insurance policy can provide the actual terms, coverages, amounts, conditions and exclusions for an insured. All products and services may not be available in all states and may be subject to change without notice. CNA is a registered trademark of CNA Financial Corporation. Copyright 2013 CNA. All rights reserved.
10 Risk Control Bulletin Preventing Sprinkler System Freeze-Ups Introduction Cold weather brings the danger of impaired fire protection because of water freezing in sprinkler piping, underground mains, gravity suction tanks or fire pumps. Such freezing not only leaves a risk vulnerable to fire and damage to the building contents, but may also necessitate expensive repairs to the system. Frequent freezing of automatic sprinkler systems occurs in climates not normally associated with cold weather. It is important that property owners be alert to unusual climatic changes that may cause freezing. They should be prepared to take preventive measures as if in a cold climate. The following preventive measures should be considered, prior to the cold season. Wet Pipe Sprinkler Systems Freeze-ups in wet sprinkler systems occur most frequently in exposed and out-of-the way places and during weekends or other shut down periods when a sudden cold snap catches a plant unprepared. Most freeze-ups result from failure to provide adequate heat. Others are caused by doors, windows, cracks, loose siding, or similar defects in building maintenance. Where false ceilings are installed under sprinklers or under piping with pendent heads, be sure the concealed space receives sufficient heat. Search for isolated drafts or cold air leaks into little frequented areas or spaces where there are sprinkler pipes. Keep in mind the possibility of high winds during periods of low temperatures. Repair windows and doors when necessary, and instruct watchmen to keep them tightly closed. Enclose pipes exposed outdoors in heated weather-tight boxing. Maintain extra heat during periods of extreme cold to keep the sprinkler piping from freezing. Check the heating system to make sure it is delivering heat to all areas of the facility. Maintain a tight building envelope. Look particularly for places where cold winds can blow in, closing up even small openings and keeping all doors, especially large shipping doors, tightly closed at all times except when they must be opened. During severe weather conditions, if an interruption of heating service extends more than a few hours, and the temperature in the building drops close to 40 degrees, you may need to drain the water from wet pipe sprinkler piping. If this is not done, ice plugs can obstruct the piping or possibly damage fittings and sprinklers. It would be advisable to become familiar with the operation of your system and drain procedures, prior to the onset of cold weather. It is likely that a contractor may not be able to respond quickly in an emergency. Should you need to do this, remember the protection afforded by the sprinkler system is no longer in effect. Any and all hazardous operations should be curtailed during this period. A continuous fire watch should be posted and provided with first aid fire fighting equipment and the means to summon assistance. Provide adequate heating capacity to prevent freezing during the severest protracted cold that might reasonably be expected. Pay particular attention to attics, under floor spaces, entries, stair towers, shipping rooms, and penthouses to ensure there are adequate heating ducts and airflow in these areas. Check room temperatures frequently, especially if they get near 40 degrees. After a prolonged period of abnormally cold weather, make drain tests of sprinkler risers, wherever practicable, to determine if underground mains are frozen. Open the drain wide, let it run 1/2 minute or more, and then shut it off. If the pressure fails to return to normal, clear the mains of ice as soon as possible. DO NOT use open flames or torches for thawing frozen water pipes near combustible materials or combustible building components. Dry Pipe Systems Dry pipe systems are generally installed in structures where temperatures are expected to drop below 40 F. They are designed for use inside buildings that are unheated, inadequately heated, or that must be open to outside cold temperature for appreciable time periods. Dry pipe systems generally freeze due to water collecting in improperly pitched pipes, failure to remove accumulated water from low point drains, or failure to drain the system properly after the valve has tripped.
11 Air is usually supplied to a dry pipe system by a compressor. The air intakes into the compressor should be located in a cold, dry atmosphere. Avoid warm, damp areas, since moisture introduced with the air condenses in the piping and collects at low points where it may freeze. Air driers should be installed on the air intake. An alternative is to use dry nitrogen gas in lieu of air. Antifreeze Systems These types of systems are generally used in small unheated areas of buildings, such as docks. The system uses an antifreeze solution generally consisting of water and watersoluble liquid, such as a glycerin or certain glycols. Valve drains should be installed at all low points that cannot be eliminated. These low point drain valves should be periodically opened (at least once a month) to see that the pipes are entirely free of water. Pay particular attention to low points under stairs or platforms. Repair, replace or refasten broken, missing or loose sprinkler pipe hangers to ensure proper pitch of sprinkler piping and to provide good drainage. Antifreeze solutions are recommended only for systems not exceeding 40 gallons. The antifreeze solution should be tested annually by a qualified contractor to assure proper solution-to-water mixture. Listed plastic CPVC sprinkler pipe and fittings should be protected from freezing with glycerin only. Repair all air leaks in the system to prevent the valve from tripping should the compressor lose power. It is mandatory that water always be present in supply piping up to the clapper of the dry pipe valve. Compressed air fills the piping from the clapper on the outermost sprinkler head. Therefore, arrangements must be made to prevent the water in the supply piping to the dry pipe valve from freezing. The best arrangement is to provide a dry pipe valve enclosure, suitably heated to at least 40 F at all times. The water supply pipe should come up through the floor in the center of the enclosure if possible. If the floor is concrete laid directly on earth, without air space, the supply pipe will be adequately protected by ground cover until it emerges in the valve enclosure. But if the floor of the enclosure is wood or any other material having appreciable air space beneath it, then the supply pipe beneath the floor must be enclosed and protected with insulation, sand or earth over its entire exposed portion until it enters the valve enclosure. The valve enclosure can be heated electrically from permanently mounted heaters under thermostatic control, so that 40 F or higher is always maintained. Steam or hot water heating systems from boilers supplied on 24-hour basis can also be used. A thermometer should be placed in the enclosure and checked at least once a day. The use of heat tape is prohibited. A temperature signaling device can be installed in the valve room or enclosure monitored by a central station alarm service. Gravity Tanks Gravity tanks require adequate heat to be maintained during cold weather to keep them from freezing. The formation of ice in the tank itself and on any part of the tank structure should not be allowed. The formation of heavy icicles through leaking of the tank is dangerous as tank collapse may ensue. People may also be endangered by falling icicles. Heating devices should be kept in good working order and the water temperature in the tank should be checked daily during freezing weather to maintain a temperature at or above 42 F. Service heating and circulation equipment well before the heating season arrives to permit adequate time for repairs or maintenance. Fire Pumps Keep pump rooms heated; maintain the room temperature above 40 F. Pay particular attention to detached buildings housing pumps. For diesel engine drives, maintain the room temperature at 70 F or above. Protect the suction source from freezing. If suction is taken from open water, make sure the pipe and intake are located so they will at all times be completely below frost level, underground and deep enough in the water to prevent their being obstructed by ice. Intake screens should be kept clear of obstruction by ice. Call your local CNA Risk Control representative for assistance in implementing this program. The information, examples and suggestions presented in this material have been developed from sources believed to be reliable, but they should not be construed as legal or other professional advice. CNA accepts no responsibility for the accuracy or completeness of this material and recommends the consultation with competent legal counsel and/or other professional advisors before applying this material in any particular factual situations. This material is for illustrative purposes and is not intended to constitute a contract. Please remember that only the relevant insurance policy can provide the actual terms, coverages, amounts, conditions and exclusions for an insured. All products and services may not be available in all states and may be subject to change without notice. CNA is a registered trademark of CNA Financial Corporation. Copyright 2013 CNA. All rights reserved.
12 Dealing with a Frozen Sprinkler System Should your best efforts fail and you discover your sprinkler system is frozen what immediate action should you take to limit the potential for further damage or an uncontrolled fire while the sprinkler system is impaired? Limiting further damage First, shut the control valve to the affected sprinkler system. Then open the 2-inch drain on the riser and any low point drains on the system. Use plastic tarps in the area of any actual pipe breakage to limit water damage to stock and supplies. After water flow has been stopped, follow these steps: 1. Notify the public fire department and CNA s risk control office that your sprinkler system is out of service and requires repairs. 9. If temporary heat is necessary, use only portable units listed by Underwriter s Laboratories or approved by Factory Mutual. Additionally these units should have constant supervision. 10. Electrical resistance heating should not be directly attached to overhead piping. If it is used to thaw underground piping, it should only be used by well-trained personnel. 11. Before the sprinkler system is restored to service, examine the system for cracked fittings, split pipes or leaking sprinkler heads. Finally, open all control valves and notify the local fire department and CNA Risk Control that the system is back in service. 2. Do not attempt to thaw piping in the building by using a torch or open flame device. 3. Cutting and welding or other operations employing an open flame should be prohibited in the area where the sprinkler system is out of service. 4. Hazardous operations such as spray painting, dipping or others using flammable liquids or producing a combustible dust should be suspended while the sprinklers are out of service. 5. A strict No Smoking policy should be enforced throughout the affected area. 6. Extra fire extinguishers should be distributed throughout the area. 7. If extensive repairs are required, efforts should be directed toward restoring as much protection as possible by plugging or blocking of the damaged section. For example, if a single branch line breaks, it is often possible to blank off that one line and return the rest of the system to service until permanent repairs are completed. Be sure to keep records of all plugs or blind flanges used so you can check they have all been removed when repairs have been completed. 8. Watch service should be provided on a 24-hour basis until repairs are completed and all valves have been reopened. In the event of a fire, the watchman should be instructed to first notify the public fire department and then reopen any closed valves.
13 Risk Control Bulletin Dry-Pipe Sprinkler Valve Heated Enclosure
14 Data Sources: National Fire Protection Association (NFPA) Codes and Standards: NFPA 13 Installation of Sprinkler Systems NFPA 25 Inspection, Testing and Maintenance of Water- Based Fire Protection Systems Dry pipe sprinkler systems are designed for use inside buildings that are unheated, inadequately heated, or that must be open to outside cold temperatures for appreciable time periods. Under these conditions, it is clear that wet-pipe systems are likely to freeze up and burst their piping. It is mandatory that water always be present in supply piping up to the clapper of the dry pipe valve - compressed air then fills the piping from the clapper on to the outermost sprinkler head. Therefore, arrangements must be made to prevent the water in the supply piping to the dry-pipe valve from freezing. The following guidelines should help you design and install a system to accomplish this. Drainage Since water spillage (or occasional leakage} may occur during valve maintenance work, it is desirable to have a small floor drain connected to the sewer. The floor should be sloped toward the drain. Heating Lighting can be ordinary electric. Heating can be electric from strip heater under thermostatic control (so that 40 F is always maintained). If steam is available on 24-hour basis from plant boilers, steam heat can be used. If central station alarm service is used on the property, the temperature within the valve enclosure can be supervised by it. Enclosure The best arrangement is a dry-pipe valve enclosure, suitably heated at all times to at least 40 F. Such an enclosure is depicted but its size has been exaggerated for clarity of constructional detail. Actually, the enclosure need merely provide working room on all sides of the dry-pipe valve, such as 30 inches to all walls from the valve. This would provide an enclosure that is 6' x 6' x 6' in size. The water supply pipe should come up through the floor in the center of the enclosure, if possible. If the floor is concrete laid directly on earth, without air-space, the supply pipe will be adequately protected by ground cover until it emerges in the valve enclosure. But if the floor of the enclosure is wood or any other material having appreciable air space beneath it, then the supply pipe must be enclosed beneath the floor and protected with insulation, sand or earth over its entire exposed portion until it enters the valve enclosure. Wall studding should be sheathed on both sides with noncombustible material and the space between filled with insulation. The door to the room should be of equivalent construction and fit tightly so as to conserve room heat. Outer corners of the enclosure should be protected with 2" angle iron. Masonry construction of these enclosures makes for better closure and minimal heat loss. A small screened ventilator allows the room to "breathe" and thus minimize condensation. Automatic sprinkler protection should be provided in the enclosure.
15 Roof Inspection CNA recommends a full inspection of the roof at least semi-annually and also after severe storms. This form can be used (or modified) as a guide and for documentation purposes. It is important that any issues be promptly corrected. Company Name Completed By Location Address Date GENERAL INFORMATION (All boxes in document will expand as needed) Age of Roof: Construction of Roof: Roof Installer: Warranty in force on roof: Comments: SURFACE YES NO Dry or cracked roof surface? Cracked or loose roof seams? Blisters or depressions? Broken/Missing shingles? Poor drainage or standing water? Bare spots in gravel covering? Comments: DRAIN YES NO Adequate maintenance of drain? (Is the drain clogged?) Obstructions present to prevent the flow of water to a drain? Roof strainers clear and functional? Gutters and downspouts damaged or clogged? Is the drain capacity adequate? Comments: FLASHING AND COPING YES NO Loose, separated or missing flashing? Signs of rust or deterioration of flashing? Comments: INTERIOR YES NO Stained ceiling tiles? Signs of rust or discoloration on underside of roof deck? Insulation wet or mildewed? Comments: MOUNTED EQUIPMENT: YES NO Signs or antennas not properly secured? Vents, chimneys and skylights unstable? Penthouses, cooling towers, air conditioner or other equipment allowing leaks? Comments:
Risk Control Bulletin Water Damage Prevention A Property Protection Imperative Water is one of the most destructive agents when released into a building. Water erodes surfaces; causes rot and deterioration
Water Damage Prevention Risk Management Guidebook PIC Loss Control Services IMPORTANT NOTICE: The enclosed loss control information is for your consideration in your loss prevention efforts. They are not
later damage - Loss ControL axisinsurance.ca Table of Contents EXECUTIVE SUMMARY... 1 FACILITY SYSTEMS WATER DAMAGE... 2 Frozen Pipes.....................................................................................
1. The leading cause of property losses is from liquid damage. A review of Zurich North America claims data highlights the problem. 2. Water damage originates from a number of sources: Domestic water lines
Water Management & Damage Prevention: A Guide for Homeowners This article provides homeowners with basic information to make these decisions and take the appropriate actions to keep their homes dry and
WATER DAMAGE LOSS PREVENTION TECHNIQUES FOR CALIFORNIA-PACIFIC ANNUAL CONFERENCE OF THE UNITED METHODIST CHURCH As your partner in managing the risk of financial loss to your ministry, we are asking every
A cure for water damage in real estate Presented for BC Non-Profit Housing Association by Jeff Shearman, Zurich Services Corporation 2010 Zurich Canada Focused on our customer Reduce overall risk by reducing:
Disclaimer: This material is designed and intended for general informational purposes only, and is not intended, nor shall it be construed or relied upon, as specific legal advice. Roof damage is a leading
Flood Checklist The following may serve as a checklist when preparing for a flood. This checklist should be tailored to processes/operations, flood protection equipment and flood potentials at your specific
WEATHER HAZARDS AND PRECAUTIONS STRATEGIC OUTCOMES PRACTICE TECHNICAL ADVISORY BULLETIN SEVERE WINTER WEATHER PROPERTY RISK CONTROL Winter weather not only brings freezing temperatures with it, but all
Fighting Fire in Sprinklered Buildings Student Guide Fighting Fire in Sprinklered Buildings Student Guide Table of Contents Purpose........................................................... 3 Instruction
Allianz Global Corporate & Specialty Americas Water Damage During Construction May 2012 A Contractor s Loss Prevention Guide Water damage losses are a major cause of loss during construction and represent
Harval Homes Custom Built Home Series TABLE OF CONTENTS Page 2 : Introduction Page 3 8 : Service Periods Page 9 : Owner s Responsibilities Page 10 : Scheduling A Repair Page 10 : Repairs After Warranty
IN THE EVENT OF UNEXPECTED WATER INTRUSION... KNOW YOUR RIGHTS AND Alex Sink Chief Financial Officer of Florida RESPONSIBILITIES Mold can adversely affect homes in Florida s humid climate. As an insured
Protecting Your School from Fire and Weather Related Losses Allianz Ireland s Leading School Insurer Protecting Schools since 1902 Our Policyi The most complete and appropriate insurance arrangement for
ABOUT YOUR HOUSE Before You Start an Energy Efficiency Retrofit The Building Envelope The building envelope is the outer layer of the building that separates the indoor living space from the outdoor environment,
1 P a g e Protecting Your Home From Water Damage The first signs of water damage might seem trivial. But warnings like water stains on the ceilings or a leak under the kitchen sink can lead to real problems,
Vision Home Inspection 324 Rams Run Shepherdsville KY 40165-7877 Inspector: James McFadden Property Inspection Report Client(s): Property address: Inspection date: View report summary This report is the
The following may serve as a checklist when preparing for a flood. This checklist should be tailored to processes/operations, flood protection equipment and flood potentials at your specific plant. The
BASEMENT FLOODING Prevention Guide for Homeowners 1 Did You Know? Floods are the most common hazards in Canada. Water damage is a common cause of loss for homeowner insurance. A heavy rainfall can result
FIRE PREVENTION INSPECTION CHECKLIST For Class A Occupancy (For Assembly Buildings, Bars, Restaurants, Gyms, Churches, Arenas, Theatres or wherever people gather) Name Of Occupancy Date Physical Address
Investigation Of Water Damage Claims For Subrogation Potential by Chris Shiver, PE and Phil Chapski, PE, Cerny and Ivey Engineers, Inc., Norcross, Georgia Water entry into homes and businesses is the cause
Freezing and Bursting Pipes How pipes freeze and burst, and what to do to prevent damage. When water freezes, it expands. That s why a can of soda explodes if it s put into a freezer to chill quickly and
Appendix C: Moisture, Mold and Mildew Molds and mildew are fungi that grow on the surfaces of objects, within pores, and in deteriorated materials. They can cause discoloration and odor problems, deteriorate
A bout your house CE 28c before you start Renovating Your Basement Moisture Problems Mold and decay on floor joists and sill plates Stuffy air, high humidity, poor air circulation Water draining in from
ACE GLOBAL RISK ENGINEERING INFORMATION BULLETIN BUSINESS FLOOD PLANNING AND MITIGATION GUIDE Introduction The most common cause of flooding is due to established water storage areas (natural and man-made)
APPENDIX 9 AFFORDABLE HOUSING PROGRAM INSPECTION CHECKLIST Participating Jurisdiction: Homeowner Name: Assisted Property Address: Date of Physical Inspection of Property: Total Square Footage of Property:
MOISTURE MANAGEMENT DURING THE CONSTRUCTION PROCESS Ed Light 1,*, James Bailey 1, and Roger Gay 1 1 Building Dynamics, LLC, Ashton, MD (USA) *Corresponding email: ELight@building-dynamics.com Published
Risk Control Bulletin Inspection, Testing & Maintenance (ITM) of Water-Based Fire Protection Systems Introduction Fire protection systems are provided in or at a building to safeguard the lives of building
De-Mystifying HVAC Why is my air conditioner dripping on my customers? By Ron Prager One of the most frequent emergency service requests is a call for an air conditioner leaking water into the store. These
Vacant properties Understanding the risks and the solutions Table of contents Top risks for vacant properties 2 Copper theft and vandalism 2 Water damage 3 Fire 4 About the E&S Properties Program 5 Vacant
Water damage prevention: Avoid costly water damage claims with a water damage mitigation program Water damage is the number one source of property claims for owners of retail establishments, commercial
4658.4500 PLUMBING SYSTEMS; NEW CONSTRUCTION. Subpart 1. Installation. All plumbing systems must be installed and tested according to this chapter and chapter 4715, the Minnesota Plumbing Code. Subp. 2.
Regular maintenance keeps your home functioning efficiently and safely and helps protect its value. We're happy to offer this checklist of ongoing and seasonal maintenance steps to help you safeguard your
PEPPER VINER HOMES WARRANTY GUIDELINES All non-emergency warranty and customer service requests MUST be made in writing. This provides you with documentation and allows Pepper Viner to operate efficiently.
Home Management Checklist: Spring HVAC System Attic Plumbing and Electrical Service air conditioning unit (Ventilation inspected as part of service call). Ensure gutters are discharging water away from
Foundations Foundation Purpose The purpose of a foundation is to distribute the weight of a structure securely into the ground. Engineering data regarding soil, rock and water conditions are used to design
www.citiesinspection.com October 5, 2015 Dear Client, On 9/14/2015, Cities Inspection Service, Inc. completed a building inspection of the property located at 123 Oak Street, Someplace, Minnesota for you.
A comfortable house is a great source of happiness. - Sydney Smith Home Maintenance Guide HOME GUIDE By conducting regular maintenance checks, you can prevent small inexpensive repairs from becoming more
Walkthrough Inspection Checklist This checklist is to aid during an IAQ Walkthrough of the school. The checklist includes considerations both inside and outside the school building: Instructions: 1. Read
A cure for water damage in Public Sector facilities Risk Services: Understanding risk across your community Focused on helping our customers At Zurich, we are focused on helping customers reduce and mitigate
WINTER INSURANCE GUIDE What you need to know to be prepared and covered Many of us look forward to that first snowfall winter brings, the pretty snowflakes falling down onto a wintery, white wonderland.
about your house CE 28 c Before You Start Renovating Your Basement Moisture Problems Mold and decay on floor joists and sill plates Stuffy air, high humidity, poor air circulation Water draining in from
1 This material is confidential and may not be copied, used or distributed without the written permission of Safeguard Properties LLC. 2 Initial training is expected to be provided by each Vendor participating
SCOPING GUIDELINES 1.0 GENERAL GUIDELINES 2.0 BUILDING ENVELOPE SCOPING GUIDELINES 3.0 CATEGORIES AND COMPONENTS: The Flood Elimination/Below Grade Capital Category may include some or all of the following
OSHA REGULATION: 9 CFR 90.5 WELDING, CUTTING, AND BRAZING ( HOT WORK ) A. POLICY. This procedure follows requirements set forth in 9 CFR 90.5.. This policy applies to all Hot Work operations being done
67 This section gives you some helpful information and tips on running your home and the equipment in it. Electricity Fuse board (electrical consumer unit) Make sure you know where your fuse board is and
OFFICE OF ENVIRONMENTAL HEALTH AND SAFETY 5255 Hampton Blvd. Spong Hall, suite 2501 Norfolk, Virginia 23529 Phone: (757) 683-4495 Fax: (757) 683-6025 Occupational Safety & Health Environmental Health Laboratory
WET/DAMP BASEMENTS PROBLEM. IS THIS BASEMENT LEAKING OR COULD WE HAVE ANOTHER PROBLEM? Water line arching up on wall in corners of basement. Water collecting on concrete floor starting in corners. ANSWER:
May 2010 DEPARTMENT OF CODES AND BUILDING SAFETY FLOOD RECOVERY INFORMATION GUIDELINES FOR PERMITS ASSOCIATED WITH THE REPAIR OF FLOOD DAMAGED HOMES AND BUILDINGS The Department of Codes and Building Safety
I. Introduction Inspection and Testing Program Fire Protection Equipment State of Minnesota Emergencies seldom give warning before they strike. Thus, it is essential that fire protection equipment be inspected,
SELF-INSPECTION CHECKLIST Maintain Your Roof and Identify Potential Issues With Bloom s Comprehensive Self-Inspection Guide Inspection Questions? Call Bloom At 800-483-9932 www.bloomroofing.com DISCLAIMER
1 Mitigating and Minimizing Potential Losses due to Water Damage Presented By: Ben Yoho and Janna Bennett September 30, 2015 Disclaimer 2 The purpose of this presentation is to provide information, rather
COWENS RISK SOLUTIONS WATER DAMAGE PREVENTION October 2014 WATER DAMAGE PREVENTION: AVOID COSTLY WATER DAMAGE CLAIMS WITH A WATER DAMAGE MITIGATION PROGRAM Water damage is the number one source of property
ABOUT YOUR HOUSE CE 50 Basement flooding is unfortunately a common occurrence in many parts of Canada. But the good news is that many types of basement flooding may be avoided. This publication explains
CITY OF WHITE BEAR LAKE BUILDING INSPECTION DEPARTMENT 4701 Highway 61 White Bear Lake, MN 55110 Fax: 651-429-8503 Re-Roofing: Asphalt Shingles This is a summary of the standard requirements based on the
DISTRICT OF COLUMBIA WATER AND SEWER AUTHORITY a guide to PREVENTING SEWER BACKUPS AND FLOODING Sewer backups and flooding can damage District homes and businesses. Sewer blockages are most commonly found
Winnipeg Fire Department Fire Prevention Branch Manitoba Fire Code Life-Safety Equipment Maintenance Requirements The Fire Prevention Branch of the Winnipeg Fire Department has prepared this document of
Maintaining Fire Protection Systems Fire continues to be a major threat to your business and your personal safety. Each year several thousand people are injured or killed by fires and billions of dollars
The Ultimate Guide To Protecting Your House From Water In The Basement Table of Contents 3 Causes of Water in the Basement!... 3 Reason Number 1: Poor Grading!... 3 Reason Number 2: Improper Drainage!...
Presentation Agenda Introduction Types of Flooding Identifying Flood Risks Property Improvements Additional Resources Discussion / Q&A 4 RainReady Home an initiative of RainReady is an initiative of the
TYPICAL FIRE SAFETY INSPECTION VIOLATIONS The following is a list of typical violations often found by inspectors and a generic solution. You can use this list to improve the safety of your facility, to
#1) BEFORE Purchasing Land Here Is A Checklist Of Things You Should Check Zoning laws Deed restrictions on home size, foundation style, roof pitch, etc. Suitability (slope, wetland issues, etc.) Accessibility
Preventing water damage in the basement Thousands of home insurance claims are filed every year. Some losses are major, others aren t, but they re always an inconvenience and usually avoidable! As prevention
HEAT PUMP FREQUENTLY ASKED QUESTIONS HEAT PUMP OUTDOOR UNIT ICED-UP DURING COLD WEATHER: It is normal for a heat pump to have a build up of white frost on the outside coil during cold damp weather. The
How to Protect Your Property Against Plumbing Disasters Over 15 Years of Experience Servicing Toronto & GTA Available 24-Hours a Day CONTENT Why Your Home Plumbing Matters...2 Plumbing 101...3 Caring For
Crawford Inspection Services C.C.B. # 76914 www.crawfordinspections.com Portland Area PO Box 665 West Linn, OR 97068 Ph: (503) 650-6957 Salem Area 5434 River Rd. N; #192 Keizer, OR 97303 Ph: (503) 362-5809
THREE Heating and Cooling 17 Condensation Drain Line The line that drains condensed moisture away from your heating and/or cooling unit needs periodic maintenance. If your unit is located in the attic,
A bout your HOUSE before you start Repairing And Replacing Materials Exterior Walls CE 28 h Exterior finish materials are expected to protect the house from the elements while providing an attractive appearance.
CHECKLIST FOR MITIGATING OR AVOIDING FLOOD DAMAGE It may not seem the case, but individuals are not powerless in influencing their potential exposure to catastrophes, such as floods. Property owners have
Air Conditioner Water Heater - A Product of HotSpot Energy LLC PLEASE READ THIS BEFORE YOU INSTALL THE UNIT 1. This air conditioner must be installed and/or repaired by a qualified technician. If you perform
COMPREHENSIVE PROPERTY INSPECTIONS Thank you for selecting CPI for your Deficiency Observation. A full home inspection was not performed on this property at the buyers request. This inspection is a limited
By: Cherie Martel Roofing 101 - Signs that Your Roof Needs Repair/Replacement 1. Tell us a little bit about your company and its foundation. In 1963, Samuel T. Martel began a small family run roofing company,
3 & cooling 17 heating 2010 PulteGroup, Inc. All Rights Reserved. condensation The line that drains condensed moisture away from your heating and/or cooling unit needs periodic maintenance. Air conditioning
Flood Response and Mold Prevention Program Prepared by the Berea College Department of Environmental Health and Safety Revised May 2010 Contents I. Introduction II. III. IV. Flood and Mold Hazards Roles
Hot Work Permit Policy Environmental Health and Safety Department 800 West Campbell Rd., SG10 Richardson, TX 75080-3021 Phone 972-883-2381/4111 Fax 972-883-6115 http://www.utdallas.edu/ehs Modified: May
HOT WORK PERMIT PROGRAM TRAINING John Braun 1.0 INTRODUCTION 1.2 Purpose The Hot Work Permit Program has been developed for University employees that work on or around hot work activities. This program