2 Page 2 of 32 Table of Contents Cover Page Table of Contents Intro Page 1 Roofing 2 Exterior 3 Garage 4 Interiors 5 Structural Components 6 Plumbing System 7 Electrical System 8 Heating / Central Air Conditioning 9 Insulation and Ventilation 10 Built-In Kitchen Appliances 11 Swimming Pools, Equipment and Safety 12 DOCK General Summary Invoice Agreement
3 Page 3 of 32 Date: 10/25/2011 Time: Report ID: Property: NAPLES FL Customer: GINA Real Estate Professional: Comment Key or Definitions The following definitions of comment descriptions represent this inspection report. All comments by the inspector should be considered before purchasing this home. Any recommendations by the inspector to repair or replace suggests a second opinion or further inspection by a qualified contractor. All costs associated with further inspection fees and repair or replacement of item, component or unit should be considered before you purchase the property. Inspected (IN) = I visually observed the item, component or unit and if no other comments were made then it appeared to be functioning as intended allowing for normal wear and tear. Not Inspected (NI)= I did not inspect this item, component or unit and made no representations of whether or not it was functioning as intended and will state a reason for not inspecting. Not Present (NP) = This item, component or unit is not in this home or building. Repair or Replace (RR) = The item, component or unit is not functioning as intended, or needs further inspection by a qualified contractor. Items, components or units that can be repaired to satisfactory condition may not need replacement. Standards of Practice: NACHI National Association of Certified Home Inspectors In Attendance: Customer representative, Vacant (inspector only) Type of building: Single Family (2 story) Style of Home: Contemporary Approximate age of building: Under 10 Years Home Faces: South Temperature: Over 65 Weather: Clear Ground/Soil surface condition: Dry Rain in last 3 days: No Radon Test: No Water Test: No Indoor Air Quality Test: YES WDO TERMITE INSPECTION: NO
4 Page 4 of Roofing The home inspector shall observe: Roof covering; Roof drainage systems; Flashings; Skylights, chimneys, and roof penetrations; and Signs of' leaks or abnormal condensation on building components. The home inspector shall: Describe the type of roof covering materials; and Report the methods used to observe the roofing. The home inspector is not required to: Walk on the roofing; or Observe attached accessories including but not limited to solar systems, antennae, and lightning arrestors. IN NI NP RR Styles & Materials Roof Covering: 1.0 ROOF COVERINGS X Tile Viewed roof covering from: 1.1 FLASHINGS X Binoculars 1.2 SKYLIGHTS, CHIMNEYS AND ROOF PENETRATIONS X 1.3 ROOF DRAINAGE SYSTEMS X IN NI NP RR IN=Inspected, NI=Not Inspected, NP=Not Present, RR=Repair or Replace Comments: 1.0 ROOF IS NOT ACCESSIBLE. CIELINGS HAVE BEEN CHECKED FOR ANY SIGNS OF WATER DAMAGE AND NONE WAS NOTICED. The roof of the home was inspected and reported on with the above information. While the inspector makes every effort to find all areas of concern, some areas can go unnoticed. Roof coverings and skylights can appear to be leak proof during inspection and weather conditions. Our inspection makes an attempt to find a leak but sometimes cannot. Please be aware that the inspector has your best interest in mind. Any repair items mentioned in this report should be considered before purchase. It is recommended that qualified contractors be used in your further inspection or repair issues as it relates to the comments in this inspection report.
5 Page 5 of Exterior The home inspector shall observe: Wall cladding, flashings, and trim; Entryway doors and a representative number of windows; Garage door operators; Decks, balconies, stoops, steps, areaways, porches and applicable railings; Eaves, soffits, and fascias; and Vegetation, grading, drainage, driveways, patios, walkways, and retaining walls with respect to their effect on the condition of the building. The home inspector shall: Describe wall cladding materials; Operate all entryway doors and a representative number of windows; Operate garage doors manually or by using permanently installed controls for any garage door operator; Report whether or not any garage door operator will automatically reverse or stop when meeting reasonable resistance during closing; and Probe exterior wood components where deterioration is suspected. The home inspector is not required to observe: Storm windows, storm doors, screening, shutters, awnings, and similar seasonal accessories; Fences; Presence of safety glazing in doors and windows; Garage door operator remote control transmitters; Geological conditions; Soil conditions; Recreational facilities (including spas, saunas, steam baths, swimming pools, tennis courts, playground equipment, and other exercise, entertainment, or athletic facilities); Detached buildings or structures; or Presence or condition of buried fuel storage tanks. The home inspector is not required to: Move personal items, panels, furniture, equipment, plant life, soil, snow, ice or debris that obstructs access or visibility. IN NI NP RR Styles & Materials Siding Style: 2.0 WALL CLADDING FLASHING AND TRIM X X Cement stucco Exterior Entry Doors: 2.1 DOORS (Exterior) X X Steel 2.2 WINDOWS X X 2.3 DECKS, BALCONIES, STOOPS, STEPS, AREAWAYS, PORCHES, PATIO/ X X COVER AND APPLICABLE RAILINGS 2.4 VEGETATION, GRADING, DRAINAGE, DRIVEWAYS, PATIO FLOOR, X WALKWAYS AND RETAINING WALLS (With respect to their effect on the condition of the building) 2.5 EAVES, SOFFITS AND FASCIAS X IN=Inspected, NI=Not Inspected, NP=Not Present, RR=Repair or Replace Comments: PIECES OF DECORATIVE TRIM DAMAGED. TRIM AT COLLUMNS SHOULD BE GROUTED. X IN NI NP RR Driveway: Brick 2.0 Picture Picture SEVERAL FRENCH DOOR LOCKS NEED MAINTENANCE AND REPAIR. DEADBOLTS NOT WORKING. SIGNIFIGANT CORROSION ON EXTERIOR HARDWARE. PAINT AT SGD'S IS PEELING.
6 Page 6 of Picture Picture Picture Picture PAINT ON EXTERIOR WINDOW FRAMES. 2.3 RAIL POST NOT SECURELY FASTENED. 2.2 Picture 1
7 Page 7 of 32 RAILINGS SHOW CORROSION TYPICAL OF WATERFRONT PROPERTIES. 2.3 Picture Picture SLIGHT ERROSION AT SEVERAL AREAS AROUND EXTERIOR. 2.4 Picture 1 The exterior of the home was inspected and reported on with the above information. While the inspector makes every effort to find all areas of concern, some areas can go unnoticed. Please be aware that the inspector has your best interest in mind. Any repair items mentioned in this report should be considered before purchase. It is recommended that qualified contractors be used in your further inspection or repair issues as it relates to the comments in this inspection report.
8 Page 8 of Garage 3.0 GARAGE CEILINGS X 3.1 GARAGE WALLS (INCLUDING FIREWALL SEPARATION) X 3.2 GARAGE FLOOR X X 3.3 GARAGE DOOR (S) X 3.4 OCCUPANT DOOR FROM GARAGE TO INSIDE HOME X 3.5 GARAGE DOOR OPERATORS (Report whether or not doors will reverse when X met with resistance) IN=Inspected, NI=Not Inspected, NP=Not Present, RR=Repair or Replace Comments: 3.2 NON STRUCTURAL SHRINKAGE CRACKING IN GARAGE FLOOR. IN NI NP RR IN NI NP RR Styles & Materials Garage Door Type: Three automatic Garage Door Material: Metal Auto-opener Manufacturer: RAYNOR 3.2 Picture Both Garage Doors will reverse when met with resistance. The sensors are in place for garage door(s) and will reverse the door.
9 Page 9 of Interiors The home inspector shall observe: Walls, ceiling, and floors; Steps, stairways, balconies, and railings; Counters and a representative number of installed cabinets; and A representative number of doors and windows. The home inspector shall: Operate a representative number of windows and interior doors; and Report signs of abnormal or harmful water penetration into the building or signs of abnormal or harmful condensation on building components. The home inspector is not required to observe: Paint, wallpaper, and other finish treatments on the interior walls, ceilings, and floors; Carpeting; or Draperies, blinds, or other window treatments. IN NI NP RR Styles & Materials Ceiling Materials: 4.0 CEILINGS X Drywall Wall Material: 4.1 WALLS X X Drywall 4.2 FLOORS X Floor Covering(s): 4.3 STEPS, STAIRWAYS, BALCONIES AND RAILINGS X X Carpet Tile 4.4 COUNTERS AND A REPRESENTATIVE NUMBER OF CABINETS X Interior Doors: 4.5 DOORS (REPRESENTATIVE NUMBER) X X Hollow core Window Types: 4.6 WINDOWS (REPRESENTATIVE NUMBER) X Storm windows 4.7 SHELVING X Casement Window Manufacturer: 4.8 MIRRORS X UNKNOWN IN NI NP RR Cabinetry: Wood IN=Inspected, NI=Not Inspected, NP=Not Present, RR=Repair or Replace Countertop: Granite Comments: 4.1 POOR PATCH JOB AT DROP IN CEILING. 4.1 Picture MOISTURE DAMAGE AT STAIR TRIM. CHECK FOR SOURCE OF DAMAGE AND REPAIR. 4.5 ADJUSMENT NEEDED AT BIFOLD DOOR. 4.3 Picture 1
10 Page 10 of Picture 1 The interior of the home was inspected and reported on with the above information. While the inspector makes every effort to find all areas of concern, some areas can go unnoticed. The inspection did not involve moving furniture and inspecting behind furniture, area rugs or areas obstructed from view. Please be aware that the inspector has your best interest in mind. Any repair items mentioned in this report should be considered before purchase. It is recommended that qualified contractors be used in your further inspection or repair issues as it relates to the comments in this inspection report.
11 Page 11 of Structural Components The Home Inspector shall observe structural components including foundations, floors, walls, columns or piers, ceilings and roof. The home inspector shall describe the type of Foundation, floor structure, wall structure, columns or piers, ceiling structure, roof structure. The home inspector shall: Probe structural components where deterioration is suspected; Enter under floor crawl spaces, basements, and attic spaces except when access is obstructed, when entry could damage the property, or when dangerous or adverse situations are suspected; Report the methods used to observe under floor crawl spaces and attics; and Report signs of abnormal or harmful water penetration into the building or signs of abnormal or harmful condensation on building components. The home inspector is not required to: Enter any area or perform any procedure that may damage the property or its components or be dangerous to or adversely effect the health of the home inspector or other persons. 5.0 FOUNDATIONS, BASEMENTS AND CRAWLSPACES (Report signs of X abnormal or harmful water penetration into the building or signs of abnormal or harmful condensation on building components.) 5.1 WALLS (Structural) X 5.2 FLOORS (Structural) X 5.3 CEILINGS (structural) X 5.4 ROOF STRUCTURE AND ATTIC X IN=Inspected, NI=Not Inspected, NP=Not Present, RR=Repair or Replace IN NI NP RR IN NI NP RR Styles & Materials Foundation: Poured concrete Floor Structure: Slab Wall Structure: Masonry Ceiling Structure: 2X4 Roof Structure: Engineered wood trusses Roof-Type: Hip Method used to observe attic: Walked Attic info: Pull Down stairs The structure of the home was inspected and reported on with the above information. While the inspector makes every effort to find all areas of concern, some areas can go unnoticed. Please be aware that the inspector has your best interest in mind. Any repair items mentioned in this report should be considered before purchase. It is recommended that qualified contractors be used in your further inspection or repair issues as it relates to the comments in this inspection report.
12 Page 12 of Plumbing System The home inspector shall observe: Interior water supply and distribution system, including: piping materials, supports, and insulation; fixtures and faucets; functional flow; leaks; and cross connections; Interior drain, waste, and vent system, including: traps; drain, waste, and vent piping; piping supports and pipe insulation; leaks; and functional drainage; Hot water systems including: water heating equipment; normal operating controls; automatic safety controls; and chimneys, flues, and vents; Fuel storage and distribution systems including: interior fuel storage equipment, supply piping, venting, and supports; leaks; and Sump pumps. The home inspector shall describe: Water supply and distribution piping materials; Drain, waste, and vent piping materials; Water heating equipment; and Location of main water supply shutoff device. The home inspector shall operate all plumbing fixtures, including their faucets and all exterior faucets attached to the house, except where the flow end of the faucet is connected to an appliance. The home inspector is not required to: State the effectiveness of anti-siphon devices; Determine whether water supply and waste disposal systems are public or private; Operate automatic safety controls; Operate any valve except water closet flush valves, fixture faucets, and hose faucets; Observe: Water conditioning systems; Fire and lawn sprinkler systems; On-site water supply quantity and quality; On-site waste disposal systems; Foundation irrigation systems; Spas, except as to functional flow and functional drainage; Swimming pools; Solar water heating equipment; or Observe the system for proper sizing, design, or use of proper materials. IN NI NP RR Styles & Materials Water Source: 6.0 PLUMBING DRAIN, WASTE AND VENT SYSTEMS X X Public Water Filters: 6.1 PLUMBING WATER SUPPLY AND DISTRIBUTION SYSTEMS AND FIXTURES X None 6.2 HOT WATER SYSTEMS, CONTROLS, CHIMNEYS, FLUES AND VENTS X Plumbing Water Supply (into home): 6.3 MAIN WATER SHUT-OFF DEVICE (Describe location) X Not visible IN NI NP RR Plumbing Water Distribution (inside home): IN=Inspected, NI=Not Inspected, NP=Not Present, RR=Repair or Replace CPVC Washer Drain Size: 2" Diameter Plumbing Waste: PVC Water Heater Power Source: Electric Water Heater Capacity: 80 Gallon (plenty) Manufacturer: RHEEM Water Heater Location: Upper level Comments: 6.0 SEVERAL SINK STOPPERS NEED ADJUSTMENT. 6.3 WATER SHUTOFF LOCATED AS SHOWN. 6.0 Picture 1
13 Page 13 of Picture 1 The plumbing in the home was inspected and reported on with the above information. While the inspector makes every effort to find all areas of concern, some areas can go unnoticed. Washing machine drain line for example cannot be checked for leaks or the ability to handle the volume during drain cycle. Older homes with galvanized supply lines or cast iron drain lines can be obstructed and barely working during an inspection but then fails under heavy use. If the water is turned off or not used for periods of time (like a vacant home waiting for closing) rust or deposits within the pipes can further clog the piping system. Please be aware that the inspector has your best interest in mind. Any repair items mentioned in this report should be considered before purchase. It is recommended that qualified contractors be used in your further inspection or repair issues as it relates to the comments in this inspection report.
14 Page 14 of Electrical System The home inspector shall observe: Service entrance conductors; Service equipment, grounding equipment, main over current device, and main and distribution panels; Amperage and voltage ratings of the service; Branch circuit conductors, their over current devices, and the compatibility of their ampacities and voltages; The operation of a representative number of installed ceiling fans, lighting fixtures, switches and receptacles located inside the house, garage, and on the dwelling's exterior walls; The polarity and grounding of all receptacles within six feet of interior plumbing fixtures, and all receptacles in the garage or carport, and on the exterior of inspected structures; The operation of ground fault circuit interrupters; and Smoke detectors. The home inspector shall describe: Service amperage and voltage; Service entry conductor materials; Service type as being overhead or underground; and Location of main and distribution panels. The home inspector shall report any observed aluminum branch circuit wiring. The home inspector shall report on presence or absence of smoke detectors, and operate their test function, if accessible, except when detectors are part of a central system. The home inspector is not required to: Insert any tool, probe, or testing device inside the panels; Test or operate any over current device except ground fault circuit interrupters; Dismantle any electrical device or control other than to remove the covers of the main and auxiliary distribution panels; or Observe: Low voltage systems; Security system devices, heat detectors, or carbon monoxide detectors; Telephone, security, cable TV, intercoms, or other ancillary wiring that is not a part of the primary electrical distribution system; or Built-in vacuum equipment. IN NI NP RR Styles & Materials Electrical Service Conductors: 7.0 SERVICE ENTRANCE CONDUCTORS X Below ground 7.1 SERVICE AND GROUNDING EQUIPMENT, MAIN OVERCURRENT DEVICE, MAIN AND DISTRIBUTION PANELS 7.2 BRANCH CIRCUIT CONDUCTORS, OVERCURRENT DEVICES AND COMPATIBILITY OF THEIR AMPERAGE AND VOLTAGE 7.3 CONNECTED DEVICES AND FIXTURES (Observed from a representative X number operation of ceiling fans, lighting fixtures, switches and receptacles located inside the house, garage, and on the dwelling's exterior walls) 7.4 POLARITY AND GROUNDING OF RECEPTACLES WITHIN 6 FEET OF X INTERIOR PLUMBING FIXTURES, AND ALL RECEPTACLES IN GARAGE, CARPORT, EXTERIOR WALLS OF INSPECTED STRUCTURE 7.5 OPERATION OF GFCI (GROUND FAULT CIRCUIT INTERRUPTERS) X X 7.6 LOCATION OF MAIN AND DISTRIBUTION PANELS X 7.7 SMOKE DETECTORS X X 7.8 CARBON MONOXIDE DETECTORS X IN=Inspected, NI=Not Inspected, NP=Not Present, RR=Repair or Replace Comments: 7.0 SOME LIGHTS NEED BULB REPLACEMENT. X X IN NI NP RR Panel capacity: (2) 200 AMP service panel Panel Type: Circuit breakers Electric Panel Manufacturer: GENERAL ELECTRIC Branch wire 15 and 20 AMP: Copper Wiring Methods: Romex 7.0 Picture GFCI IN UPSTAIRS GUEST BATH NOT TRIPPING. RECOMMEND ELECTRICIAN REPLACE AND CHECK ALL FOR PROPPER OPERATION.
15 Page 15 of Picture ALL SMOKE DETECTORS SHOULD HAVE BATTERIES REPLACED AND BE RETESTED PRIOR TO OCCUPANCY. The electrical system of the home was inspected and reported on with the above information. While the inspector makes every effort to find all areas of concern, some areas can go unnoticed. Outlets were not removed and the inspection was only visual. Any outlet not accessible (behind the refrigerator for example) was not inspected or accessible. Please be aware that the inspector has your best interest in mind. Any repair items mentioned in this report should be considered before purchase. It is recommended that qualified contractors be used in your further inspection or repair issues as it relates to the comments in this inspection report.
16 Page 16 of Heating / Central Air Conditioning The home inspector shall observe permanently installed heating and cooling systems including: Heating equipment; Cooling Equipment that is central to home; Normal operating controls; Automatic safety controls; Chimneys, flues, and vents, where readily visible; Solid fuel heating devices; Heat distribution systems including fans, pumps, ducts and piping, with supports, insulation, air filters, registers, radiators, fan coil units, convectors; and the presence of an installed heat source in each room. The home inspector shall describe: Energy source; and Heating equipment and distribution type. The home inspector shall operate the systems using normal operating controls. The home inspector shall open readily openable access panels provided by the manufacturer or installer for routine homeowner maintenance. The home inspector is not required to: Operate heating systems when weather conditions or other circumstances may cause equipment damage; Operate automatic safety controls; Ignite or extinguish solid fuel fires; or Observe: The interior of flues; Fireplace insert flue connections; Humidifiers; Electronic air filters; or The uniformity or adequacy of heat supply to the various rooms. IN NI NP RR Styles & Materials Heat Type: 8.0 HEATING EQUIPMENT X Forced Air Energy Source: 8.1 NORMAL OPERATING CONTROLS X Electric 8.2 AUTOMATIC SAFETY CONTROLS X 8.3 DISTRIBUTION SYSTEMS (including fans, pumps, ducts and piping, with X supports, insulation, air filters, registers, radiators, fan coil units and convectors) 8.4 PRESENCE OF INSTALLED HEAT SOURCE IN EACH ROOM X 8.5 COOLING AND AIR HANDLER EQUIPMENT X X 8.6 NORMAL OPERATING CONTROLS X 8.7 PRESENCE OF INSTALLED COOLING SOURCE IN EACH ROOM X IN NI NP RR Number of Heat Systems (excluding wood): Three Ductwork: Insulated Filter Type: Disposable Number of AC Only Units: Three IN=Inspected, NI=Not Inspected, NP=Not Present, RR=Repair or Replace Comments: 8.5 COLLING SYSTEMS ARE WORKING BUT SHOULD BE CHECK FOR OPTIMAL OPERATION AND EFFICIENCY AND AMINTENANCE BY A PROFFESIONAL. The heating and cooling system of this home was inspected and reported on with the above information. While the inspector makes every effort to find all areas of concern, some areas can go unnoticed. The inspection is not meant to be technically exhaustive. The inspection does not involve removal and inspection behind service door or dismantling that would otherwise reveal something only a licensed heat contractor would discover. Please be aware that the inspector has your best interest in mind. Any repair items mentioned in this report should be considered before purchase. It is recommended that qualified contractors be used in your further inspection or repair issues as it relates to the comments in this inspection report.
17 Page 17 of Insulation and Ventilation The home inspector shall observe: Insulation and vapor retarders in unfinished spaces; Ventilation of attics and foundation areas; Kitchen, bathroom, and laundry venting systems; and the operation of any readily accessible attic ventilation fan, and, when temperature permits, the operation of any readily accessible thermostatic control. The home inspector shall describe: Insulation in unfinished spaces; and Absence of insulation in unfinished space at conditioned surfaces. The home inspector shall: Move insulation where readily visible evidence indicates the need to do so; and Move insulation where chimneys penetrate roofs, where plumbing drain/waste pipes penetrate floors, adjacent to earth filled stoops or porches, and at exterior doors. The home inspector is not required to report on: Concealed insulation and vapor retarders; or Venting equipment that is integral with household appliances. IN NI NP RR Styles & Materials Attic Insulation: 9.0 INSULATION IN ATTIC X Blown Batt 9.1 VENTILATION OF ATTIC AND FOUNDATION AREAS X Ventilation: 9.2 VENTING SYSTEMS (Kitchens, baths and laundry) X Soffit Vents Exhaust Fans: 9.3 VENTILATION FANS AND THERMOSTATIC CONTROLS (ATTIC) X None IN NI NP RR Dryer Power Source: 220 Electric IN=Inspected, NI=Not Inspected, NP=Not Present, RR=Repair or Replace Dryer Vent: Unknown The insulation and ventilation of the home was inspected and reported on with the above information. While the inspector makes every effort to find all areas of concern, some areas can go unnoticed. Venting of exhaust fans or clothes dryer cannot be fully inspected and bends or obstructions can occur without being accessible or visible (behind wall and ceiling coverings). Only insulation that is visible was inspected. Please be aware that the inspector has your best interest in mind. Any repair items mentioned in this report should be considered before purchase. It is recommended that qualified contractors be used in your further inspection or repair issues as it relates to the comments in this inspection report.
18 Page 18 of Built-In Kitchen Appliances The home inspector shall observe and operate the basic functions of the following kitchen appliances: Permanently installed dishwasher, through its normal cycle; Range, cook top, and permanently installed oven; Trash compactor; Garbage disposal; Ventilation equipment or range hood; and Permanently installed microwave oven. The home inspector is not required to observe: Clocks, timers, self-cleaning oven function, or thermostats for calibration or automatic operation; Non built-in appliances; or Refrigeration units. The home inspector is not required to operate: Appliances in use; or Any appliance that is shut down or otherwise inoperable. IN NI NP RR Styles & Materials Dishwasher Brand: 10.0 DISHWASHER X BRAND NOT VISIBLE Disposer Brand: 10.1 RANGES/OVENS/COOKTOPS X IN SINK ERATOR 10.2 RANGE HOOD X Exhaust/Range hood: RE-CIRCULATE 10.3 TRASH COMPACTOR X Range/Oven: 10.4 FOOD WASTE DISPOSER X UNKNOWN 10.5 MICROWAVE COOKING EQUIPMENT X X Built in Microwave: DACOR 10.6 REFRIDGERATOR X Trash Compactors: 10.7 WASHING MACHINE X NONE 10.8 DRYER X 10.9 WINE COOLER X IN NI NP RR IN=Inspected, NI=Not Inspected, NP=Not Present, RR=Repair or Replace Comments: 10.5 MICROWAVE CONTROLS NOT WORKING PROPERLY. REPAIR AS NEEDED, LED LIGHT NOT WORKING Picture 1 The built-in appliances of the home were inspected and reported on with the above information. While the inspector makes every effort to find all areas of concern, some areas can go unnoticed. Please be aware that the inspector has your best interest in mind. Any repair items mentioned in this report should be considered before purchase. It is recommended that qualified contractors be used in your further inspection or repair issues as it relates to the comments in this inspection report.
19 Page 19 of Swimming Pools, Equipment and Safety Pools are fun, but children and adults can lose their life quickly. Over 4000 lives annually are lost with one-third under the age of 14. A child can drown in the time it takes to answer a phone. A swimming pool is 14 times more likely than a motor vehicle to be involved in the death of a child age 4 and under. An estimated 5,000 children ages 14 and under are hospitalized due to near-drownings each year; 15 percent die in the hospital and as many as 20 percent suffer severe, permanent brain damage. Of all preschoolers who drown, 70 percent are in the care of one or both parents at the time of the drowning and 75 percent are missing from sight for five minutes or less. Drowning surpasses all other causes of death to children age 14 and under in Arizona, California, Florida, Hawaii, Montana, Nevada, Oregon, Utah and Washington. A pool alarm with a loud speaker system to sound outside as well as inside the home could save a life. Even if you do not have children you should be concerned. 35% of children that drowned did so in someone else's pool. For more info, do an Internet search on pool safety or visit this website: OPERATIONAL CONDITION OF POOL X 11.1 POOL LINER CONDITION X 11.2 SURFACE WALLS AND FLOOR OF POOL X 11.3 PERMANENT ACCESSORIES CONDITION X 11.4 PUMPS FOR CIRCULATION OF WATER X X 11.5 PUMPS FOR VACUUM OR CLEANING X 11.6 POOL HEATERS X X 11.7 VERIFY THE ELECTRICAL OUTLET(S) AND ANY LIGHTING FOR X POOL IS ON A GROUND FAULT CIRCUIT (GFCI) 11.8 OVERFLOW SKIMMERS AND DRAINS X 11.9 CHEMICALS FOR POOL CAPABLE OF BEING STORED WITH A X X LOCK DOES POOL HAVE ANY RESCUE EQUIPMENT X X DO STEPS OR LADDERS EXIST ON BOTH SIDES OF THE POOL X X IS THE POOL DEPTH MARKED ON OUTSIDE AREA OF POOL X IS THERE A DEPTH OF AT LEAST 8 FEET TO ALLOW SAFE X DIVING ARE THERE ANY OBSTRUCTIONS (WALLS, SHRUBS etc.) THAT X WOULD PREVENT FULL VIEW OF POOL FROM HOME IS THE POOL FENCED X DOES FENCE HAVE A SELF CLOSING LATCH AND LOCK ON X DOOR CAN FENCE BE CLIMBED BY THE USE OF PERSONAL ITEMS OR X STRUCTURES AGAINST FENCE DOES THE DOOR LATCH HEIGHT AND LOCATION ATTEMPT TO X BE REASONABLY DIFFICULT FOR YOUNG CHILDREN TO REACH ELECTRIC LIGHTS SECURE X WATER LEVEL SHOULD BE WITHIN INCHES FROM RIM TO X ALLOW AN EASIER CLIMB OUT POOL DESIGN AT WATERS EDGE SHOULD NOT INCLUDE X OBVIOUS PROTRUSIONS THAT COULD INJURE SWIMMER DOES THE SURFACE AROUND POOL ENCOURAGE DRAINAGE X AWAY FROM POOL Safety Alarms From Exterior Doors and Windows To Pool Area X X DECK X X POOL HEATER X X IN=Inspected, Yes=Yes, NI=Not Inspected, NP=Not Present, RR=Repair or Replace, No=No Comments: 11.4 LEAK IN PIPING AT POOL WATER HEATER. IN Yes NI NP RR No IN Yes NI NP RR No Styles & Materials Style: In ground Shape: Rectangle Wall Material: Gunite (concrete)
20 Page 20 of Picture MUST BE CHECKED FOR PROPER OPERATION BY SPECIALIST SETTLMENT OF BRICK PAVERS AT POOL DECK. REMOVE PAVERS AND ADD ADDITIONAL SAND AND REPLACE Picture Picture Picture 3 Unless so mentioned in this report, I did not test water for bacteria or quality. The pool was inspected and reported on with the above information. While the inspector makes every effort to find all areas of concern, some areas can go unnoticed. Please be aware that the inspector has your best interest in mind. Any repair items mentioned in this report should be considered before purchase. It is recommended that qualified contractors be used in your further inspection or repair issues as it relates to the comments in this inspection report.
21 Page 21 of DOCK IN NI NP RR 12.0 DECK X X 12.1 PILINGS X 12.2 STRUCTURE X 12.3 SEAWALL X X 12.4 BOAT LIFT EQUIPMENT X IN NI NP RR IN=Inspected, NI=Not Inspected, NP=Not Present, RR=Repair or Replace Comments: 12.0 DECK IS AGED. RECOMMEND REPLACEMENT WITH NEWER DECKING MADE FROM RECYCLED MATERIALS SOME SLIGHT CRACKING IN SEAWALL CAP Picture Picture 2 Prepared Using HomeGauge : Licensed To ARCHIVISION 4D LLC
22 Page 22 of 32 General Summary ARCHIVISION 4D LLC 8542 Chase PreserveDr. Naples, Fl., Customer GINA Address NAPLES FL The following items or discoveries indicate that these systems or components do not function as intended or adversely affects the habitability of the dwelling; or warrants further investigation by a specialist, or requires subsequent observation. This summary shall not contain recommendations for routine upkeep of a system or component to keep it in proper functioning condition or recommendations to upgrade or enhance the function or efficiency of the home. This Summary is not the entire report. The complete report may include additional information of concern to the customer. It is recommended that the customer read the complete report. 2. Exterior 2.0 WALL CLADDING FLASHING AND TRIM Inspected, Repair or Replace 2 PIECES OF DECORATIVE TRIM DAMAGED. TRIM AT COLLUMNS SHOULD BE GROUTED. 2.0 Picture Picture 2
23 Page 23 of Exterior 2.1 DOORS (Exterior) Inspected, Repair or Replace SEVERAL FRENCH DOOR LOCKS NEED MAINTENANCE AND REPAIR. DEADBOLTS NOT WORKING. SIGNIFIGANT CORROSION ON EXTERIOR HARDWARE. PAINT AT SGD'S IS PEELING. 2.1 Picture Picture Picture Picture WINDOWS Inspected, Repair or Replace PAINT ON EXTERIOR WINDOW FRAMES.
24 Page 24 of Exterior 2.2 Picture DECKS, BALCONIES, STOOPS, STEPS, AREAWAYS, PORCHES, PATIO/ COVER AND APPLICABLE RAILINGS Inspected, Repair or Replace RAIL POST NOT SECURELY FASTENED. RAILINGS SHOW CORROSION TYPICAL OF WATERFRONT PROPERTIES. 2.3 Picture Picture VEGETATION, GRADING, DRAINAGE, DRIVEWAYS, PATIO FLOOR, WALKWAYS AND RETAINING WALLS (With respect to their effect on the condition of the building) Inspected, Repair or Replace SLIGHT ERROSION AT SEVERAL AREAS AROUND EXTERIOR.
25 Page 25 of Exterior 2.4 Picture 1 3. Garage 3.2 GARAGE FLOOR Inspected, Repair or Replace NON STRUCTURAL SHRINKAGE CRACKING IN GARAGE FLOOR. 3.2 Picture 1 4. Interiors 4.1 WALLS Inspected, Repair or Replace POOR PATCH JOB AT DROP IN CEILING.
26 Page 26 of Interiors 4.1 Picture STEPS, STAIRWAYS, BALCONIES AND RAILINGS Inspected, Repair or Replace MOISTURE DAMAGE AT STAIR TRIM. CHECK FOR SOURCE OF DAMAGE AND REPAIR. 4.3 Picture DOORS (REPRESENTATIVE NUMBER) Inspected, Repair or Replace ADJUSMENT NEEDED AT BIFOLD DOOR.
27 Page 27 of Interiors 4.5 Picture 1 6. Plumbing System 6.0 PLUMBING DRAIN, WASTE AND VENT SYSTEMS Inspected, Repair or Replace SEVERAL SINK STOPPERS NEED ADJUSTMENT. 6.0 Picture 1 7. Electrical System 7.5 OPERATION OF GFCI (GROUND FAULT CIRCUIT INTERRUPTERS) Inspected, Repair or Replace GFCI IN UPSTAIRS GUEST BATH NOT TRIPPING. RECOMMEND ELECTRICIAN REPLACE AND CHECK ALL FOR PROPPER OPERATION.
28 Page 28 of Electrical System 7.5 Picture SMOKE DETECTORS Inspected, Repair or Replace ALL SMOKE DETECTORS SHOULD HAVE BATTERIES REPLACED AND BE RETESTED PRIOR TO OCCUPANCY. 8. Heating / Central Air Conditioning 8.5 COOLING AND AIR HANDLER EQUIPMENT Inspected, Repair or Replace COLLING SYSTEMS ARE WORKING BUT SHOULD BE CHECK FOR OPTIMAL OPERATION AND EFFICIENCY AND AMINTENANCE BY A PROFFESIONAL. 10. Built-In Kitchen Appliances 10.5 MICROWAVE COOKING EQUIPMENT Inspected, Repair or Replace MICROWAVE CONTROLS NOT WORKING PROPERLY. REPAIR AS NEEDED, LED LIGHT NOT WORKING Picture 1
29 Page 29 of DOCK 12.0 DECK Inspected, Repair or Replace DECK IS AGED. RECOMMEND REPLACEMENT WITH NEWER DECKING MADE FROM RECYCLED MATERIALS SEAWALL Inspected, Repair or Replace SOME SLIGHT CRACKING IN SEAWALL CAP Picture Picture 2 Home inspectors are not required to report on the following: Life expectancy of any component or system; The causes of the need for a repair; The methods, materials, and costs of corrections; The suitability of the property for any specialized use; Compliance or non-compliance with codes, ordinances, statutes, regulatory requirements or restrictions; The market value of the property or its marketability; The advisability or inadvisability of purchase of the property; Any component or system that was not observed; The presence or absence of pests such as wood damaging organisms, rodents, or insects; or Cosmetic items, underground items, or items not permanently installed. Home inspectors are not required to: Offer warranties or guarantees of any kind; Calculate the strength, adequacy, or efficiency of any system or component; Enter any area or perform any procedure that may damage the property or its components or be dangerous to the home inspector or other persons; Operate any system or component that is shut down or otherwise inoperable; Operate any system or component that does not respond to normal operating controls; Disturb insulation, move personal items, panels, furniture, equipment, plant life, soil, snow, ice, or debris that obstructs access or visibility; Determine the presence or absence of any suspected adverse environmental condition or hazardous substance, including but not limited to mold, toxins, carcinogens, noise, contaminants in the building or in soil, water, and air; Determine the effectiveness of any system installed to control or remove suspected hazardous substances; Predict future condition, including but not limited to failure of components; Since this report is provided for the specific benefit of the customer(s), secondary readers of this information should hire a licensed inspector to perform an inspection to meet their specific needs and to obtain current information concerning this property. Prepared Using HomeGauge : Licensed To ARCHIVISION 4D LLC
30 Page 30 of 32 INVOICE ARCHIVISION 4D LLC 8542 Chase PreserveDr. Naples, Fl., Inspected By: KEVIN CABRAL Customer Info: GINA Inspection Property: NAPLES FL Inspection Date: 10/25/2011 Report ID: Customer's Real Estate Professional: Inspection Fee: Service Price Amount Sub-Total Heated Sq Ft 5, MOLD TEST WIND MITIGATION Payment Method: Payment Status: Note: Tax $0.00 Total Price $900.00
31 Page 31 of 32 This sample agreement is provided as a reference and should be edited as necessary to produce a final inspection agreement for your business. Note: Some items must be removed or altered by the inspector (including this note) in order to be used by the inspector. This may involve re-wording, or copying and pasting from the other agreements. It is recommended that someone with a strong legal understanding review and modify your final agreement as necessary to meet your local area and business requirements. You can use the drop down list above to insert merge fields that will automatically populate as necessary. The address of the property is: NAPLES FL Fee for the home inspection is $ INSPECTOR acknowledges receiving a deposit of $ from CLIENT. THIS AGREEMENT made on 10/25/2011 by and between KEVIN CABRAL (Hereinafter INSPECTOR ) and the undersigned (hereinafter CLIENT ), collectively referred to herein as the parties. The Parties Understand and Voluntarily Agree as follows: 1. INSPECTOR agrees to perform a visual inspection of the home/building and to provide CLIENT with a written inspection report identifying the defects that INSPECTOR both observed and deemed material. INSPECTOR may offer comments as a courtesy, but these comments will not comprise the bargained-for report. The report is only supplementary to the seller s disclosure. 2. Unless otherwise inconsistent with this Agreement or not possible, INSPECTOR agrees to perform the inspection in accordance to the current Standards of Practice of the National Association of Certified Home Inspectors posted at CLIENT understands that these standards contain certain limitations, exceptions, and exclusions. 3. The inspection and report are performed and prepared for the use of CLIENT, who gives INSPECTOR permission to discuss observations with real estate agents, owners, repairpersons, and other interested parties. INSPECTOR accepts no responsibility for use or misinterpretation by third parties. INSPECTOR S inspection of the property and the accompanying report are in no way intended to be a guarantee or warranty, express or implied, regarding the future use, operability, habitability or suitability of the home/building or its components. Any and all warranties, express or implied, including warranties of merchantability and fitness for a particular purpose, are expressly excluded by this Agreement. 4. INSPECTOR assumes no liability for the cost of repair or replacement of unreported defects or deficiencies either current or arising in the future. CLIENT acknowledges that the liability of INSPECTOR, its agents, employees, for claims or damages, costs of defense or suit, attorney s fees and expenses and payments arising out of or related to the INSPECTOR S negligence or breach of any obligation under this Agreement, including errors and omissions in the inspection or the report, shall be limited to liquidated damages in an amount equal to the fee paid to the INSPECTOR, and this liability shall be exclusive. CLIENT waives any claim for consequential, exemplary, special or incidental damages or for the loss of the use of the home/building even if the CLIENT has been
32 Page 32 of 32 advised of the possibility of such damages. The parties acknowledge that the liquidated damages are not intended as a penalty but are intended (i) to reflect the fact that actual damages may be difficult and impractical to ascertain; (ii) to allocate risk among the INSPECTOR and CLIENT; and (iii) to enable the INSPECTOR to perform the inspection at the stated fee. 5. INSPECTOR does not perform engineering, architectural, plumbing, or any other job function requiring an occupational license in the jurisdiction where the inspection is taking place, unless the inspector holds a valid occupational license, in which case he/she may inform the CLIENT that he/she is so licensed, and is therefore qualified to go beyond this basic home inspection, and for additional fee, perform additional inspections beyond those within the scope of the basic home inspection. Any agreement for such additional inspections shall be in a separate writing or noted here:. 6. In the event of a claim against INSPECTOR, CLIENT agrees to supply INSPECTOR with the following: (1) Written notification of adverse conditions within 14 days of discovery, and (2) Access to the premises. Failure to comply with the above conditions will release INSPECTOR and its agents from any and all obligations or liability of any kind. 7. The parties agree that any litigation arising out of this Agreement shall be filed only in the Court having jurisdiction in the County in which the INSPECTOR has its principal place of business. In the event that CLIENT fails to prove any adverse claims against INSPECTOR in a court of law, CLIENT agrees to pay all legal costs, expenses and fees of INSPECTOR in defending said claims. 8. If any court declares any provision of this Agreement invalid or unenforceable, the remaining provisions will remain in effect. This Agreement represents the entire agreement between the parties. All prior communications are merged into this Agreement, and there are no terms or conditions other than those set forth herein. No statement or promise of INSPECTOR or its agents shall be binding unless reduced to writing and signed by INSPECTOR. No change or modification shall be enforceable against any party unless such change or modification is in writing and signed by the parties. This Agreement shall be binding upon and enforceable by the parties and their heirs, executors, administrators, successors and assignees. CLIENT shall have no cause of action against INSPECTOR after one year from the date of the inspection. 9. Payment of the fee to INSPECTOR (less any deposit noted above) is due upon completion of the on-site inspection. The CLIENT agrees to pay all legal and time expenses incurred in collecting due payments, including attorney s fees, if any. If CLIENT is a corporation, LLC, or similar entity, the person signing this Agreement on behalf of such entity does personally guaranty payment of the fee by the entity. 10. HOLD HARMLESS AGREEMENT: CLIENT agrees to hold any and all real estate agents involved in the purchase of the property to be inspected harmless and keep them exonerated from all loss, damage, liability or expense occasioned or claims by reason of acts or neglects of the INSPECTOR or his employees or visitors or of independent contractors engaged or paid by INSPECTOR for the purpose of inspecting the subject home. CLIENT HAS CAREFULLY READ THE FOREGOING, AGREES TO IT, AND ACKNOWLEDGES RECEIPT OF A COPY OF THIS AGREEMENT. FOR INSPECTOR CLIENT OR REPRESENTATIVE
Page 1 of 25 Inspection Report Atlanta Strip Mall Property Address: Smyrna GA 30082 Page 2 of 25 South East Building Consultants Ray Thoroman Serving the entire State of Georgia 6 678-410-3005 Page 3 of
Page 1 of 24 Inspection Report Ms. Laurie Property Address: Spencer Oklahoma 73084 AAOK Home Inspections LLC Donald I. McCreary 70001429 3413 Terry Way Del City, OK 73115 405-778-4488 Page 2 of 24 Table
STATE OF FLORIDA HOME INSPECTION STANDARDS OF PRACTICE: 61-30.801 Standards of Practice, General. (1) Home inspections performed to these Standards of Practice are intended to provide the client with information
Summary of Oregon Home Inspector Certification Law and Standards of Practice for Home Inspections This is a summary of your rights and responsibilities when having a home inspection done by an Oregon certified
Inspection Report Mr. Sample Sample Property Address: 1234 USA Drive Indianapolis IN 12345 1234 USA Drive Morris Home Inspection Group, LLC Cedric Morris HI01200039 Fishers, IN 46037 317-550-6281 Table
Inspection Report Justin Property Address: 987 Bluffs Drive Thistown Ia 65765 JP's Home Inspection Services Jeff Peiffer 925 46th St. Sioux City, Ia 51104 (712) 301-8220 987 Bluffs Drive Page 2 of 23 Table
Inspection Report Mr. JOHN SMITH Property Address: 12345 S. Main St Denver Co 12349 A Happy House Home Inspection, LLC Hans Coleman Centennial, Co 80015 720-988-4830 Table of Contents Cover Page...1 Table
SECTION.1100 - NC HOME INSPECTOR STANDARDS OF PRACTICE AND CODE OF ETHICS.1101 DEFINITIONS The following definitions apply to this Section: (1) Automatic safety controls means devices designed and installed
Page 1 of 35 Inspection Report Mr. Happy Property Address: Joseph Poelsterl 450.010220 6334 W. Grace st Chicago Illinois 60634 1-773-454-6700 Page 2 of 35 Table of Contents Cover Page Table of Contents
South Carolina Home Inspector Standards of Practice The following Standards provide guidelines for the Residential Home Inspector and outline what the Residential Home Inspector should observe, identify,
Inspection Report Mr. Sample Customer Property Address: 1234 Sample Street Castle Rock Co 80000 1234 Sample Street, Castle Rock, CO 80000 Seven Stars Home Advisors Chad Chadwick 6839 W. Jackson Cr Rd Sedalia,
Inspect Before You Invest 2625 NE 14 TH AVE #113 WILTON MANORS, FL 33334 THIS IS INTENDED TO BE A LEGAL BINDING AGREEMENT. WE SUGGEST YOU READ IT CAREFULLY BEFORE SIGNING. ELECTRONIC SIGNATURE IS DEEMED
Inspection Report Mister Sample Misses Sample Property Address: 234 Your Street Anytown, PA 99999 Classic Inspections, LLC Steve Maurer 3633 Buttonwood Drive Doylestown, PA 18902 267-884-4047 1 of 25 5/9/08
Inspecton Report Provided by: National Home Inspections Inspector: Bob Smith 456 S Main Denver, CO 46312 (645) 423-3242 firstname.lastname@example.org www.nationalhomeservices.com Property Address: 873
105 Dixie Dr., Chapel Hill, NC 27514 page1 of 32 Inspection Report Mr. John Cauthen Property Address: 105 Dixie Dr. Chapel Hill NC 27514 First Call Home Inspections LLC John B. Cauthen 8004 Morrell Lane,
Page 1 of 37 Inspection Report Prepared For: Sampath Sample Property Address: Alpharetta, GA 30004 Atlanta Home Inspections Matthew A Thoroman 6625 Hwy. 53 E. Ste. 410-151 Dawsonville Ga 30534 (678)-410-8062
Inspection Sample Property Address: 123 Main St Madison Wi 53704 Badger Property Inspection Trent Stein 2723-106 3603 Rolling hills Middleton, Wi. 53562 608-469-0249 Table of Contents Cover Page...1 Table
SC Standards of Practice SOUTH CAROLINA RESIDENTIAL BUILDERS COMMISSION HOME INSPECTOR STANDARDS OF PRACTICE Adopted by the Residential Builders Commission May 13, 1998 PURPOSE: The purpose of a residential
(850) 297-1998 1716 Monticello Dr Tallahassee, Florida 32303 PROPERTY INSPECTION REPORT THIS INSPECTION IS A DETAILED LISTING OF AREAS VISUALLY INSPECTED AT:, Tallahassee FL Client Tallahassee, FL 32304
ASHI STANDARD OF PROFESSIONAL PRACTICE FOR HOME INSPECTIONS 1. INTRODUCTION 1.1 This ASHI Standard of Professional Practice for Home Inspections (Standard) defines the scope of home inspections performed
BUILDING ANALYSIS REPORT July 25, 2014 John Doe 1234 Smith Road Atlanta, Georgia 30396 Agent: Ausker and Barbara Morris AT Morris Realty Group, Inc. 3162 Johnson Ferry Road, Suite 260-25 Marietta, Georgia
Page 1 of 14 Inspection Report Mr. John Homebuyer Property Address: 123 Main Street Houston TX 77007 Front View EDP Consulting Engineers, PLLC Gerald C. Reece, PE TREC #7825 14119 Willowsong Ct Missouri
Standards of Practice 301. Minimum Standards A. This Chapter sets forth the minimum Standards of Practice required of licensed home inspectors. 303. Definitions A. The definitions in 109 are incorporated
Page 1 of 14 Article I. SECTION 1.01 INTRODUCTION PREFACE THE INTERNATIONAL SOCIETY OF HOME INSPECTORS, INC. (ISHI) IS A NOT-FOR-PROFIT PROFESSIONAL SOCIETY ESTABLISHED IN 1995. MEMBERSHIP IN ISHI IS VOLUNTARY
South Carolina Home Inspector Standards of Practice The following Standards provide guidelines for the Residential Home Inspector and outline what the Residential Home Inspector should observe, identify,
Page 1 of 58 Inspection Report Prepared For: Atlanta Commercial Customer Property Address: Building 5 Marietta, GA 30066 Superior Home Inspections Ray Thoroman 8070 Ivy Shaw Dr. Gainesville,GA 30506 678-410-3005
Edgewood Home Inspections, Inc. 407 W. Smith Valley Rd. #1032 Greenwood, IN 46142 (317) 833-6048 HOME INSPECTION REPORT Indianapolis IN 46000 Inspector's Name: License Number: Scott Kissel HI00800073 TABLE
Cover Page Vari Inspection Services Property Inspection Report Inspection prepared for: Sample Real Estate Agent: None - Date of Inspection: 5/13/2015 Inspector: Tony Vari License # HI8047 23110 STRD 54
Inspection Report Sample Property Address: XXXX N. Atolia Drive Tucson AZ 85743 House and Home Brian Pemble #45238 6909 E. Kingston Drive Tucson, AZ. 85710. 520-245-7897 Table of Contents Cover Page...1
Inspection Report John Doe Property Address: Any Town Ga. 30097 Sample Report Georgia State Inspections Jake Accardi ICC 8034454- B2 www.gastateinspections.com 404.514.7457 email@example.com
COMPREHENSIVE PROPERTY INSPECTIONS Thank you for selecting CPI for your Deficiency Observation. A full home inspection was not performed on this property at the buyers request. This inspection is a limited
Report for Dick and Jane Homeowner 1234 Lovers Lane, Houston, Texas 77000 March 17, 2004 I NI NP R Inspection Item I. STRUCTURAL SYSTEMS o o o A. Foundations (If all crawl space areas are not inspected,
Inspection Report Joe Report Property Address: 111 Main Street St Augustine FL 32080 Eagle Eye Home Inspections Rick Glodowski HI 4677 5255 Atlantic View St Augustine, FL 32080 904-461-2550 111 Main Street
Crepps Home Inspection 651 Lincoln Drive Elizabethown, KY 42701 (270) 734-3845 www.crepps-hi.com firstname.lastname@example.org Inspected By: Josh Crepps HI - 3058 Repair Report Prepared For: John & Jane Doe Property
Page 1 of 53 Inspection Report Jacksonville Property Address: Jacksonville FL 32204 South East Building Consultants Ray Thoroman Inspecting Jacksonville FL and entire South East Page 2 of 53 Table of Contents
Inspection Report Property Address: St. Marks Ave. Brooklyn NY 11213 Five Borough Home Inspection, LLC Derek Lomer NYS Licence Lic # 16000051234 790 Washington Ave., Unit 112 Brooklyn, NY, 11238 917-494-8474
Representing CERTIFIED PROPERTY INSPECTORS in British Columbia ASTTBC PI STANDARDS OF INSPECTION Part 1: Glossary (CONTAINS ITALICIZED WORDS IN THIS DOCUMENT) ASTTBC & ASTTBC PI: COMMON AREA(S): DIRECT
Inspection Report Property Address: 1234 Anywhere street Phoenix AZ Veteran Inspection Professionals Mark Mandery 040901 4725 W. Aire Libre Ave Glendale AZ, 85306 480-694-2111 Table of Contents Cover Page...1
Crawford Inspection Services C.C.B. # 76914 www.crawfordinspections.com Portland Area PO Box 665 West Linn, OR 97068 Ph: (503) 650-6957 Salem Area 5434 River Rd. N; #192 Keizer, OR 97303 Ph: (503) 362-5809
Report# 21009 Page 1 of 24 Home Inspection Report Property Address: 123 Maple Lane, St. Augustine, FL 32092 Prepared For: Mr. Smith Prepared By: EDGE Inspections www.edgeinspections.com PO Box 601055 Jacksonville,
BOROUGH OF NATIONAL PARK APPLICATION FOR A CERTIFICATE OF OCCUPANCY FOR CHANGE OF OCCUPANCY ADDRESS OF PROPERTY FOR INSPECTION # BLOCK LOT VACANT YES NO CURRENT OWNER NAME ADDRESS TELEPHONE # PROSPECTIVE
Vision Home Inspection 324 Rams Run Shepherdsville KY 40165-7877 Inspector: James McFadden Property Inspection Report Client(s): Property address: Inspection date: View report summary This report is the
Page 1 of 41 Inspection Report Inspection Date: 12/1/2010 Commercial Property Sample Report Property Address: City State Zip All In One Home Inspection LLC Joseph W Fleming III - Home Inspector License
New Jersey Property Inspections LLC NJ State Home Inspector License # 24GI00105100 27 Neshanic Drive, Ringoes NJ 08551 908-642-2112/908-788-0055 PRE-INPECTION AGREEMENT READ THIS DOCUMENT CAREFULLY. IT
A.C.E. Home Inspection Service www.acehomeweb.com St. Peters, MO 63376 (636) 978-9111 Inspector Name: Tim Knight, ASHI Member 202490 Inspection No: 12121212 Inspection Date: 1/1/2012 Client: Address: John
6/ /07 The Inspection of the property listed above must be performed in compliance with the rules of TREC. The inspection is of conditions which are present and visible at the time of the inspection, and
608 State St. South Kirkland, WA 98033 www.faira.com email@example.com +1.800.571.FAIR FAIRA TRANSPARENCY REPORTS, Renton, WA 98059 March 11, 2016 Thank you for your interest in this Faira Certified home.
HOME INSPECTION HANDOUT FOR HOME BUYERS 1. How do I select a reputable home inspector? The Inspection Contingency in the residential offer to purchase calls for a Wisconsin registered home inspector. Ask
Total Home Inspection Checklist Use a checklist like this to make sure that you are looking at all parts of the house. Check off those items that are in good condition and make notes about those that are
www.citiesinspection.com October 5, 2015 Dear Client, On 9/14/2015, Cities Inspection Service, Inc. completed a building inspection of the property located at 123 Oak Street, Someplace, Minnesota for you.
Standards of Professional Practice Adapted with permission from Standards of Practice, Effective June 1, 1992, Copyright 1993 American Society of Home Inspectors, Inc. Adopted by AZ ASHI Effective January
RULES OF TENNESSEE DEPARTMENT OF COMMERCE AND INSURANCE DIVISION OF REGULATORY BOARDS CHAPTER 0780-5-12 HOME INSPECTORS TABLE OF CONTENTS 0780-5-12-.01 Purpose 0780-5-12-.07 Qualifying and Continuing Education
AMERICAN SOCIETY OF HOME INSPECTORS STANDARDS OF PROFESSIONAL PRACTICE FOR RESIDENTIAL SWIMMING POOL AND SPA INSPECTIONS 1. INSPECTION PURPOSE AND SCOPE 1.1 The purpose of these Standards of Professional
Page 1 of 21 Inspection Report Condo Association Property Address: Swamptown, IL Front View William Decker, IL Lic. # 450.0002240 Page 2 of 21 Date: 10/10/2008 Time: 1:00 PM Report ID: Sample 4 Property:
Page 1 of 33 Inspection Report Joe and Sue Property Address: Bothell WA 98011 Transparent Inspections Austin McFeeley 13221 Meridian Ave S Unit A Everett WA 98208 425-773-6637 Page 2 of 33 Table of Contents
HOMEOWNER S PERMIT GUIDE WHEN IS A PERMIT REQUIRED? Department of Development and Permits 306 Cedar Road, City Hall 2 nd Floor P.O. Box 15225 Chesapeake, VA 23328 Phone: (757) 382-6018 Fax: (757) 382-8448
CHRIS CURLES and ASSOCIATES INSPECTION SERVICES Inc. Chris Curles, President www.homeinspectionsatlanta.com firstname.lastname@example.org Office: 770-493-0227 Professional Member Of: GAHI # 93006 ASHI # 211725
LIMITED ONE-YEAR WARRANTY SELLER S RESPONSIBILITY Except as covered by a manufacturers limited warranty, the Seller hereby provides a Limited Warranty for the dwelling against defects in the original material
Inspection Report Mr. Doug Smith Property Address: 123 House Street SAINT LOUIS MO 63116 Street View CANDID HOME INSPECTION SERVICE, LLC. STEVE SHORETTE 3 ELK TRAIL COURT ARNOLD, MO. 63010 636.282.2747
Selling your home Does Wall Township require an inspection by the building department on resale of a home? No. We do not require a Certificate of Continued Occupancy on the resale of home. A Smoke Detector,
PROPERTY INSPECTION OR ASSESSMENT OF DAMAGES ADDRESS: Somewhere, FL CLIENT: GAIA GC ID No: 2015000 DATE: 12/31/2015 INSPECTION OR ASSESSMENT BY: GAIA CONSTRUCTION INC. CGC 1516136 FLORIDA HI-2792 FLORIDA
Inspection Report Bob and Betty Property Address: 4567 Home street Anchorage AK 99507 Inspection Connection LLC Richard A. Long Alaska Registered #183 8621 Barney Circle Anchorage, AK 99507 (907) 868-8096
Inspection Report provided by: Zimmel Home Inspections Inspector: Tyson Zimmel Tyson Zimmel (Lic.#862) (360) 775-0708 www.zimmelhomeinspections.com Property Address: 123 Fake Street Port Angeles WA 98362
A TO Z HOME INSPECTIONS PROFESSIONAL HOME INSPECTION SERVICES FOR HOME BUYERS AND SELLERS Insurance Inspection Report 1234 Main Street Tallahassee, Florida Report Prepared For: Charles Smith Report Prepared
APPENDIX 9 AFFORDABLE HOUSING PROGRAM INSPECTION CHECKLIST Participating Jurisdiction: Homeowner Name: Assisted Property Address: Date of Physical Inspection of Property: Total Square Footage of Property:
Building Permits: When are they required? Generally, you need to obtain a building permit from the City whenever you construct, enlarge, alter, repair, move, remove, improve, convert, or demolish a building
GUARDIAN HOME 26 EAST MADISON AVENUE CRESSKILL, NEW JERSEY 07626 (201) 568 2783 (201) 568 8117 FAX REPORT NUMBER: 2007/01/01/100 PROPERTY LOCATION: 123 Main Street, Cresskill, New Jersey PRESENT OWNERS:
To be used as a first home visit for note taking. Visit www.homeinspectiondirect.com for more tips and information about buying a home and hiring a home inspector. This form in no way replaces a professional
Home Inspection Report Report Number: 144 For The Property Located On: 123 Any Street 27587 Prepared For Exclusive Use By: Mr. Sample N/A,,, Report Prepared By: Edward Carapezza; License No.: 3447 Inspector
Cover Page Property Inspection Report My street, Anytown GA, 30000 Inspection prepared for: John Doe Inspection Date: 7/18/2011 Time: 5pm Age: 25+ Size: >1500 Weather: Clear This ranch style home is in
Inspection Report Ms. Onah Holmes 123 Maple Street Springfield, Ontario 123 Maple Street Page 2 of 30 Cover Page Table of Contents Table of Contents Intro Page 1 Roof 2 Exterior 3 Basement, Foundation,
THIS FORM APPROVED BY THE LAWRENCE HOME BUILDERS ASSOCIATION [REV. 05/00] WARRANTY ADDENDUM TO RESIDENTIAL CONSTRUCTION SALE CONTRACT [Limited One Year Warranty] SECTION 1 - DEFINITIONS Owner's Name: Street
#1) BEFORE Purchasing Land Here Is A Checklist Of Things You Should Check Zoning laws Deed restrictions on home size, foundation style, roof pitch, etc. Suitability (slope, wetland issues, etc.) Accessibility