1 Commercial Lighting Requirements of the 2006 International Energy Conservation Code U.S. Department of Energy Building Energy Codes Program Eric Richman, PNNL Materials developed by: Eric Richman, PNNL and Britt/Makela Group, Inc.
2 What We Plan to Cover Some history and basis for energy codes and standards Why we have them Where they apply Specific Requirements Focus on IECC 2006 Comparisons with other codes/standards where applicable Intent and application The intent of major requirements What the requirements mean in actual practice
3 Some History: The Basis for Energy Requirements Energy Conservation and Production Act, as amended, requires States to adopt a commercial energy code...this drives state adoption of energy codes DOE determines the effective stringency level to meet or exceed currently set at ASHRAE/IESNA Many code/standard versions available and currently adopted varies by state: Some adopt nationally available codes/standards Some develop state-specific codes Some have no code!
4 Energy Codes/Standards CODES MCEC MEC MEC MEC MEC MEC MEC IECC IECC IECC IECC IECC NFPA IECC IECC STANDARDS Codified A FEDERAL CFR 435 COSTSAFR CFR 435 FEDCOM 0 FEDRES 10CFR 434 FEDCOM II 10CFR 434 FEDCOM II II STATE SPECIFIC (Unique or based on a Code/Standard)
5 Commercial Lighting Requirements in IECC 2006 Commercial provisions contained in Chapter 5 with reference to ASHRAE Covers lighting controls and power density for interior and exterior Exception: Lighting within dwelling units Major changes in the 2006 version Revised Interior Lighting Power Allowances New Lighting Power Densities for Building Exteriors
6 The IECC Code Compliance Process Must the Project Comply with the IECC? Comply with the Envelope Requirements Comply with the Mechanical Requirements Comply with the Power & Lighting Requirements Section Section 5 Section Section 6 Section Section 9 Document Compliance with the IECC Plan Review Inspection
7 Does My Project Need to Comply with the Commercial Requirements of IECC? First: Is IECC (2006) the applicable code in your state or jurisdiction? If yes, is the building commercial or high-rise residential other than: One- and two-family residential R-2, R-3, R-4 three stories or less in height
8 When do the Lighting and Power Requirements Apply? Original Installed Lighting System in a New Building, Addition, or Tenant Build-out Existing Lighting System that is Altered Change in Occupancy that Increases Energy Exceptions: Historic buildings State or National listing Eligible to be listed Lighting within dwelling units
9 The IECC Code Compliance Process Must the Project Comply with the IECC? Comply with the Envelope Requirements Comply with the Mechanical Requirements Comply with the Power & Lighting Requirements Section Section 5 Section Section 6 IECC Section Section 9 Document Compliance with the IECC IECC Section 506 Building Performance Method Plan Review Inspection
10 What s Covered Under Electrical Power and Lighting System Requirements? Mandatory Interior Lighting requirements Required Controls Wattage/Efficiency Limits Interior Lighting Power Allowances (watts/ft 2 ) Exterior Lighting Controls Required Controls Lamp Efficiency Exterior Lighting Power Allowances (watts/ft 2 ) Electric Metering
11 Interior Lighting Control (505.2): Basic Control Independent Lighting Control required for each space surrounded by floor-to-ceiling partitions Must be located in the space served, -or- Switched from a remote location Must have indicator that identifies the lights served and their status (off or on) Exemptions Security or emergency areas that must be continuously lighted Lighting in stairways or corridors that are elements of the means of egress Intent: Allow occupants to control unneeded lighting!
12 Interior Lighting Control: Light Reduction Light Reduction Controls must allow the occupant to reduce connected lighting By at least 50% In a reasonably uniform illumination pattern Note: Alternate Standard ASHRAE/IESNA does not require Light Reduction Control Intent: Allow occupants to moderate light levels to save energy!
13 Light Reduction Control Options Controlling all lamps or luminaires Dual switching of alternate rows of luminaires, alternate luminaires or lamps Switching middle lamp luminaires independently from the outer lamps Each luminaire or each lamp Alternating Luminaires Dimming Alternating lamps SS D Dimmer Switch SS
14 Interior Lighting Control: Light Reduction Exemptions Light Reduction Control Not required for the following: Areas with only one luminaire Areas controlled by occupancy sensor Corridors, storerooms, restrooms or public lobbies Sleeping units Spaces with <0.6 w/ft 2
15 Interior Lighting Control: Automatic Shutoff Automatic lighting shutoff control device required in all buildings larger than 5,000 ft 2 Building Defined: Any structure used or intended for supporting or sheltering any use or occupancy Building area surrounded by exterior walls and fire walls Exempted spaces Sleeping units Lighting for patient care When an automatic shutoff would endanger occupant safety or security Intent: Eliminate after hours lighting waste!
16 Interior Lighting Control: Automatic Shutoff Options Automatic Lighting Shutoff Compliance Options 1. Control lights on a scheduled basis (automatic time switch) Time-of-day controller Automatic Lighting Control Controls 25,000 ft 2 and not more than one floor, or 2. Occupant sensor Turn lights off within 30 minutes of occupant leaving the space 3. Signal from another control or alarm that indicates the area is unoccupied 50 Office Conference Room Occupancy Sensor Open Bay Office Connect to Lighting in Open Bay Office Connect to Lighting in Lobby Lobby Restrooms 110
17 Interior Lighting Control: Automatic Shutoff Override Automatic Time Switch Override Requirements Readily accessible Within view of the lights or area controlled Manually operated 2 hour override Controls an area 5,000 ft 2 Exemptions to Override Requirements Can be over 2 hour override in malls and arcades, auditoriums, single-tenant retail space, industrial facilities and arenas when using captive key override Override in malls and arcades, auditoriums, single-tenant retail space, industrial facilities and arenas can cover up to 20,000 ft 2
18 Interior Lighting Control: Holiday Scheduling Automatic Time Switch Holiday Scheduling Must have feature that turns off all loads for 24 hours then resumes the normally scheduled operation Retail stores and associated malls, restaurants, grocery stores, places of religious worship and theaters are exempt
19 Interior Lighting Control: Sleeping Unit Lighting Control Sleeping Unit Control Applies to Hotel/Motel Guest Room, boarding houses, or similar Master switch required at each room or main room entry Must control all permanently wired luminaires or switched receptacles Intent: Allow occupant to turn off lights at exit point! $ $ $ $ $ Standard Room Suite
20 Tandem Wiring (505.3) Tandem Wiring for all Odd Numbered Lamp Configurations Exceptions: Where electronic high frequency ballasts are used Luminaires on emergency circuits Luminaires with no available pair in the same area Intent: Eliminate the use of magnetic ballasts driving single lamps!
21 Exit Signs (505.4) Exit Signs Internally illuminated exit signs shall not exceed 5 watts per side
22 Interior Lighting Power Limits (505.5) Connected Interior Lighting Power must not exceed Interior Lighting Power Allowance 1. Calculate Interior Lighting Power Allowance Building Area type allowance Additional allowances 2. Calculate proposed connected lighting power Wattage calculation rules Exempted lighting 3. Compare values: proposed wattage must be less than or equal to allowed wattage Intent: Eliminate waste from sloppy lighting design and application!
23 Interior Lighting Power Allowances New for the 2006 version: Building Area Type Only! Retail Additional Allowance Only! This is a simplification of the previous 2003 version that included building and tenant area allowances plus decorative and medical additional allowances Note: Alternate Standard ASHRAE/IESNA provides whole building and space-by-space options
24 Interior Lighting Power Allowance Calculation First, choose an appropriate Building Area Type from the allowance table ( ). Building Area includes all spaces that are associated with that business or function type. For example a space with: Corridors, Restrooms, A lobby, and Office space would be considered an office Building Area Type Then...multiply the lighting power density (W/ft 2 ) by the building square footage to get allowed watts for compliance
25 Office - Example A 200,000 ft 2 office building that contains corridor, restrooms, break rooms and a lobby is given 1.0 watt/ft 2 for the entire building Office: 200,000 ft w/ft 2 = 200,000 w
26 Interior Lighting Power Allowance for Multiple Occupancy Building How is an allowance determined if the building has more than one Building Area Type? Example A building contains the following area types Museum: 40,000 ft 2 Retail: 5,000 ft 2 Cafeteria: 10,000 ft 2 Use the more specific building area type where more than one area type exists in the building Sum the individual (lighting power density X area square footage) values for Total Power Allowance
27 Multiple Occupancy Building - Example Museum: 40,000 ft 2 at 1.1 w/ft 2 = 44,000 w Cafeteria:10,000 ft 2 at 1.4 w/ft 2 = 14,000 w Retail: 5,000 ft 2 at 1.5 w/ft 2 = 7,500 w Total watts allowed = 65,500 w
28 Additional Retail Lighting Power Allowance (Table Footnote a ) Lighting installed to highlight specific merchandise in addition to general lighting Additional lighting is added to the general lighting allowances Lighting for merchandise display Add additional 1.6 w/ft 2 X display area Display area cannot exceed 50% of the floor area Lighting for displaying and selling jewelry, china and silver 3.9 w/ft 2 X the actual case or shelf area Note: Display lighting must be switched or dimmed on separate circuit from general lighting Intent: Allow flexibility in design for critical retail applications!
29 With Retail - Example Museum: 40,000 ft 2 at 1.1 w/ft 2 = 44,000 w Cafeteria:10,000 ft 2 at 1.4 w/ft 2 = 14,000 w Retail: 5,000 ft 2 at 1.5 w/ft 2 = 7,500 w + retail allowance: Wall Display (10X40) = 400 ft 2 at 1.6 w/ft 2 = 640 w New Total Allowance = 66,140 w
30 Proposed Lighting Power Calculation Sum the wattage of all proposed connected lighting power This must include all lighting that is part of the design for the space including: Overhead lighting Task lighting Decorative lighting Note: Wattage must be calculated based on actual power draw not just nominal lamp rating
31 Proposed Lighting Calculation: Example Lighting wattage must be documented in accordance with Section Screw lamp holders: maximum rated wattage of the luminaire Low voltage lighting: transformer wattage Line voltage track: Use the GREATER of 30 w/linear foot or the actual wattage proposed for line-voltage track or plug-in busway lighting Other: manufacturer s rated wattage of lamp and associated ballast Luminaire Description Ballast Type Lamp (+Ballast) Wattage # Lamps per Luminaire Luminaire Quantity Luminaire Wattage A Inc. Downlight NA B Fl. 2X4 RecesseElec C Biax 2X2 Elec D CFL Wallwash Elec Dim E Fl. Cove Elec F MH Downlight Mag TOTAL WATTAGE: 14692
32 Exemptions to Proposed Lighting Power Calculation What lighting can I exempt from the Proposed Lighting Power Calculation? Specialized medical, dental and research lighting Professional sports arena playing field lighting Display lighting for exhibits in galleries, museums and monuments Sleeping unit lighting in hotels, motels, boarding houses or similar buildings Emergency lighting automatically off during normal building operation
33 What if My Proposed Design Does Not Meet Code? Check calculations and design Appropriate building types used? Actual lighting equipment wattages used? and design Reasonable illuminance levels provided? Efficient light sources used? Use alternate Standard Use total Building Performance Method
34 Exterior Lighting Control Requirements ( ) Lighting designated for dusk to dawn operation Control by astronomical time switch or photocell Lighting not designated for dusk to dawn operation Control by astronomical time switch Exceptions: Lighting for covered vehicle parking entrances or exits from buildings or parking structures if required by safety, security or eye adaptation
35 Exterior Efficiency Requirement ( ) Building grounds lighting luminaires over 100 watts must have source efficacy of at least 60 lumens per watt Exceptions: Controlled by motion sensor Any of the exterior lighting power allowance exceptions As approved for a historical, safety, signage, or emergency consideration
36 Exterior Lighting Power Limits ( ) Connected Exterior Lighting Power must not exceed Exterior Lighting Power Allowance Calculate exterior Lighting Power Allowance Lighting power densities by exterior function Additional 5% added to total allowance Calculate proposed connected lighting power Wattage calculation rules Exempted lighting Compare values: proposed wattage must be less than or equal to allowed wattage Intent of 5% adder: Allow flexibility in design for critical or unusual applications!
37 Exterior Lighting Power Limits ( ) What areas are covered under exterior lighting allowances? Tradable surfaces Common exterior lighted needs that can be traded for other needs. For example, wattage allowed for parking lot lighting can be traded and used for canopy lighting. Non-tradable surfaces Less common exterior lighted needs that cannot be traded for other needs. These applications have more specific security or task illuminance needs.
38 Tradable Surfaces Uncovered parking lots and areas Walkways (under and over 10 feet wide) Stairways Main building entrances Other doors Canopies and overhangs free standing and attached Open sales areas Street frontage sales areas
39 Non-tradable Surfaces Building facades Automated teller machines and night depositories Entrances and gatehouse inspection stations at guarded facilities Loading areas for law enforcement, fire, ambulance and other emergency vehicles Drive-up windows at fast food restaurants Parking near 24-hour retail entrances
40 Exterior Lighting Power Example Parking Lot Walkway 5 ft wide ATM Bank Canopy: 100 ft 2 Walkway: 200 ft long Parking: 10,000 ft 2 ATM One location Canopy How many tradable watts are allowed for this project? How many nontradable watts?
41 Example Calculation Parking : 10,000 ft 2 at 0.15 w/ft 2 = 1,500 w Canopy: 100 ft 2 at 1.25 w/ft 2 = 125 w Walkway: 200 ft at 1.0 w/ft = 200 w ATM (one): = 270 w Total = 2,095 w Total watts allowed: 1.05 x 2,095 = 2,200
42 Exemptions from Exterior Calculation The following lighting does not need to be included in the proposed lighting calculation: Specialized signal, directional, and marker lighting associated with transportation Advertising signage or directional signage Lighting integral to equipment or instrumentation and installed by its manufacturer Lighting for theatrical purposes, including performance, stage, film production, and video production Lighting for athletic playing areas Temporary lighting Lighting for industrial production, material handling, transportation sites, and associated storage areas Theme elements in theme/amusement parks Lighting used to highlight features of public monuments and registered historic landmark structures or buildings
43 What if My Proposed Exterior Lighting Does Not Meet Code? Check calculations and design Appropriate surface allowances used? Actual lighting equipment wattages used? and design Reasonable illuminance levels provided? Efficient light sources used? Use total Building Performance Method Note: Alternate Standard has same requirements
44 Electrical Energy Consumption Mandatory Requirement Separate Metering Required for Each Dwelling Unit Intent: Occupant understanding of actual energy use can promote effective energy use!
46 Setting the Standard Newsletter Register on-line to receive the latest up-to-date information on energy code related issues Newsletter:
47 Questions/Comments Help Desk on-line electronic form U.S. Department of Energy s Building Energy Codes Program
ASHRAE/IESNA Standard 90.1-1999 Lighting Requirements Joseph G. Howley Jr., IESNA GE Lighting Immediate Past Chair of ASHRAE SSPC 90.1 Lighting Subcommittee 1 How to Get the Standard Standard 90.1-2001
Lighting Compliance Forms Compliance Forms Instructions Compliance forms are provided in the User s Manual to assist in understanding and documenting compliance with the lighting requirements. Copies of
Instructions for Electronic Forms 2009 Washington State Energy Code Compliance Forms for Nonresidential and Multifamily Residential Revised December 2010 Chapters 11-15 of the 2009 Washington State Energy
TABLE 9.6.1 Lighting Densities Using the -by- Method Atrium Common Types a First 40 ft in height Height above 40 ft Audience/Seating Area Permanent 0.03 per ft (height) 0.02 per ft (height) For auditorium
CA Title 24 2013 Lighting and Receptacle Control Requirements for Commercial Buildings Michael Jouaneh, CEM, LEED AP July 1, 2014 This document summarizes the mandatory lighting control requirements and
AEDG Implementation Recommendations: Interior Lighting Sample Layouts for Office Buildings The Advanced Energy Design Guide (AEDG) seeks to achieve 30 percent savings over Standard 90.1-1999. This guide
Instructions for Electronic Forms, pg 1 2015 Washington State Energy Code Compliance Forms for Commercial Buildings including R2, R3, R4 over 3 stories and all R1 Revised July 2016 Commercial Provision
WHAT S NEW IN THE 2013 CODE? Changes to mandatory Title 24 lighting requirements California's new Building Energy Efficiency Standards take effect in 2014. They improve the energy efficiency of homes by
CHAPTER 29 SYSTEMS Note: The amendments to Chapter 29 are different than the 2009 Seattle Building Code and are not marked with margin bars or arrows. SECTION 2901 GENERAL [P] 2901.1 Scope. The provisions
California's new building energy efficient standards took effect July 2014. The goal is to make nonresidential buildings 30% more energy efficient than the previous 2008 standards. The next 16 slides give
PRESCRIPTIVE APPROACH 1. Actual and allowed LPD 2. Complete Building Method 3. Area Category Method 4. Tailored Method THE COMPLIANCE PROCESS There are two major steps to Title 24 compliance: 1. Meet all
Design Guidelines for Energy Efficient Lighting Systems Thank you for your interest in energy efficiency! According to the US Department of Energy, 51% of the energy used in commercial buildings is consumed
COMPLIANCE OVERVIEW 1. Compliance and enforcement 2. Permitting and certification 3. Compliance approaches 4. Required forms 5. New additions and major changes COMPLIANCE AND ENFORCEMENT Primary responsibility
Illuminating the Title 24 2013 Residential Lighting Requirements Copyright 2014 Lutron Electronics Co., Inc. All rights reserved. Reproduction or display of this presentation, or any of the contents herein,
BUILDING TECHNOLOGIES PROGRAM Lighting Development, Adoption, and Compliance Guide I Lighting Development, Adoption, and Compliance Guide BUILDING TECHNOLOGIES PROGRAM Lighting Development, Adoption, and
A NGuide a t i o n a l for G r i d Applicants a n d E v e r s o uand r c e Lighting Practitioners V4-20150202 Sustainable Office Design (SOD) is different than existing programs The new SOD Lighting Initiative
Vestibule Case Study [2003 IECC, 2006 IECC, 2003 IBC, 2006 IBC, 90.1-2001, 90.1-2004] Vestibule Requirement Intent Page 1 of 14 The primary intent behind the requirement for a vestibule is to reduce infiltration
Lighting High Efficiency Lighting Units Date added to ETL 2001 (Revised 2013). 1. Definition of Technology High efficiency lighting units are products that are specifically designed to provide efficient
CHAPTER 29 PLUMBING SYSTEMS > SECTION 2901 GENERAL [P] 2901.1 Scope. The provisions of this chapter and the Phoenix Plumbing Code shall govern the erection, installation, alteration, repairs, relocation,
Welcome to the 2011 Energy Efficiency Expo! Thank you to our session sponsors! Comparison Between the 2009 and 2012 International Energy Conservation Code What s coming when the new commercial energy code
Part III - Administrative, Procedural, and Miscellaneous Deduction for Energy Efficient Commercial Buildings Notice 2006-52 SECTION 1. PURPOSE This notice sets forth interim guidance, pending the issuance
BayREN Codes & Standards Training Program Compliance Enhancement Strategies: Nonresidential Lighting Introduction Example Projects and Forms The goal for the BayREN 2013 T24 Part 6 Compliance Enhancement
National Electrical Manufacturers Association Guidance on Energy Policy Act Commercial Building s Tax Deduction Certification Letters Revised June 18, 2007 1 National Electrical Manufacturers Association
15.20A0 CHAPTER 20A OUTDOOR LIGHTING REQUIREMENTS 15.20A1 SECTION 20A.1 PURPOSE GRAND HAVEN CHARTER TOWNSHIP The purpose of this Chapter is to provide a regulatory strategy for outdoor lighting that will:
City of Riverside Building & Safety Division Phone: (951) 826-5697 www.riversideca.gov BUILDING CODE REQUIREMENTS FOR CHILD DAY CARE The purpose of this document is to provide the user with a basic level
New Mexico Small Business Lighting LIGHTING RETROFIT REBATE For use with invoices dated on or after March 15, 2011 Business Customer Information Company name Date submitted Billing address City State ZIP
The Building Code of Australia (BCA) is a national code that applies to all states and territories through their own building control legislation. 1 Artificial lighting and power 3 Building class 3 Adjustable
Part III. Administrative, Procedural, and Miscellaneous Deduction for Energy Efficient Commercial Buildings Notice 2006 52 SECTION 1. PURPOSE This notice sets forth interim guidance, pending the issuance
Sam Docknevich, PSP, Security Service Portfolio Manager Are You Prepared? The impending impact of Code on Servicing Security Systems usa.siemens.com/infrastructure-cities Share current and upcoming standards
WALT WHITE Fire Chief 5770 Freeport Blvd., Suite 200 Sacramento, CA 95822-3516 Ph: (916) 808-1300 Fax: (916) 808-1629 www.sacfire.org Fire Alarm Systems Requirements by Occupancy Type 2013 California Building
New Section 135 Requirements for Electrical Distribution Systems 2013 California Building Energy Efficiency Standards Architectural Energy Corp. Draft Final Report August 15 2011 James R Benya, PE Principal
CHAPTER 9 FIRE PROTECTION SYSTEMS SECTION 901 GENERAL 901.1 Scope. Provisions of this chapter shall govern the application, design, installation, testing and maintenance of automatic sprinklers, standpipes
DESIGN REVIEW CHECKLIST Chapter 6 Special Consideration Design Guidelines A. Offices a. Office buildings should be built to the minimum required setback. b. Surface parking should be located towards the
Small Business Lighting Business Customer Information Opportunity ID: For a free lighting assessment, please contact the Small Business Lighting program at 1-877-287-2250. Company name Date submitted Billing
Title 24 Standards Essentials What triggers the Energy Code (Title 24, part 6)? Jon McHugh McHugh Energy Consultants Inc. April 2014 This program is funded by California utility customers under the auspices
Fire Alarm Systems Permit Packet City of Greer Fire Department Updated July 2004 If you have any questions or comments regarding the information contained within; or of you need assistance interpreting
FIRE SAFETY REQUIREMENTS 156.200 GENERALLY. A. Scope. The provisions of this chapter shall govern the minimum conditions and standards for fire safety relating to structures and exterior premises, including
SUPPLEMENT 4 Life Safety Code Enabling References Editor s Note: Supplement 4 provides users of NFPA 72, National Fire Alarm and Signaling Code, with a summary of requirements from NFPA 101, Life Safety
907.2.1.1 System initiation in Group A occupancies with an occupant load of 1,000 or more. Activation of the fire alarm in Group A occupancies with an occupant load of 1,000 or more shall initiate a signal
COUNTY OF LOS ANGELES BUILDING AND SAFETY DIVISION ELECTRICAL CODE FEE SCHEDULE (Title 27 of the County of Los Angeles Code, Ord No. 2013-0049) Effective July 1, 2014, Electrical Permit Fees in the unincorporated
High Efficiency Lighting Units Date added to ETL 2001 (Revised 2015). 1. Definition of Technology High efficiency lighting units are products that are specifically designed to provide efficient illumination.
TEXT (CO Detection Commercial Buildings Final) Part 1228 of Title 19 NYCRR is amended by adding a new section 1228.4, to read as follows: Section 1228.4. Carbon Monoxide Detection in Commercial Buildings
TAMARAC FIRE RESCUE INSTRUCTIONS FOR FIRE ALARM PRE-SUBMITTAL CHECKLIST In order to provide a comprehensive plan review in a timely manner, and to insure the design and installation of fire alarm systems
DCD-0304 Identification # Rev. 9/08 County Date of Inspection NAME OF OPERATION BUILDING INSPECTORS INSPECTION FORM FOR CHILD CARE CENTERS ADDRESS TELEPHONE: CITY STATE ZIP BUILDING INSPECTORS CERTIFICATE
RedVector.com, LLC 4890 W. Kennedy Blvd., Ste. 740 Tampa, FL 33609 813-425-7372 Ellen.Sakamoto@RedVector.com Advanced Florida Building Code including the Electrical Provisions of the Building, Energy Conservation,
ENERGY SAVING SOLUTIONS: LIGHTING CONTROLS ARCHITECTURAL ARCHITECTURAL & LANDSCA LANDSCA RECEPTION FRONT FRONT PARKING PARKING LOT LOT Interior and Exterior Layout and Design for Maximum Energy Savings
We see here that we have two ways to calculate our interior lighting power allowance and that we can use those methods on either the building as a whole or on separately metered or permitted portions of
General Safety & Health Standards Published by the Division of Building Safety In Cooperation with the Idaho Industrial Commission Local Fire Alarm 064. FIRE ALARM SYSTEMS 01. Scope 02. Definitions 03.
Tool 1: Assessing Robbery Risk Physical Security Checklist and Inventory Any assessment of robbery risk begins with an evaluation and inventory of the measures you are already taking as a financial institution.
CLARK COUNTY FIRE DEPARTMENT Fire Hazard & Prevention Services 575 E. Flamingo Road, Las Vegas, NV 89119 (702) 455-7316 FAX (702) 455-7347 105.8a-6.1 TITLE: FIRE ALARM SYSTEM REQUIREMENTS SCOPE: This guideline
U. S. A CCESS B O A R D T E C H N I C A L G U I D E ADA Scoping: This guide provides an introduction to the scoping requirements that form the basis for the Department of Justice s 2010 ADA Standards and
General Inspection FIRE SAFETY SELF-INSPECTION FORM FOR CULTURAL INSTITUTIONS 1. All Floors (inspect from top floor to basement): Yes are fire exits and directional signs properly illuminated? is the emergency
DISSCUSSION ITEM 3 ATTACHMENT E Chapter 16.130 PLUMBING CODE 16.130.100 Plumbing Code - Incorporation. There is incorporated by reference, for purpose of adopting regulations, provisions, conditions, terms,
PERMITS REQUIRED & PERMIT EXEMPTIONS This guideline is intended to assist the applicant in determining what types of construction work require a permit. The 1997 California Uniform Administrative Code,
California Energy Efficiency Codes for Lighting Manufacturers Gary Flamm Supervisor, Building Standards Development firstname.lastname@example.org (916) 654 2817 Certification Requirements Manufacturer is responsible
PNNL-20263 Prepared for the U.S. Department of Energy under Contract DE-AC05-76RL01830 Comparison of 2006 IECC and 2009 IECC Commercial Energy Code Requirements for Kansas City, MO Y Huang K Gowri March
F l u o rescent dimming solutions Presentation spaces Higher performance, economical lighting controls for: conference rooms auditoriums lecture halls classrooms computer rooms LEED is a registered trademark
Alpharetta Green Construction: 1. Alpharetta offers expedited plan review, plans processing and site inspections for LEED, EarthCraft, and EnergyStar certified projects. 2. Affordable Housing* Projects:
REGULATIONS for INSTALLATION, MAINTENANCE, and TESTING FIRE SUPPRESSION SYSTEMS APPLICATION PACKET CITY OF NAPERVILLE 400 S. EAGLE STREET NAPERVILLE, Il 60540 PHONE: 630.420.6070 FAX: 630.420.6657 Fire
Guide to new, energy-efficient lighting technologies for your business Commercial lighting systems are changing rapidly, with new or improved technologies continuously becoming available. Whether you re
Chapter 3: Use and Occupancy Classification General Comments Chapter 3 provides for the classification of buildings, structures and parts thereof based on the purpose or purposes for which they are used.
Open Office Plan Function and Orientation The open office plan on the top floor of the Westwood Community church holds 14 cubicles and doubles as the circulation space for the entire top floor. The area
TEXT (CO Detection Commercial Buildings) Part 1228 of Title 19 NYCRR is amended by adding a new section 1228.4, to read as follows: Section 1228.4. Carbon Monoxide Detection in Commercial Buildings (a)
Lighting Control in the Office Space Lutron Electronics Co., Inc. 2008 AIA/CES Program Registration This program is registered with the AIA/CES for continuing professional education. As such, it does not
LIGHTING and LIGHTING SYSTEMS Introduction Lighting is an important area of opportunity for energy savings, since it is a large fraction of use of electricity in residential and commercial buildings. Lighting
FIRE AND LIFE SAFETY REQUIREMENTS FOR CONVENTIONS, TRADE SHOWS AND EXHIBITS November 2011 COLORADO SPRINGS FIRE DEPARTMENT Division of the Fire Marshal If you have any questions or comments regarding the
2009 IFC Performing Commercial Fire Inspections Inventory Number: 1424S09 Second Printing; July 2014 Changes HAVE been made- Third Printing: September 2014 Errata has been identified as follows: 1. Page
Electrical Plan Requirements / Diagrams of Feeders 18-27-215.5 Diagrams of Feeders Electrical Plan Requirements / Diagrams of Feeders / Required Plans In new or remodeled buildings, complete and detailed
New Construction Program Energy-Efficient Lighting Design Reference Guide for Lighting Calculator Version 2.7-1 - TABLE OF CONTENTS 1. Introduction... 3 2. Program Information... 3 3. Luminaire Schedule...
16551 EMERGENCY LIGHTING SYSTEMS PART 1: GENERAL 1.01 SUMMARY A. This Section provides the University guidelines for the installation of Emergency Lighting Systems. B. This standard was developed primarily
Fire Alarm System Plans Review Checklist Property location Date of Review 1. Is application completed in entirety? 2. Are the plans review fee submitted with the application? 3. Does floor plan include
! Building Codes Update: The 2009 International Fire Code and the Apartment Industry Apartment operators and developers should be aware of organizational changes in the 2009 edition of the International
FORT COLLINS LIGHTING WATTAGE WORKSHEET ALLOWANCE SHEET For new buildings and whenever 60% or more of the luminaries are added or replaced for a tenant finish, and to verify compliance to the Fort Collins
FIRE SAFETY SELF-INSPECTION FORM FOR CULTURAL INSTITUTIONS The attached self-inspection form is intended for staff use at regular, frequent intervals. It should not take the place of two other vital measures
BRANCH: Date: Section 1 Physical Vulnerability 1. Do all office windows permit an unobstructed view of the bank s interior? 2. Are all exterior doors and windows equipped with tamper-resistant locks? 3.
NFPA 101 Life Safety Code Section 5-8 Illumination of Means of Egress 5-8.1 General. 5-8.1* Illumination of means of egress shall be provided in accordance with this section for every building and structure