1 Right choice for ultimate yield LSIS strives to maximize customers' profit in gratitude of choosing us for your partner. Programmable Logic Controller Temperature Controller XGT Series User s Manual XGF-TC4RT Read this manual carefully before installing, wiring, operating, servicing or inspecting this equipment. Keep this manual within easy reach for quick reference.
2 Safety Instruction Before using the product For your safety and effective operation, please read the safety instructions thoroughly before using the product. Safety Instructions should always be observed in order to prevent accident or risk with the safe and proper use the product. Instructions are divided into Warning and Caution, and the meaning of the terms is as follows. Warning This symbol indicates the possibility of serious injury or death if some applicable instruction is violated Caution This symbol indicates the possibility of severe or slight injury, and property damages if some applicable instruction is violated Moreover, even classified events under its caution category may develop into serious accidents relying on situations. Therefore we strongly advise users to observe all precautions properly just like warnings. The marks displayed on the product and in the user s manual have the following meanings. Be careful! Danger may be expected. Be careful! Electric shock may occur. The user s manual even after read shall be kept available and accessible to any user of the product.
3 Safety Instruction Safety Instructions for design process Warning Please install a protection circuit on the exterior of PLC so that the whole system may operate safely regardless of failures from external power or PLC. Any abnormal output or operation from PLC may cause serious problems to safety in whole system. - Install protection units on the exterior of PLC like an interlock circuit that deals with opposite operations such as emergency stop, protection circuit, and forward/reverse rotation or install an interlock circuit that deals with high/low limit under its position controls. - If any system error (watch-dog timer error, module installation error, etc.) is detected during CPU operation in PLC, all output signals are designed to be turned off and stopped for safety. However, there are cases when output signals remain active due to device failures in Relay and TR which can t be detected. Thus, you are recommended to install an addition circuit to monitor the output status for those critical outputs which may cause significant problems. Never overload more than rated current of output module nor allow to have a short circuit. Over current for a long period time maycause a fire. Never let the external power of the output circuit to be on earlier than PLC power, which may cause accidents from abnormal output oroperation. Please install interlock circuits in the sequence program for safe operations in the system when exchange data with PLC or modify operation modes using a computer or other external equipments Read specific instructions thoroughly when conducting control operations with PLC.
4 Safety Instruction Safety Instructions for design process Caution I/O signal or communication line shall be wired at least 100mm away from a high-voltage cable or power line. Fail to follow this Safety Instructions on installation process Caution Use PLC only in the environment specified in PLC manual or general standard of data sheet. If not, electric shock, fire, abnormal operation of the product may be caused. Before install or remove the module, be sure PLC power is off. If not, electric shock or damage on the product may be caused. Be sure that every module is securely attached after adding a module or an extension connector. If the product is installed loosely or incorrectly, abnormal operation, error or dropping may be caused. In addition, contact failures under poor cable installation will be causing malfunctions as well. Be sure that screws get tighten securely under vibrating environments. Fail to do so will put the product under direct vibrations which will cause electric shock, fire and abnormal operation. Do not come in contact with conducting parts in each module, which may cause electric shock, malfunctions or abnormal operation.
5 Safety Instruction Safety Instructions for wiring process Warning Prior to wiring works, make sure that every power is turned off. If not, electric shock or damage on the product may be caused. After wiring process is done, make sure that terminal covers are installed properly before its use. Fail to install the cover may cause electric shocks. Caution Check rated voltages and terminal arrangements in each product prior to its wiring process. Applying incorrect voltages other than rated voltages and misarrangement among terminals may cause fire or malfunctions. Secure terminal screws tightly applying with specified torque. If the screws get loose, short circuit, fire or abnormal operation may be caused. Securing screws too tightly will cause damages to the module or malfunctions, short circuit, and dropping. Be sure to earth to the ground using Class 3 wires for FG terminals which is exclusively used for PLC. If the terminals not grounded correctly, abnormal operation or electric shock may be caused. Don t let any foreign materials such as wiring waste inside the module while wiring, which may cause fire, damage on the product or abnormal operation. Make sure that pressed terminals get tighten following the specified torque. External connector type shall be pressed or soldered using proper equipments.
6 Safety Instructions for test-operation and maintenance Warning Safety Instruction Don t touch the terminal when powered. Electric shock or abnormal operation may occur. Prior to cleaning or tightening the terminal screws, let all the external power off including PLC power. If not, electric shock or abnormal operation may occur. Don t let the battery recharged, disassembled, heated, short or soldered. Heat, explosion or ignition may cause injuries or fire. Caution Do not make modifications or disassemble each module. Fire, electric shock or abnormal operation may occur. Prior to installing or disassembling the module, let all the external power off including PLC power. If not, electric shock or abnormal operation may occur. Keep any wireless equipment such as walkie-talkie or cell phones at least 30cm away from PLC. If not, abnormal operation may be caused. When making a modification on programs or using run to modify functions under PLC operations, read and comprehend all contents in the manual fully. Mismanagement will cause damages to products and accidents. Avoid any physical impact to the battery and prevent it from dropping as well. Damages to battery may cause leakage from its fluid. When battery was dropped or exposed under strong impact, never reuse the battery again. Moreover skilled workers are needed when exchanging batteries.
7 Safety Instruction Safety Instructions for waste disposal Caution Product or battery waste shall be processed as industrial waste. The waste may discharge toxic materials or explode itself.
8 Revision History Revision History Version Date Contents Chapter V First edition - The number of User s manual is indicated right part of the back cover. c 2009 LS Industrial Systems Co., Ltd All Rights Reserved. 1
9 About User s Manual Thank you for purchasing PLC of LS Industrial System Co.,Ltd. Before use, make sure to carefully read and understand the User s Manual about the functions, performances, installation and programming of the product you purchased in order for correct use and importantly, let the end user and maintenance administrator to be provided with the User s Manual. The User s Manual describes the product. If necessary, you may refer to the following description and order accordingly. In addition, you may connect our website (http://eng.lsis.biz/) and download the information as a PDF file. Relevant User s Manuals Title XG5000 User s Manual (for XGK, XGB) XG5000 User s Manual (for XGI, XGR) XGK/XGB Instructions & Programming User s Manual XGI/XGR/XEC Instructions & Programming User s Manual XGK CPU User s Manual (XGK-CPUA/CPUE/CPUH/CPUS/CPUU) XGI CPU User s Manual (XGI-CPUU/CPUH/CPUS) XGR redundant series User s Manual Description XG5000 software user manual describing online function such as programming, print, monitoring, debugging by using XGK, XGB CPU XG5000 software user manual describing online function such as programming, print, monitoring, debugging by using XGI, XGR CPU User s manual for programming to explain how to use instructions that are used PLC system with XGK, XGB CPU. User s manual for programming to explain how to use instructions that are used PLC system with XGI, XGR,XEC CPU. XGK-CPUA/CPUE/CPUH/CPUS/CPUU user manual describing about XGK CPU module, power module, base, IO module, specification of extension cable and system configuration, EMC standard XGI-CPUU/CPUH/CPUS user manual describing about XGI CPU module, power module, base, IO module, specification of extension cable and system configuration, EMC standard XGR- CPUH/F, CPUH/T user manual describing about XGR CPU module, power module, extension drive, base, IO module, specification of extension cable and system configuration, EMC standard Current XGF-TC4UD manual is written based on the following version. Related OS version list Product name OS version XGK-CPUH, CPUS, CPUA, CPUE, CPUU V3.3 XGI-CPUU, CPUH, CPUS V3.1 XGR-CPUH/F, CPUH/T V1.6 XG5000(XG-PD) V3.5 1
10 Contents Chapter 1 Introduction 1-1 ~ Features Terms Chapter 2 Specifications 2-1 ~ General Specifications Performance Specifications Names and Functions of Major Components Characteristics of Input and Output Conversion Characteristics of Input Conversion Precision by Input Type Characteristics of output part conversion Main Functions Chapter 3 Installation and Wiring 3-1 ~ Installation Conditions for Installation Cautions in Handling the Module Wiring Wring of the Input Part Wiring of the Output Part Chapter 4 Configuration and Functions of Internal Memory (XGK) 4-1 ~ U Device Area U Device Area Parameter Setting Area (using PUT/GET command) Parameter Setting Area How to Use PUT/GET Command Chapter 5 Configuration and Functions of Internal Memory (XGI/XGR) 5-1 ~ Global Variables (Data Area) Global Variables (Data Area) How to Use Global Variables PUT/GET Function Block Area (Parameter Area) PUT/GET Function Block Area (Parameter Area) PUT/GET function block Example of Use of PUT/GET function block Chapter 6 Function ~ Input Parameter Type of input Input processing Control Parameter Configuration of the control target Address the control target Control type
11 6.2.4 Control processing technique Auto tuning Output Parameter Output settings Heating output Cooling output Other Functions Alarm function Output alarm Chapter 7 Software Package (XG-TCON) 7-1 ~ Introduction Features of XG-TCON Functions of XG-TCON Files Created with XG-TCON Main Screen Title Menu Tool Bar Project Window Main Screen Command Window Message Window Status Bar Screen Components New Project Dialog Open Project Save As Add Module Compare Projects Print Preview Window Print Project Parameter Register Information Connection Setting Customize Option Dialog Graph Setting Trend Setting Logging Data Setting Error Code Chapter 8 Programming (for XGK) 8-1 ~ Pre-operation Setting-up Procedure Sample Program Auto Tuning Temperature Control Program Sample Program using PUT/GET Command Chapter 9 Programming (for XGI/XGR) 9-1 ~ Pre-operation Setting-up Procedure Sample Program Auto Tuning Temperature Control Program...9-3
12 9.2.3 Sample Program Chapter 10 Diagnosis 10-1 ~ Error Code Diagnosis RUN LED is OFF ALM LED is ON ERR LED is ON ERR LED flashes at 1 second intervals A/D Converted value is not changed The digital output is not in relation with the analog input value Out of Control Checking Temperature Controller Module Status with Software Package Appendix Appendix 1
13 Chap. 1 Introduction Chapter 1 Introduction This User Manual describes the specifications, handling and programming method of the XGF-TC4RT RTD input type Temperature Controller Module (hereinafter, Temperature controller module ) which is used in combination with the CPU modules of XGT PLC series. The Temperature controller module converts the analog signals (temperature) from the external devices of PLC to i6 bit binary digital signals with signs. The module also provides transistor output for temperature control through PID operation. 1.1 Features (1) Optimized temperature control function Temperature control function can be implemented using the built-in input/output function by setting up the PID parameters only. (2) 3 types of RTD input PT100, JPT100, PT1000 (3) Isolation between input loops High reliability signal process can be accomplished without interference between loops. (4) Transistor outputs Transistor output available for control output. (5) Operation parameter setting/monitoring using exclusive software package Easy to use by using exclusive software package supporting enhanced user interface, which replaced previous method setting operation parameter by instruction. If you use exclusive software package, you can reduce the sequence program. And you can monitor temperature controller module easily by using [Data monitor] and [Trend monitor]. (6) Diverse control type 2 types of control type are supported and each type is as follows. PID control: general control method using Proportional, Integral, Derivative item. On/Off control: control method turning on/off MV based on SV (7) Function detecting disconnection When using temperature input range, you can detect disconnection of circuit. (8) Diverse input operation functions Supports bias, averaging function (9) Auto-tuning function Calculation of PID coefficient by auto-tuning is available. 1-1
14 Chap. 1 Introduction 1.2 Terms PID control (Proportional Integral Derivative Control) This is one of the feed-back controls keeping output in reference voltage and combination of Proportional control, Proportional-Integral control and Proportional-Derivative control. P control multiplies deviation between reference signal and current signal by P coefficient and makes the control signal. I control executes integral for deviation and adds the result to P control in parallel. D control executes derivative for deviation and adds the results to P control in parallel. It is used to measure reaction of automation system or control reaction. And it is usually used to control temperature, pressure, flow, speed of rotation and can improve the problem of PI or PD control such as transient Proportional Control As one of the control methods, the bigger gap between target value and current value, the bigger manipulated value to return to target value. It is smoother than On/Off control On/Off Control As one of the control methods, it reiterates turning manipulated value on/off and is called Bang Bang control. It has hysteresis characteristic so error within hysteresis range occurs Integral Action Makes the manipulated value proportional to integral value of action signal and called I action. If you use this action, you can eliminate the remaining deviation Derivative Action Makes the manipulated value proportional to derivative value of action signal and called D action. When action signal is getting bigger, it is used to modify action signal properly and make the control stable Cascade Control A series of control steps are connected continuously so one control unit is controlled by other front control unit and controls other back control unit Feedback Control It compares current value with target value and makes the current be target value by using output signal as input signal. Control that removes external disturbance is called constant value control and control whose target value changes rapidly is called variable value control. Both controls make the deviation 0. Process control, automatic control, servo device are classified as Feedback control XG-TCON Exclusive software tool to set and monitor input/control/output parameter of temperature controller 1-2
15 Chap. 2 Specifications Chapter 2 Specifications 2.1 General Specifications Table 2.1 shows the general specifications of the XGT series. [Table 2.1] General specifications No. Items Specifications Related standards 1 2 Operating temperature Storage temperature 0 ~ 55 C 25 ~ +70 C 3 Operating humidity 5 ~ 95%RH (Non-condensing) 4 Storage humidity 5 ~ 95%RH (Non-condensing) Occasional vibration - Frequency Acceleration Amplitude How many times 10 f < 57Hz 0.075mm 5 6 Vibration resistance Shock resistance 7 Noise resistance 57 f 150Hz 9.8m/s 2 (1G) Continuous vibration Frequency Acceleration Amplitude 10 f < 57Hz 0.035mm 57 f 150Hz 4.9m/s 2 (0.5G) Peak acceleration: 147 m/s 2 (15G) Duration: 11ms Half-sine, 3 times each direction per each axis Square wave Impulse noise Electrostatic discharge Radiated electromagnetic field noise Fast transient/bust noise 10 times each directions (X, Y and Z) IEC IEC ±1,500 V LSIS standard 4kV 80 ~ 1,000 MHz, 10V/m Segme Power supply Digital/analog input/output nt module communication interface Voltage 2kV 1kV 8 Environment Free from corrosive gasses and excessive dust 9 Altitude Up to 2,000 ms 10 Pollution degree Less than equal to 2 11 Cooling Air-cooling IEC IEC IEC , IEC IEC IEC Note 1) IEC (International Electrotechnical Commission): An international nongovernmental organization which promotes internationally cooperated standardization in electric/electronic field, publishes international standards and manages applicable estimation system related with. 2) Pollution degree: An index indicating pollution degree of the operating environment which decides insulation performance of the devices. For instance, Pollution degree 2 indicates the state generally that only non-conductive pollution occurs. However, this state contains temporary conduction due to dew produced. 2-1
16 Chap. 2 Specifications 2.2 Performance Specifications Table 2.2 shows the performance specifications of the thermo-controller module. RTD type and input range Precision Control parameter Transistor output Insulation Access terminal IO occupation point Power supply Current consumed Items Control loop Specifications 4 loop Pt ~ 850 JPt ~ 600 Pt ~ 800 Standard precision Temperature coefficient ±0.2% or less (25, normal temperature) ±60ppm/ (0.006%/ ) Resolution 0.1 Sampling period Control method Target value(sv) Proportional gain 400ms/ 4 loop PID CONTROL, ON/OFF CONTROL Setting within range according to input type (temperature unit setting) 0: ON/OFF CONTROL, REAL Integral time 0: Except integral control, REAL Derivative time 0: Except derivative control, REAL Output point 4 Rated load voltage DC 24 V Load voltage range 21.6V~26.4V Max. load current 0.1 A / Output point Max. voltage drop when on DC 0.3 V or less Leakage current when off 0.1 ma or less Response time On => Off 1 ms or less Off => On 1 ms or less Control output cycle 0.5 ~ sec (Setting unit: 0.1 sec.) Time proportional resolution Larger one of either 10 ms or 0.05% of the full-scale Between input channels Insulation method: transformer, photo-coupler Input terminal PLC power Withstanding voltage: 1500V AC, 50/60Hz 1min, leakage current 10mA or less Output terminal- PLC power Insulation resistor: 500V DC, 10 MΩ or above Between output channels 18 point terminal Non-insulation Fixed: 64 points, movable: 16 points 5 V, DC 24 V DC 5 V : 310 ma, DC 24 V : 28 ma [Table 2.2] Performance specifications Note 1) When you use the XGR system - XGR system can be used in an extension base but not in a basic base. 2-2
17 Chap. 2 Specifications 2.3 Names and Functions of Major Components No. Name Description 1 RUN LED Indicates H/W operating status On: normal operation Off: H/W error (request a custom service) Flicker: error have been occurred 2 ALM LED Alarm status Off: normal input status flicker: alarm have been occurred 3 Input part Connect RTD sensor 4 Terminal block Output part Terminal block for connecting a external device 5 External 24V power supply part Connect a 24V power supply device 2-3
18 Chap. 2 Specifications 2.4 Characteristics of Input and Output Conversion Characteristics of Input Conversion RTD input characteristics It directly connects 3 types of RTD sensors and the input characteristics are as follows. RTD type Applying Temperature range standard Resistance range Pt100 JIS C ~ ~ ~ JPt100 JIS C ~ ~ ~ Pt1000 DIN ~ ~ ~ Precision by Input Type The precision by input type is as follows. RTD type Display range [ ] Room temperature (25 ) Precision 55 (±100 ppm/ ) Resolution Pt ~ 850 ±2.1 ± JPt ~ 600 ±1.6 ± Pt ~ 850 ±2.1 ± Precision in case of 55 <How to calculate> Precision at room temperature + (55-25 ) 60ppm whole temperature range (e.g.) Pt100 type 55 Precision ±[2.1 + (55-25 ) 60ppm 1050] = ±3.99 = about ±
19 Chap. 2 Specifications Characteristics of output part conversion Transistor output characteristics Transistor output characteristics are as follows. Item Specifications Output point 4 Transistor output Rated load voltage Max. load current Max. voltage drop when on Leakage current when off DC 24 V 0.1 A / output point DC 0.3 V or less 0.1 ma or less Response time On -> Off Off -> On 1 ms or less 1 ms or less Control output cycle Time proportional resolution 0.5 ~ sec Larger one of 10 ms or 0.05% of full-scale 2-5
20 Chap. 2 Specifications 2.5 Main Functions Items Functions Description Choose input type The sensor type can be chosen. Input type Handles disconnect The set input value applies in case of input disconnect. Upper limit of effective input The user defines the effective upper range of the input Lower limit of effective input The user defines the effective lower of the input Functions of input part Functions of control part Input bias Bias applies to the input. Input Average type Select weighted averaging or moving averaging processing Average value Set averaging value or moving averaging value The further upper limit, upper limit, lower limit and further lower limit are Input alarm Input alarm defined for alarm. Alarm HVS Set hysteresis for 4 types of input alarm Auto-tuning Auto-tuning SV Ordinary SV and Auto-tuning SV are dualized. Auto-tuning Hysteresis Auto-tuning considering the sensor vibration. Target SV upper/lower limit Caps the SV upper and lower limits. setting PV tracking Set to go along PV to prevent sudden change of SV Control type Select one from PID or ON/OFF control ON/OFF control HYS Set hysteresis used for ON/OFF control Forward/reverse action Forward/reverse action can be converted Dead band Set SV upper/lower dead band area Control setting Anti-windup No impulse manual escape Choose proportional source Choose differential source Removes overshoot by preventing over-integration occurring from start, disturbance and rapid change in SV When manual operation converts auto operation, it relieve the impulse and protect the driver Choose the source to perform the proportional operation between PV/EV. Choose the source to perform differential operation between PV/EV. Functions of output part Control factor Basic setting Output setting Heating/ Cooling Setting Output alarm Set control factor Control BIAS Heating/cooling PWM output Output upper/lower limit Output change limit Output reference Failure output Output alarm Alarm HYS Control factors can be changed as a whole set. Bias to MV after control Heating/cooling/heating and cooling can be set. PWM output is supported and the cycle can be set. The output value can be capped as the upper and lower limit. Limited when the output gets out of a certain range. Bias after setting the reference value to the output. Output can be set in case of failure. When output reaches the designated upper/lower limit, it creates alarm Sets hysteresis for output alarm 2-6
21 Chap. 3 Installation and Wiring Chapter 3 Installation and Wiring 3.1 Installation Conditions for Installation Although this module has high reliability regardless of the surrounding conditions, pay attention to the following conditions to secure the reliability and stability of the system. (1) Environment - Install on a water-proof and vibration-proof control panel. - Where there is no persistent shock or vibration - Where there is no direct sun - Where there is no condensation due to sudden change in the temperature - Where the temperature is kept at 0-55 (2) Installation work - Be careful so that foreign substances do not enter the PLC when you drill screw holes or do the wiring work. - Put the module where you can easily manipulate. - Do not install the module in the same panel as a high voltage device. - Place the module at lest 50mm away from a duct and other nearby modules. - Connect the module to earth where there is not much noise Cautions in Handling the Module The following is what you need to pay attention to from when you open the module to when you install it. (1) Do not drop it or give a strong shock. (2) Do not detach the PCB from the case, which might cause a failure. (3) Be careful so that foreign substances do not enter the PLC when you drill screw holes or do the wiring work. If there is any inside, remove them. (4) Do not mount or dismount the module while the power is on. (5) Install the module more than 100mm away when you place the module in front of the PLC to avoid the radiating noise or heat (inside the door). Any device should be placed more than 50mm away from either side of the base. Over 100mm Base Over 100mm Other device Base High voltage Over 50mm Heat emitter 3-1
22 Chap. 3 Installation and Wiring 3.2 Wiring Wiring of the Input Part (1) Input part 2-wire type wiring Terminal block 3, 5 short 4, 6 short 9, 11 short 10, 12 short *1 In case sensor and compensating wire is shielded, shield connection to PLC FG is available. 3-2
23 Chap. 3 Installation and Wiring (2) Input part 3-wire type wiring Terminal block *1 In case sensor and compensating wire is shielded, shield connection to PLC FG is available. (2) Input part 4-wire type wiring Terminal block *1 In case sensor and compensating wire is shielded, shield connection to PLC FG is available. 3-3
24 Chap. 3 Installation and Wiring Wiring of the Output Part (1) Output part wiring It is recommended you use the noise filter for the module when you use an external power supply. 3-4
25 Chapter 4 Configuration and Functions of Internal Memory (XGK) 4.1 U Device Area U Device Area Table 4.1 shows the U device area of the temperature-controller. Device Word Bit Symbol Description U00.00 U _00_CH0_ACT channel0 operating U _00_CH1_ACT channel1 operating U _00_CH2_ACT channel2 operating U _00_CH3_ACT channel3 operating These are read-only areas and display the operating information of each channel. When the corresponding bit is On, it means the corresponding channel is operating. U _00_CH0_BOUT channel0 disconnect U _00_CH1_BOUT channel1 disconnect U _00_CH2_BOUT channel2 disconnect U _00_CH3_BOUT channel3 disconnect These are read-only areas and display the disconnection of each channel. When the corresponding bit is On, it means the sensor of the corresponding channel is disconnected. U _00_CH0_ADCERR channel0 A/D CONVERSION error U _00_CH1_ADCERR channel1 A/D CONVERSION error U00.00.A _00_CH2_ADCERR channel2 A/D CONVERSION error U00.00.B _00_CH3_ADCERR channel3 A/D CONVERSION error These are read-only areas and display the input part error of each channel. When the corresponding bit is On, it means there is an error at the input part of the channel. U00.00.D _00_CHECKSUMERR module backup memory error These are read-only areas and display the backup memory error of the module. When the corresponding bit is On, it means there is an error during the backup of the module. U00.00.E _00_ERR module error These are read-only areas and display the action error of the module. When the corresponding bit is On, it means there is an error about the action of the module. U00.00.F _00_RDY module Ready These are read-only areas and display the action error of the module. When the corresponding bit is On, the module is on normal standby. U00.01 U _00_WR_ING saving parameter (writing) These are read-only areas and display the backup action of the module. When the corresponding bit is On, the module data is being saved U _00_RD_ING Restoring parameter (reading) These are read-only areas and display the backup action of the module. When the corresponding bit is On, the module data is being restored. [Table 4.1] U device area 4-1
User s Manual LG Programmable Logic Controller GLOFA G3F PIDA G4F PIDA LG Industrial Systems CONTENTS Chapter 1. INTRODUCTION 1.1 Features 1-1 Chapter 2. SPECIFICATIONS 2.1 General specifications 2-1 2.2
User s s Manual LG Programmable Logic Controller GLOFA MASTER-K G3F TC4A G4F TC2A G6F TC2A LG Industrial Systems REVISIONS Date REV. No Description 2001.4. 702004908 G6F-TC2A Module added SAFETY PRECAUTIONS
213/1/2 Series Digital Controller Instruction Sheet Thank you very much for purchasing DELTA DTC Series Temperature Controller. Please read this instruction sheet before using your DTC series to ensure
User s Manual LS Programmable Logic Controller PID Control modules G3F PIDB G4F PIDB CONTENTS Chapter 1. INTRODUCTION 1.1 Features 1-1 Chapter 2. SPECIFICATIONS 2.1 General specifications 2-1 2.2 Performance
F4 Process Controller Installation and Operation Guide SAFETY ALERTS The symbols below are used on the equipment and throughout this document to draw the user s attention to important operational and safety
Ⅰ. Warn Warning of connection Temperature Controller CD401/CD901/CD701/CD501/CD100/CD101 Instruction Manual If the controller fails to operate or error occurs, the system will bring fault for it, please
GETTING STARTED CHAPTER 1 In This Chapter... Manual Overview.........................1 2 SOLO Temperature Controller Introduction......1 3 SOLO Temperature Controller Specifications.....1 5 Manual Overview
User s Manual LG Programmable Logic Controller GLOFA MASTER-K G3F-DA4V G3F-DA4I G4F-DA1A LG Industrial Systems CONTENTS Chapter 1. INTRODUCTION 1.1 Features 1-1 1.1.1 G3F-DA4V G3F-DA4I 1-1 1.1.2 G4F-DA1A
User s Manual LG Programmable Logic Controller GLOFA MASTER-K ANALOG I/O MODULE LG Industrial Systems CONTENTS Chapter 1. INTRODUCTION 1.1 Features 1-1 1.2 Terminology 1-2 1.2.1 Analog Value : A 1-2 1.2.2
Programmable Relays ZEN Series Relay, Timer, Counter, and Time Switch Functions Weekly Timer and Calendar Timer Functions Twin Timer Function (Separate ON/OFF Times) Two Analog Input Channels (DC Models
DVPPF02-H2 PROFIBUS DP Slave Communication Module Application Manual Warning Please read this instruction carefully before use and follow this instruction to operate the device in order to prevent damages
SLATE Analog I/O Module R8001U3001 INSTALLATION INSTRUCTIONS Scan for more information Application SLATE brings configurable safety and programmable logic together into one single platform. The platform
COMMUNICATION INSTRUCTION MANUAL TEMPERATURE CONTROLLER KT4, KT8 and KT9 No.KTC1E6 2009.05 To prevent accidents arising from the misuse of this controller, please ensure the operator receives this manual.
MOUNTING AND OPERATING INSTRUCTIONS CF 51/55 1. Delivery CF 51/55-1 calculator with battery (optionally with mains power supply) - 1 wall mounting bracket - package with material for sealing, screws, wall
MILLENIUM Table of contents 1. INTRODUCTION 1 2. HARDWARE DESCRIPTION 2 3. INSTALLATION 5 4. CONNECTION 6 5. USER SAFETY AND PROTECTION OF EQUIPMENT 8 1. Introduction The MILLENIUM series has been designed
EPSOLAR LS1024B / LS2024B/ LS3024B Solar Charge Controller USER MANUAL Thank you very much for selecting our product! This manual offers important information and suggestions with respect to installation,
How to read this guide The following shows the symbols used in this Quick start guide with descriptions and examples. Symbol Description Example P oint Reference Caution [ ] This symbol explains information
User s Manual LG Programmable Logic Controller GLOFA MASTER-K G3F-AD4A G3F-AD4B G4F-AD2A LG Industrial Systems CONTENTS Chapter 1. INTRODUCTION 1.1 Features 1-1 1.1.1 G3F-AD4A/G3F-AD4B 1-1 1.1.2 G4F-AD2A
Automation System TROVIS 6400 TROVIS 6493 Compact Controller For panel mounting (front frame 48 x 96 mm/1.89 x 3.78 inch) Application Digital controller to automate industrial and process plants for general
Isolated AC Sine Wave Input 3B42 / 3B43 / 3B44 FEATURES AC averaging technique used to rectify, amplify, and filter 50 Hz to 400 Hz sine-wave signals. Accepts inputs of between 20 mv to 550 V rms to give
Product datasheet Characteristics TM7BDM8B expansion block - TM7 - IP67-8 DI/DO - 24V DC - 0.5 A - M8 connector Main Range of product Product or component type Range compatibility Enclosure material Bus
Safety Precautions Observe the following notices to ensure personal safety or to prevent accidents. To ensure that you use this product correctly, read this User s Manual thoroughly before use. Make sure
USER S MANUAL MaxPower 400-600 UPS Uninterruptible Power System 28-2MAXPO0018 IMPORTANT SAFETY INSTRUCTIONS SAVE THESE INSTRUCTIONS This manual contains important instructions for models MaxPower 400 and
Auto-tune PID Temperature Controller FEATURES Easy-to-use Fuzzy modified PID heat & cool control Fast A-D sampling rate (5 times/s) Universal input (PT100, thermocouple) with high accuracy 18-bit A-D Analog
BRAVER UPS (Uninterruptible Power System) User s Manual Safety CAUTION! This UPS utilizes voltages that may be hazardous. Do not attempt to disassemble the unit. The unit contains no user replaceable parts.
User s Manual AURORA 1.2K/2.2K Uninterruptible Power System Safety CAUTION This UPS utilizes voltages that may be hazardous. Do not attempt to disassemble the unit. The unit contains no user serviceable
Type: EASY719 DC RC Article.: 274119 Ordering information Relay outputs Quantity 6 Power supply V DC 24 V DC Description 12 digital inputs (4 inputs available as analog inputs) 6 relay outputs LCD display
COLOR VIDEO DOOR PHONE CDV-71BE/D 513-11, Sangdaewon-dong, Jungwon-gu, Seongnam-si, Gyeonggi-do, Korea Int l Business Dept. : Tel.; +82-31-7393-540~550 Fax.; +82-31-745-2133 Web site : www.commax.com Printed
CLAMP-ON GROUND RESISTANCE TESTER DET10C/DET20C USERS MANUAL EN 61010-2-032 CAT III 300V, CAT II 600V Pollution Degree 2 Definition of Symbols: Caution: Refer to Accompanying Documents Caution: Risk of
User Manual Video Doorphone CDV-1020AQ 513-11, Sangdaewon-dong, Jungwon-gu, Seongnam-si, Gyeonggi-do, Korea Int l Business Dept. Tel. : +82-31-7393-540~550 Fax. : +82-31-745-2133 Web site : www.commax.com
Features 220.127.116.11.0010 18.104.22.168.1010 1 - Phase 230 V Over & Under voltage monitoring relays 22.214.171.124.0010 - Fixed Over & Under voltage detection - Link selectable 5 or 10 minute lock-out delay
38 Series - Relay interface modules 0.1-2 - 3-5 - 6-8 - 16 A 38 SERIES Common features Instant ejection of relay by plastic retaining clip Integral coil indication and protection circuit EMR Electromechanical
aseries A13B Mini Bullet Camera User Manual Thank you for purchasing our product. If there are any questions, or requests, please do not hesitate to contact the dealer. This manual applies to the MicroView
Instruction Manual BEFORE USING THE POWER SUPPLY UNIT Pay attention to all warnings and cautions before using the unit. Incorrect usage could lead to an electrical shock, damage to the unit or a fire hazard.
Application : The RISH CON - Hz transducer is used for frequency measurement. The output signal is proportional to measured frequency and is either load independent DC Current or load independent DC Voltage.
Smart DeviceNet Remote I/O Terminals ather and Use Information for Effective Preventive Maintenance et more useful data for preventive maintenance when you build cost-effective parallel information systems
Samba OPLC SM35-J-R20 Installation Guide The Unitronics SM35-J-R20 offers the following onboard I/Os: 12 Digital Inputs, configurable via wiring to include: 1 HSC/Shaft-encoder Input, 2 Analog inputs (only
Programmable indoor transmitter of temperature T0118 Programmable indoor transmitter of atmospheric pressure T2118 Programmable indoor transmitter of temperature, relative humidity and other derived humidity
Servo Drive Current Loop Tuning Procedure (intended for Analog input PWM output servo drives) The standard tuning values used in ADVANCED Motion Controls drives are conservative and work well in over 90%
68117 XC series BD board for special functions Operate Manual Catalog 一 CONFIGURE METHOD OF BD BOARD...3 二 ANALOG INPUT AND OUTPUT SAMPLING BOARD XC-2AD2DA-BD...4 2 一 Configure method of BD board Configure
XGK series XGK-CPUA XGK-CPUE XGK-CPUH XGK-CPUS Programmable ogic Controller Read this manual carefully before installing, wiring, operating, servicing or inspecting this equipment. Keep this manual within
Programming Logic controllers Programmable Logic Controller (PLC) is a microprocessor based system that uses programmable memory to store instructions and implement functions such as logic, sequencing,
IO-PT4 I/O Expansion Module 4 PT100 Inputs (-50 to 460 C) The IO-PT4 is an I/O Expansion Module that can be used in conjunction with specific Unitronics OPLC controllers. The module offers 4 PT100 inputs
DC/AC CLAMP METER Model CM-01 USERS MANUAL PROVA INSTRUMENTS INC. EN 61010-2-032 CAT II 600V CAT III 300V Pollution Degree 2 SYMBOLS showed on the clamp meter or in this manual: Caution, risk of danger.
CMC-DN01 DeviceNet Slave Communication Card Operation Manual 2011-12-26-A Warning This operation manual provides introduction on the functions, specifications, installation, basic operation and settings
Smart "Compact" range with display CD12 Smart Part number 88974043 Highly visible blue LCD with 4 lines of 18 characters and configurable backlighting Allow the use of the entire library of specific functions
RHINO PSM Series Supplies Our versatile switching power supplies are DIN-rail mountable Features Industrial grade design Sturdy metal case to withstand harsh industrial environments Model PSM4-090S-N meets
Instruction n Manual Copy Adapter "CPAD-C1A" Thank you for purchasing our Copy Adapter CPAD-C1A. This product is designed to copy function codes and their data, which are stored in the FRENIC-Mini series
38 Series - Relay interface modules 0.1-2 - 3-5 - 6-8 - 16 A Common features Instant ejection of relay by plastic retaining clip Integral coil indication and protection circuit EMR Electromechanical Relays
Highlights & Features Protection Class II, Double Isolation (No Earth connection is required) Universal AC input voltage without power de-rating Efficiency > 87.0% @ 115Vac & 230Vac NEC Class 2 / Limited
E031026 000823 Process modules Digital input PMI for inputs for 120 V AC inputs PMI Input E4, E5, GND L- PMI 120 V AC Input E4, E5, Common C E6, E7, GND L- E6, E7, Common C LEDs for the inputs operation
Dual and triple output models with two 30V/1.5A (45W) channels and a 6V/5A (30W) channel on the triple output supply All channels are independently controlled and have isolated outputs for maximum flexibility
1H/G-CPU@@H 1-series Programmable Controllers Indicators Inner Board Compartment An Inner Board can be mounted here. Peripheral Port The peripheral port connects Programming Devices, such as a Programming
YSmart Technology Co.,Ltd GWV Series Grid Tie Microinverter User Manual The copyright of this user manual belong to YSmart TechnologyCompany Limited. Without the written permission of the copyright holder,
HITACHI PROGRAMMABLE CONTROLLER Counter Module EH-CU/CUE APPLICATION MANUAL NJI-321B(X) Revision History No. Description of Revision Data of Manual Number 1 First edition NJI-321(X) 2 Count value record
Fire Alarm Control Panel Family Operating Manual CONTENTS System Description AH-03312 System Characteristics... Fire Signal Receiving Board Description-4L... Fire Signal Receiving Board Description-8L...
Current transducer LF 21-S I PN = 2 A For the electronic measurement of current: DC, AC, pulsed..., with galvanic separation between the primary and the secondary circuit. Features Bipolar and insulated
INSTALLATION MANUAL EKRTR EKRTETS 1 2 1 2 3 60 87 170 161 ±1.5 m >0.2 m 3 5 4 34 125 4 5 28 50 EKRTR EKRTETS Contents Read this manual attentively before starting up the unit. Do not throw it away. Keep
NX-S@ NX safety stand-alone stand-alone into machine automation Expandable safety system up to 32 safety connections or 63 standard connections controller flexible system lets your freely mix safety I/O
AUTOMATIC LPG BOOKING, LEAKAGE DETECTION AND A REAL TIME LPG MEASUREMENT MONITORING SYSTEM R.Padmapriya, E.Kamini, firstname.lastname@example.org,email@example.com, IV Year Electronics and Communication Engineering,
+ - A + B B - V + - NO NC COM + - + - V + - PV PV Ramp Soak 100 70 50 30 3 5 3 8 5 3 Minute Steam Heating Sensor Cooling Water PID Hotplate Specifications Input power supply AC 100 to 240V, 50/60Hz, DC
MasterINTERFACE 39 Series - Relay interface modules Common features Space saving 6.2 mm wide Connections for 16-way jumper link Integral coil indication and protection circuit Secure retention and easy
38 Relay interface modules 0.1-2 - 3-5 - 6-8 - 16 A 38 Common features Instant ejection of relay by plastic retaining clip Integral coil indication and protection circuit 6.2 mm wide EMR - DC, AC or AC/DC
AK-650 series Features : Universal AC input with active PFC Programmable output Voltage ( 0% ~ 05% ) Programmable output Current ( % ~ 05% ) High efficiency up to 9% + / 0.5A auxiliary output Intelligent
FEATURES: Click on Series name for product info on aimtec.com Models Single output Model Max Output Power (W) 1 AC-DC Constant Current or Constant Over temperature protection Voltage LED Driver Over current
Ametek, Rotron Technical Products Division 627 Lake Street Kent, Ohio 44240 User's Guide 120 Volt, 800 Watt and 240 Volt, 1200 Watt Brushless Motor Drive Electronics 5.7" (145 mm) and 7.2" (183 mm) Windjammer
Digital Temperature Controller Compact and Intelligent Temperature Controller Auto-tuning and self-tuning available. Can auto-tune even during execution of self-tuning Heating or heating/cooling control
Inwall Room Temperature Unit TM11B01KNX TM11B11KNX TM11B21KNX Product Handbook Product: Inwall Room Temperature Unit Order Code: TM11B01KNX TM11B11KNX TM11B21KNX Application Program ETS: TM11B_1KNX Inwall
Solar Eye User Manual Edition JIANGSU EVER-SOLAR NEW ENERGY CO., LTD. Revision History Date Edition Specification 17/08/2011 1.0 Create File 02/09/2011 1.1 Add Micro SD function description www.ever-solar.com
Power-monitoring unit PowerLogic System Technical data sheet 2003 Power Meter Series 800 Function and characteristics PB100313 The PowerLogic Power Meter Series 800 offers all the high-performance measurement