2 Introduction Lighting is an important area of opportunity for energy savings, since it is a large fraction of use of electricity in residential and commercial buildings. Lighting energy use is not a big percentage of overall electric energy used in a manufacturing or industrial plant, but it may still be a relatively large number of kilowatthours or dollars.
3 Our oldest lamp is the incandescent lamp, and it is not much different from the first practical lamp that Thomas Edison made. The incandescent lamp contains a resistive filament that is connected directly to the supply voltage. The filament burns white hot, and produces a lot of heat and a little bit of light. Less than 10 percent of the input energy is converted to light. Eventually, even that light energy turns into heat in the space where the lighting is operating.
4 Lighting Terminology Lumen - The light output of a lamp is measured in a physical quantity called lumens, abbreviated Lu. This value is provided to users as a catalog or product specification. For example, a typical 100 watt incandescent lamp has a light output of about 1700 lumens. A typical 1200 mm fluorescent lamp has a light output of about 3000 lumens. Input - The lamp input is in terms of electrical power and has the units of watts.
5 Principles of Efficient Lighting Design Meet target light levels Produce light efficiently Deliver light efficiently Control lighting operation automatically
6 Factors in Successful Lighting Applications Amount of light required in Lux (Lu/m 2 ) Lumen output of lamps and fixtures - Lu Energy efficiency Efficacy in Lumens/watt Color Rendering Index - CRI Color Temperature in Kelvins Types of light sources Lighting quality
7 Amount of Light Required For Specific Applications Light levels are measured in Lux, using a lightmeter. Acceptable minimum standards of light levels are set by the Illuminating Engineers Society (IES). Typical requirements are: School, commercial office 500 Lux at the task location Factory floor 300 Lux at the task location
8 Lux - Lighting levels or illuminances are measured in Lux with a light meter. One Lux is one lumen per square metre. Lighting level standards are set by the Illuminating Engineering Society (IES), and are listed in detail in the IES Lighting Handbook. Lighting standards for watts/square metre for common buildings are listed in the ASHRAE 90.1 commercial building code, and the IES requirements are referenced. ASHRAE 90.1 is an IEC standard.
9 Efficacy - the performance measure for electric lamps Efficacy is measured in units of lumens per watt (Lu/W). This is not a measure of efficiency since it has units. Efficiency has no units, and is either expressed as a decimal number like 0.90, or is stated in percent, like 90 %.
10 Efficacies vary with type and size of lamps. A 100 watt incandescent lamp has about 17 lumens per watt A modern T8 lamp with electronic ballast has about 100 lumens per watt. To calculate the efficacy for a lamp that requires a ballast, you must add the ballast power to the lamp power to get the correct total wattage input. The higher the lumen per watt rating of a lamp the better -- meaning greater light output for a fixed wattage input.
11 Example A 60 watt incandescent lamp has an output of 1100 lumens. What is the efficacy? The efficacy equals 1100 lumens divided by 60 watts = 18.3 Lu/W (lumens/watt)
12 Example A fluorescent fixture contains two 40 watt lamps and a ballast that draws 20 watts. If each lamp produces 3000 lumens, what is the efficacy of the lamps and the fixture? Lumens total = = 6000 lumens Wattage total = = 100 watts Efficacy = 6000 lumens divided by 100 watts = 60 Lu/W
13 Efficacy of Light Sources Light Source Standard Incandescent Tungston Halogen Halogen Infrared Reflecting LED Compact Fluorescent 5-26 Watts Compact Fluorescent Watts Linear Fluorescent Mercury Vapor Compact Metal Halide Metal Halide High Pressure Sodium Low Pressure Sodium Lamp plus Ballast - Initial Lumens/Watt 180
14 Color temperature - another physical property of a lamp. It is measured in Kelvins, not degrees. The color temperature of a lamp varies from about 2600 to 2800 Kelvins for an incandescent lamp, to around 6500 K for a daylight lamp.
15 The color temperature of a lamp tells us what the light from the lamp looks like. A low color temperature like 2600 K means that the light from the lamp appears warm in color meaning it has a red, yellow or orange tint. A 4100 K lamp is called a cool white lamp, since it appears cool in color meaning that it produces stronger green, blue or violet colors.
16 Color Rendering Index (CRI) - Another property of lamps that is related to how we see different colors under its light. The CRI is a number between 0 and 100. The reference standard is a very special incandescent lamp at a lighting laboratory. The light output of this lamp sets the standard for CRI as 100. Users can find data on the CRI of lamps in catalog or product specifications.
17 Most incandescent lamps have CRIs in the range. The CRI is generally associated with the quality of lighting. The U.S. EPA Green Lights program rates CRI and lighting quality as follows: Excellent Good Fair 0 55 Poor CRI and the color temperature of a particular lamp determine how we see colors under that lamp.
18 For any color temperature, the higher the CRI, the more closely we see colors correctly.
19 Types of Lamps - Common types of lamps include: incandescent tungsten halogen (also incandescent) compact fluorescent full-size fluorescent mercury vapor metal halide high-pressure sodium low-pressure sodium LED
20 Ballasts - Except for incandescent lamps (including tungsten halogen lamps), all other lamps are discharge lamps that require a ballast to start and run the lamps. Older ballasts were large, heavy parts called coil and core or magnetic ballasts, because they contained a coil of wire wrapped around a heavy iron core. Newer ballasts are electronic, and are lighter, cooler, more efficient, and last longer.
21 A ballast usually does three things. It: 1. Conditions the lamp to start (usually meaning warming up the filaments) 2. Provides a big spike of high voltage to start the gas discharge process 3. Quickly inserts a current limiter into the circuit to reduce the lamp current down to a safe and sustainable value
23 Lumen Method Formula N = F1 x A Lu x LLF x Cu where N = the number of lamps required F1 = the required lux level at the task A = area of the room in square metre Lu = the lumen output per lamp Cu = the coefficient of utilization LLF = the combined light loss factor
24 Example of Lumen Method Find the number of lamps required to provide a uniform 500 lux on the working surface in a 12 x 10 metre room. Assume two 3000 lumen lamps each per fixture, and assume that LLF is 0.65 and CU is 70%. N = 500 x 120 = x 0.65 x 0.7 The number of two-lamp fixtures needed is 22.
25 Four Areas for Lighting Improvements Most of the cost savings from new retrofit lighting can be achieved in four areas: 1. Replace incandescent lamps with fluorescent, or compact fluorescent lamps 2. Upgrade fluorescent fixtures with improved components New T8s and T5s Electronic ballasts 3. Install lighting controls to minimize energy costs 4. Replace old exit lights with new LED models
26 Application of Compact Fluorescent Lights Task lights Downlights Wallwashers Outdoor fixtures Refrigerators and freezers Exit lights if you don t want LEDs Can now be dimmable
27 CFL Savings Example Replace a 75 watt incandescent lamp with an 18 watt self-ballasted CFL. The lamps are used 3000 hours per year. The CFL uses ¼ the energy of an incandescent The savings is = 57 watts The kwh savings for the lamp is 57 watts 3000 hours = 171 kwh The life of the CFL is 7500 hours. The life of a standard incandescent lamp is 750 hours. The CFL lasts ten times as long and saves additional $ on maintenance costs.
28 Upgrading Fluorescent Fixtures Improved fluorescent lamps T8, T5 and T5 HO Tri-phosphor lamps Higher efficacy and higher CRI Long life T8s Electronic ballasts All electronic vs. hybrid No flicker, no hum Induction lamps and ballasts --100,00 hours!
29 Lighting Savings Example Consider a room 7 by 25 metres with old 40 watt cool white T12 fluorescent lamps in four lamp fixtures or troffers and each troffer has two magnetic ballasts using 15 watts each. Our lighting retrofit project is to replace the old systems with T8 lamps and electronic ballasts. The room was very overlighted with the original design, and our retrofit will be to put three 32 watt T8 s in each fixture, together with two ballasts, having a total power requirement of 90 watts. Find the lighting energy savings if the lights are on 4000 hours each year.
30 Solution Old system 4 lamps 40 W 2 ballasts 15 W Fixture W = + = 190 lamp ballast W New system Fixture W = 90 W (given) 190 W 90 W Wattage savings = = fixture Energy savings 100 W fixture 100 W 16 fixtures 4000 h KWh / yr = = fixture yr 6,400 KWh yr
31 Lighting Power Density Lighting power density is another performance measure that is used in design and in Building Codes. Find the lighting power density for the example just given for the new system kw = (16 fixtures) x (90W/fixture) = 1440 watts The area of the space is 7 x 25 = 175 square metres The LPD = (1440 watts)/(175 square metres) = 8.23 watts/square metre
32 Lighting Retrofits Replacing older lights with newer, more efficient lights often offers a very attractive energy and cost saving project. Many older buildings and facilities still use 40-watt T12 cool-white fluorescent lamps, or 34-watt T12, low-wattage lamps, and magnetic ballasts. New T8 lamps with electronic ballasts are probably still the most popular choice for office and commercial retrofits. In new construction, T8 or T5 lamps with electronic ballasts may be used.
33 Fluorescent Upgrades From T12s with Magnetic Ballasts T8 (32 W) electronic ballasts Same light but less energy Multiple lamps per ballast option Tandem wiring option T8 (30 W) available now Very little lumen depreciation (95%) T5 (28 W) electronic ballasts Same light but least energy HID type retrofit option popular -- May need to use indirect lighting
34 Lighting Savings Calculations DS in kw = (kw old kw new ) ES in kwh = (kw old kw new ) (hours of use) kw old = (wattage of old lamp + wattage of old ballast) (number of lamps)/1000 kw new = (wattage of new lamp + wattage of new ballast) (number of lamps)/1000 Cost savings = Demand cost savings + Energy cost savings
35 Lighting Savings Example A 244,000 square foot high bay facility is presently lit with 800 twin 400 watt mercury vapor fixtures (455 watts per lamp including ballast). What are the annual savings of replacing the existing lighting system with 800 single 400- watt high-pressure sodium fixtures (465 watts per lamp including ballast)? Assume 8000 hours operation per year, an energy cost of $0.05 per kwh, and a demand cost of $6.00 per kw-month.
37 On/off switch Lighting Controls Timers and control systems (DDC) Solid-state dimmers Dimming electronic ballasts or bi-level ballasts Occupancy sensors Day lighting level sensors Daylight harvesting 40-60% savings compared to full artificial lighting Better productivity and attendance
38 Lighting controls Timers, dimmers and occupancy sensors can provide large savings by turning lights down when they are not needed at full light output levels, and turning them off when they are not needed at all. Occupancy sensors can detect heat using PIR (passive infrared radiation) technology, or detect sound using ultrasonic technology. Newer occupancy sensors are dual mode with both PIR and ultrasonic technology.
39 Daylight harvesting This used to be called daylighting; it is the use of sunlight to augment our artificial lighting system.
41 Comparison of exit sign alternatives Light Source Wattage Life Incandescent lamp to 8 months LEDs years CFLs to 2 years Electroluminescent years panels Photoluminescent years materials Cold cathode 5 10 years Source: E SOURCE
42 Lighting Audits Conduct a room-by-room lighting inventory Light fixtures Lamp types, size and numbers Levels of illumination Uses of task lighting Hours of operation Ballasts Use of occupancy sensors
43 Lighting Audit Checklist Data Form Area Lamp Type Lamp Wattage Light Level (lux) No. of fixtures Lamps per fixture Reflector use (Y/N) Usage Time Ballast info A/C (Y/N)
44 Lighting ECMs T12 Lamps Magnetic Ballasts Incandescent lamps Lighting Controls Color rendition Productivity & Safety T8 Lamps Electronic Ballasts CFL Check That They are Operating Properly Add If Not Present Lamp Change out Improve to Meet Facility Requirements
45 Exit Sign ECMs 2-40 Watt lamp style LED retrofit kit Cold cathode kit LED exit signs
46 Exit Sign Upgrades Source Wattage Life Replacement Cost Incandescent 40 8 months lamp(s) NA Low wattage incandescent Compact Fluorescent Light Emitting Diode Electroluminescent Self-luminous (tritium) 8 10 years light tube $30 (retrofit) years lamp(s) $30 (retrofit) $120 (new) years circuit board $45 (retrofit) $120 (new) 1 8+ years light panel $190 (new) years luminous tube $250 (new)
ENERGY EFFICIENT LIGHTING Prof. Suryanarayana y Doolla IIT Bombay Dept. of Energy Science & Engineering Content 2 Basics of Illumination Types of light source, lighting Comparison of commercial lamps Energy
Small Business Lighting Business Customer Information Opportunity ID: For a free lighting assessment, please contact the Small Business Lighting program at 1-877-287-2250. Company name Date submitted Billing
Design Guidelines for Energy Efficient Lighting Systems Thank you for your interest in energy efficiency! According to the US Department of Energy, 51% of the energy used in commercial buildings is consumed
Small Commercial Business Energy Audits Recognizing and addressing the special requirements of the small business market segment. Class 4 Class 4: Lighting Fundamentals Basic Lighting Technology Advanced
Business lighting guide Table of contents Advantages of energy-efficient lighting... Take Control & Save Business Lighting Program overview... Implementation and lighting audit walk-through... Introduction
Fluorescent T8 Fixtures with High Efficiency Electronic Ballasts Replacing T12 Fluorescent with Magnetic Ballast -- Rebate per fixture All 4 foot lamps and ballasts must be on Consortium for Energy Efficiency
Guide to new, energy-efficient lighting technologies for your business Commercial lighting systems are changing rapidly, with new or improved technologies continuously becoming available. Whether you re
Home lighting Bright ideas for energy savings Shedding light on new technologies Lighting is one of the most visible ways you use energy in your home. While a single light bulb doesn t use much energy,
Retrofit HID High Bay Fixtures to Long Life High Efficiency LED 2013 DyoCore Call us today for sales and pricing information: Toll Free: 877.849.6668 www.dyocore.com It is no hidden secret that LED bulbs
A Guide to Energy Efficient and Cost Effective Lighting This guide provides information on how specifiers and designers can improve the quality and cost effectiveness of lighting schemes through the use
Shedding Light on Unexpected Market Response to High Bay Retrofits Wendy Tobiasson and Bill Biesemeyer, KEMA Services, Inc. Steve Baab, ComEd/Exelon Wayne Dobberpuhl, Arizona Public Service Co. Mary Ann
$6.00 Volume 15, No. 3 Fall 2011 LicensedArchitect 2011 Chicago Architecture Conference - Tuesday, October 18 Accessibility Requirements for Hotels ALA Student Merit Winners CE Article - LED Illumination
Cree Edge and LEDway by Cree Compared to Induction Lamp Luminaires Executive Summary There are many excellent reasons to select a Cree lighting system over one based upon induction technology, even though
The Revolution in Warehouse Lighting: LEDs and Intelligent Lighting Systems SUMMARY In a standard warehouse, lighting electricity can represent 38% of total operating expenses; 15% in a refrigerated facility.
John J. White, PE, Business Unit Manager, Energy Solutions, Eaton and Council Member for Borough of Seven Fields, Pa. Improve your municipality s image with LED lighting paid from energy savings Executive
ENERGY SAVER Energy efficient lighting Technology report Second edition 2014 Published by: Office of Environment and Heritage Department of Premier and Cabinet 59-61 Goulburn Street, Sydney Australia Ph:
Dimming LFL Systems By: Shelli Sedlak, LC, Senior Specification Engineer Mike Smith, GE Lighting and Electrical Institute Specialist Introduction There are many myths and misunderstandings regarding dimming
C A S E S T U D I E S Commercial/Office Space Newmark Knight Frank Making -Efficiency Their Standard Orange Health Care Center Gets an -Efficiency Check-up 1 Long Wharf Drive in New Haven owned by Newmark
New Mexico Small Business Lighting LIGHTING RETROFIT REBATE For use with invoices dated on or after March 15, 2011 Business Customer Information Company name Date submitted Billing address City State ZIP
Lighting Retrofit Application for Business Customers 2015 A Cash Energy Efficiency Program brought to you by: Instructions for Use: For complete instructions, please refer to the Terms and Conditions on
1. I want to replace my fixture and put LED tubes in it. Do I get rebates for both the fixture and the tubes? No. This type of project qualifies for the LED tube rebate only. 2. Can I install any LED product
Pulse Start vs. Probe Start By Dick Erdmann GE Specification Engineer As we enter this new age of energy awareness, the lighting community has been at the forefront finding more and more ways to conserve
Application and Instructions SCE&G s EnergyWise for Your Business Program is designed to help nonresidential customers replace aging, inefficient equipment and systems with energy-efficient technologies.
Lighting for Schools James R. Benya, PE Benya Lighting Design December 2001 Lighting is and always has been an important factor in designing and operating schools. Until the 1950s, natural light predominated
Training programme on Energy Efficient technologies for climate change mitigation in Southeast Asia ENERGY EFFICIENT LIGHTING SYSTEM ( Industries, Public Utilities & Residential Buildings) Introduction
T8 Fluorescent Lamps Answers........................................................ Volume 1 Number 1 April 1993 Background Throughout the 1970s, manufacturers of fluorescent lamps introduced new products
Header Title Subheadline Electric Sign Energy Certification Service To California Energy Commission Title 24 Technical Requirements and Audit Instructions (ENVS) Electric Sign Energy Certification Service
Announcing... Realtime Distance Learning For Lighting-Involved Professionals The Association of Energy Engineers, in conjunction with the University of Wisconsin-Madison Engineering Professional Development
AEDG Implementation Recommendations: Interior Lighting Sample Layouts for Office Buildings The Advanced Energy Design Guide (AEDG) seeks to achieve 30 percent savings over Standard 90.1-1999. This guide
Troubleshooting LED Downlights From time to time issues arise with the performance of LED recessed lighting products after installation. Due to the newness of LED technology it can be difficult to diagnose
TECHNOLOGY SynJet: Low-Power Green Cooling Nuventix, Inc. 4301 Westbank Dr. Building A150 Phone: 512-382-8100 Fax: 512-382-8101 Email: email@example.com Introduction The realities of finite petroleum resources
Dealing with the Downlight: Australian Residential Lighting Discoveries, Challenges and Future Directions Jack Brown and Lloyd Harrington, Energy Efficient Strategies Steven Beletich, Beletich Associates
Flicker happens. But does it have to? Introduction Nearly all AC-powered traditional light sources exhibit some degree of periodic modulation or flicker. The effects of undesired flicker from artificial
ARTIFICIAL LIGHTING lecture notes Dr. Habil. András Majoros Figures, images and tables by Levente Filetóth Budapest University of Technology and Economics Faculty of Architecture Department of Building
Schools GUIDE TO ENERGY EFFICIENT ND COST EFFECTIVE LIGHTING This guide provides information on how to improve the effectiveness of lighting in school buildings by using energy efficient lighting technology
www.osram.com SubstiTUBE Advanced ST8A-0.6m-8.9W-840-HF Datasheet Innovative LED-lamp, easy and safe to use in ECG installations as direct retrofit. Energy saving potential of up to 35% by replacing 0.6
Save money, reduce energy use and earn incentives by improving the energy efficiency of your business. Georgia Power s Commercial Energy Efficiency Program makes incorporating energy-efficient improvements
RETROFIT LIGHTING & CONTROLS SOLUTIONS Automotive Dealerships The Challenge and the Opportunity There are over 17,000 automotive dealerships in North America and on average, they use up to 18% more energy
Solid-State Lighting Series Low / High Bay Datasheet Low/high bay lighting is typically used in industrial applications. They have the same features as high bay lighting but with a different sized enclosed
ENERGY SAVING TIPS IN DOMESTIC SECTOR LIGHTING SYSTEM 1. One of the best energy-saving devices in the light switch. Turn off lights when not required. 2. Fluorescent tube lights and CFLs convert electricity
COMBINING QUALITY DESIGN AND ENERGY EFFICIENCY FOR SMALL INDUSTRIAL FACILITIES Basics of Quality Lighting Economics of Energy Effective Lighting General Industrial Workspace Lighting Industrial Cleanrooms
Fact Sheet #3 Tips on Saving Energy in Your Business In this fact sheet you will discover: Quick and easy changes to save energy. Cost effective ways to reduce your heating, cooling, lighting and office
High Pressure Mercury E27 B Product Description Mixed Light lamps Product Features High-pressure mercury tube in series with a tungsten filament Runs on mains voltage without additional gear Combines a
With green technology at your service Led lighting products 3 years guarantee save up to 70% energy at the same time increasing luminosity! tisztaled.hu firstname.lastname@example.org Products list LED Tubes 3 LED
High performance industrial lighting 50% energy against traditional fittings Up to 75% energy saving with sensing Zero maintenance, no need to relamp IK10 rated durable construction Advanced LED lighting
Business Energy Rebates Application Business Energy Rebates make it easy and affordable for you to select energy efficient products for your business. and mail-in rebates are available for energy efficient
This questionnaire matches the one you can use to perform an online energy audit of your business. You complete the online questionnaire, or if you prefer, you can print this form and answer the questions
The Great Internet Light Bulb Book, Part I Incandescent including halogen light bulbs Copyright (C) 1996, 2000, 2005, 2006 Donald L. Klipstein (Jr) (email@example.com) Freely distributing copies of this entire
Benchmark Report January 2009 Performance of T12 and T8 Fluorescent Lamps and Troffers and LED Linear Replacement Lamps Prepared for the U.S. Department of Energy by Pacific Northwest National Laboratory
Moving Targets and Moving Markets in Commercial Lighting Mitchell Rosenberg, DNV KEMA Energy & Sustainability ABSTRACT This paper develops recommendations for changes in some of the most common features
HIGH-BAY / LOW-BAY LIGHTING NEW ALTERNATIVES TO H.I.D. New from SPI LIGHTING, an exciting addition to our family of fluorescent alternatives to traditional HID high-bay and low-bay lighting. The IPS Series
Proof of Concept - Solar Energy DG Distribution Warehouse This is for a proof of concept for a high efficiency renewable energy lighting system at a Distribution Center in Rochester, NY. This LEED gold-rated
Solid-State Lighting Series High / Low Bay Datasheet High / Low Bay lighting is typically used in industrial applications. They have the same features as high bay lighting but with a different sized enclosed
A NGuide a t i o n a l for G r i d Applicants a n d E v e r s o uand r c e Lighting Practitioners V4-20150202 Sustainable Office Design (SOD) is different than existing programs The new SOD Lighting Initiative
ECOPTIMO T8 Version 11.6 Features and Benefits Lifetime & Warranty Very high Energy Savings: More than 50% energy savings over traditional tubes Extremely bright High Ra-color Rendering Index Top Uniformity:
Xcel Energy s Commercial Industrial Energy Efficiency Programs Overview of Colorado Business Rebate Programs Trade Relation Managers Derek Shockley 303-294-2082 John.D.Shockley@XcelEnergy.com Commercial
5 Energy Efficiency Best Practice Guide Contents 1 Introduction 4 2 The business benefits of good lighting 5 2.1 Improved productivity 5 2.2 Improved safety 5 2.3 Improved colour rendering 5 2.4 Improved
GE Lighting ConstantColor CMH MR16 Reflector Ceramic Metal Halide Lamps W and 35W DATA SHEET Product information ConstantColor CMH lamps combine HPS technology (providing stability, efficiency & uniformity)
Rocky Mountain Power - State of Utah Price Summary - In Effect as of June 1, 016 Tariff Schedules Base Rate Schedule 195 Rate Schedule 94 1, Schedule 98 1, Schedule 193 1,3 Schedule 91 1 Schedule 1 - Residential
LIGHTING SOLUTIONS for Power Plants Power Plants need to operate efficiently on a consistent basis without sacrificing quality. WESCO understands the unique needs of these facilities and offers the most
GE Lighting GE ConstantColor CMH Precise MR16 2 & 35W DATA SHEE T TECHNOLOGY ConstantColor CMH lamps combine HPS technology (providing stability, efficiency & uniformity) and Metal Halide Technology (providing
Lighting Technologies Dishna Schwarz Elmar Dimpl George C. Bandlamudi September 2005 Information & Knowledge Management Technical Information Energy / Environment (E) Water / Sanitation (W) Agriculture
LBNL-3714E ERNEST ORLANDO LAWRENCE BERKELEY NATIONAL LABORATORY Managing Your Energy An ENERGY STAR Guide for Identifying Energy Savings in Manufacturing Plants Ernst Worrell Tana Angelini Eric Masanet
Energy Assessment Questionnaire Energy Assessment Questionnaire Page 2 of 11 Xcel Customer No.: First Name: Last Name: Company Name: Address: City State: Zip: Phone: Email Address: You may send me information
120W High Bay II Datasheet Solid-State Lighting Series Features : Solid State Lighting Technology Superior Light Quality Reduce CO₂ Emission Energy Saving(120W) Ecologically Friendly Long Life-Time IP65
CONSUMERS ENERGY BUSINESS SOLUTIONS PROGRAM 2015 Incentive Catalog HELPING MICHIGAN BUSINESSES SAVE ENERGY. THAT S OUR PROMISE. December 2014 Table of Contents About This Program 1 Variable Frequency Drives
Cat Work Lights Make time work for you with Cat Work Lights When you re working against the clock, Cat Work Lights help turn night into day and increase productivity of both machines and operators in a
Lighting Control in the Office Space Lutron Electronics Co., Inc. 2008 AIA/CES Program Registration This program is registered with the AIA/CES for continuing professional education. As such, it does not
LED Lighting Emergency LED Products The Philips Bodine BSL Driver Family ELI-S-20 Emergency Lighting Micro Inverter ELI-S-100 Dimming Inverter Philips Bodine emergency LED drivers answer the call for LED
Hello and Welcome to this presentation on LED Basics. In this presentation we will look at a few topics in semiconductor lighting such as light generation from a semiconductor material, LED chip technology,
SpaceBuild Specification Worksheet GLPHASE System The GLPHASE SpaceBuilder system is ideal for medium-sized spaces that require additional options such as expansion modules for more load types, touch screens,
CONSERVATION AND LIGHTING Light is essential for the examination and enjoyment of collection items. But in a museum light also means damage: dyes and pigments fade or change appearance and the materials
BOMA I n t e r n a t i o n a l 30 EASY WAYS TO SAVE ENERGY For Little or No Cost Energy efficiency is easy and doesn t require significant capital expenditures to make a big difference in your operating
Identify Ways to Save with Energy Audits Kristine Chalifoux Director of Management and Operations, SEDAC Mary Bentsen Education & Training Coordinator, SAIC, an Ameren Illinois ActOnEnergy partner Kristine
Preliminary Recommendations for Energy Savings For Galloway Township Municipal Facilities A preliminary assessment of the Galloway municipal facilities main building and post office building were conducted
LED tube 18W 1500mm Type: QLT1500GB (120 ) QLT1500GH (60 ) 1500MM/420LED/18W LED TUBE LIGHT. Main feature: -High brightness and long life,up to 50000hr; -70%-80%energy saving than conventional Flourescent
Solid-State Lighting Series High / Low Bay Datasheet High / Low Bay lighting is typically used in industrial applications. They have the same features as high LED4 solution of light in low/high ceiling
ENERGY STAR Program Requirements Product Specification for Lamps (Light Bulbs) Eligibility Criteria Version 1.0, DRAFT 4 Following is the fourth draft of Version 1.0 ENERGY STAR Product Specification for
LIGHTING INCENTIVE CATALOG 2015 SAVING ENERGY AND MONEY FOR WISCONSIN For more information, call 800.762.7077 or visit focusonenergy.com Focus on Energy, Wisconsin utilities statewide program for energy
Apples & Pears, a CELMA guiding paper: Why standardisation of performance criteria for LED luminaires is important Enabling like-for-like comparison of LED luminaire performance starts with published initial
Green Guide for Businesses Strategy: Energy Reduce Energy Use in New and Existing Businesses - In the United States buildings account for: o 72% of electricity consumption, o 39% of energy use, o 38% of
Energy'Saving,'Thermal'Comfort'and'Solar'Power'Information'Sheet' We ve prepared this information sheet to help you to minimise energy consumption and energy costs while maximising thermal comfort at home.
General Bulb Standard Ultra Bright 7 SMT LED Light-45859.....1 Standard Ultra Bright 6 Watt LED Light-78469.........1 Standard Ultra Bright Five 1 Watt LED Light-42522.....2 Side Firing LED Light-45376..
DuroSite TM High Bay Lighting LED White Lighting Brochure for Industrial Applications CE version Application: The first of its kind, the Dialight DuroSite TM LED High Bay luminaire was designed specifically
HOW TO CONDUCT ENERGY SAVINGS ANALYSIS IN A FACILITY VALUE ENGINEERING STUDY Benson Kwong, CVS, PE, CEM, LEED AP, CCE envergie consulting, LLC Biography Benson Kwong is an independent consultant providing
GE Lighting maximize GE energy-efficient T5 linear fluorescent systems 2 a bright way to improve efficiency Your business is valuable. And when workers have to take time out of the day to climb scaffolds