1 Install Guide CT100 PG 1 Caution top cover Your thermostat is a precise instrument, handle it with care. Turn off electricity to the system before installing or servicing thermostat or any part of the system. Do not turn electricity back on until work is completed. Do not short (jumper) across electric terminals at the control on the furnace or air conditioner to test the system. This may damage the thermostat. All wiring must conform to local codes and ordinances. This thermostat is designed for use with 4AA alkaline batteries and/or 24 VAC C-wire (or a AC or DC source) and millivolt gas systems. Each thermostat relay load should be limited to 1.0 amp; higher amperage may cause damage to the thermostat. Power Grid status indicator Reset button ire terminals MENU button Mode button selections switches Touch screen Caution To avoid electrical shock and to prevent damage to the furnace, air conditioner, and thermostat, disconnect the power supply before beginning work. This can be done at the circuit breaker. bottom cover ENGLISH
2 PG 2 TOOLS You will need a small Phillips screwdriver and a drill with 3/16-in. (4.8mm) bit for wall mounts. LOCATION Replacement installations - mount the CT100 in place of the old thermostat. A new location will require moving your wiring. For new installations and relocating the CT100 - follow the guidelines listed below: Locate the thermostat on an inside wall, about 5 ft. (1.5m) above the loor, and in a room that is used often. Do not install it where there are unusual heating conditions, such as: in direct sunlight; near a lamp, radio, television, radiator register, ireplace; near hot water pipes in a wall; or near a stove on the other side of a wall. Do not locate in unusual cooling conditions, such as: on a wall separating an unheated room; or in a draft from a stairwell, door, or window. Do not locate in a damp area. This can lead to corrosion that will shorten thermostat life. Do not locate where air circulation is poor, such as: in a corner, an alcove; behind an open door. Do not install the CT100 until all construction and painting has been completed. This thermostat does not require leveling. Good 5ft. (1.5m)
3 REMOVE OLD UNIT Switch OFF electricity to the HEATING and COOLING systems. Then follow these steps: Remove cover from old thermostat. Most are snap-on types and simply pull off. Some have locking screws on the side or front. These must be loosened. DO NOT remove wires. Note the letters printed near the terminals. Attach labels (enclosed) to each wire for identiication. Caution Read instructions carefully before removing any wiring from existing thermostat. ires must be labeled before they are removed. THERE IS NO STANDARD COLOR CODE. hen removing wires from their terminals, ignore the color of the wires and LABEL THEM by the lettered terminal where they were screwed. Label the wires one at a time. You must label all the wires before you proceed. ith all wires labeled, remove them from the old unit. Make sure the wires do not fall back inside the wall. You can wind them around a pencil to keep them from falling. Loosen all screws on the old thermostat and remove it from the wall. R G PG 3
4 PG 4 hat wires do you have? Make sure your wires are labeled. This may require you to ind the other end connection for each wire on your heating or air conditioning equipment and read the label there. Refer to the ire Reference page at end of install section for better understanding of wire labels from different system makers. IMPORTANT: The CT100 runs on 4 AA alkaline batteries and/or the C wire if available. If you do not have a C wire you can run a new wire from the or use a standard 12-24V [AC or DC] wall transformer. IMPORTANT: If you have both RH and RC you need to remove the jumper wire between these 2 terminals. Prepare ires Jumper wire Y RH RC G A Y2 from System 2.6" ire Terminals C Y R Please follow these guidelines for safe and secure wire connections: You will need at least 2.6 of wire for each of your connections to the CT100. If you do not have enough wire, splice additional wire to allow enough slack. Terminals accept wires from 16-22awg. Fan out wires below the hole as shown. Remove insulation 1/8 from the tip of each wire. hen handling, take care not to damage the labels for each wire. G
5 IRES IRES Find the step-by-step diagram for your system From C R 2 ire Heat R n Yn R G From C IRES From R G 3 ire Heat C R G IRES From C Y R G 4 ire Heat/Cool Y R G From Y RH RC G C Y RH 5 ire Heat/Cool Go To Page 13 Go To Page 13 Go To Page 14 Go To Page 14 n Multi-stage Cool Multi-Stage Heat Yn R G Go To Page 15 IRES B or O Y R G From B C O or 4 ire Heat Pump w/o Aux Heat Y R G IRES RC G B or O AUXn Yn R G From B C O or Multi-stage Heat Pump w/ Multi-stage Aux Heat n Go To Page 15 Go To Page 16 IRES Yn R G Select the reference page with your wiring diagram and set-up information below. The C-wire is optional but preferred for all installations. It will make batteries last a long time. (This connection is shown as dotted in diagrams). Hot ater systems accessories are on Page 16. If your combination of wires is not shown, you can use the wiring table at the end of the install section to ind your connections. If additional help is required, please contact customer service. PG 5
6 PG 6 from HEAT/COOL system Fan out wires as illustrated with CT100 below the wall opening. As in the example: fan out the wires so that the C wire is above the C terminal, the above the. This allows the CT100 to it snug to the wall. C Y G RH Caution Do not allow wires to touch each other or parts on thermostat. C B O 2 Y Y2 RHRCG A Position the wires behind the CT100 and up over the terminal area. Do not bunch wires behind the CT100. Feed any slack back into the wall opening. Connect Your ires Connect labeled wires only to a terminal with the same letter label. Insert the wire in the terminal well and tighten the screw securely. NOTE: If you wish you can mount the CT100 to the wall irst, and then connect the wires. The CT100 can be externally powered with a power source rated from 12V to 24V, AC or DC, at 100ma or greater. If used, connect to the C and RH terminals (no polarity).
7 Mount the CT100 to all 1. Hold the CT100 against the wall, with the wires coming over the top; above terminal block. The CT100 will cover the hole in the wall. 2. Position CT100 for best appearance. 3. Attach the CT100 to the wall with the screws provided. 4. If you are mounting the CT100 to sheet rock or if you are using the old mounting holes, use the plastic anchors provided. 5. Mark irst and drill a 3/16-in.(4.8mm) hole for the insert at each screw location, then mount the unit. from HEAT/COOL system C Y RH G Place wires like this all CT100 ires Screw to wall all anchor PG 7
8 PG 8 Selection Set the TYPE switch in the NORMAL position if you have conventional natural gas, propane, oil, or electric heat. If you have a HEAT PUMP system, set the TYPE switch to HEAT PUMP. They are located in the battery area. Set the HEAT TYPE switch in the GAS position if you have normal gas or oil heat or if you have a heat pump with gas or oil auxiliary heat. Put the HEAT SOURCE in the ELEC position if you have normal electric heat or if you have a heat pump with electric auxiliary heat. IMPORTANT: Press the RESET button (under top cover) to implement the switch selections. HEAT PUMP NORMAL TYPE TYPE ELEC GAS HEAT TYPE HEAT TYPE Install 4 AA Batteries Install 4 AA alkaline batteries [required] following the marked polarity in the battery compartment. Put the battery in negative end irst against the spring, then push the positive end in. AA AA AA AA ith all the wires connected it is time to turn the AC power back on. Do this at the breaker you used to switch it off. The CT100 will power-up in the OFF mode. Your CT100 is not conigured to operate your system yet. You must now conigure your thermostat for your system.
9 Caution Special Battery arning Always replace the batteries as soon as the Low Batt lashes. The thermostat is a battery powered device. You must be responsible to replace batteries before they run out. Failure to replace batteries can result in overheating or excessive cooling of your house. Even if the Low Batt indicator does not lash, you should always replace the batteries at least once a year. Replacing the batteries also helps to prevent leakage that can corrode and damage the thermostat. If you are leaving your home for a month or more, you should replace the batteries as a precaution against battery failure in your absence. Always use new alkaline batteries. Failing to replace the batteries, when necessary, could cause the thermostat to lose power or malfunction. If the thermostat loses power, then the thermostat will not control the temperature which could result in your system not functioning as you intended and lead to possible damage from overheating or excessive cooling. If the thermostat batteries fail with the heat OFF, this can result in NO HEAT and possible frozen or broken pipes and water damage. If the thermostat batteries fail with the cool OFF, this can result in NO COOL and could cause possible damage or excessive temperatures. PG 9
10 PG 10 Setup on Screen IMPORTANT: Make sure the CT100 is powered up and the mode is set to OFF. Remember that the two selection switches must be set irst [pg 8]. ith mode in OFF press MENU and touch SETUP. Use +/- icons to select SET UP number on screen. The LCD display will show your selection and indicate the number of stages you have selected. During setup, 2nd STG will blink when both heat and cool have 2nd stages. HEAT 2ND STG COOL SETUP If you have a Normal system... HEAT and COOL select 1 2 stage HEAT, 1 stage COOL select 2 1 stage HEAT, 2 stage COOL select 3 2 stage HEAT, 2 stage COOL select 4 If you have a HEAT PUMP system... HEAT PUMP with no AUX heat select A 2 stage HEAT PUMP with no AUX select b HEAT PUMP with AUX heat select C HEAT PUMP with 2 stage AUX heat select d 2 stage HEAT PUMP with AUX heat select E 2 stage HEAT PUMP with 2 stage AUX heat select F Caution Do not change the setup or selection switches if the thermostat is included to Z-ave network. The system must be changed, irst EXCLUDE the thermostat from the network, change the setup, and INCLUDE the thermostat to the network.
11 Test Installation FAN Follow these procedures to verify you have correctly installed the CT100. TO CHECK FAN (If you connected the G wire): Touch the fan icon on the HOME screen to turn the fan ON. Verify that air is blowing from the system. Touch the fan icon again to return to AUTO. RADIO 1 LINK TARGET TEMP F AUTO HEAT MENU MODE TO CHECK HEAT MODE Set the mode to HEAT by pressing the MODE button until HEAT is displayed. Touch the temperature display to bring up the MANUAL screen. Touch the + icon and raise the target temp to 90 o F; allow the system 2 minutes to respond. Verify that heat is blowing from the system. Return the Target Temperature to a normal setting. Return mode to OFF by pressing the mode button. If you have a heat pump, leave in off for 4 minutes before checking COOL. TO CHECK COOL (do not operate AC if the outside temp is below 65 o F) Set the mode to COOL by pressing the MODE button until COOL is displayed. Touch the - icon and lower cool Target Temperature to 50 o F. Allow the system 5 minutes to respond. Verify that cool air is blowing from the system. Return the Target Temperature to a normal setting. Return mode to OFF by pressing the mode button. PG 11
12 Congratulations, you have successfully installed your unit. Please proceed to the OPERATING Guide to initialize the CT100. PG 12 IMPORTANT: If you have labeled and connected your wires and followed the correct setup, and your system still does not operate, contact technical support. AUTO STATEMENT OF USE: This thermostat can be used with 4AA batteries, 24VAC (C wire), 24VAC adapter, heating and cooling systems and also millivolt heating. It cannot be used with line voltage systems. This thermostat is digital and your desired heat or cool temperatures can easily be set on the large touch screen with the +/- buttons. A minimum 4 minute off time protects the compressor from damage. RADIO 1 LINK TARGET TEMP F HEAT MENU MODE This thermostat runs on 4AA batteries. The CT100 can be externally powered with a power source rated from 12V to 24V, AC or DC, at 100ma or greater. If used, connect to the C and RH terminals (no polarity). The 24VAC C wire is the other side of the 24VAC heating transformer and can be found where the other thermostat wires connect at the wall or at the furnace. Do not use the common or ground side of the line voltage.
13 Step-by-step wiring diagrams IRES 2 ire Heat GAS MILLIVOLT or 24VAC system STEP 1 - Connect the R wire to the RH terminal. This connects the heat power. STEP 2 - Connect the wire to the terminal. This connects the heat. STEP 3 - Optional - Connect the C wire to the C terminal. Your heater is now connected to the CT100. Please Go To Page 6 POER SYSTEM C B O 2 Y Y2 RH RC G A THERMOSTAT THERMOSTAT TERMINALS C R 3 ire Heat STEP 1 - Connect the R wire to the RH terminal. This connects the heat power. STEP 2 - Connect the wire to the terminal. This connects the heat. STEP 3 - Connect the G wire to the G terminal on the thermostat. This SYSTEM connects the fan. C R G POER STEP 4 - Optional - Connect the C wire to the C terminal. Your system is now connected to the CT100. Please Go To Page 6 C B O 2 Y Y2 RH RC G A IRES THERMOSTAT THERMOSTAT TERMINALS PG 13
14 PG 14 Y R G 4 ire Heat/Cool STEP 1 - Connect the wire to the terminal. This connects the heat. STEP 2 - Connect the Y wire to the Y terminal. This connects the cooling compressor. STEP 3 - Connect the RH or R wire to the RH terminal. This connects the power. STEP 4 - Connect the G wire to the G terminal on the thermostat. This connects the fan. SYSTEM STEP 5 - Optional - Connect the C wire to the C terminal. POER C Y R G Your system is now connected to the CT100. Please Go To Page 6 C B O 2 Y Y2 RH RC G A IRES Y RH RC G 5 ire HEAT/Cool STEP 1 - Connect the wire to the terminal. This connects the heat. STEP 2 - Connect the Y wire to the Y terminal. This connects to the cooling compressor. STEP 3 - Remove the jumper between RC and RH terminals [small silver wire]. STEP 4 - Connect the RH wire to the RH terminal and the RC wire to the RC terminal. This connects the power. STEP 5 - Connect the G wire to the G terminal. This connects the fan. STEP 6 - Optional - Connect the C wire to the C terminal. IRES Your system is now connected to the CT100. Please Go To Page 6 THERMOSTAT TERMINALS POER SYSTEM C Y RH RC G C B O 2 Y Y2 RH RC G A THERMOSTAT TERMINALS *RC and RH disconnected
15 n Yn R G Multi-stage Heat and Multi-stage Cool The CT100 can handle up to 2 stages of HEAT and 2 stages of COOL. STEP 1 - Connect the, 2 wires to the terminals. This connects the stages of HEAT. STEP 2 - Connect the Y and Y2 wires to the Y terminals. This connects the stages of COOL. STEP 3 - Connect the RH or R wire to the RH terminal. This connects the power. STEP 4 - Connect the G wire to the G terminal. This connects the fan. STEP 5 - Optional - Connect the C wire to the C terminal. Your system is now connected to the CT100. Please Go To Page 6 THERMOSTAT TERMINALS SYSTEM POER C 2 Y Y2 R G C B O 2 Y Y2 RH RC G A Heat Pump (heat/cool) without Auxiliary Heat STEP 1 - Connect O wire to the O terminal or B wire to the B terminal. This connects the change-over valve. IMPORTANT NOTE: If you have both O and B - connect only the O wire to the O terminal and DO NOT connect B to the B terminal (see wire reference under Trane for B wire terminal). STEP 2 - Connect the Y wire to Y terminal. This connects the compressor. STEP 3 - Connect the R wire to the RH terminal. This connects the power. STEP 4 - Connect the G wire to the G terminal. This connects the fan. STEP 5 - Optional - Connect the C wire to the C terminal. Your system is now connected to the CT100. Please Go To Page 6 POER or THERMOSTAT TERMINALS SYSTEM C B O Y R G or C B O 2 Y Y2 RH RC G A PG 15
16 PG 16 O or B AUXn Yn R G Multi-stage Heat Pump with Multi-stage Aux Heat The CT100 can handle up to 2 stages of Pump compression and 2 stages of AUX heat. STEP 1 - Connect O wire to the O terminal or B wire to the B terminal. This connects the change-over valve. If you have both O and B - connect only the O wire to the O terminal and DO NOT connect B to B terminal (see wire reference under Trane for B wire terminal). STEP 2 - Connect the AUX 1, AUX 2, to the AUX 1 and 2 respectively. SYSTEM This connects the auxiliary heat. C B O AUX1 AUX2 Y Y2 R POER or STEP 3 - Connect the Y and Y2 wires to the Y terminals. This connects the compressor. or STEP 4 - Connect the R wire to RH terminal. This connects the power. STEP 5 - Connect the G wire to G terminal. This connects the fan. C B O 2 Y Y2 RH RC G A STEP 6 - Optional - Connect the C wire to the C terminal. THERMOSTAT TERMINALS Your system is now connected to the CT100. Please Go To Page 6 G Accessory iring - 3 ire Zoned Hot ater Heat - For 3 wire solenoid or motor valves connect the wires shown to the correct terminals on the CT100. If you have different letters than shown, go to page 18 ire Reference Table. CT100 RH FOR 3IRE ZONED HOT ATER R A A CT100 A RH R A MOTOR VALVE SOLENOID VALVE
17 ire Reference Table Possible ires R or V or VR RH or 4 RC 2 AUX or AUX1 AUX2 Y Y2 G or F C or X H DH EX B O B and O E L T hat They Control RH and RC Single power for HEAT and COOL RH Power for HEAT (RH not connected to RC jumper wire removed) RC Power for COOL (RH not connected to RC jumper wire removed) Heat control 2 2nd stage HEAT AUX1 1st stage of AUX heat in the CT100 AUX2 2nd stage of AUX heat in the CT100 Y COOL control or 1st stage compression for heat pump Y2 2nd stage COOL control or 2nd stage compression for a heat pump G FAN control C 24VAC power (to power thermostat) NOTE: TRANE, AMERICAN STANDARD and YORK often use the letter B for C H External Humidiier DH External Dehumidiier EX external fresh air bafle B Heat pump changeover (cool to heat, powered in heat) O Heat pump changeover (heat to cool, powered in cool) IMPORTANT: If there are both B and O wires (Trane pump products) DO NOT CONNECT B to B terminal, connect B to C terminal. n/a Emergency heat (do not connect, tape off) n/a System monitor (do not connect, tape off) n/a Outdoor sensor (do not connect, tape off) ire Reference PG 17
18 PG 18 ire Reference cont. Possible ires hat They Control Lennox Heat Pump V or VR or R RH Power for HEAT M or Y Y COOL control Y or or 2 2 2nd stage HEAT F or G G Fan control R or O O X or X2 or C C Trane Products [American Standard] B C 24VAC power (to power thermostat) X2 Emergency heat (do not connect, tape off) Zoned Hot ater 2 wire Your ires R 3 ire Motor Driven Valves R or 5 or 4 Y or G or 6 (the 3rd wire) Thermostat Terminal RH RH (power) (heat ON) A (heat OFF) 3 ire Solenoid Valves R RH (power) A (heat ON) Y or G (the 3rd wire) (heat OFF)
19 APPENDIX 1 Multi staged theory of operation for the CT100 Staging for 2 stage normal or heat pump Cool Target Temperature Maintenance in COOL - If the room temperature is within the target temperature plus the DIFF setting, the irst stage of cool will turn on. If the target temperature is not reached within 15 minutes, the second stage of cooling will turn on and join the irst stage to reach the target temperature. Target Temperature Recovery in COOL- If the room temperature is beyond the new target temperature plus the DIFF setting, the irst stage will turn on. Ten seconds later, the second stage will turn on with the irst stage to help reach the new target. ith FAST recovery, both stages stay on until the new target temperature is reached. ith ECON recovery, both stages stay on until the DIFF setting is reached. Then, the second stage shuts off and the irst stage stays on to the new target. Staging for 2 stage normal Heat Target Temperature Maintenance in HEAT - If the room temperature is within the target temperature minus the DIFF setting, the irst stage of heat will turn on. If the target temperature is not reached within 15 minutes, the second stage of heat will turn on and join the irst stage to reach the target temperature. Example: Target temperature 70F, DIFF at 2F, maintenance occurs at room temperatures of 69F and 68F. Target Temperature Recovery in HEAT- If the room temperature is beyond the new target temperature minus the DIFF, the irst stage will turn on. Ten seconds later, the second stage will turn on and join the irst stage to help reach the target temperature.. ith FAST recovery, both stages stay on until the target temperature is reached. ith ECON recovery, both stages stay on until the DIFF setting is reached. Then, the second stage shuts off and the irst stage stays on until the target temperature is reached. Staging for a 2 stage Heat Pump with no auxiliary heat Target Temperature Maintenance - If the room temperature is within the target temperature minus the DIFF setting, the irst stage heat pump will turn on. If the target temperature is not reached within 15 minutes, the PG 19
20 PG 20 second stage of heat pump will turn on and join the irst stage to reach the target. Target Temperature Recovery - If the room temperature is beyond the new target temperature minus the DIFF setting, the irst stage will turn on. Ten seconds later, the second stage will turn on and join the irst stage to reach the target temperature. ith FAST recovery, both stages stay on until the new target temperature is reached. ith ECON recovery, both stages stay on until the DIFF setting is reached. Then the second stage shuts off and the irst stage stays on until the new target temperature is reached. Staging for Heat Pump with 1 or 2 stages of compression and 1 or 2 stages of auxiliary heat Target Temperature Maintenance - If the room temperature is within the target temperature minus the DIFF setting, the auxiliary heat will not be used, just the heat pump (1 or 2 stages) as explained above in target temperature maintenance. Target Temperature Recovery - If the room temperature is beyond the new target minus the DIFF setting, the irst stage of heat pump will turn on, ten seconds later the second stage of heat pump will turn on, ten seconds later the irst stage of auxiliary heat will turn on. If the new target temperature is then not reached after 15 minutes, the second stage of auxiliary heat will turn on. If the new target temperature is not reached 15 minutes after that, the third stage of auxiliary heat will turn on. ith FAST recovery all stages will stay on until the new target temperature is reached. ith ECON recovery all stages will stay on until the DIFF setting is reached. Then only the heat pump stays on until the new target temperature is reached. ELECTRIC vs. GAS or OIL auxiliary heat - ith electric auxiliary heat, the heat pump stays on while the auxiliary heat is on. ith gas or oil auxiliary heat, the heat pump will shut off while the auxiliary heat is on. This is required by heat pump design.
PG 1 Install Guide 3M-50 aution Your thermostat is a precise instrument, handle it with care. Turn off electricity to the HVA system before installing or servicing thermostat or any part of the system.
Builder MODEL 1010 Series Non-Programmable Single Stage Heat/Cool Thermostat USER MANUAL Compatible with low voltage single stage gas, oil or electric heating or cooling systems, including single stage
FAILURE TO READ AND FOLLOW ALL INSTRUCTIONS CAREFULLY BEFORE INSTALLING OR OPERATING THIS CONTROL COULD CAUSE PERSONAL INJURY AND/OR PROPERTY DAMAGE. DESCRIPTION ELECTRICAL DATA Electrical Rating: 20 to
Installation Questions How do I determine what type of heat I have? There may be several ways to determine what type of heat you have. First, if you can access the unit that is responsible for creating
Installation and Operation Manual Environ TM Smart Thermostat 2 Copyright Enphase Energy Inc. 2010 141-00010 Rev 01 Contact Information Enphase Energy Inc. 201 1 St Street Petaluma, CA 94952 Phone: 707-763-4784
1F85-275 Heating & Air Conditioning 5-1-1 Programmable/Non-programmable, Auto Changeover, Multi-Stage/Heat Pump Thermostat INSTALLATION INSTRUCTIONS Operator tor: Save these instructions for future use!
FAQs Conserve package Gateway... 2 Range Extender... 3 Smart Plug... 3 Thermostat... 4 Website... 7 App and Mobile Devices... 7 FAQs Gateway Can I have someone install my system for me? If you are concerned
UP400 Programmable Thermostat Installation Instructions & User Guide For Installation Help 1-877-654-9394 White-Rodgers.com 2011 Printed in China White-Rodgers 8100 West Florissant Avenue St. Louis, MO
Installation Guide VisionPRO TH8000 Series Touch-screen Programmable Thermostat This manual covers the following models TH8110U: For 1 Heat/1 Cool systems TH8320U: For up to 3 Heat/2 Cool systems TH8321U:
QUICK INSTALLATION GUIDE Read Installer Notes before removing cover from Thermostat. 1F85RF-275 Wireless Remote Kit INSTALLER NOTES IMPORTANT Do not apply power to the thermostat or wireless sensor until
SINCE 1 8 8 6 AUTO SAVER 550 5: 7 2 2 3 2 OwnerÕs Manual Model 44550 Ask Your Local Retailer for Other Quality Products from unter Fans Air Purifiers umidifiers To locate your nearest unter Dealer, call
Operation 3M-30 Day Time of day Target Temperature Time Slot Touch Screen Current Room Temperature Thermostat Mode Statement of use: The 3M-30 can be used with millivolt, 24VAC, single and 2 stage conventional
SERVICE MANUAL FOR 6535 SERIES TWO TON HIGH EFFICIENCY PACKAGED HEAT PUMPS TABLE OF CONTENTS 1. Warnings...2 2. Accessibility Of Appliance...3 3. Unit Dimensions And Specifications...3 4. Unit Specifications
Blue 2 Heat Pump Thermostat Heat Pump Installation and Operating Instructions Save these instructions for future use! FAILURE TO READ AND FOLLOW ALL INSTRUCTIONS CAREFULLY BEFORE INSTALLING OR OPERATING
Installation guide Welcome! If you have questions, we have answers. Visit ecobee.com/support/ecobee3 for tutorials, how-to videos and FAQs. Technical support is also available by email or by phone: email@example.com
Honeywell CT3500/CT3595 PROGRAMMABLE THERMOSTAT Weekday, Saturday and Sunday Programmable Heat and/or Cool Low Voltage (20 to 30 Vac) Thermostat and Wallplate Model CT3500/CT3595 OWNER S GUIDE Para pedir
CT3200 Programmable Thermostat Welcome to the world of comfort and energy savings with your new Honeywell Programmable Thermostat. Your new thermostat will automatically control the temperature in your
SERVICE MANUAL 12VDC WALL THERMOSTAT AIR CONDITIONING SYSTEMS ROOFTOP UNITS ONLY! WARNING - SHOCK HAZARD! TO PREVENT THE POSSIBILITY OF SEVERE PERSONAL INJURY, DEATH, OR EQUIPMENT DAMAGE DUE TO ELECTRICAL
HITE-RDERS 1F86-244 Non-Programmable Electronic Digital Thermostat INSTALLATIN AND PERATIN INSTRUCTINS perator: Save these instructions for future use! FAILURE T READ AND FLL ALL INSTRUCTINS CAREFULL EFRE
HITE-RDERS 1F80-51 Programmable Electronic Digital Thermostat INSTALLATIN AND PERATIN INSTRUCTINS perator: Save these instructions for future use! FAILURE T READ AND FLL ALL INSTRUCTINS CAREFULL EFRE INSTALLIN
INSTALLATI DESCRIPTI WHITE-RODGERS COMFORT-SET 90 SERIES MULTI-STAGE INSTALLATI/CFIGURATI This White-Rodgers Automatic Setback Digital Thermostat uses microcomputer technology to provide precise time and
Split-type Air-Conditioner MXZ-3A30NA MXZ-4A36NA INSTALLATION MANUAL Refer to the installation manual of each indoor unit for indoor unit installation. English Français Español ATTENTION This manual mentions
SMART TEMP ELECTRONIC THERMOSTAT INSTALLATION AND OPERATIN INSTRUCTIONS Installs Easily Set Day & Time IMPORTANT! Please read all instructions carefully before beginning installation. Save them for future
User Manual THR840DUK Digital Thermostat 50051982-001 Rev. A WARNING: This product must be correctly installed and configured to work properly (see pages 12-24). If you are not experienced in wiring electrical
Operation 8022C HEAT O AN HEAT COOL AUTO ON HEAT O AN HEAT COOL AUTO ON Customer Support: 888-515-2585 or Visit our webiste www.ritetemp-thermostats.com Made In China 401-006 Operation 8022C TEMP UP Time/
Save these instructions for future use! FAILURE TO READ AND FOLLOW ALL INSTRUCTIONS CAREFULLY BEFORE INSTALLING OR OPERATING THIS CONTROL COULD CAUSE PERSONAL INJURY AND/OR PROPERTY DAMAGE. APPLICATIONS
TS EMR T/PT/TDE Surface applied door closer Installation instructions: Pull side track mount door closer with smoke detector (EMR T) Push side track mount door closer with smoke detector (EMR PT) Double
37-7498 Professional Contractor INSTALLATION GUIDE Wireless Setup Connect Exit Next Exit 3 EASY STEPS Installing Sensi thermostat isn t that different than installing a non Wi-Fi thermostat. 1. Install
Website: www.andico.com.au Service manual CAUTION - BEFORE SERVICING THE UNIT, READ THE SAFETY - PRECAUTIONS IN THIS MANUAL. - ONLY FOR AUTHORISED SERVICE PERSONNEL. MODELS: MPK1-09CR-QB8 MPK1-12ER-QB6
REMOTE CONTROL MANUAL ENGLISH CONTENT PRECAUTIONS...1-2 USING THE REMOTE CONTROL UNIT...3 OPERATION...4-9 Thank you for purchasing our Room Air Conditioner. Before using your air-conditioner, please read
Air Conditioning Sign-Off Sheet Printed Technician Name Address Social Security Number Telephone Number City State Zip Code Install Or Verify The Accuracy Of An Air Conditioner s Installation The candidate
INSTALLATION MANUAL AIR CONDITIONER Please read this installation manual completely before installing the product. Installation work must be performed in accordance with the national wiring standards by
14. Guide 14.1 Refrigeration Cycle System In order to diagnose malfunctions, ensure the air conditioner is free from electrical problems before inspecting the refrigeration cycle. Such problems include
SC 2201 Manual Changeover Non-Programmable Hardwired Non-Programmable Electronic Thermostat For use with Heat Pumps Up to 2-Stage Heat, 2-Stage Cool 30-Minute Power Loss Memory etention For use with 24
Proliphix Internet Managed Thermostat (IMT) Installation Guide December 2011 Technical Support Technical Support is available through the Proliphix partner from whom you purchased your product. For technical
Air Conditioner Water Heater - A Product of HotSpot Energy LLC PLEASE READ THIS BEFORE YOU INSTALL THE UNIT 1. This air conditioner must be installed and/or repaired by a qualified technician. If you perform
Thermostatic Wiring Principles by Bob Scaringe Ph.D., P.E. Basic Thermostat Types Many technicians have great difficulty understanding how to properly wire a thermostat or how to replace a thermostat with
CHAPTER 4 UTILITY SYSTEMS ELECTRICAL Utility Systems Electrical The electrical supply to your home begins outside, where you will see either an overhead feed and piping down the side of your home or (if
RV Products Division SERVICE MANUAL FOR 12 VDC WALL THERMOSTAT AIR CONDITIONING SYSTEMS ROOF TOP UNITS ONLY Airxcel, Inc. RV Products Division P.O. Box 4020 Wichita, KS 67204 1976A376 (1-11) TABLE OF CONTENTS
Pocket Manual Service Diagnosis SPLIT & MULTI Service Diagnosis SPLIT & MULTI 1. Troubleshooting with LED...5 1.1 Indoor Unit... 5 1.2 Outdoor Unit... 10 2. Troubleshooting by Symptoms...11 2.1 Air conditioner
RANCO INSTALLATION INSTRUCTIONS ETC TWO STAGE ELECTRONIC TEMPERATURE CONTROL Relay Electrical Ratings PRODUCT DESCRIPTION The Ranco ETC is a microprocessor-based family of electronic temperature controls,
Instruction Bulletin EAV85226 08/2014 Wiser Panel Meter, Model Number WISERCTPM200 Installer s Guide Retain for future use. Product Description Kit Contents The Wiser Panel Meter is for use in energy management
18-HD64D1-3 ComfortLink II Installation Guide Other Installation Guides may be necessary, based on system configuration. A complete list of other optional components is shown below. 1 Control 2 Relay Panel
HEAT PUMP FREQUENTLY ASKED QUESTIONS HEAT PUMP OUTDOOR UNIT ICED-UP DURING COLD WEATHER: It is normal for a heat pump to have a build up of white frost on the outside coil during cold damp weather. The
Heating and Cooling Basics Thermostat Control UNI-LINE PRODUCT KNOWLEDGE 2012 Invensys. All Rights Reserved. The names, logos, and taglines identifying the products and services of Invensys are proprietary
TS1200 Intelligent Lead Free Soldering Station Operation Manual Thank you for purchasing an Intelligent Lead Free Soldering Station. It is designed for lead free soldering. Please read this manual before
Home omfort ontrol Model 8910 READ AND SAVE THESE INSTRUTIS Safety & Installation Instructions Table of contents Installation Thermostat installation location recommendations.. 2 Thermostat mounting...
Blue Easy Reader Thermostat 1F95EZ-0671 Homeowner s Guide Message to Homeowners Congratulations on choosing the Emerson Blue Easy Reader Thermostat. Blue Easy Reader is designed to be the easiest thermostat
DUAL SENSING DIGITAL THERMOSTAT PRODUCT INSTRUCTIONS www.rehau.com Construction Automotive Industry SCOPE This guide gives instruction regarding REHAU Programmable Digital Thermostat installation and operation.
3 072 RDJ10RF RCR10/433 Wireless room temperature controller with 24-hour time switch and LCD Programmable, for heating systems RDJ10RF/SET Operating modes: Automatic, Comfort, Energy Saving, and Frost
TP-PRH-A, TP-NRH-A Performance Series Edge Thermidistat Control Installation Instructions Programmable Control A07049 A07048 Non Programmable Control Designed and Assembled in the USA. NOTE: Read the entire
HOUSING QUALITY STANDARDS (HQS) Series 5 Electrical Safety And INSPECTIONS 5.01 ELS Revised 8-17-06 Electricity is Dangerous All electrical repairs should be made by licensed professionals. Touching any
RCS MODEL ZC4 4 ZONE HVAC INSTALLATION AND OPERATION MANUAL DCN: 141-0020-02 /0/03 INTRODUCTION The 4 Zone HVAC Controller series allows up to 4 standard electronic thermostats to independently control
1F87-361 Programmable Electronic Digital Thermostat INSTALLATIN AND PERATIN INSTRUCTINS perator: Save these instructions for future use! FAILURE T READ AND FLL ALL INSTRUCTINS CAREFULL EFRE INSTALLIN R
Oil and Coolant Circulating Heating System Model - OCSM Installation & Operation Manual 216280-000 REV 2 Identifying Your System The HOTSTART heating system is designed to heat fluids for use in marine
A General Guide To Room Style Products Pipework Pipe sizes and lengths should be as the relevant Technical Guide Both lines should be insulated No line accessories or oil traps should be fitted In cooling
Failure code manual content 一 wall split AC series 2 二 floor standing AC series. 4 三 portable AC series.. 5 四 dehumidifer 6 五 DC inverter single split series...7 六 DC inverter multi-split series 10 1 一
RS4110 RS5110 RS4220 RS5220 RS6220 INSTAATIN MANUA 352-00060-001 Rev. A RS4000 Series RS5000 Series RS6000 Series Thank you for purchasing a Robertshaw thermostat. This manual will describe how to install
LIEBERT VNSA Installation Sheet Description The Liebert vnsa network switch is designed for connecting multiple Ethernet-ready devices and comes in various models. The unit may have: A Liebert icom display
SERVICE INSTRUCTION SPLIT TYPE ROOM AIR CONDITIONER WALL MOUNTEDtype INVERTER Models Indoor unit Outdoor unit ASYG07LECA ASYG09LECA ASYG12LECA ASYG14LECA AOYG07LEC AOYG09LEC AOYG12LEC AOYG14LEC R410A CONTENTS
Alpha Climatic Programmable Modulating Boiler Energy Manager Part No 3.022144 (Hard Wired) Part No 3.022143 (Radio Frequency) Installation and User Instructions 1. Description The Alpha Climatic energy
T7560A,B,C Digital Wall Module HONEYWELL EXCEL 5000 OPEN SYSTEM BEFORE INSTALLATION All wiring must comply with local electrical codes and ordinances or as specified on installation wiring diagrams. Digital
MAKING MORN LIVING POSSIBLE Danfoss heating living connect Installation and User Guide Contents 1.0 System overview... 3 2.0 Overview of display and control buttons... 3 3.0 Installation - step by step...
Ducoterra Radiant Heating Panel Installation Manual 1. Introduction Your new radiant heating panels are designed to heat living and working spaces rapidly and efficiently by radiant heating. Like the sun,
TESTING, SERVICE & REPAIR GUIDE (For SH Space Heating Models & RA Water Heating Models) WARNING - HIGH VOLTAGE AC electrical circuits are connected to this heater. Do not attempt any service work on the
Roof Top Air Conditioner INSTALLATION AND OPERATING INSTRUCTIONS Ducted System RECORD THIS UNIT INFORMATION FOR FUTURE REFERENCE: Model Number: Serial Number: Date Purchased: This manual must be read and
543-0032-00, 943-0032-00 User s Manual 1 Comfort Alert Diagnostics Faster Service And Improved Accuracy The Comfort Alert diagnostics module is a breakthrough innovation for troubleshooting heat pump and
Installation Instructions Model TSTATG2111 Use with most systems: 2-Heat, 1-ool 1- Day Prog ram m ab l e Digital Thermostat u p t o 2 - H e a t & 1 - o o l ontrol up to 2 Heat & 1 ool Stages Backlit Display
QUICK REFERENCE BRCEC BRCEC BRCEC BRCEC Table of contents Page Operation General safety precautions Features and functions Name and function of switches Name and function of icons Description of the operation
Comfort Control Center 2 Thermostat Operating Instructions Programmable Thermostat MODEL 3312026.XXX With Dehumidify 3312024.XXX With Out Dehumidify TABLE OF CONTENTS About your new thermostat Features...2
CHRONOMITE INSTANT-FLOW MICRO WATER HEATER INSTALLATION AND OPERATION INSTRUCTIONS - (LOW FLOW MODELS) (Before installation, compare electrical needed for the model of heater selected) TABLE 1 Model No.