1 30"-64" Ductile Iron industrial Applications, water & Wastewater
2 2 Table of Contents Flanged Fittings for Water 3 Flange Details 5 Flanged Fittings 6 90º and 45º Bend /2º and 11-1/4º Bends 7 Tees 8 Crosses Base Bends 14 Base Tees 15 Base Drilling Details for Base Bends and Tees 18 Concentric Reducers 19 Eccentric Reducers 21 90º Long Radius Bends 23 Reducing Bends Blind Flanges 25 Wye Branches 26 True Wyes 27 Straight Flare 28 Flange and Flare 90º Bends (Standard and Long Radius) 29 Method of Designating Outlets of Reducing Fittings in Specifications 30 Method of Designating Location of Tapped Holes When Specified 31 Combination of Standard Fittings That May be Used in lace of Special Fittings 32 roducts for Water, Waste Water and Fire rotection 33 Note: If specifiers and users believe that corrosive soils will be encountered where our products are to be installed, please refer to ANSI/AWWA C105/A21.5 olyethelene Encasement for Ductile Iron ipe Systems for proper external protection procedures.
3 3 Flanged Fittings for Water and Other Liquids are typical components in rigid piping systems. Such systems are particularly suited for above ground installation: water filtration plants, sewage disposal plants, wastewater treatment plants, pumping stations and industrial plants. Our Special rojects Department has the knowledge and experience to assist with the unique design challenges of plant work. Coating Systems Unless otherwise specified, flanged fittings will be furnished with a standard thickness cement-mortar lining with asphaltic coating inside and outside. Fittings are furnished coated or uncoated in accordance with the purchasers requirements. ANSI /AWWA Standards ANSI/AWWA C110/A21.10 Ductile-Iron and Gray-Iron Fittings. For Water (3-through 48" sizes). ANSI/AWWA C153/A21.53 Ductile-Iron Compact Fittings, For Water Service (54" through 64" sizes). U.S. ipe s Flanged Fittings are produced of Ductile Iron and conform to the applicable requirements for Ductile Iron fittings specified in ANSI/AWWA C110/A21.10 ANSI/AWWA C104/21.4 Cement-Mortar Lining for Ductile-Iron and Gray-Iron Fittings for Water. Coating system options include primer base coat and cement-mortar lining with asphaltic coating inside. ASTM A536 "Standard Specification for Ductile Iron Castings." The underground use of the flanged joint is generally not recommended due to the rigidity of the joint. Unequal settlement or other stressing of such piping may result in excessive strain on the flanges or the pipe.
4 4 Flanged Fittings for Water and Other Liquids (cont.) Accessories The gaskets and bolts to be used with flanged pipe and fittings should be selected by the purchaser with due consideration for the particular service and installation requirements. Flanged joint accessories (bolts, nuts and gaskets) can be furnished by U.S. ipe if so specified. U.S. ipe's FULL FACE FLANGE-TYTE Gaskets or RING FLANGE-TYTE Gaskets (4" through 64"size) are recommended for all flanged joints. Flange Compatibility and ressure Ratings The flanges of ANSI/AWWA C110/A21.10 and C153/A21.53 standards conform to the drilling and facing of ANSI B16.1 Class 125 flanges. This B16.1 Class 125 designation leads some to conclude that these AWWA flanges are only rated at 125 psi service which is not correct. ANSI/AWWA C110/A21.10 flanged fittings are rated for 350 psi operating pressure for 3" through 12" sizes, 250 psi operating pressure for 14" through 48" sizes and ANSI/AWWA C153/A21.53 fittings are rated for 150 psi operating pressure for 54" through 64" sizes. These ratings are at ambient temperatures with at least a 2:1 factor of safety. Special gaskets such as U.S. ipe s FULL FACE FLANGE-TYTE Gaskets or RING FLANGE-TYTE Gaskets are required for operating pressures greater than 250 psi. (Flanges of Ductile Iron fittings meeting the requirements of ANSI/AWWA C110/A21.10 cannot be joined with Class 250 ANSI B16.1 flanges.) Special Service Requirements When requesting prices for flanged piping other than water service, please furnish complete information regarding the type of material to be conveyed, composition, concentration, ph, pressure and temperature. NOTE: U.S. ipe recommends the use of FULL FACE FLANGE-TYTE Gaskets or RING FLANGE-TYTE Gaskets with Ductile Iron flanged joint products supplied by U.S. ipe. These gaskets were designed specifically for the unique surface of Ductile Iron. Flat rubber gaskets are NOT considered equal in performance and may not provide the sealing capability the project requires. In addition, their use could result in unintended damage to the flanges and threads of the fabricated pipe by applying excess torque to the bolts/flanges in order to seal the joint.
5 5 Flanged Fittings - Flange Details Dimensions Inches Size Bolt Hole Bolt Qty. of Inches OD BC T Diameter Diameter & Length Bolts ±.12 3/4 5/8 x 2-1/ ±.12 3/4 5/8 x ±.12 7/8 3/4 x 3-1/ ±.12 7/8 3/4 x 3-1/ ± /8 x ± /8 x ± /8 1 x 4-1/ ± /8 1 x 4-1/ ± /4 1-1/8 x ± /4 1-1/8 x ± /8 1-1/4 x 5-1/ ± /8 1-1/4 x 6-1/ ± /8 1-1/2 x ± /8 1-1/2 x 7-1/ ± /8 1-1/2 x ± /4 x 8-1/ ± /4 x ± /4 x 9 52 LAYING LENGTH DIMENSIONS: ipe face-to-face dimensions conform to a tolerance of ±.12" for sizes 3"-64" Fittings face-to-face dimensions conform to a tolerance of ±.06" for sizes 3"-10" and ±.12" for sizes 12"-64". The largest opening governs the tolerance for all openings. Center-to-face tolerances are one half the face-to-face tolerances. FLANGES: The bolt circle and bolt holes of these flanges match those of ANSI/AWWA C115/A21.15 and Class 125 flanges shown in ANSI B16.1 and can be joined with A21.15 and Class 125 B16.1 flanges. The flanges do not match the Class 250 flanges shown in ANSI B16.1 and cannot be joined with Class 250 B16.1 flanged fittings and valves. For technical information on Class 250 flanges see U.S. ipe's Class 250 Flanges submittal document at FACING: Class 125 flanges are plain faced without projection and are furnished smooth or with shallow serrations. CERTIFICATION: Complies with ANSI/AWWA C115/A21.15 Flanged Ductile Iron ipe.
6 6 Flanged Fittings - 90º and 45º Bends Dimensions Weight ressure Inches ounds Size Rating 90º 45º 90º 45º Inches psi t A R A R NOTE: Actual weights of fittings, sizes 54"-64", may exceed those shown. For flange details see page 5. Sizes 30"-48" conform to ANSI/AWWA C110/A2l.10. Sizes 54"-64" conform to ANSI/AWWA C153/A21.53.
7 7 Flanged Fittings /2º and 11-1/4º Bends Dimensions Weight ressure Inches ounds Size Rating 22-1/2º 11-1/4º 22-1/2º 11-1/4º Inches psi t A R A R NOTE: Actual weights of fittings, sizes 54"-64", may exceed those shown. For flange details see page 5. Sizes 30"-48" conform to ANSI/AWWA C110/A2l.10. Sizes 54"-64" conform to ANSI/AWWA C153/A21.53.
8 8 Flanged Fittings - Tees Size ressure Rating Dimensions Weight Inches psi Inches ounds Run Branch t T 1 H J Tee NOTE: Actual weights of fittings, sizes 54"-64", may exceed those shown.
9 9 Flanged Fittings - Tees (cont.) Size ressure Rating Dimensions Weight Inches psi Inches ounds Run Branch t T 1 H J Tee NOTE: Actual weights of fittings, sizes 54"-64", may exceed those shown.
10 10 Flanged Fittings - Tees (cont.) Size ressure Rating Dimensions Weight Inches psi Inches ounds Run Branch T T 1 H J Tee NOTE: Actual weights of fittings, sizes 54"-64", may exceed those shown.
11 11 Flanged Fittings - Crosses Size ressure Rating Dimensions Weight Inches psi Inches ounds Run Branch t T 1 H J Cross NOTE: Actual weights of fittings, sizes 54"-64", may exceed those shown.
12 12 Flanged Fittings - Crosses (cont.) Size ressure Rating Dimensions Weight Inches psi Inches ounds Run Branch t T 1 H J Cross NOTE: Actual weights of fittings, sizes 54"-64", may exceed those shown.
13 13 Flanged Fittings - Crosses (cont.) Size ressure Rating Dimensions Weight Inches psi Inches ounds Run Branch T T 1 H J Cross NOTE: Actual weights of fittings, sizes 54"-64", may exceed those shown.
14 14 Flanged Fittings - 90º Base Bends Size ressure Dimensions Weight Inches Rating Inches ounds psi R S Diameter t u Base BeND Base Only * * * NOTE: Actual weights of fittings, sizes 54"-64", may exceed those shown. For flange detail see page 5. Dimension R is a finished dimension; unfinished bases will be 1/8" longer. For base drilling details see page 18. *Not included in AWWA C110 or C153
15 15 Flanged Fittings - Base Tees SIZE Inches pressure rating psi diameter Inches weight ounds run branch R S diameter T U base bend base only NOTE: Actual weights of fittings, sizes 54"-64", may exceed those shown. For flange detail see page 5. Dimension R is a finished dimension; unfinished bases will be 1/8" longer. For base drilling details see page 18. *Not included in AWWA C110 or C153
16 16 Flanged Fittings - Base Tees (cont.) SIZE Inches pressure rating psi diameter Inches weight ounds run branch R S diameter T U base bend base only NOTE: Actual weights of fittings, sizes 54"-64", may exceed those shown. For flange detail see page 5. Dimension R is a finished dimension; unfinished bases will be 1/8" longer. For base drilling details see page 18. *Not included in AWWA C110 or C153
17 17 Flanged Fittings - Base Tees (cont.) SIZE Inches pressure rating psi diameter Inches weight ounds run branch R S diameter T U base bend base only NOTE: Actual weights of fittings, sizes 54"-64", may exceed those shown. For flange detail see page 5. Dimension R is a finished dimension; unfinished bases will be 1/8" longer. For base drilling details see page 18. *Not included in AWWA C110 or C153
18 18 Flanged Fittings-Base Drilling Details for Base Bends and Base Tees Size Fitting Inches Dimensions Inches Bolt Bolt Hole Number Circle DiameteR of Bolts / /4 4 54* /4 4 60* /8 4 64* /8 4 * Not included in AWWA C110 or C153
19 19 Flanged Fittings - Concentric Reducers Concentric Size ressure Rating Dimensions Weight Inches psi Inches ounds run BRANCH t t 1 L
20 20 Flanged Fittings - Concentric Reducers (cont.) Size ressure Rating Dimensions Weight Inches psi Inches ounds run BRANCH t t 1 L NOTE: Actual weights of fittings, sizes 54"-64" may exceed those shown. Sizes 3"-48" conform to ANSI/AWWA C110/A Sizes 54"-64" conform to ANSI/AWWA C153/A For flange details see page 5. On reducers of certain end combinations the number of bolt holes on one flange have an odd number in one quadrant and the opposite flange has an even number of holes in the same quadrant so that there are only four positions in which the reducers can be placed to properly assemble with the adjacent piping. lease take particular note that flange reducers have the vertical centerline marked on the edge of the flange. If assembled with the centerline in the vertical plane, the casting will properly assemble.
21 21 Flanged Fittings - Eccentric Reducers Eccentric Size ressure Rating Dimensions Weight Inches psi Inches ounds run BRANCH t t 1 L
22 22 Flanged Fittings - Eccentric Reducers (cont.) Size Inches ressure Rating psi Dimensions Inches Weight ounds run BRANCH t t 1 L NOTE: Actual weights of fittings, sizes 54"-64" may exceed those shown. Sizes 3"-48" conform to ANSI/AWWA C110/A Sizes 54"-64" conform to ANSI/AWWA C153/A For flange details see page 5. On reducers of certain end combinations the number of bolt holes on one flange have an odd number in one quadrant and the opposite flange has an even number of holes in the same quadrant so that there are only four positions in which the reducers can be placed to properly assemble with the adjacent piping. lease take particular note that flange reducers have the vertical centerline marked on the edge of the flange. If assembled with the centerline in the vertical plane, the casting will properly assemble. *Not included in AWWA C110 or C153
23 23 Flanged Fittings 90º Long Radius Bends 90º Bend Long Radius Nominal ressure Wall B Weights Size Rating Thickness Inches ounds Inches psi Inches NOTE: Thicknesses and Dimensions Conforming to ANSI B16.1 For flange details see page 5.
24 24 Flanged Fittings Reducing Bends 90º Size Inches A R T T1 Weight ounds 30 X X X X X X X X X X X X X X X X X X X X X X X X X X X X X
25 25 Flanged Fittings Blind Flanges 2" - 10" 12" - 48" NOTE: Actual weights of fittings, sizes 54"-64", may exceed those shown. For bolt hole details see page 5. Dimensions Inches Size ressure Rating Diameter Thickness Wall Blind Flanges Inches psi of Flange of Flange thickness ounds o Q V
26 26 Flanged Fittings Wye Branches Size ressure Rating Dimensions Weight Inches psi Inches ounds RUN BRANCH RUN BRANCH For flange details see page 5 Wall Thickness A B C
27 27 Flanged Fittings Straight Flare Size T R B L Weight Inches ounds For flange details see page 5.
28 28 Flange and Flare 90º Bends Standard and Long Radius Miscellaneous Flanged Fittings DIMENSIONS Inches WEIGHT ounds DIMENSIONS Inches WEIGHT ounds STANDARD LONG RADIUS SIZE A B C DIAMETER WALL T SIZE A B For flange details see page 5.
29 29 Method of Designating Outlets of Reducing Fittings in Specifications NOTE: The largest opening establishes the basic size of a reducing fitting. The largest opening is named first, except for bullhead tees which are reducing on both runs and for double branch elbows where both branches are reducing, the outlet is the largest opening and named last in both cases. In designating the openings of reducing fittings they should be read in the order indicated by the sequence of the letters a, b, c and d. In designating the outlets of side outlet reducing fittings the side outlet is named last and in the case of the cross which is not shown the side outlet is designated by the letter e. Fittings of the configurations shown on this page that are not covered on pages 6 through 28 may be furnished on special order. Consult your nearest U.S. ipe Sales Representative.
30 30 Method of Designating Location of Tapped Holes When Specified NOTE: The above sketches show two views of the same fitting and represent fittings with symmetrical shapes, with the exception of the side outlet elbow and the side outlet tee (straight sizes). Fittings of the configurations shown on this page that are not covered on pages 6 through 28 may be furnished on special order. Consult your nearest U.S. ipe Sales Representative.
31 31 Combination of Standard Fittings That May be Used in lace of Special Fittings The illustrations in the SECIAL columns on this page indicate typical fittings that are often required with a combination of bell, plain end, and flange outlets. The laying dimensions of these fittings are not covered by any standard and they are therefore usually named SECIAL inasmuch as they are made to order to suit certain conditions in piping installations. To the right of each SECIAL fitting is shown a combination of Standard fittings that can be used to obtain the same outlet effects as the Specials. The laying dimensions may not be interchangeable since the dimensions of the Standard fittings are fixed whereas the Special can be made to a variety of desired lengths. The use of Standard fittings wherever possible is always recommended as the most economical and such fittings can usually be shipped out of stock. In sending inquiries for fittings of dimensions deviating from the Standard, state specifically the type of outlets wanted, reading, sizes, etc., as shown on this page, and give exact dimension from the center line to outlet.
32 32 roducts for Water, Wastewater and Fire rotection ductile iron pipe TYTON JOINT ipe Mechanical Joint ipe TR FLEX ipe H LOK ipe Flanged ipe Grooved ipe USIFLEX Boltless Ball Joint ipe For Subaqueous Installations size range 3"-64" Ductile Iron 4"-12" Ductile Iron 4"-36" Ductile Iron 30"-64" Ductile Iron 3"-64" Ductile Iron 4-36 Ductile Iron 4"-48" Ductile Iron restrained Joints TR FLEX Restrained Joint 4"-36" Ductile Iron H LOK Restrained Joint 30"-64" Ductile Iron MJ FIELD LOK Gaskets 4"-24" FIELD LOK 350 Gaskets 4"-24" FIELD LOK Gasket 30" & 36" TR FLEX GRIER Rings 4"-36" Ductile Iron TR TELE FLEX Assemblies 4"-24" Ductile Iron Fittings TYTON Fittings TRIM TYTON Fittings TR FLEX Fittings and TR FLEX Telescoping Sleeves H LOK Fittings and H LOK Telescoping Sleeves Mechanical Joint Fittings Flanged Fittings XTRA FLEX Couplings 14"-24" Ductile Iron 4-12 Ductile Iron 4"-36" Ductile Iron Ductile Iron 30"-48" Ductile Iron 30"-64" Ductile Iron 4"-24" Ductile Iron Miscellaneous products ROTECTO 401 Lined Ductile Iron ipe for 4"-64" Ductile Iron Domestic Sewage and Industrial Wastes GLASS Lined Ductile Iron ipe for Wastewater Treatment lants 4-30 Ductile Iron RING FLANGE-TYTE Gaskets 4"-36" FULL FACE FLANGE-TYTE Gaskets 4"-64" MJ Harness-Lok 4-48 Ductile Iron Saddle Outlets Various Ductile Iron Welded Outlets Various Ductile Iron olyethylene Encasement 4"-64" Our products are manufactured in conformance with National Standards so that our customers may be assured of getting the performance and longevity they expect. Use of accessories or other appurtenances that do not comply with recognized standards may jeopardize the performance and longevity of the project.
33 33 All U.S. ipe brochures and/or products are subject to change without further notice..o. BoX BIRMINGHAM, AL DI.Ie ( ) FAX:
DUCTILE IRON PIPE JOINTS AND THEIR USES Ductile Iron Pipe Joints and Their Uses By Richard W. Bonds, P.E. DIPRA Research and Technical Director Introduction Joints for Iron pipe have come a long way. About
Mueller Pipe Repair Products Saddles Tapping Sleeves Pipe Repair Clamps A complete selection for all types of pipe... all from a single source. SERVICE SADDLES Mueller service saddles, available in bronze,
STANDARDS AND CONSTRUCTION MANUAL : Reclaimed water Pipes, Valves, and Appurtenances February 11, 2011 PART 1 - GENERAL 1.01 SCOPE OF WORK A. These specifications cover the pipes, fittings, and appurtenances
Model Specification 509 DRISCOPLEX 4200 and DRISCOPLEX 4300 Gravity Flow Sanitary Sewer The user may choose to adopt part or all of this Model Specification; however, the user should ensure that all parts
Section Four: Linings and Coatings SPIRALWELD PIPE The majority of steel water pipe furnished today is specified to be provided with both an interior lining and an exterior coating. AMERICAN offers a wide
60.1 D-O-L FxE expansion couplings are a bolted, split-sleeve design that provides for expansion and contraction at the coupled joint. These couplings are furnished with restraint rings that, when affixed
STANDARD SPECIFICATIONS FOR PRIVATE BUILDING SEWER LINES IN PUBLIC RIGHT-OF-WAY Approved and adopted as Official Document Number 800576 this 10th day of December, 1980 Donald R. Boyd, P.E., Director Water
PART 1 - GENERAL 1.1 DESCRIPTION A. The WORK under this Section includes providing all labor, materials, tools and equipment necessary for furnishing and installing sanitary sewer pipe, in accordance with
SECTION INCLUDES Domestic Water Fire Water Service Water Well Sanitary Sewer Storm Drains Foundation Drainage RELATED SECTIONS 03 30 00 Concrete 21 00 00 Fire Suppression - Sprinklers 22 00 00 Plumbing
CERAMIC EPOXY LINED DUCTILE IRON PIPE AND FITTINGS FOR FORCE MAINS, GRAVITY AND INDUSTRIAL SEWER LINES P 2 Table of Contents PROTECTO 401 3 Suggested Specification For PROTECTO 401 5 Procedures for Sealing
PIPING SYSTEM - ABRASIVE SLURRIES Engineering Standard Specification Number: 3503-11.2.610 Rev. 2 Rubber Lined Steel Pipe and Fittings Mechanically Coupled Plain End Type System Issued Revised Approved
Section C-1 Pipes and Fittings C1.00 Work Included The work under this Division of the Specifications shall include all labor, materials, and equipment necessary to furnish and install all piping, pipelines,
DIVISION 2 - SEWERAGE AND DRAINAGE SECTION 02720 - STORM DRAIN SYSTEMS PART 1 - GENERAL 1.01 DESCRIPTION A. Furnish and install all storm drains, including manholes, inlets, service lines and other appurtenant
EXHIBIT "A Technical Specifications for Water and Sewer Service Lines Water and Sewer Line Bedding and Backfill: Drawings show cross-section of trench, pipe laid on top of 6" min. bedding material, bedding
6.01 SCOPE The work covered by this section of the specifications consists of the furnishing of all plant, labor, materials, equipment and supervision and performing all operations involved in the construction
San Antonio Water System Standard Specifications for Construction ITEM NO. 854 SANITARY SEWER LATERALS 854.1 DESCRIPTION: This item shall govern sanitary sewer laterals installed in accordance with these
SUBDRAINS AND FOOTING DRAIN COLLECTORS PART 1 - GENERAL 1.01 SECTION INCLUDES A. Subdrains B. Subdrain Cleanouts and Outlets C. Footing Drain Collectors D. Storm Sewer Service and Connections 1.02 DESCRIPTION
Section 3 AMERICAN Ductile Iron Pipe AMERICAN Ductile Iron Pipe Centrifugally Cast in Metal Molds or Sand-Lined Molds For Water or Other Liquids. What is AMERICAN Ductile Iron? The ideal of cast iron with
SECTION 02110 - ASBESTOS CEMENT PIPE REPAIRS, DEMOLITION, AND DISPOSAL PART 1 - GENERAL 1.1 WORK INCLUDED IN THIS SECTION A. The WORK of this Section includes the repair, demolition, and disposal of asbestos
APPLICATIONS Process Industry Weak Acids Alkalies Compressed Air Pulp & Paper MODELS ASM - Flanged Connection OPTIONS Control Rods Oil & Gas Water & Waste Pump suction & discharge Sea water Chemical lines
WATER & SEWER CORROSIVE RESISTANT PRODUCTS The Standard of Excellence in the Industry CASING SPACERS COUPLINGS & FLANGE COUPLING ADAPTERS REPAIR CLAMPS DUCTILE IRON SADDLES STAINLESS STEEL SADDLES TAPPING
ARTICLE II - REQUIRED USE OF PUBLIC SEWERS. PARAGRAPH 020001 Purpose and Application. Article II provides rules governing the allowable connection to the City POTW and the construction and inspection of
DUCTILE IRON PIPE FOR WASTEWATER APPLICATIONS DUCTILE IRON PIPE FOR WASTEWATER APPLICATIONS The 1972 AMENDMENTS to Public Law 92-500 (the Clean Water Act) established the federal government s largest domestic
SANITARY SEWER SPECIFICATIONS OCTOBER 2003 HARVEST-MONROVIA WATER, SEWER, AND FIRE PROTECTION AUTHORITY SECTION 1.00 1.10 Purpose The purpose of this document is to assemble the sewer specifications, policies,
PVC Installation and Tapping For Potable Water and Sanitary Sewer Handling and Installation Practices Manual Table of Contents Introduction...1 Shipping and Handling...1 Handling and storage of pipe and
CITY AND COUNTY OF DENVER ENGINEERING DIVISION Wastewater Capital Projects Management Standard Construction Specification 10.1 Precast Concrete Pipe 10.1.1 General This section covers material requirements,
Section 33 0200- Page 1 of 4 PART 1 - GENERAL 1.1 DESCRIPTION OF WORK The work of this Section includes furnishing and installing Reinforced Concrete Pressure Pipe as shown on the Drawings and as specified.
Page 1 of 6 Section 1. PURPOSE This policy is an Engineering checklist of the Local Review Program for sanitary sewer improvement projects by the Bedford Regional Water Authority ( Authority ). Section
SECTION 33 41 13 PUBLIC STORM PART 1 - GENERAL 1.01 SECTION INCLUDES A. Storm drainage piping, fittings, and accessories at proposed station areas and locations other than under and immediately adjacent
STANDARD SPECIFICATIONS SECTION 02512 CLEANING AND LINING WATER MAINS PART 1 GENERAL 1.1 DESCRIPTION A. Section includes requirements for cleaning and lining existing cast iron and ductile iron water mains
22.214.171.124 53-03-15 Referring to Section 126.96.36.199, can a surface BOP stack arrangement with one annular, one blind shear ram, and two pipe rams, with the fifth device being optional, be considered a Class
515 General Guidelines for Repairing Buried PE Potable Water Pressure Pipes Introduction Traditional piping systems have gasket-sealed bell and spigot joints every 20 feet, which can be a potential maintenance
SECTION 9 AMERICAN Restrained Joint Pipe AMERICAN Restrained Joint Pipe The principal standards relating to applicable features of AMERICAN Restrained Joint Pipe and Fittings are ANSI/AWWA C151/A21.51,
SECTION 27 05 36 CABLE TRAYS FOR COMMUNICATIONS SYSTEMS PART 1 GENERAL 1.01 DESCRIPTION A. The work covered by this section of the Specifications includes all labor necessary to perform and complete such
State of Illinois Department Of Transportation CONSTRUCTION INSPECTOR S CHECKLIST FOR STORM SEWERS While its use is not required, this checklist has been prepared to provide the field inspector a summary
James M. Pleasants Company SUBMITTAL DATA GAINESVILLE MECHANICAL DECEMBER 20, 2013 PROJECT: GSU: J-183 HUMANITIES LAW BLDG. QUOTE NO:12116 ENGINEER: STEVENS & WILKINSON GASKETED PLATE HEAT EXCHANGER Tag:
SECTION 02845 GUARDRAILS PART 1 - GENERAL 1.01 SCOPE OF WORK A. Furnish all labor, materials, equipment and incidentals necessary and repair, replace or install all types of guardrails as specified herein
GAS DISTRIBUTION PRODUCTS STEEL SERVICE TEES CONTINENTAL INDUSTRIES ABOUT US THE ULTIMATE CONNECTION Our Company Continental Industries, headquartered in Tulsa, Oklahoma, was formed in 1958 and is today
SECTION LS 2530 SANITARY SEWERS PART 1 GENERAL 1.1 SUBMITTALS A. General: Submit the following in accordance with The General Conditions. 1. Product data for drainage piping specialties. 2. Shop drawings
VERTICAL TURBINE AND PROPELLER PUMPS INTRODUCTION Vertical Turbine and Propeller Pumps Model 7000 Series Turbine Pump Model 800 Series Axial Flow Propeller Pump Model 800 Series Mixed Flow Propeller Pump
STANDARD SPECIFICATIONS SECTION 15076 CEMENT-MORTAR LINED AND COATED STEEL PIPE PART 1 - GENERAL A. Description This section describes materials, fabrication, installation, and testing of cement-mortar
PART 1 - GENERAL Section 02702 SEWER PIPE INSTALLATION AND TESTING 1-1. SCOPE. This section covers the installation and testing of all sewer pipe furnished under the following specification sections: Concrete
Hydraulic Jack Units Elevator Equipment Corporation (EECO) has been manufacturing hydraulic elevator equipment since 1946, and is one of the leading suppliers in the industry for hydraulic jack units and
1.0 GENERAL 1.1 DESCRIPTION This section addresses the procedures to be employed for pipe bursting existing water/sewer pipelines, as identified on the drawings, and replacing with new Restrained Joint
SECTION 5: SANITARY SEWER SYSTEM DESIGN 5.01 GENERAL Sanitary sewer improvements shall be designed to serve the ultimate level of City development as defined in the General Plan and the Wastewater Facilities
SECTION 5200 - STORM SEWER PART 1 - GENERAL 1.01 SCOPE: This Section covers installation of storm sewer mains and culverts. Topics include permits and fees, trench widths, pipe laying, bedding, initial
CHAPTER 11 STORM DRAINAGE SECTION 11 GENERAL 11.1 Scope. The provisions of this chapter shall govern the materials, design, construction and installation of storm drainage. 11.2 Where required. All roofs,
SECTION 02612 PART 1 GENERAL 1.1 SUMMARY A. Section Includes: Furnishing and installing nonreinforced concrete sewer pipe. Provide concrete sewer pipe less than 12 inches in diameter, and in other sizes
Engineering Bulletin Rental Services Temporary Cooling - Flexible Water Hose September 2006 CHS-PRB007-EN Warnings and Cautions Warnings and Cautions. Notice that warnings and cautions appear at appropriate
Strength and Durability for Life APPLIATIONS Ductile Iron Pipe for Wastewater Applications Last Revised: May The 72 AMENDMENTS to Public Law 2-500 (the lean Water Act) established the federal government
Section 16122 PRIMARY POWER CABLES PART 1 GENERAL: WORK INCLUDED The Contractor shall furnish and install all shielded power cable suitable for use on this project. RELATED WORK Section 16020: Tests SUBMITTALS
SEE VICTAULIC PUBLICATION 10.01 FOR DETAILS Victaulic Tri-Service valve is an assembly (shipped as individual components) of a standard Victaulic butterfly or Vic-Plug valve and a check valve. This combination
QUALITY INSIDE When it comes to long life piping for drinking water, sewage, industrial water or gas, there is one name that continues to lead the way - ECOPUR by vonroll. Delivering precision-engineered
ITY OF PRLN UGRING PIP OR SING FOR SWRS Section 02415 UGRING PIP OR SING FOR SWRS 1.0 G N R L 1.01 STION INLUS Installation of pipe and casing for sanitary sewer by methods of augering. References to Technical
SECTION 02600 - PART 1 -- GENERAL 1.1 WORK OF THIS SECTION A. The WORK of this Section includes providing general requirements for pipelines, including pipejoints, specials, and appurtenances, complete
8.01 STORM SEWERS, CATCH BASIN LEADS, AND EXTENSIONS 8.01.01 Description This work shall consist of installing lines of storm sewer pipe of the required inside diameter, and the necessary appurtenances,
Beacon Hill Sewer District Standard Specifications Residential Gravity Side Sewer Including Design Criteria and Standard Construction Drawings Residential Gravity Side Sewer Design Criteria 1. Provisions
FORM A PTS HELICAL PIERS INSTALLATION SPECIFICATIONS NOTICE The following suggested specifications are written as a guide to assist the specifier in writing his own specifications. Specific circumstances
CITY OF JOHNSTOWN DEPARTMENT OF COMMUNITY & ECONOMIC DEVELOPMENT 401 MAIN STREET ROOM 200 JOHNSTOWN, PA 15901 814-533-2017 FAX 814-539-5816 RENEE K. DALY DIRECTOR Sewage Compliance Form Instructions 1)
LS 2540 SEWER LATERALS AND INSPECTION TEES A. Summary B. Submittals C. Site Information D. Sewer Pipe and Fittings E. Lateral Locations F. Lateral Installation G. Inspection Tee Installation H. Removal
June 2014, Draft 01 22 1316 Sanitary and Waste Vent Piping PART 1. GENERAL 1.01 Summary A. This Section includes the following for soil, waste, and vent piping inside the building: 1. Pipe, tube, and fittings.
PART 1 GENERAL 1.1 SCOPE A. This item shall include the work necessary for the installation of storm sewer line construction. B. Reference Section 3800 Trenching and Backfill and the General Conditions,
SimplexGrinnell TXMAS ecommerce Ferguson Fire and Fabrication Sprinkler Price List Based on SG GSA Fire & Security Products Contract GS-07F-0396M, Mod PO-0099 January 30, 2013 Product ID Description TXMAS
1.0 GENERAL 1.1 DESCRIPTION: This specification shall cover the rehabilitation of existing water lines using the GRUNDOCRACK PIPE BURSTING SYSTEM. Pipe bursting is a system by which the pneumatic bursting
Construction and operation 8.03.00 Instructions for installation 8.03.00 Types of stress 8.04.00 Diagrams for static deformation of the coupling ring 8.05.00 Coupling size 8.07.00 Examples of combinations
ALIGNMENT Pump and Driver Alignment Alignment Subject: Pump and Driver Alignment In the pump business alignment means that the centerline of the pump is aligned with the centerline of the driver. Although
Fabricated Drainage Products Complete Drainage System Inline Drains are used At the beginning of a drain line Add a new water inlet to an existing drain line using a riser pipe and tee HARCO Surface Drainage
A Discussion of Steel Pipe versus Ductile Iron Pipe The comparison of spiral-welded steel pipe to ductile iron pipe below highlights how steel is not only equal to ductile iron as a material for use in
HDPE Pipe Joining System The System The fast, easy, and economical way to mechanically join HDPE pipe. Fast, easy bolted connection Faster installation Easy to remove and rotate pipe for increased pipe