2 1.0 INTRODUCTION 1.2 Purpose The Hot Work Permit Program has been developed for University employees that work on or around hot work activities. This program will help ensure employee health and safety at the University of Nevada, Reno. 1.3 Scope For the purposes of this program, hot work is defined as any temporary operation involving open flames or producing heat and/or sparks. This includes, but is not limited to: grinding, cutting, brazing, soldering, thawing frozen pipes by torch, torch applied roofing and welding. Thi li ll l i l di h This program applies to all personnel, including contractors, who are involved with/or who may be involved in hot work activities.
3 2.0 RESPONSIBILITIES 2.1 Directors, Deans and Department Managers Provide administrative and financial support Implement and maintain the Hot Work Permit Program Designate Permit Authorizing Individual(s) (PAI) Ad i t t b t fl bl t i l h d diti i Advise contractors about flammable materials or hazardous conditions in areas where they will be working prior to start of work
4 2.0 RESPONSIBILITIES 2.2 Supervisors, Foreman, Principal Investigators, Project Leaders, and Project Coordinators Subordinates are trained and understand the program Submit Permit Authorizing Individuals (PAI) to the Director or Department Managers Ensure Subordinates fulfill all requirements prior to performing hot work Maintain all equipment in safe operating condition Precautions listed on the Hot Work Permit are understood and followed Inform outside contractors the expectations of this policy Verify contractors have the necessary hot work permits required for their work
5 2.0 RESPONSIBILITIES 2.3 Environmental Health and Safety Technical resource Hot Work Permit Program instruction, as needed Review and revise the Hot Work Permit Program Conduct Hot Work Permit safety assessments to determine if any engineering and/or other controls are needed, and how they should be implemented Recommend appropriate engineering controls, administrative controls and personal protective equipment Conduct Hot Work Permit training Inspect and approve Designated Hot Work Areas
6 3.0 HOT WORK BASICS On occasion, UNR employees are required to perform hot work operations. When the need arises, the use of a Hot Work Permit may be required, and when specific procedures and regulations are followed, injuries to workers and damage to property are prevented. The purpose of this guide is to provide an overview of safety standards as they relate to Hot Work Permitting.
7 3.0 HOT WORK BASICS Hot Work Operations All welding, cutting, open torches and other hot work operations and equipment shall comply with this program. Hot work shall only be conducted in areas designed or authorized for that purpose by the personnel responsible for the Hot Work Program. Hot work shall not be conducted in the following areas unless approval has been obtained. 1. Areas where the sprinkler system is impaired. 2. Areas where there exists the potential of an explosive atmosphere, such as locations where flammable gases, liquids, or vapors are present. 3. Areas with readily ignitable materials, such as storage of large quantities of bulk sulfur, baled paper, cotton, lint, dust, or loose combustible materials. 4. At other locations as specified by the code official
8 4.1 Designated Hot Work Rooms A designated hot work room is a permanent location designed for hot work. These rooms do not require a permit to perform hot work. For a room to be classified as a designated hot work room, it must meet the following requirements: It must be of noncombustible fire resistive construction, essentially free of combustible and flammable contents. It must be suitably segregated from adjacent areas. It must be equipped with fire extinguishers. It must be inspected and approved by EH&S Must meet these standards or disciplinary action will be taken and/or the Designation will be removed!!
9 4.2 Not Requiring a Hot Work Permit Operations that produce a flame, sparks, hot slag or enough heat to ignite combustible materials should be considered hot work with a few exceptions. The following operations do not require a Hot Work Permit: Bunsen burners in laboratories fixed grinding wheels electric soldering irons
10 5.0 PEOPLE INVOVLED 5.1 A Permit Authorizing Individual (PAI) inspects hot work sites prior to the start of hot work operations using the checklist found on the Hot Work Permit Form. Any employee who has successfully completed hot work safety training and is designated by the Director, Asst Director or Principal Investigator can serve as a PAI
11 5.0 PEOPLE INVOVLED 5.2 Hot Work Operators (HWOs) are employees who perform hot work operations. A HWO must always obtain a Hot Work Permit before beginning hot work. Any employee, who has successfully completed hot work safety training and is trained on the equipment being operated, can serve as a HWO. The HWO must do the following: Ensure that conditions are safe before commencing the hot work operation. Understand the hazards associated with the work and the actions needed to minimize or eliminate the hazard.
12 5.0 PEOPLE INVOVLED 5.2 Hot Work Operators (HWOs) Be prepared to contact their supervisor should conditions change or warrant reassessment during the hot work project. Use appropriate personal protective equipment (PPE) while performing hot work (welding helmets, gloves, jackets, etc.). Must have successfully completed annual fire extinguisher training, including hands-on. (2006 IFC ) Complete the appropriate sections of the hot work permit. NOTE: A HWO can also be a PAI, but they are NOT allowed to issue their own Hot Work Permits.
13 5.0 PEOPLE INVOVLED 5.3 A Fire Watch Is posted to monitor the safety of hot work operations and watch for fires. If the situation requires one, Fire Watches are posted by a PAI during hot work, and for at least 30 minutes after work has been completed. Any employee who has successfully completed hot work safety training can serve as the Fire Watch. Fire Watch individuals are responsible for: No other duties except to watch for fire, extinguish spot fires, and communicate an alarm. (2006 IFC ) Being aware of the inherent hazards involved in the hot work
14 5.0 PEOPLE INVOVLED 5.3 A Fire Watch Safe conditions are maintained during hot work operations Watch for fires Ensuring that appropriate fire extinguishers are readily available. Knowing how to report a fire or other emergency situation. Using the appropriate PPE Completing the appropriate section of the hot work permit. Completing annual fire extinguisher e training, including hands-on. (2006 IFC )
15 6.0 SAFETY MEASURES 6.1 The 35-Foot Rule All flammable and combustible materials within a 35-foot radius of hot work must be removed. When flammable and combustible materials within a 35-foot radius of hot work cannot be removed they must be covered with flame retardant tarps and a fire watch must be posted. Floors and surfaces within a 35-foot radius of the hot work area must be swept free of combustible dust or debris. All openings or cracks in the walls, floors, or ducts that are potential travel passages for sparks, heat and flames must be covered.
16 6.0 SAFETY MEASURES 6.2 Fire Detection and Suppression A fire extinguisher must be readily available and accessible. Entire building smoke detection and alarms systems cannot be shut down. Instead smoke detectors in the area of hot work may be covered for the duration of hot work to prevent false alarms. Contact Fire & Life Safety Shop when alarm devices are required to be covered. A t ti i kl t t b h t d t f Automatic sprinkler systems may not be shut down to perform hot work. Contact Fire & Life Safety for coordination.
17 6.0 SAFETY MEASURES 6.3 Fire Watch A Fire Watch must be posted by a PAI if the following conditions exist: Combustible b materials cannot be removed from within a 35-ft radius of the hot work Wall or floor openings of hot work expose combustible materials in adjacent areas, including concealed spaces in walls and floors within the 35-ft radius Combustible materials are adjacent to the opposite side of partitions, walls, ceilings or roofs and are likely to be ignited. Fire extinguishers will be provided by the Fire & Life Safety Shop rather than people removing them from building locations
18 7.0 GENERAL Work should be performed using alternative methods other than hot work whenever possible Hot work should be performed in designated hot work rooms/areas whenever practical. A Hot Work Permit is valid for one day and one area and should be posted in the area of hot work for the duration of the activity. it Communication devices shall be readily available at the job site. A minimum of one portable fire extinguisher shall be readily accessible within 30 feet of the location where hot work is performed. (2006 IFC ) A copy of every permit shall be filed by the PAI and kept for one A copy of every permit shall be filed by the PAI and kept for one year.
19 FIRE WATCH When Required: A fire watch shall be provided during hot work activities specified in section 6.3 and shall continue for a minimum of 30 minutes after the conclusion of the work. The fire code official or the PAI is authorized to extend the fire watch based on the hazards or work being performed. (2006 IFC ) Exception: Where the hot work area has no fire hazards or Exception: Where the hot work area has no fire hazards or combustible exposures, then a Fire Watch is not required.
20 FIRE WATCH Location: The fire watch shall be positioned so that the extinguishment of a spot fire is not delayed. Hot work conducted in areas with vertical or horizontal fire exposures that are not observable by a single individual shall have additional personnel assigned to fire watches to ensure that exposed areas are monitored. (2006 IFC ) Duties: Individuals designated to fire watch shall have no other duties except to watch for fire, extinguish spot fires, and communicate an alarm. (2006 IFC )
21 FIRE WATCH Fire Training: The individuals responsible for performing the hot work and individuals responsible for providing the fire watch shall have fire-extinguishing equipment readily available and shall be trained in the use of such equipment. (2006 IFC ) Fire Extinguisher: A minimum of one portable fire extinguisher within 30 ft, but within 10 ft of the Fire Watch, of the location where hot work is performed. (2006 IFC ) Contact Fire & Life Safety for Fire Extinguishers
22 9.0 PROCEDURES 9.1 Hot Work Permit Form The Hot Work Permit [see Appendix A] shall be the permit system. Alternative permits may be used only after approved by EH&S
23 9.0 PROCEDURES 9.2 Prior To Hot Work Several tasks must be performed before hot work begins. These include, but are not limited to: When the hot-work area is accessible to persons other than the operator of the equipment, conspicuous signs shall be posted to warn others before they enter the hot-work area. (2006 IFC ) Such signs shall display the following warning: CAUTION HOT WORK IN PROGRESS STAY CLEAR
24 9.0 PROCEDURES 9.3 During Hot Work During the hot work there are other precautions that must be taken: Appropriate fire extinguishing equipment shall be maintained in close proximity to the hot work for its entire duration, plus 30 minutes. Combustible floors shall be kept wet during the hot work. Work on a noncombustible or hot work blanket whenever possible. Store acetylene and other fuel cylinders in a secure and upright position. Place hoses so that they will not be crushed or damaged. Be constantly aware of conditions that may cause a fire to start. Floors shall be kept clean within the hot work area. (2006 IFC )
25 9.0 PROCEDURES 9.4 After Hot Work There are some responsibilities that must be undertaken after hot work is completed: A fire watch shall be provided during hot work activities as specified in section 6.3 and shall continue for a minimum of 30 minutes after the conclusion of the work. The PAI is authorized to extend the fire watch based on the hazards or work being performed. (2006 IFC ) 2 ONLY WHEN A FIRE WATCH IS REQUIRED; the hot work area shall be inspected by the Permit Authorizing Individual at least once a day to ensure that the area remains fire-safe. (2006 IFC ) The PAI will complete the appropriate sections of the hot work permit and return the completed form to the supervisor. Fire extinguishing equipment must remain accessible in the area until the fire watch is completed and all paperwork has been signed by the PAI.
26 9.5 Prohibited Hot Work Situations Hot work activities are not permitted when the following conditions exist: In sprinkler buildings, where the entire sprinkler system is impaired. When the entire building s fire detection system is shut down. In the presence of explosive atmospheres, where mixtures of flammable gases, vapors, liquids or dust may exist. In tanks, drums or other containers or equipment that contains or previously contained materials that could create explosive atmospheres. On pipes that are in contact with combustible walls, ceilings, roofs or partitions where heat by conduction can cause ignition. On containers where flammable liquids, solids or vapors may be present. On O metal walls, ceilings or roofs built of composite, combustible, and sandwich-type panel construction or having combustible coverings.
27 9.5 Prohibited Hot Work Situations cont. Areas, including those with confined spaces, where atmospheres of explosive gases, vapors, or dusts exist or could accumulate. Areas where there are large amounts of combustibles not practical to move or cover, such as roll paper, cotton or jute storage. On partitions, walls, ceilings, or roofs with combustibles coverings such as expanded plastic insulation. On partitions of combustible sandwich types construction. Areas where processes involving flammable liquids, gases, and dusts can not be shut down or made safe. Where lint conditions are severe and beyond correction. On pipes and other metals that can conduct enough heat to ignite nearby combustibles. Areas that contain combustibles or shall be provided d with appropriate shielding to prevent sparks, slag or heat from igniting exposed combustibles. (2006 IFC )
28 10.00 SAFETY TRAINING 10.1 Safety Training Individuals involved in hot work are required to complete hot work safety training; this includes Supervisors, Permit Authorizing Individuals, Hot Work Operators and Fire Watch personnel. The following EH&S courses must be completed: Hot Work Permit Training Required upon initial assignment and refresher training required every 5 years. Fire Extinguisher Training Required once a year. The hands-on classroom training must be completed for the initial class. The fire extinguisher training course (without Hands-on) may be completed for the annual refresher requirement.
29 10.2 Dept Training Supervisors shall train employees on departmental Hot Work Permit procedures and specific safety procedures for the type of hot work equipment used. This training shall be completed upon initial assignment and cover the following subjects: Safety procedures specific to the equipment used Required personal protective equipment for tasks Identification of Permit Authorizing Individuals and how they can be contacted Where to file copies of completed Hot Work Permits Locations of designated hot work rooms where a Hot Work Permit is not required
30 11.0 CONTRACTORS Outside contractors that are under contract with UNR are required to have hot work safety program as a part of their project safety programs. All contractors must have at least an equivalent hot work permit program. Contractors working on capital projects at UNR are required to follow the hot work guidelines outlined in project specifications. Every contractor should submit their hot work procedure prior to the start of a construction project and if any metal cutting, welding, soldering or grinding occurs that they follow their procedure. Coordinate fire alarms with the Fire & Life Safety shop as they need to be notified in advance of pending hot work. Contractors are responsible for completing and their own Hot Work Permit and must have their own fire watch person.
31 12.0 RECORDKEEPING 12.1 Hot Work Permits All hot work permits shall be returned to the issuing supervisor for their record retention. Records of hot work permits should be maintained for one calendar year. Hot work permits on record should be reviewed for program improvement or modification purposes prior to disposal Training Copies of records of all program related training conducted by individual departments should be maintained in the department personnel e files. Copies of training records shall be sent to Occupational Safety Officer.
OSHA REGULATION: 9 CFR 90.5 WELDING, CUTTING, AND BRAZING ( HOT WORK ) A. POLICY. This procedure follows requirements set forth in 9 CFR 90.5.. This policy applies to all Hot Work operations being done
Hot Work Permit Policy Environmental Health and Safety Department 800 West Campbell Rd., SG10 Richardson, TX 75080-3021 Phone 972-883-2381/4111 Fax 972-883-6115 http://www.utdallas.edu/ehs Modified: May
Hot Work Safe Operating Procedure Purpose The purpose of the Hot Work Program is to establish safety procedures for employees, contractors, and subcontractors engaging in any temporary operation involving
HOT WORK PROGRAM Introduction The University of Kentucky recognizes a potential for fire from hot work operations. For that reason this program should be implemented in all departments at the University
FIRENET FIRE PREVENTION DEPARTMENT November 2010 Welding, Brazing & Cutting Guidelines Hot Work is any work activity that generates a flame, heat or sparks such as soldering, brazing, welding, torch cutting
Standards for Construction Site Fire Safety For Use by Unidocs Member Agencies or where approved by your Local Jurisdiction Authority Cited: California Fire Code (CFC) These standards are intended to prescribe
Pressure Vessels (Air Compressors) and LPG Tanks 1. Identification of Workplace Hazard Any container, tank or vessel that contains pressurized material is a potential hazard to employees due to the force
FIRE PREVENTION PLAN 1 FIRE PREVENTION PLAN OSHA s Fire Prevention Plan regulation, found at 29 CFR 1910.38(b) and 29 CFR 1926.24, requires Northern Clearing, Inc. to have a written fire prevention plan
EMERGENCY ACTION, EVACUATION AND FIRE PREVENTION SAFETY PROGRAM REGULATORY STANDARD: OSHA - 29CFR1910.36-29CFR1910.38-29CFR1910.157-29CFR1910.165 NFPA-10 BASIS: The OSHA Emergency Action Planning and the
FACILITY FIRE PREVENTION AND EMERGENCY PREPAREDNESS INSPECTION CHECKLIST Date of Inspection: Conducted by: Location: Reviewed by: Date of Review: Comments or additional corrective action taken as a result
Process Safety Management of Highly Hazardous & Explosive Chemicals Safe Work Practices Safe Work Practices 1910.119(f)(1) The employer shall develop and implement safe work practices to provide for the
General Inspection FIRE SAFETY SELF-INSPECTION FORM FOR CULTURAL INSTITUTIONS 1. All Floors (inspect from top floor to basement): Yes are fire exits and directional signs properly illuminated? is the emergency
1.0 Policy Statement The University of New Haven has developed a Fire Alarm and Protection Impairment Plan in accordance with the National Fire Protection Associations (NFPA) codes. Specific codes referenced
TYPICAL FIRE SAFETY INSPECTION VIOLATIONS The following is a list of typical violations often found by inspectors and a generic solution. You can use this list to improve the safety of your facility, to
Fire Safety Plan Contents: Fire Safety Plan Introduction... ii Plan Cover Sheet... 1 Responsibility... 2 Fire Exits... 2 Portable Fire Extinguishers... 3 Emergency Evacuation Planning... 4 Fire Prevention
Document owner and change code Document Owner Aaron Perronne Title HSSE Manager Mark X Change Code Description X N/A First Issue A Typographical/Grammatical correction; formatting change; text clarification-no
. GENERAL WELDING AND CUTTING GUIDELINES Only authorized employees who have been properly trained shall be permitted to perform welding or cutting. Employees performing cutting or welding must wear the
FIRE SAFETY SELF-INSPECTION FORM FOR CULTURAL INSTITUTIONS The attached self-inspection form is intended for staff use at regular, frequent intervals. It should not take the place of two other vital measures
Department of Development Service 135 North D Street, Perris CA. 92570 Phone: (951) 443-1029 Fax: (951) 943-3293 PURPOSE The intent of this guideline is to provide the information necessary to ensure that
F I R E D E P A R T M E N T SANTA CLARA COUNTY 14700 Winchester Blvd., Los Gatos, CA. 95032-1818 (408) 378-4010 (408) 378-9342 (fax) www.sccfd.org STANDARDDETAILS&SPECIFICATIONS SpecNo SI 7 Rev.Date 04/30/09
Commons for Commons 1655 Musketeer Drive Xavier University November 7, 2006 Ken Grossman Page 1 10/29/2013 Table of Contents Introduction... 3 Responsibilities... 3 Major Workplace Fire Hazards... 3 Methods
Sample Written Program For Flammable Liquids 1 Flammable Liquids. (YOUR COMPANY NAME) Purpose Proper Storage and use of flammable liquids can significantly reduce the possibility of accidental fires and
Requirements for Hydrogen Storage and Use I. INTRODUCTION Fire and Life-Safety Group (FLS) The following is a summary of the fire and building code requirements for the storage and use of hydrogen. These
Purpose Responsibilities Proper Storage and use of flammable liquids can significantly reduce the possibility of accidental fires and injuries. To minimize risk to life and properly, the requirements of
UNIVERSITY OF TOLEDO SUBJECT: INTERIM LIFE SAFETY MEASURES AND INFECTION Procedure No: LS-08-008 CONTROL PROCEDURE STATEMENT Interim life safety and infection control measures will be implemented to protect
SITE CONTRACTOR PROCEDURES Asset Collection Type B Assets are considered High risk ; the site activities must be in accordance with Graysonline contractor procedures and are to be collected by appointment
Overview Compressed gas cylinders are used in many workplaces to store gases that vary from extremely flammable (acetylene) to extremely inert (helium). Many compressed gas cylinders are stored at extremely
A Code Review for Emergency Generators and Indoor Use of Portable Generators By: the Fire and Life-Safety Group (FLS) Fire Code requires that emergency generators be stationary generators. Therefore, a
Fire Safety Requirements for Child Care Centre A. Restrictions on Location Child care centre shall not be located : - (a) (b) in any premises designed for residential use; in any industrial building, warehouses,
Course of Construction Questionnaire CLIENT DETAILS Broker: Contact: Insured s name: Policy number: Address undergoing works: Insured s contact phone number: 1) Name and address of Contractor: 2) Contractor
INTRODUCTION This Fire Safety Training module is designed to teach you preventive measures that will eliminate or minimize causes of fire or fire hazards in the workplace, and to teach you proper emergency
TYPICAL HAZARDOUS MATERIALS INSPECTION VIOLATIONS The following is a list of typical violations often found by inspectors and a generic solution. You can use this list to improve the safety of your facility,
Electrical Classification Using NFPA 70 and NFPA 499 to Classify Hazardous Locations Electrical classifications are established in accordance with the National Electrical Code, NFPA 70, also referred to
Flammable and Combustible Liquids OSHA Office of Training and Education 1 Introduction The two primary hazards associated with flammable and combustible liquids are explosion and fire Safe handling and
Page No: 1 of 7 6.0 PURPOSE (192.751) All possible precautions shall be exercised to prevent the accidental escape and ignition of gas. Whenever possible, potential sources of ignition should be eliminated
Flammable and Combustible Liquids Slide 1 (of 23) Introduction The two primary hazards associated with flammable and combustible liquids are explosion and fire Safe handling and storage of flammable liquids
work permits What is a work permit? A work permit is a written form used to authorize jobs that expose workers to serious hazards. It identifies the work to be done, the hazards involved, and the necessary
Compressed Gas Cylinders Safety Policy This is an example of a compressed gas safety policy for a client whose operations include welding. Oxygen and acetylene tanks are in use and in storage at this client's
Introduction Fire Protection is an organized approach designed to prevent fires. In the event of a fire, a fire protection program will help prevent or minimize personal injuries, losses, and harm to the
EXHIBIT A SUBCONTRACTOR SAFETY, HEALTH, AND ENVIRONMENTAL MINIMUM PERFORMANCE STANDARDS (MPS) Panattoni Construction, Inc. ( Panattoni ) constantly strives to provide a safe and productive work environment.
April, 2009 1 SOP-Chem-08 1.0 Introduction This document is intended as a guide to the Queen s University requirements for handling and storing flammable and combustible material in non-laboratories areas.
OREGON FIRE CODE Interpretations and Technical Advisories A collaborative service by local and state fire professionals, along with our stakeholders and customers, to provide consistent and concise application
LIFE SAFETY UPDATE FULL SPRINKLERING OF ALL NURSING FACILITIES ADDITIONAL CLARIFICATIONS Prepared by Eric Rosenbaum, P.E. Hughes Associates, Inc. The purpose of this update is as follows: Remind all state
CONSTR '!: N INSURANCE- =:] Wrap-Up Liability Builders Risk Please complete general information section for all pro j ects and specific sections for wrap-up Liability and builders risk according to requirements.
FIRE CODE INTERPRETATION November 2009 FCI-09-03 Page 1 of 8 ISSUE: FIRE SAFETY PLAN Construction and Demolition Sites Safety provisions at construction and demolition sites are established in Division
Attachment D Subcontractor Safety, Health, and Environmental Minimum Performance Standards (MPS) TABLE OF CONTENTS Introduction... Page 2 General Expectations... Page 2 Staffing Requirements and Expectations...
Checklist for Residential Care Premises Name of Premises: Address of Premises: Name of Responsible Person: What area / location does the assessment cover? Does the assessment cover the whole site YES or
Contractor Health & Safety Guidelines 002 of 008 Contents 1.0 The Knight Frank Australia (KFA) Contractor Health and Safety Guidelines 3 2.0 Introduction 3 3.0 Contractor Health and Safety Management 3
Checklist for Educational Premises Name of Premises: Address of Premises: Name of Responsible Person: What area / location does the assessment cover? Does the assessment cover the whole school YES or NO?
CONTRACTOR SAFETY POLICY Revised September 2012 TABLE OF CONTENTS COMPLIANCE ACKNOWLEDGMENT COMPLIANCE GENERAL SAFETY REQUIREMENTS/HOUSEKEEPING INSURANCE COVERAGE SIGN IN AND OUT INCIDENT REPORTING CHEMICAL
A Health and Safety Guideline for Your Workplace What is a Work Permit? A work permit is a written form used to authorize jobs that expose workers to serious hazards. It identifies the work to be done,
Competency 1.20 Mechanical systems personnel shall demonstrate a working level knowledge of the safety and health fundamentals of mechanical systems and/or components. 1. Supporting Knowledge and Skills
Department of Environmental Health & Safety Procedures Compressed Gas Cylinder Program March 2010 Compressed Gas Cylinder Program Page 1 of 8 Table of Contents I. Introduction II. III. IV. Policy Scope
Exit Routes, Emergency Action Plans, Fire Prevention Plans, and Fire Protection OSHA Office of Training and Education 1 Introduction Fires and explosions kill more than 200 and injure more than 5,000 workers
Improving Workers Lives Worldwide FLA S FIRE SAFETY INITIATIVE Preventing fires and saving lives by empowering workers and factory managers SCENARIO 1 OCCURS AT FACTORY ABC, WHICH HAS NOT IMPLEMENTED NECESSARY
COMMERCIAL COOKING HOODS, VENTILATION & FIRE SUPPRESSION SYSTEM GUIDELINES AND PROCEDURES These guidelines are to be used for ALL commercial cooking hoods, ventilation systems and related fire suppression
REGULATORY REFORM (FIRE SAFETY) ORDER 2005 FIRE RISK ASSESSMENT This template has been provided to assist the Responsible Person with the preparation of a Fire Risk Assessment and is not intended for commercial
Fire Safety PROCEDURES January 2011 email@example.com Campus Phones EMERGENCY Dial 911 Fire Safety Service is the focal point for the coordinated administration of the University Fire Safety program and
FLAMMABLE AND COMBUSTIBLE LIQUIDS OSHA Changes Introduction This module covers the two primary hazards associated with flammable and combustible liquids: explosion and fire. In order to prevent these hazards,
Labeling Compressed Gas Cylinder Safety Cylinders should be labeled with the name of the gas or gas mixture and the primary hazard associated with that chemical (flammable, oxidizer, etc.) Do not accept
SMALL TO MEDIUM PREMISES Fire Risk Assessment The Regulatory Reform (Fire Safety) Order 2005 Premises: Address: Telephone number: Date of Fire Risk Assessment: Person responsible for premises: Deputy person
Winnipeg Fire Department Fire Prevention Branch Manitoba Fire Code Life-Safety Equipment Maintenance Requirements The Fire Prevention Branch of the Winnipeg Fire Department has prepared this document of
General Safety & Health Standards Published by the Division of Building Safety In Cooperation with the Idaho Industrial Commission Laboratories and Chemical Storage Safety Rules 111 111. LABORATORIES AND
PAGE 1 Warehouse Checklist Recent NFPA statistics estimate that in 1998 approximately 36,000 fires occurred in structures used for storage, accounting for $687mm of damage (over 10% of total fire damage
Minnesota State Department of Public Safety 444 Cedar Street, Suite 145, St. Paul, Minnesota 55101-5145 Phone: 651/215-0500 FAX: 651/215-0525 TTY: 651/282/6555 Internet: http://www.fire.state.mn.us Inspection
Dennis Fire Department Fire Prevention Mark Dellner Fire Chief FIRE SAFETY INSPECTION GUIDELINES FOR COMMERCIAL PROPERTIES (MA Fire Prevention Regulations 527 CMR, MGL Chapter 148) FIRE PREVENTION CHECKLIST-
Fire Safety ISSUE AX173 JULY 2011 Guidance Table of Contents Introduction Use of Amine Catalysts in Polyurethanes Manufacture Polyurethanes are generally made by reacting a diisocyanate, such as toluene
FDNY C14 Certificate of Fitness Quiz Name: Date: 1. Who issues a New York City laboratory permit? a) Department of Environmental Protection (DEP) b) Department of Environmental Conservation (DEC) c) Occupational
Laboratory Inspection Conducted By: Date: Location (room # & building): I. Lab Work Practices No smoking, food & beverages rules are observed. Food and beverages are not stored in the laboratory areas,
Location: Date: Inspected by: Safety and Health Office WORKPLACE SAFETY CHECKLIST WORK ENVIRONMENT Ventilation Removal of fumes and dust Temperature and humidity control Noise levels Vibration Lighting
I. Competencies Oxy-Fuel Gas Welding Given a functional oxy-fuel gas unit, instruction and demonstration of use, each student will be able to: A. Identify the major parts of the oxy-fuel gas unit. B. Pass
Model Confined Space Entry Policy and Procedures for Public Works Departments and State Agencies in Massachusetts This model plan, based on OSHA Confined Space Entry Standards, was developed by the Massachusetts
Imperial College London FIRE SERVICES ROOM 174, SHERFIELD BUILDING Code of Practice Revision No: 1 Date: 20 th October 2010 FIRE SAFETY CODE OF PRACTICE FOR PROJECTS WORKS AND CONTRACTORS INTRODUCTION..
H & S Guidance - Flammable Liquids See also: other pages INTRODUCTION Flammable liquids are liquids with a flashpoint of 55ºC or below and hence includes all liquids that are classified as flammable, highly
5.13 Fire Safety Rules And Practices For Roofing Operations Reference. The requirements of this bulletin are referenced from the San Francisco Fire Code and the National Fire Protection Association Standard
FIRE RISK ASSESSMENT GUIDANCE NOTES THE FIRE SAFETY ORDER 2005 CONTENTS Introduction Fire Risk Assessment Section 1 Premise Particulars 2 General Statement of Policy 3 Management System 4 General Description
Job Hazard/Safety Analysis For the Cabinet Maker 1 INTRODUCTION Job Hazard/Safety Analysis for the Cabinet Maker is a partial list of known task performed by the professional cabinet maker. We have placed
GUIDELINES FOR INSTALLATION OF TEMPORARY AND PERMANENT ABOVEGROUND DIESEL FUEL TANKS FOR EMERGENCY AND STANDBY POWER SYSTEMS LOCATED OUTSIDE OF BUILDINGS For Use by Unidocs Member Agencies or where approved