1 Solar Eye User Manual Edition <1.1> JIANGSU EVER-SOLAR NEW ENERGY CO., LTD.
3 Revision History Date Edition Specification 17/08/ Create File 02/09/ Add Micro SD function description Page 1 of 25
4 Table of Contents 1. Introductions Packing List Safety and Notes Product Installation Connecting Solar Bee and Straight Networking Cable Solar Bee Wall Attach Installation SD Card (Optional) in Solar Eye and Battery Installation Solar Eye Installation Detachable Chassis Fixation Wall Mounting Interface Introduction Main Interface Sub Interface Set & Operation Initial Setting Set Time Set Currency Set Yield Coefficient Set Emission Coefficient Wireless Connection Connection Type Set Up Wireless Connection Alarm Warning Setting Data Storage Interval Time Setting Restore Factory Default Settings History Energy and Power Value Yield View Micro SD File Structure Description Check the History Data Update software Reference: Error Message Contact Page 2 of 25
5 1. Introductions Solar Eye is desktop monitoring device, developed for home and small commercial PV solar system. This device is able to monitor up to 5 inverters simultaneously, transfer data through wireless network and display relevant data on the LCD. Features: Integrated Large LCD display Multiple display - Graph or bar chart display options Wireless Technology (Up to 150 meter in open area and up to 100 meter in building) Retro fit on any Ever-solar inverter, monitor up to 5 inverters Micro SD card storage for history monitoring data Real time monitoring of Power Generation, Export value and Carbon Saving 1.1 Packing List The packing list of Solar Eye as below: A B C D E F G H I J K Table 1-1 Packaging List Location Quantity Name Purpose A 1 Solar Eye Display terminal of inverter data B 1 Solar Bee Collect inverter data C 1 Waterproof Seal Sets D 1 Operating& Instruction Installation Secure water and dust protection of Solar Bee (IP65) Product operating & installation instruction E 4 wall plug For Solar Bee wall mounting F 2 Screw ST2.7 6 Fix the suspension loop to Solar Bee G 2 Solar Bee Suspension Loop For Solar Bee wall mounting H 1 The base of Solar Eye For Solar Eye installation on the table I 4 Screw ST3 25 For Solar Bee & Solar Eye wall mounting Page 3 of 25
6 J 1 Direct network Cable between Solar Bee & inverter K 1 Quick installation guide of Solar Eye Product quick installation guide 1.2 Safety and Notes 1)Read the instructions before installation 2)Disconnect inverter power before installing Solar Bee 3)If the product is damaged, please contact your local maintenance center or return to the dealers/distributors for repair 4)Please do NOT try to open the Solar Eye and Solar Bee, or force it in any way as it will VOID your warranty and we will not be able to exchange it 5)Please do not put Solar Eye in the water or any other liquids. 6)Please do not place Solar Eye near heat or flame, or any place with high humidity or low temperature 7)Please handle the product carefully 9)Please keep the product away from children 10)Please use the product under the environment with temperature ranging from -20 to 50, and relative humidity 80% 11)When Solar Eye is not in use for a long time, please remove the battery or cut off the power. 2. Product Installation The installation process includes the installation of Solar Bee and Solar Eye. Please follow below steps. 2.1 Connecting Solar Bee and Straight Networking Cable 1) Please remove the square silica gel plug, and then insert network cable, as shown in Fig2-1 Fig 2-1 Insert network cable Attention: Connection cable is standard CAT5 network cable with RJ45 connectors, CAT5, CAT5E is compatible. 2) Fix the accessories (waterproof seal sets) to Solar Bee, as shown in Fig 2-2 Page 4 of 25
7 Fig 2-2 Installation of waterproof seal sets 2.2 Solar Bee Wall Attach Installation 1) Use the ST2.7*6 screws to fix two suspension loops onto the pillars of Solar Bee. Fig 2-3 as below Fig 2-3 Suspension loop installation 2) Drill twoφ6 holes on the wall with 39mm space distance as Fig 2-4 Fig 2-4 Drill the wall mounting holes Attention: Hold the handgrip tightly; keep right direction, no shaking to prevent the damages to the wall and bias of the holes. The depth of holes must more than 30mm. Please keep the surface clean before measurement. 3) Use the rubber hammer to tap wall plugs into the holes. 4) Wring two ST3 25 screws into wall plugs, and keep the screw head 5mm space outside. Fig 2-5 as below Page 5 of 25
8 Fig 2-5 Fix screws 5) Hang the Solar Bee on the screws fixed to the wall. Tighten the screw with a screwdriver slightly. Fig 2-6 as below Fig2-6 Install Solar Bee 6) Connect Solar Bee and the PV inverter together with the straight networking cable. Fig 2-7 as below Fig 2-7Connect inverter and Solar Bee 2.3 SD Card (Optional) in Solar Eye and Battery Installation Solar Eye adopts SD card (compatible up to 4GB). Users is able to upgrade Solar Eye Firmware through SD card. 1)Open the battery cover of Solar Eye. Fig 2-8 as below Fig 2-8 Open battery cover 2)Put SD card into the slot, then lock the MICRO SD card clamping plate. Fig 2-9 as below Page 6 of 25
9 Fig 2-9 Insert SD card 3)Put three pieces AA alkaline battery into battery box following the + - marks as Fig Fig2-10 Battery loading Warning: Make sure the battery polarity. The product also could be powered by 4.5V DC adapter showing in the Fig Solar Eye Installation There are two ways for Solar Eye installation: one is on the removable base, the other way is wall mounting Detachable Chassis Fixation Press the Solar Eye bottom groove into the convex of base. With a sound of clattering, installation will be finished. Fig 2-11 as below: Fig 2-11 Solar Eye base setting If want to remove Solar Eye from the base, press the base button and release connection. Fig 2-12 as below: Page 7 of 25
10 Fig2-12 Remove Solar Eye from base Warning: When remove the base, there should be no force in case of mechanical damage Wall Mounting 1)Drill two φ6 holes with 43mm space distance. Fig 2-13 as below: Fig 2-13 Drill the wall mounting holes Warning: Stay vertical angle between driller and wall with no shake in case of incline. The hole should be no less than 30mm deep. When measure the hole depth, clear the dust inside. 2)Place the wall plugs into the holes with the rubber hammer. 3)Wring the screws ST3 25 into wall plugs, and keep the screw head 5mm space outside. Fig 2-14 as below: Fig 2-14 Fix screws 4)Hook the Solar Eye over the two screw nails. Fig 2-15 as below: Fig 2-15 Hook Solar Eye on the wall 3. Interface Introduction 3.1 Main Interface Solar Eye main interface as Fig 3-1: Page 8 of 25
11 Fig 3-1 Solar Eye main interface Table 3-1 Fig3-1 Description Pos. Fig 3-1 A B C D E F G H I Description Date Time Power trend Sub menu Gross generation Intraday generation Current generated power Connected inverter quantity Battery display(when battery power shortage happens, it will twinkle) 3.2 Sub Interface Under main interface, press enter key to switch among ENERGY, YIELD, CO2 and HISTORY interfaces. 1)ENERGY interface:display E-today & E-total as Fig 3-2 Fig 3-2 ENERGY Interface 2)YIELD interface:display E-today yield & E-total yield as Fig 3-3 Fig 3-3 YIELD Interface Page 9 of 25
12 3)CO2 interface:display CO2 emission volume today and in total as Fig3-4 Fig 3-4 CO2 Interface 4)HISTORY interface:display hourly, daily, weekly, monthly and yearly generated electricity as Fig 3-5. For details, pls refer to chapter 4.6 history energy and power value yield view. Fig 3-5 HISTORY Interface 4. Set & Operation Three keys left ( C ), right ( B ), and enter ( A ) are available as Fig 4-1, which can help achieve all functions. Fig 4-1 Key Guide 4.1 Initial Setting Initial setup is required for first time use. Users are allowed to change these parameters as following: Set Time Hold Enter key for 3 seconds for setting as Fig 4-2. At this interface, press left & right key to change time, and switch to the next setting by enter key. All time & dates will flash to indicate the setting is finished; at this time, press right key to enter into currency setting interface. Page 10 of 25
13 Fig 4-2 Set Time Set Currency Currency setting interface is as Fig 4-3. Press left & right key to switch among $ and then choose the target one by enter key. When it s finished, press right key to enter into yield coefficient setting interface. Fig 4-3 Set Currency Set Yield Coefficient Yield coefficient indicates the yield per 1Kwh electricity generated from PV inverter and its setting interface is as Fig 4-4. Press left & right key to change coefficient, and then confirm it by enter key. All digits flash to indicate the setting is finished. At this time, press right key enter into emission coefficient setting interface. Fig 4-4 Set Yield Coefficient Set Emission Coefficient Emission Coefficient indicate the decreased CO2 volume (kg) per 1Kwh electricity generated from PV inverter and its setting interface is as Fig 4-5. left & right key to change coefficient, and then confirm it by enter key. All digits flash to indicate the setting is finished. At this time, press right key enter into main interface. Page 11 of 25
14 Fig 4-5 Set Emission Coefficient 4.2 Wireless Connection Solar Eye can be connected to Ever-solar inverter (up to 5 inverters) as the following two ways Connection Type Type 1:One Solar Eye connects to multiple Solar Bee as Fig 4-6. Fig 4-6 one Solar Eye connects to several Solar Bee Type 2:One Solar Eye connects to one Solar Bee, and then the Solar Bee connects to several pieces of inverters as Fig 4-7. Fig 4-7 one Solar Eye connects to one Solar Bee Set Up Wireless Connection 1) Press the key of Solar Bee under normal working state for 15 seconds, until LED of Solar Bee flashes, which indicates Solar Bee has been into connection state. 2) Press right key of Solar Eye to go into connection state as Fig 4-8. At this time, the channel Solar Bee stays in will show on top left corner on Solar Eye, and press left & right key to choose channels Solar Bee stays in. For example, in channel 1. icon indicates Solar Bee stays Page 12 of 25
15 Fig 4-8 Wireless Connection Adjust 3) Press Enter button on the Solar Eye to connect, while symbol flashing, stop flashing after connection is ready, while LED is off. Solar Eye goes back to the main menu automatically after 1 minute. 4) Please repeat operation process above again if the connection failure, One Solar Eye connects to several Solar Bee (up to 10); avoid to setting to same communication cannel. 4.3 Alarm Warning Setting The alarm waning note user to deal with when inverter error happens, in the main menu, press and hold left and right buttons enter the interface of alarm warning setting, show as Fig 4-9. Press left and right to chose ON or OFF, then press enter button quit the interface to the main menu. Fig 4-9 interface of alarm warning setting Setting alarm on, solar-eye alarm warning every 5 minutes to note user when inverter error happens. 4.4 Data Storage Interval Time Setting Data storage interval means the frequency of writing data to SD card. In the main menu, press and hold left button enter the interface of data storage interval. as show in Fig 4-1. User can choose the interval time from 1 to 5 minutes by pressing left or right buttons, Then press enter button go back to the main menu. Page 13 of 25
16 Fig 4-10 Interface of data storage interval 4.5 Restore Factory Default Settings In the main menu, you press and hold both left and right buttons, while switch on the power. LCD display in full screen, LED flash after 3 seconds, then device restore to default factory setting. After completion, device can be used again by switch on power. Attention: history data will be lost if recover to factory default setting. therefore, copy the data in SD card before restore to factory default setting! 4.6 History Energy and Power Value Yield View Call up HISTORY menu, you press right button to view history data by switching the unit of Y axis among Hour Day Week Month and Year by pressing right button. Operation process show as below: 1)Hour Hour:Press right button, you can view the energy and power values/hour of last 34 hours yield by your PV system, Shown as in Fig 3-1 B means the time you check, F means energy and power values yield in this hour. 2)Day Day:Press right button, you can view the energy and power values/day of this day yield by your PV system, Shown as in Fig 3-1 A means the data you check, F means energy and power values yield in the day. 3)Week Week:Press right button, you can view the energy and power values/week of last 34 weeks yield by your PV system, Shown as in Fig 3-1 B means the week you check, F means energy and power values yield in this week. 4)Month Month:Press right button, you can view the energy and power values/month of last 34 months yield by your PV system. Shown as in Fig 3-1 A means year you check, F means energy and power values yield in this month. 5)Year Year:Press right button, you can view the energy and power values/year of last 4 years yield by your PV system. Shown as in Fig 3-1 A means year you check, F means energy and power values yield in this year. 4.7 Micro SD File Structure Description Take out Micro SD from Solar Eye, insert into PC, and then you will see the file structure as Page 14 of 25
17 below: Fig 4-11 Micro SD Directory Structure Table 4-1 file description Name Type Description hist folde Store files of history data & fault info r SN_YM.csv file Store working data of inverter, SN serial number of inverter; YM year/month ErrorLog.cs file Store fault info of inverter v update folde r Store software upgrading program, named as S-update.bin 4.8 Check the History Data Solar Eye records all data of generated electricity and the user can review it as the following way: Take out Micro SD card from Solar Eye Copy into PC files SN YM.csv & ErrorLog.csv under file directory hist of Micro SD Open file SN YM.csv via Excel or OpenOffice etc Attention: If there s any abnormity when opening the files via Excel or OpenOffice, please ensure the separator of the Excel or OpenOffice files is, ; if not, please set into,. 4.9 Update software Solar Eye can improve the performance and stability by updating software, the detailed Page 15 of 25
18 procedures are as below: Receive the latest program from or distributors of Ever-solar; Read carefully announcement of the new program; Copy file S-update.bin into update folder of Micro SD, and then insert Micro SD card into Solar Eye; Press left button and power on, 3 seconds later LED blinks, it enters into upgrading state; real-time power of Solar Eye shows P is flashing; P stop flashing when upgrading finished. If it shows F, the upgrading fails, and please check whether all procedures are done as told. Repeat the steps after reviewing. Attention: The following conditions can cause upgrading fail: Power of Solar Eye is not enough; SD card doesn t exist; S-update.bin S-update.bin file in update folder of SD card doesn t exist; The file of upgrading program is not named as S-update S-update. Page 16 of 25
19 5. Reference: Table 5-1 Solar Eye specifications table Item Specifications Power supply Wireless communication range Maxim MicroSD capacity support Wireless Operating frequency Solar Eye waterproof level DC 4.5V/100mA or AA*3 batteries Max. 100m 4GByte/FAT32 Format 433MHz IP20 Monitor the max. number of inverter 5 Max. number of connected Solar Bee 5 Currency,, $ Error alarm LCD display & audible alarm Operating temperature range -10~50 Operating humidity range 80% Table 5-2 Solar Bee specifications table Item Power supply Wireless communication range Specifications Inverter power Max. 100m Maxim RS485 length support Max. 20M Operating temperature range -20~60 Max. number of connected Inverter 5 Operating humidity range 98% Wireless Operating frequency Solar Eye waterproof level 433MHz IP65 Page 17 of 25
20 6. Error Message Table 6-1 Error Message(1) Error Code Single phase error message Three phases error message 1 GFCI Failure GFCI Failure 2 AC HCT Failure AC HCT Failure 3 Reference Voltage Fault NA 4 DC inj. differs for M-S DC inj. differs for M-S 5 Ground I differs for M-S Ground I differs for M-S 6 Low DC Bus Low DC Bus 7 High DC Bus High DC Bus 8 Device Fault Device Fault 9 NA NA 10 No-Utility Grid voltage =0 11 Ground I Fault Ground I Fault 12 NA Output Current High Protect 13 NA Output Current High Protect By Hardware 14 Over Temperature in Inverter Over Temperature in Inverter 15 Auto Test NA 16 PV Over Voltage PV Over Voltage 17 Fan Lock Fan Lock 18 AC Voltage Out of Range AC Voltage Out of Range 19 Isolation Fault Isolation Fault 20 DC Injection High DC Injection High 21 Fac, Vac Differs for M-S 22 NA Consistent Fault Consistent Fault: Fac, Vac Differs for M-S 23 Fac differs for M-S Consistent Fault: Fac differs for M-S 24 Vac differs for M-S Consistent Fault: Vac differs for M-S 25 NA Output Relay Check Failure 26 AC Relay-Check Fails AC Relay-Check Fail 27 NA Output HCT Failure 28 NA GFCI Device Failure 29 NA M-S Version Unmatched 30 Fac Out of Range Fac Failure: Fac Out of Range 31 EEPROM R/W Fail EEPROM R/W Fail 32 Communication Fails between M-S 33 SPI Failure: Communication Fails between M-S 34 EEPROM R/W Fail 35 Relay check Fail 36 DC Injection High 37 The result of Auto Test unction is fail 38 DC bus is too high 39 The voltage reference inside is abnormal 40 AC HCT Failure 41 GFCI Device Failure 42 Device fault 43 M-S version unmatched reserve 55 Fac Failure: Fac Out of Range 56 AC Voltage Out of Range 57 Utility Loss 58 GFCI Failure 59 PV Over Voltage 60 Isolation Fault SPI Failure: Communication Fails between M-S Page 18 of 25
21 62 Over temperature in Inverter Table 6-1 Error Message(2) Error Code Single phase error message Three phases error message 63 Consistent Fault: Vac differs for M-S 64 Consistent Fault: Fac differs for M-S 65 Consistent Fault: Ground I differs for M-S 66 DC inj. differs for M-S 67 Consistent Fault: Fac, Vac differs for M-S 68 High DC bus Page 19 of 25
22 7. Contact If you have technical problems concerning our products, please contact us. We will get back to you as soon as possible. The contact details as below: Page 20 of 25
EPSOLAR LS1024B / LS2024B/ LS3024B Solar Charge Controller USER MANUAL Thank you very much for selecting our product! This manual offers important information and suggestions with respect to installation,
2013 Wireless Video Intercom INSTALLATION GUIDE INDEX System configuration and wiring VL-SWD501 System Component.. 4 VL-SWD501EX wiring schematic diagram VL-SWD501EX wiring type and length... 5.... 6 Door
Altenergy Power System Energy Communication Unit (ECU) Installation and User Manual (For ECU-3 V3.8) ALTENERGY POWER SYSTEM INC. All rights reserved TABLE OF CONTENTS 1.0 Introduction... 2 2.0 Installation...
4KVA/5KVA Parallel Installation Guide 1. Introduction This inverter can be used in parallel with two different operation modes. 1. Parallel operation in single phase with up to 4 units. The supported maximum
MAKING MORN LIVING POSSIBLE Danfoss heating living connect Installation and User Guide Contents 1.0 System overview... 3 2.0 Overview of display and control buttons... 3 3.0 Installation - step by step...
WatchPower User s Manual Management Software for Inverter Table of Contents 1. WatchPower Overview... 2 1.1. Introduction... 2 1.2. Features... 2 2. WatchPower Install and Uninstall... 2 2.1. System Requirement...
Grid PV-inverter 1500W/2000W/3000W/4000W/6000W Installation and Operation Manual 1 Only an electro-skilled person or trained assembly staff can install or open the Inverter. 2 Before you start Thanks for
PCS300 Universal IP Reporting Module V1.0 Reference and Installation Manual Patents: One or more of the following US patents may apply: 7046142, 6215399, 6111256, 6104319, 5920259, 5886632, 5721542, 5287111,
User Manual Humidity-Temperature Chart Recorder Model RH520 Introduction Congratulations on your purchase of the Extech RH520 Temperature + Humidity Chart Recorder. The RH520 measures and displays Temperature,
2M IR Mini Dome 2M IR Mini Dome Quick Installation Guide Please follow the installation steps below to set up 2M IR Mini Dome IP Camera. Check the package contents against the list below. See P.1 Physical
SNMP Web Management User s Manual For SNMP Web Card/Box Management Software for Off-Grid Inverter Version: 1.2 Table of Contents 1. Overview... 1 1.1 Introduction... 1 1.2 Features... 1 1.3 Overlook...
Outdoor 33.6W Dual Port Passive Power-over-Ethernet Midspan For External Security Cameras and Wireless Access Points Features SELV Compliant No Detection Passive Injector Gigabit Compatible Full Protection
AXIS 291 1U Video Server Rack Installation Guide About This Document This document describes how to install Axis blade video servers in the AXIS 291 1U Video Server Rack. Updated versions of this document
TruPower-Portable-500W Solar Starter kit This Solar starter kit is an easy to use solar power supply system that is the complete solution for all your solar power needs. It is a solar generator that converts
Alpha Climatic Programmable Modulating Boiler Energy Manager Part No 3.022144 (Hard Wired) Part No 3.022143 (Radio Frequency) Installation and User Instructions 1. Description The Alpha Climatic energy
GPRS/MMS/SMS Digital Infrared Trail Camera User s Manual WCM-3004 1 Table of Contents 1. Instructions... 1 1.1 General Description... 1 1.2 Camera Body Interface... 1 1.3 Camera components and features...
LIEBERT VNSA Installation Sheet Description The Liebert vnsa network switch is designed for connecting multiple Ethernet-ready devices and comes in various models. The unit may have: A Liebert icom display
VZ-M7 HDMI Field Monitor 7 Class HD LCD The VZ-M7 HDMI monitor provides sharp, accurate images for improved framing and focus assist on any camera equipped with an HDMI output. Utilizing top-quality Grade
Text Edit message GSM Autodialer Professional GJD700 Speech & Text Autodialer Introduction The GSM Autodialer Professional works in conjunction with standard alarm systems and makes use of your preferred
Quick Start Guide RRL Radio Telemetry Antenna External Power Connection LED Activity Light RS232 Connection Serial Number Levelogger Connections RRL Station High Quality Groundwater and Surface Water Monitoring
Point of view HDMI Smart TV dongle Mini RF Keyboard English Contents Contents... 1 General notices for use... 2 Disclaimer... 2 Box Contents... 2 1. HDMI TV dongle... 3 1.1. Product display... 3 1.2. Instructions
User Manual -Installation -Operation Omniksol-13k-TL Omniksol-17k-TL Omniksol-20k-TL Omnik New Energy Co.,Ltd. 2 User Manual CATALOG Catalog... 3 1. Notes on this manual... 5 1.1 General notes... 5 1.2
Rev. D PRODUCTIVITY THROUGH INNOVATION 600 CONTROL DIRECT DRIVE TECHNICAL/OPERATION MANUAL 10 BORIGHT AVENUE, KENILWORTH NEW JERSEY 07033 TELEPHONE: 800-524-0273 FAX: 908-686-9317 TABLE OF CONTENTS Page
INSTALLATION MANUAL EKRTR EKRTETS 1 2 1 2 3 60 87 170 161 ±1.5 m >0.2 m 3 5 4 34 125 4 5 28 50 EKRTR EKRTETS Contents Read this manual attentively before starting up the unit. Do not throw it away. Keep
ISSUE 5 VIP-802 DUAL ENHANCED NETWORK AUDIO PORT INTRODUCTION The VIP-802 Dual Enhanced Network Audio Port enables voice access to two zones of one-way paging over an IP network, allowing page zones to
Technaxx FMT600BT Transmitter User Manual Transfer of music and calls directly from your Bluetooth device to your car radio This device complies with the requirements of the standards referred to the Directive
33.6W Power over Ethernet Waterproof Adapter PoE Plus Single Port Injector for Outdoor Application Features Compliant with the IEEE802.3at Standard -40 to +60 C Temperature Range Diagnostic LEDs Full Protection
LUCCI AIRFUSION QUEST II CEILING FAN WITH IR REMOTE INSTALLATION OPERATION MAINTENANCE WARRANTY INFORMATION CAUTION READ INSTRUCTIONS CAREFULLY FOR SAFE INSTALLATION AND FAN OPERATION. V1.0 QUEST II IR
instalert 2 units to cover any application instalert 18 (ia18): 18 x 28 full matrix instalert 24: (ia24): 24 x 60 full matrix Size, Weight without battery ia18: 30 x 20 x 2.74, 29 lbs ia24: Folds to fits
Generator Meter Model: VAAFH Installation/Operation Manual I) Introduction The VAAFH is an ideal monitor system for 240/120 generators and grid power sources and provides monitor of load balancing on the
Dual-Bay RAID Storage Enclosure for two 3.5-inch Serial ATA Hard Drives User Manual March 31, 2014 v1.2 www.akitio.com EN Table of Contents Table of Contents 1 Introduction... 1 1.1 Technical Specifications...
TEMPERATURE SENSOR This sensor measures temperature in degrees Celsius or Fahrenheit. It works with all SensorHawk base units (SensorHawk-2, SensorHawk-8 and SensorHawk8/20) as well as the SecurityHawk-8
K3 K4 www.sebury.com.cn Digital Keypad Use s Manual Contents Introduction Introduction Specifications Intramural Interface Circuit 3 Mounting 3 Wiring 5 Power UP 7 Engineer Programming Mode 7 The K3/K4
Back-UPS Pro 1300/1500 Installation and Operation Inventory Safety Do not install the Back-UPS in direct sunlight, in excessive heat, humidity, or in contact with fluids. Connect the battery bu059a bu058a
GSM Desktop phone DPH101 User manual v1.00 LEGAL NOTICE Copyright 2011 TELTONIKA Ltd. All rights reserved. Reproduction, transfer, distribution or storage of part or all of the contents in this document
FWT-8848 GSM (GATEWAY) USER S MANUAL COPYRIGHT -2009 1 ST VERSION 1 1,General Description: FWT-8848 is a GSM to Analog Converter(single port,insert 1 sim card only), the device can produce a FXS line to
CHAPTER 3 This chapter includes the following topics, which help you install the Cisco Unified IP Phone on an IP telephony network: Before You Begin, page 3-1 Understanding the Cisco Unified IP Phone 7962G
96-01101 / rev. 2e / 2-2-12 Uninterruptible Power Supply EXCEPTIONAL SUPPORT & PROTECTION Uninterruptible Power Supply with Energy Saver design that is optimized to address the needs of A/V systems Features
Installation and Operation Back-UPS 1250, 1300, 1500 Inventory bu001a Safety and General Information This unit is intended for indoor use only. Do not operate this unit in direct sunlight, in contact with
MAKING MODERN LIVING POSSIBLE AK-SC255 On-Site Installation Guide DANFOSS ELECTRONIC CONTROLS & SENSORS How to Use This Guide Read this Guide completely as you install and start up your new AK-SC 255 controller.
www.xenta.co.uk Xenta Mini DV Camcorder Instruction Manual Model: MD800 Please Read These Instruction Carefully Thank you for purchasing MINI DV MD800. It has adopted unique ultra-portable design, which
Installation Guide TH3210D Non-programmable Digital Thermostat Product Application This thermostat provides electronic control of 24 VAC heat pump systems with auxiliary heat (2 heat/1 cool). Power Type
SNMP Web card User s Manual Management Software for Uninterruptible Power Supply Systems Table of Contents 1. Overview... 3 1.1 Introduction... 3 1.2 Features... 3 1.3 Overlook... 3 1.4 Installation and
RI-215A Operator s Manual Part Number: 71-0045RK Revision 0 Released: 10/3/05 Warranty RKI Instruments, Inc., warrants gas alarm equipment sold by us to be free from defects in materials and workmanship,
CHAPTER 3 This chapter includes this following topics, which help you install the Cisco IP Phone on an IP telephony network: Before You Begin, page 3-1 Installing the Cisco IP Phone, page 3-6 Adjusting
REMOTE METER TM Installation and Operation Manual. Digital Remote Meter for Monitoring System Performance. Version: RM-1 1098 Washington Crossing Road Washington Crossing, PA 18977 USA www.morningstarcorp.com
Options for ABB drives, converters and inverters User s manual FDPI-02 diagnostics and panel interface Table of contents Table of contents 3 1. FDPI-02 diagnostics and panel interface Safety..............................................
User Guide USB Starter Kit AMS 5812 Phone:+49 (0)6131/91 0730-0 Fax: +49 (0)6131/91 073-30 Internet: E Mail: firstname.lastname@example.org Analog Microelectronics GmbH An der Fahrt 13, D 55124 Mainz May 2012 - Rev.
COLOR VIDEO DOOR PHONE CDV-71BE/D 513-11, Sangdaewon-dong, Jungwon-gu, Seongnam-si, Gyeonggi-do, Korea Int l Business Dept. : Tel.; +82-31-7393-540~550 Fax.; +82-31-745-2133 Web site : www.commax.com Printed
PU-USBX USB over Ethernet Extender OPERATION MANUAL Safety Precautions Please read all instructions before attempting to unpack or install or operate this equipment, and before connecting the power supply.
Neo-Neon LED Vision Mesh Screen Operation Manual He Shan Decorative Lighting Company Limited LED Display Engineering Department 1 Contents Chapter1 Specification and Function Parameters 3 Chapeter2 Structure
Digital Photo Bank / Portable HDD Pan Ocean E350 User Manual Installing a hard disk 1. Power off the unit. 2. Remove the bottom cover from the unit by removing four screws. 3. Insert the 2.5 HDD to the
User Guide Temperature and Humidity Datalogger Model 42280 Introduction Congratulations on your purchase of the Extech 42280 Thermometer and Relative Humidity Datalogger. The 42280 is a wall-mount, tripod
User Manual of Omnik Internal Data Collector Omnik New Energy Co. Ltd. Catalog Part 1. WiFi Card Install SOP... 3 1. Disassembly... 3 2. Preparation... 3 3. Installation... 5 Part 2. Wifi card user manual...
User Guide Heavy Duty Dissolved Oxygen Meter Model 407510 Introduction Congratulations on your purchase of Extech's Heavy Duty Dissolved Oxygen / Temperature Meter which simultaneously displays Dissolved
PK5500 v1.1 Installation Instructions 1 2 3 4 5 6 7 8 9 * 0 # WARNING: Please refer to the System Installation Manual for information on limitations regarding product use and function and information on
Catalog Number 6234218 Hydras 3 LT Quick Start SOFTWARE MANUAL December 2005, Edition 2 Hach Company, 2005. All rights reserved. Printed in the U.S.A. Catalog Number 6234218 Hydras 3 LT SOFTWARE MANUAL
Wireless Home Security Alarm System AM 500 12 MONTH GUARANTEE Installation & Operating Instructions INTRODUCTION The AM500 is a simple self-contained alarm system. It protects the home by sounding a siren
FCC COMPLIANCE STATEMENT FOR AMERICAN USERS This equipment has been tested and found to comply with the limits for a CLASS A digital device, pursuant to Part 15 of the FCC Rules. These limits are designed
HP UPS R1500 Generation 3 Installation Instructions Part Number 650952-001 NOTE: The rating label on the device provides the class (A or B) of the equipment. Class B devices have a Federal Communications
MX MANUAL CONGRATULATIONS to the purchase of your new professional switch mode battery charger. This charger is included in a series of professional chargers from CTEK SWEDEN AB and represents the latest
About This Guide 3 About This Guide This user guide is intended for Photovoltaic (PV) system owners, installers, technicians, maintainers, administrators and integrators who are authorized to configure
GERONIMO ANALOGUE HEAVY DUTY TELEPHONE Installation and Connection Instructions K a l i k a L t d., I n n o v a t i o n H o u s e, A l e x a n d e r B e l l C e n t r e, H o p k i n s o n Wa y, A n d o
The Cable Ferret Company wigcam CF2810B Wireless Inspection Camera and LCD Display Instruction Manual Model: wigcam CF2810B Version 2.0 2014 The Cable Ferret Company Pty Ltd (AU) The Cable Ferret Company
User Manual GOODWE SS SERIES Ver 02 Table of Contents 1 Symbols..................................... 01 2 Safety....................................... 02 3 Installation...................................
MODE 24V/ MANUAL MXT 14 CONGRATULATIONS to the purchase of your new professional switch mode battery charger. This charger is included in a series of professional chargers from CTEK SWEDEN AB and represents
IDEAL INDUSTRIES, INC. TECHNICAL MANUAL MODELS: 61-763 61-765 The Service Information provides the following information: Precautions and safety information Specifications Performance test procedure Calibration
56 / Accessories for inverters Accessories for inverters / Our accessories complement all PV systems, simplify installation and ensure that the system meets the required safety standards. FRONIUS STRING
MAKING MODERN LIVING POSSIBLE living connect Installation and User Guide Danfoss Heating Solutions 2 living connect Thank you for buying a Danfoss product Danfoss Heating Solutions 3 Contents 1. System
This Quick Start Guide is designed to familiarize the user with the connection and configuration of the DTS-305 DIN rail mounted single / 3 phase power & energy meter with RS-485 or TCP communications.
P55 V3.0 Congratulations on your purchase of the GIGABYTE Notebook. This manual will help you to get started with setting up your notebook. The final product configuration depends on the model at the point
User's Guide 99 Washington Street Melrose, MA 02176 Phone 781-665-1400 Toll Free 1-800-517-8431 Visit us at www.testequipmentdepot.com Back to the Extech 407780 Product Page Integrating Sound Level Datalogger