Power factor correction and harmonic filtering. Catalogue. Propivar capacitors and MV banks


 Herbert Barrett
 1 years ago
 Views:
Transcription
1 and harmonic filtering Catalogue 2007 Propivar capacitors and MV banks
2 Contents Overview 2 MV capacitor bank selection guide 2 Propivar capacitors 4 Insulation level 7.2 kv (20/60)50/60 Hz 6 Insulation level 12 kv (28/75)50/60 Hz 8 Insulation level 17.5 kv (38/95)50/60 Hz 9 Insulation level 24 kv (50/125)50/60 Hz 10 Insulation level 36 kv (70/170)50/60 Hz 11 MV capacitor banks 12 Fixed compensation 12 CP214 fixed capacitor bank 13 Insulation level 7.2 kv (20/60)  50/60 Hz 13 Standard type (slightly polluted network) 13 Insulation level 12 kv (28/75)  50/60 Hz 14 Standard type (slightly polluted network) 14 CP214 SAH fixed capacitor bank 15 Insulation level 7.2 kv (20/60)  50/60 Hz 15 SAH type (highly polluted network) 15 Insulation level 12 kv (28/75)  50/60 Hz 16 SAH type (highly polluted network) 16 CP227 fixed capacitor bank 17 Insulation level 7.2 kv (20/60)  50/60 Hz 17 Standard type (slightly polluted network) 17 Insulation level 12 kv (28/75)  50/60 Hz 18 Standard type (slightly polluted network) 18 Insulation level 17.5 kv (38/95)  50/60 Hz 19 Standard type (slightly polluted network) 19 Insulation level 24 kv (50/125)  50/60 Hz 20 Standard type (slightly polluted network) 20 Insulation level 36 kv (70/170)  50/60 Hz 21 Standard type (slightly polluted network) 21 MV capacitor banks 22 Automatic compensation 22 CP253 automatic capacitor bank 23 Insulation level 7.2 kv (20/60)  50/60 Hz 23 Standard type (slightly polluted network) 23 Insulation level 12 kv (28/75)  50/60 Hz 25 Standard type (slightly polluted network) 25 CP253SAH automatic capacitor bank 26 Insulation level 7.2 kv (20/60)  50/60 Hz 26 SAH type (highly polluted network) 26 Insulation level 12 kv (28/75)  50/60 Hz 28 SAH type (highly polluted network) 28 CP254 automatic capacitor bank 29 Insulation level 17.5 kv (38/95)  50/60 Hz 29 Standard type (slightly polluted network) 29 Insulation level 24 kv (50/125)  50/60 Hz 30 Standard type (slightly polluted network) 30 Insulation level 36 kv (70/170)  50/60 Hz 31 Standard type (slightly polluted network) 31
3 Overview 0 MV capacitor bank selection guide Step 1: basic data collection How to choose the right power factor correction capacitor bank? The recommended method consists of five successive steps Network characteristics: b voltage U (V) b network frequency f (50 or 60 Hz). Characteristics of the installation: b insulation voltage U insulation b rated power of the transformer Sn (kva) b transformer short circuit voltage Usc (%) b existing capacitor bank (Qc (kvar), type of capacitor bank, ). Operating conditions: b energy bills b measurements of power: P (kw) cos phi. Step 2: calculation of the reactive power Qc (kvar) DB The reactive power is determined either: b from the electricity bills, depending on the method of recording the consumption of kvar applied by the energy supplier b from the electrical data of the installation. The aim is: b not to pay for the consumption of reactive energy and to ensure optimum use of the transformers, cables and control and protection switchgear b to satisfy the standards currently in force: compliance with a minimum cos phi, energy quality standards. Step 3: choice of type of capacitor bank according to the harmonics The presence of nonlinear loads (variable speed drives, UPS, etc.) creates harmonic currents and voltages. The compensation equipment is chosen according to the value of these harmonics. b either the installation has no harmonics and there is no risk of resonance b either the installation has harmonics and/or there is a risk of resonance b in the absence of information about the installation and as a precautionary measure V Select a capacitor bank for a slightly polluted network (see selection table in step 5) V Select a capacitor bank for a highly polluted network (see selection table in step 5) V Select a capacitor bank for a highly polluted network (see selection table in step 5) Harmonic filtering To improve the quality of electrical power, Merlin Gerin provides a range of compensation and filtering solutions. The HV or MV filters that absorb the harmonic currents in the electrical installation consist mainly of capacitors associated with filtering reactors. They are used to: b bring the percentage of distortion back to the acceptable values recommended by the energy distributors b and also compensate for the reactive power. Schneider Electric can undertake compensation and filtering analyses.
4 Overview 0 MV capacitor bank selection guide (cont.) Step 4: choice of type of compensation Global compensation The type of compensation should be chosen by taking into account the calculated reactive power Qc (kvar) and the apparent power Sn (MVA) of the upstream transformer. Qc/Sn < 15% the reactive power of the capacitor banks is constant and they are started up or shut down when a predetermined kvar value is reached. It is an on/off type of operation. V Fixed compensation Qc/Sn > 15% the customer specifies automatic startup or shutdown for the capacitor bank (controlled by Varlogic varmetric relay). The reactive power of the capacitor banks is split into steps with the possibility of starting or stopping more or fewer steps. The reactive power corresponds to the change in load requirements V Automatic compensation Motor compensation b if there is no risk of selfexcitation V The capacitor bank will be connected in parallel with the motor b if there is a risk of selfexcitation. V But it is only possible to connect to the motor terminals, the capacitor bank will be connected to the busbar independently of the motor. Step 5: selection table The recommended choice is based on the network insulation voltage, network harmonic pollution level and on the type of compensation. b if the power of the capacitor bank to be installed is less than 600 kvar b if the power of the capacitor bank to be installed u 600 kvar. V A low voltage solution is recommended V See the following table. Insulation level 7.2 kv 12 kv 17.5 kv 24 kv 36 kv Slightly polluted network Fixed CP214 CP214 CP227 CP227 CP227 CP227 CP227 Auto CP253 CP253 CP254 CP254 CP254 Highly polluted network Fixed CP214 SAH CP214 SAH Auto CP253 SAH CP253 SAH CP227 SAH and CP254 SAH as a specific order.
5 Propivar capacitors E The Propivar capacitors are used to compensate reactive power on medium and high voltage networks. Singlephase Propivar capacitor. Presentation A Propivar medium voltage capacitor is a steel case or tank provided with resin insulators. The tank comprises an assembly of capacitor elements having a maximum permissible rated voltage of 2250 V. When connected in seriesparallel groups, they provide high power units for elevated system voltages. There are two types of capacitors: b with internal fuses (singlephase capacitor) b without internal fuses (threephase or singlephase capacitor). Each capacitor is normally provided with discharge resistors to bring the residual voltage down to 75 V 10 minutes after the capacitor has been switched off. If requested, the capacitors can be supplied without discharge resistors. Construction The Propivar capacitors are composed of elements which include: b aluminium foil electrodes b a dielectric liquid with no PCB or chlorine and a polypropylene film. Compliance with standards The Propivar capacitor complies with standard NF C and with the following standards: b IEC 60871, 1 and 2 b BS 1650 b VDE 0560 b C222 N 190M1985 b NEMA CP1. Capacitors with internal fuses comply with the following standards: NF C , IEC Protection by internal fuse Propivar capacitors can be supplied with internal protection: each element or unit capacitor is equipped with a fuse. In the event of a breakdown of an element, the element is disconnected and isolated. Breakdown of a unit capacity may occur: b when capacitor voltage is close to its maximum amplitude. In this case, it is the power stored in the capacitances of the parallel elements which guarantees a current sufficient to rupture the internal fuse (fig. 1) b when capacitor voltage is close to zero. This current ensures breaking of the internal fuse (fig. 2). Advantages of this protection type: b instantaneous disconnection of the shortcircuiting element b lifetime of the capacitor b reduction in material costs and maintenance b continuity of service is ensured b possiblity of programming site maintenance. E14445B E14445A Propivar capacitor with internal fuses, composed of 4 groups connected in series, each group comprising 12 elements connected in parallel. Fig. 1 Fig. 2 Main characteristics The exceptional life of Propivar capacitors is due to their temperature withstand, small temperature rise, chemical stability and overvoltage and overcurrent withstand. Temperature withstand These capacitors can be put into service at low temperatures without any special precautions being taken. At higher ambient temperatures, the temperature rise is very low, so they can be operated without any risk of modifying the insulation characteristics of the dielectric. Chemical stability Transient overvoltages in circuits and partial discharge levels in tanks cause accelerated ageing of capacitors. The exceptional life of Propivar capacitors is closely connected with the intrinsic properties of the dielectric liquid: b very high chemical stability b high absorption capacity for gases generated during partial discharges b very high dielectric strength. Overvoltage and overcurrent withstand The capacitors can accept: b an overvoltage of 1.10 Un for 12 hours a day b a power frequency overvoltage of 1.15 Un for 30 minutes a day b a permanent overcurrent of 1.3 In. The withstand of capacitors is verified by: v cycles at an overvoltage level of 2.25 Un (cycle duration 1 s) v ageing tests at 1.4 Un. 4
6 Propivar capacitors0 Insulating voltage of the Propivar capacitors in accordance with IEC and 2 standard in the majority of european and several other countries: Highest voltage for equipment Um kv Insulation level Rms kv, 50 Hz1 mn Basic impulse level (BIL) kv, 1.2/50 µs In accordance with NEMA CP1 standard based on current practice in some countries of North America and others: Highest voltage for equipment Um kv Insulation level Rms kv, 50 Hz1 mn Basic impulse level (BIL) kv, 1.2/50 µs Environmental protection / biodegradability Propivar capacitor contains a dielectric liquid with no PCB or chlorine. Other characteristics Service frequency 50 Hz  (available in 60 Hz, please consult us) Temperature range 25 to +45 C Average loss factor at 20 C after stabilisation Maximum rated single phase capacitors reactive power (1) 600 kvar three phase capacitors 450 kvar 0.16 W/kvar with internal fuses 0.12 W/kvar without internal fuses Capacitance value tolerance 5, +15 % Capacitance variation DC/C / C Connection to resin insulators for cables with a section y 50 mm 2 Tank welded steel Thickness 1.5 mm Colour Grey RAL 7038 Anticorrosion treatment Fixing system 2 perforated brackets for M10 screw (1) Other reactive powers, on request. 5
7 Propivar capacitors Insulation level 7.2 kv (20/60) 50/60 Hz Three phase capacitors DB Network voltage (V) Capacitor voltage (V) (H x L x D / b / H2) 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 300 x 347 x 190 / 135 / R 300 x 347 x 190 / 135 / R 400 x 347 x 190 / 135 / R 500 x 347 x 190 / 135 / R 500 x 347 x 190 / 135 / R 600 x 347 x 190 / 135 / R 700 x 347 x 190 / 135 / R D Three phase capacitors Threephase Propivar capacitor. Network voltage (V) Capacitor voltage (V) (H x L x D / b / H2) 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 300 x 347 x 190 / 135 / R 300 x 347 x 190 / 135 / R 400 x 347 x 190 / 135 / R 500 x 347 x 190 / 135 / R 810 x 347 x 165 / 135 / R 700 x 347 x 190 / 135 / R 700 x 347 x 190 / 135 / R 810 x 347 x 190 / 135 / R 810 x 347 x 190 / 135 / R Options Set of 3 clamps for delta connexion Set of 3 clamps for star connexion R R
8 Propivar capacitors Insulation level 7.2 kv (20/60) 50/60 Hz Single phase capacitors with internal fuses DB Network voltage (V) Capacitor voltage (V) (H x L x D / b / H2) 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 400 x 347 x 165 / 233 / R 400 x 347 x 190 / 233 / R 500 x 347 x 190 / 233 / R 500 x 347 x 190 / 233 / R 600 x 347 x 190 / 233 / R 700 x 347 x 190 / 233 / R D Singlephase Propivar capacitor. Single phase capacitors without internal fuses Network voltage (V) Capacitor voltage (V) (H x L x D / b / H2) 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 300 x 347 x 190 / 233 / R 300 x 347 x 190 / 233 / R 400 x 347 x 190 / 233 / R 400 x 347 x 190 / 233 / R 500 x 347 x 190 / 233 / R 600 x 347 x 190 / 233 / R Options Set of 2 clamps for delta connexion Set of 2 clamps for star connexion R R 7
9 Propivar capacitors Insulation level 12 kv (28/75) 50/60 Hz Three phase capacitors DB Network voltage (V) Capacitor voltage (V) (H x L x D / b / H2) 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 300 x 347 x 190 / 233 / R 400 x 347 x 190 / 233 / R 500 x 347 x 190 / 233 / R 600 x 347 x 190 / 233 / R 600 x 347 x 190 / 233 / R 700 x 347 x 190 / 233 / R 810 x 347 x 190 / 233 / R D Threephase Propivar capacitor. Options Set of 3 clamps for delta connexion Set of 3 clamps for star connexion R R Single phase capacitors with internal fuses DB Network voltage (V) Capacitor voltage (V) (H x L x P / b / H2) 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 400 x 347 x 165 / 233 / R 500 x 347 x 180 / 233 / R 600 x 347 x 180 / 233 / R 700 x 347 x 190 / 233 / R 810 x 347 x 190 / 233 / R 1000 x 347 x 190 / 233 / R D Singlephase Propivar capacitor. Single phase capacitors without internal fuses Network voltage (V) Capacitor voltage (V) (H x L x P / b / H2) 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 300 x 347 x 190 / 233 / R 300 x 347 x 190 / 233 / R 400 x 347 x 190 / 233 / R 500 x 347 x 190 / 233 / R 600 x 347 x 190 / 233 / R 700 x 347 x 190 / 233 / R 900 x 347 x 190 / 233 / R Options Set of 2 clamps for delta connexion Set of 2 clamps for star connexion R R
10 Propivar capacitors Insulation level 17.5 kv (38/95) 50/60 Hz Single phase capacitors with internal fuses DB Network voltage (V) Capacitor voltage (V) (H x L x D / b / H2) 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 400 x 347 x 165 / 282 / R 500 x 347 x 190 / 282 / R 600 x 347 x 190 / 282 / R 700 x 347 x 190 / 282 / R 900 x 347 x 190 / 282 / R 1000 x 347 x 190 / 282 / R D Singlephase Propivar capacitor. Single phase capacitors without internal fuses Network voltage (V) Capacitor voltage (V) (H x L x D / b / H2) 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 300 x 347 x 190 / 282 / R 300 x 347 x 190 / 282 / R 400 x 347 x 190 / 282 / R 400 x 347 x 190 / 282 / R 500 x 347 x 190 / 282 / R 600 x 347 x 190 / 282 / R 810 x 347 x 190 / 282 / R 900 x 347 x 190 / 282 / R Options Set of 2 clamps for delta connexion Set of 2 clamps for star connexion R R
11 Propivar capacitors Insulation level 24 kv (50/125) 50/60 Hz Single phase capacitors with internal fuses DB Network voltage (V) Capacitor voltage (V) (H x L x D / b / H2) 50 Hz 60 Hz 50 Hz 60 Hz 810 x 347 x 165 / 282 / R 810 x 347 x 165 / 282 / R 810 x 347 x 190 / 282 / R 1000 x 347 x 190 / 282 / R D Singlephase Propivar capacitor. Single phase capacitors without internal fuses Network voltage (V) Capacitor voltage (V) (H x L x D / b / H2) 50 Hz 60 Hz 50 Hz 60 Hz 300 x 347 x 190 / 282 / R 400 x 347 x 190 / 282 / R 400 x 347 x 190 / 282 / R 500 x 347 x 190 / 282 / R 600 x 347 x 190 / 282 / R 700 x 347 x 190 / 282 / R 900 x 347 x 190 / 282 / R Options Set of 2 clamps for delta connexion Set of 2 clamps for star connexion R R 10
12 Propivar capacitors Insulation level 36 kv (70/170) 50/60 Hz Single phase capacitors with internal fuses DB Network voltage (V) Ref Capacitor voltage (V) (H x L x D / b / H2) 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 600 x 347 x 190 / 377 / R 700 x 347 x 190 / 377 / R 810 x 347 x 190 / 377 / R 1000 x 347 x 190 / 377 / R D Singlephase Propivar capacitor. Single phase capacitors without internal fuses Network voltage (V) Capacitor voltage (V) (H x L x D / b / H2) 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 300 x 347 x 190 / 377 / R 400 x 347 x 190 / 377 / R 500 x 347 x 190 / 377 / R 500 x 347 x 190 / 377 / R 600 x 347 x 190 / 377 / R 810 x 347 x 190 / 377 / R 1000 x 347 x 190 / 377 / R Options Set of 2 clamps for delta connexion Set of 2 clamps for star connexion R R 11
13 MV capacitor banks Fixed compensation Schneider Electric can supply all types of capacitor banks, whatever the: b complexity of the network in the presence or absence of harmonics b demand for reactive power b nominal insulation voltages. To make it easier to choose the right capacitor banks, they are supplied: b CP214 fixed capacitor banks b CP227 fixed capacitor banks. CP214 and CP227 fixed capacitor banks Fixed capacitor banks CP214 CP227 Rated voltage y 12 kv y 36 kv Reactive power range y 960 kvar y 5760 kvar Example of application Individual motor compensation Global installation compensation Composition Protection HBC fuse CT and relay unbalance Switching current limitation by: 3 reactors 3 reactors Connection Delta Double star Type of capacitor bank CP214 fixed capacitor bank DB CP227 fixed capacitor bank DB Insulation voltage: Technical data The capacitor banks have the following common characteristics: b environmentally compatible Propivar capacitors with no PCB or chlorine dielectric liquid b service frequency: 50 Hz (available in 60 Hz, please consult us) b maximum temperature: 45 C b average temperature over 24 hours: 35 C b installation altitude y 1000 m b IP23 cubicle mounted b incoming cables from below with power cables connected to the copper pads b optional: outdoor type, fuse blow indicator, fast discharge reactors, lockable door. 12
14 CP214 fixed capacitor bank Insulation level 7.2 kv (20/60)  50/60 Hz Standard type (slightly polluted network) DB CP214. Network voltage (V) Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz (L x D x H) 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R DB Network voltage (V) Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz (L x D x H) 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R CP214 options Melted fuse indication device Quick discharge coils: kv (set of 2) Door with lock for indoor type enclosure Outdoor type Door with lock for outdoor type enclosure Double roof for outdoor type enclosure R R R R R R 13
15 CP214 fixed capacitor bank Insulation level 12 kv (28/75)  50/60 Hz Standard type (slightly polluted network) DB DB CP214. D Network voltage (V) Dimensions 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz (mm) (L x D x H) 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R 1180 x 905 x R CP214 options Melted fuse indication device Quick discharge coils: kv (set of 2) Door with lock for indoor type enclosure Outdoor type Door with lock for outdoor type enclosure Double roof for outdoor type enclosure R R R R R R 14
16 CP214 SAH fixed capacitor bank Insulation level 7.2 kv (20/60)  50/60 Hz SAH type (highly polluted network) DB DB CP214 SAH. Network voltage (V) Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz (L x D x H) 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R Network voltage (V) Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz (L x D x H) 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R CP214 SAH options Melted fuse indication device Quick discharge coils: kv (set of 2) Door with lock for indoor type enclosure Outdoor type Door with lock for outdoor type enclosure Double roof for outdoor type enclosure R R R R R R 15
17 CP214 SAH fixed capacitor bank Insulation level 12 kv (28/75)  50/60 Hz SAH type (highly polluted network) DB DB CP214 SAH. Network voltage (V) Réf. 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz (L x D x H) 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R 2000 x 1100 x R CP214 SAH options Melted fuse indication device Quick discharge coils: kv (set of 2) Door with lock for indoor type enclosure Outdoor type Door with lock for outdoor type enclosure Double roof for outdoor type enclosure Réf R R R R R R 16
18 CP227 fixed capacitor bank Insulation level 7.2 kv (20/60)  50/60 Hz Standard type (slightly polluted network) DB Network voltage (V) Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz (L x D x H) 1400 x 1400 x R 1400 x 1400 x R 1400 x 1400 x R CP227. CP227 options Unbalance protection relay (separately delivered) Quick discharge coils: kv (set of 2) Door with lock for indoor type enclosure Outdoor type Door with lock for outdoor type enclosure R R R R R DB
19 CP227 fixed capacitor bank Insulation level 12 kv (28/75)  50/60 Hz Standard type (slightly polluted network) DB Network voltage (V) Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz (L x D x H) 1400 x 1400 x 2000 (1) R (1) 1400 x 1400 x 2000 (1) R (1) 1400 x 1400 x 2000 (1) R (1) 1900 x 1400 x 2000 (2) R (2) 1900 x 1400 x 2000 (2) R (2) 1900 x 1400 x 2000 (2) R (2) (1) 6C: 6 capacitors. (2) 12C: 12 capacitors. DB CP227. CP227 options Unbalance protection relay (separately delivered) Quick discharge coils: kv (set of 2) Door with lock for indoor type enclosure Outdoor type CP2276C Outdoor type CP22712C Door with lock for outdoor type enclosure R R R R R R 18
20 CP227 fixed capacitor bank Insulation level 17.5 kv (38/95)  50/60 Hz Standard type (slightly polluted network) DB CP227. Network voltage (V) (L x D x H) 50 Hz 60 Hz 50 Hz 60 Hz 1400 x 1400 x 2000 (1) R (1) 1400 x 1400 x 2000 (1) R (1) 1400 x 1400 x 2000 (1) R (1) 1400 x 1400 x 2000 (1) R (1) 1400 x 1400 x 2000 (1) R (1) 1400 x 1400 x 2000 (1) R (1) 1400 x 1400 x 2000 (1) R (1) 1900 x 1400 x 2000 (2) R (2) 1900 x 1400 x 2000 (2) R (2) 1900 x 1400 x 2000 (2) R (2) 1900 x 1400 x 2000 (2) R (2) 1900 x 1400 x 2000 (2) R (2) (1) 6C: 6 capacitors. (2) 12C: 12 capacitors. DB CP227 options Unbalance protection relay (separately delivered) Quick discharge coils: kv (set of 2) Door with lock for indoor type enclosure Outdoor type CP2276C Outdoor type CP22712C Door with lock for outdoor type enclosure R R R R R R 19
21 CP227 fixed capacitor bank Insulation level 24 kv (50/125)  50/60 Hz Standard type (slightly polluted network) DB DB CP227. Network voltage (V) (L x D x H) 50 Hz 60 Hz 50 Hz 60 Hz 1400 x 1400 x 2000 (1) R (1) 1400 x 1400 x 2000 (1) R (1) 1400 x 1400 x 2000 (1) R (1) 1400 x 1400 x 2000 (1) R (1) 1400 x 1400 x 2000 (1) R (1) 1400 x 1400 x 2000 (1) R (1) 1400 x 1400 x 2000 (1) R (1) 1900 x 1400 x 2000 (2) R (2) 1900 x 1400 x 2000 (2) R (2) 1900 x 1400 x 2000 (2) R (2) 1900 x 1400 x 2000 (2) R (2) 1900 x 1400 x 2000 (2) R (2) 1900 x 1400 x 2000 (2) R (2) (1) 6C: 6 capacitors. (2) 12C: 12 capacitors. CP227 options Unbalance protection relay (separately delivered) Quick discharge coils: kv (set of 2) Door with lock for indoor type enclosure Outdoor type CP2276C Outdoor type CP22712C Door with lock for outdoor type enclosure R R R R R R 20
22 CP227 fixed capacitor bank Insulation level 36 kv (70/170)  50/60 Hz Standard type (slightly polluted network) DB Network voltage (V) (L x D x H) 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 2500 x 2100 x R 2500 x 2100 x R 2500 x 2100 x R 2500 x 2100 x R 2500 x 2100 x R 2500 x 2100 x R 2500 x 2100 x R 2500 x 2100 x R DB CP227. CP227 options Unbalance protection relay (separately delivered) Door with lock for indoor type enclosure Outdoor type Door with lock for outdoor type enclosure R R R R 21
23 MV capacitor banks Automatic compensation Schneider Electric can supply all types of capacitor banks, whatever the: b complexity of the network in the presence or absence of harmonics b demand for reactive power b nominal insulation voltages. To make it easier to choose the right capacitor banks, they are supplied: b CP253 automatic capacitor banks b CP254 automatic capacitor banks. CP253 and CP254 automatic capacitor banks Type of capacitor bank CP253 CP254 Rated voltage y 12 kv y 36 kv Reactive power range y 4500 kvar y 5760 kvar Example of application Global installation compensation Energy distribution substation compensation Composition Protection HBC fuse Unbalance CT and relay Switching device Rollarc contactor SF1 circuit breaker Switching current limitation via: 3 reactors 3 reactors Regulation Varlogic varmetric controller Varlogic varmetric controller Connection Delta Double star Type of capacitor bank CP253 automatic capacitor bank CP254 automatic capacitor bank DB DB Insulation voltage: Technical data The capacitor banks have the following common characteristics: b environmentally compatible Propivar capacitors with no PCB or chlorine dielectric liquid b service frequency: 50 Hz (available in 60 Hz, please consult us) b maximum temperature: 40 C b average temperature over 24 hours: 35 C b installation altitude y 1000 m b IP23 cubicle mounted b incoming cables from below with power cables connected to the copper pads b optional: outdoor type, fuse blow indicator, fast discharge reactors, lockable door. 22
24 CP253 automatic capacitor bank Insulation level 7.2 kv (20/60)  50/60 Hz Standard type (slightly polluted network) DB DB CP253. L Network voltage (V) Dimensions 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz (mm) (L x D x H) 1 stage 1500 x 1600 x R 1500 x 1600 x R 1500 x 1600 x R 1500 x 1600 x R 1500 x 1600 x R 1500 x 1600 x R 1500 x 1600 x R 2 stages 2600 x 1600 x R 2600 x 1600 x R 2600 x 1600 x R 2600 x 1600 x R 2600 x 1600 x R 2600 x 1600 x R 2600 x 1600 x R 2600 x 1600 x R 2600 x 1600 x R 2600 x 1600 x R 2600 x 1600 x R 3 stages 3700 x 1600 x R 3700 x 1600 x R 3700 x 1600 x R 3700 x 1600 x R 3700 x 1600 x R 3700 x 1600 x R 3700 x 1600 x R 3700 x 1600 x R 3700 x 1600 x R 3700 x 1600 x R 3700 x 1600 x R 3700 x 1600 x R 4 stages 4800 x 1600 x R 4800 x 1600 x R 4800 x 1600 x R 4800 x 1600 x R 4800 x 1600 x R 4800 x 1600 x R 4800 x 1600 x R 5 stages 5900 x 1600 x R 5900 x 1600 x R CP253 options Quick discharge coils: kv (set of 2) n x R Door with lock for indoor type enclosure n x R Outdoor type n x R Door with lock for outdoor type enclosure n x R Control and protection box, for one (1) stage R Local manual control switch, for one (1) stage R Control and protection box, for two (2) stages R Local manual control switch, for two (2) stages R Control and protection box, for three (3) stages R Local manual control switch, for three (3) stages R Control and protection box, for four (4) stages R Local manual control switch, for four (4) stages R Control and protection box, for five (5) stages R Local manual control switch, for five (5) stages R n is the quantity of steps required. 23
25 CP253 automatic capacitor bank Insulation level 7.2 kv (20/60)  50/60 Hz Standard type (slightly polluted network) DB DB CP253. L Network voltage (V) Dimensions 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz (mm) (L x D x H) 1 stage 1350 x 1350 x R 1350 x 1350 x R 1350 x 1350 x R 1350 x 1350 x R 1350 x 1350 x R 1350 x 1350 x R 1350 x 1350 x R 2 stages 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 3 stages 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 4 stages 3650 x 1350 x R 3650 x 1350 x R 3650 x 1350 x R 3650 x 1350 x R 3650 x 1350 x R 3650 x 1350 x R 3650 x 1350 x R 5 stages 4600 x 1350 x R 4600 x 1350 x R CP253 options Quick discharge coils: kv (set of 2) n x R Door with lock for indoor type enclosure n x R Outdoor type n x R Door with lock for outdoor type enclosure n x R Control and protection box, for one (1) stage R Local manual control switch, for one (1) stage R Control and protection box, for two (2) stages R Local manual control switch, for two (2) stages R Control and protection box, for three (3) stages R Local manual control switch, for three (3) stages R Control and protection box, for four (4) stages R Local manual control switch, for four (4) stages R Control and protection box, for five (5) stages R Local manual control switch, for five (5) stages R n is the quantity of steps required. 24
26 CP253 automatic capacitor bank Insulation level 12 kv (28/75)  50/60 Hz Standard type (slightly polluted network) DB DB CP253. L Network voltage (V) Dimensions 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz (mm) (L x D x H) 1 stage 1350 x 1350 x R 1350 x 1350 x R 1350 x 1350 x R 1350 x 1350 x R 1350 x 1350 x R 1350 x 1350 x R 2 stages 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 2050 x 1350 x R 3 stages 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 2950 x 1350 x R 4 stages 3650 x 1350 x R 3650 x 1350 x R 3650 x 1350 x R 3650 x 1350 x R 3650 x 1350 x R 3650 x 1350 x R 3650 x 1350 x R 5 stages 4600 x 1350 x R 4600 x 1350 x R 4600 x 1350 x R 4600 x 1350 x R 4600 x 1350 x R CP253 options Quick discharge coils: kv (set of 2) n x R Door with lock for indoor type enclosure n x R Outdoor type n x R Door with lock for outdoor type enclosure n x R Control and protection box, for one (1) stage R Local manual control switch, for one (1) stage R Control and protection box, for two (2) stages R Local manual control switch, for two (2) stages R Control and protection box, for three (3) stages R Local manual control switch, for three (3) stages R Control and protection box, for four (4) stages R Local manual control switch, for four (4) stages R Control and protection box, for five (5) stages R Local manual control switch, for five (5) stages R n is the quantity of steps required. 25
27 CP253SAH automatic capacitor bank Insulation level 7.2 kv (20/60)  50/60 Hz SAH type (highly polluted network) DB DB CP253 SAH. L Network voltage (V) Dimensions 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz 50 Hz 60 Hz (mm) (L x D x H) 1 stage 1500 x 2400 x R 1500 x 2400 x R 1500 x 2400 x R 1500 x 2400 x R 1500 x 2400 x R 1500 x 2400 x R 1500 x 2400 x R 2 stages 2600 x 2400 x R 2600 x 2400 x R 2600 x 2400 x R 2600 x 2400 x R 2600 x 2400 x R 2600 x 2400 x R 2600 x 2400 x R 2600 x 2400 x R 2600 x 2400 x R 2600 x 2400 x R 2600 x 2400 x R 3 stages 3700 x 2400 x R 3700 x 2400 x R 3700 x 2400 x R 3700 x 2400 x R 3700 x 2400 x R 3700 x 2400 x R 3700 x 2400 x R 3700 x 2400 x R 3700 x 2400 x R 3700 x 2400 x R 3700 x 2400 x R 3700 x 2400 x R 4 stages 4800 x 2400 x R 4800 x 2400 x R 4800 x 2400 x R 4800 x 2400 x R 4800 x 2400 x R 4800 x 2400 x R 4800 x 2400 x R 5 stages 5900 x 2400 x R 5900 x 2400 x R CP253 SAH options Quick discharge coils: kv (set of 2) n x R Door with lock for indoor type enclosure n x R Outdoor type n x R Door with lock for outdoor type enclosure n x R Control and protection box, for one (1) stage R Local manual control switch, for one (1) stage R Control and protection box, for two (2) stages R Local manual control switch, for two (2) stages R Control and protection box, for three (3) stages R Local manual control switch, for three (3) stages R Control and protection box, for four (4) stages R Local manual control switch, for four (4) stages R Control and protection box, for five (5) stages R Local manual control switch, for five (5) stages R n is the quantity of steps required. 26
Capacitors and banks 50 Hz network 0 400/415 V network voltage Varpact Classic power factor correction modules
Varpact Classic power factor correction modules PB10197268 PB10197568 Varpact power factor correction module form a prewired automatic compensation subassembly designed for fixing in standalone cubicles
More informationPower factor correction and harmonic filtering. Catalogue Rectimat 2 Automatic capacitor banks
Catalogue 2005 Automatic capacitor banks Contents 0 Power factor correction 2 Power factor equipment selection guide 3 General technical data 4 Capacitors and banks 50 z 6 230 V network voltage 6 400 V
More informationProduct brochure. ABBACUS Metal Enclosed Capacitor Banks The ABB comprehensive solution for low voltage automatic power factor correction
Product brochure ABBACUS Metal Enclosed Capacitor Banks The ABB comprehensive solution for low voltage automatic power factor correction ABB LV capacitor banks The most comprehensive solution for automatic
More informationPower factor correction and harmonic filtering. Rectimat 2 Automatic capacitor banks. Catalogue. Building a New Electric World
Catalogue 2002 Automatic capacitor banks Building a New Electric World 0Contents Power factor correction 2 Power factor equipment selection guide 3 General technical data 4 Capacitors and banks 50 z 6
More informationDYNACOMP. The topclass reactive power compensator
DYNACOMP The topclass reactive power compensator Dynacomp vs Electromechanical switching of capacitors Electromechanical switching of capacitors Transients at switching Conventional banks with contactors
More informationLow Voltage Capacitor LVCP. The new choice for Power Factor Correction
Low Voltage Capacitor LVCP The new choice for Power Factor Correction LVCP : the new choice for Power Factor Correction The LVCP is a compact and powerful capacitor. It offers high modularity, unmatched
More informationMEDIUM AND HIGH VOLTAGE CAPACITORS, CAPACITOR BANKS AND SYSTEMS
MEDIUM AND HIGH VOLTAGE CAPACITORS, CAPACITOR BANKS AND SYSTEMS Meher Capacitors offers reliable and innovative products and solutions in the fields of Reactive Power Compensation, Power Quality and Energy
More information7. Reactive energy compensation
593 7. Reactive energy compensation 594 7. REACTIVE ENERGY COMPENSATION Reactive energy compensation is an important element for reducing the electricity bill and improving the quality of the electrical
More informationMEDIUM AND HIGH VOLTAGE HARMONIC FILTERS & CAPACITOR BANKS
Elements of a Quality Power System MEDIUM AND HIGH VOLTAGE HARMONIC FILTERS & CAPACITOR BANKS Agenda An overview of Transmission and Distribution system equipment for Power Factor Improvement and Harmonic
More informationCLASS 5840 REACTIVAR Medium Voltage Power Factor Capacitors Fixed: Fused and Unfused
CLASS 5840 REACTIVAR Medium Voltage Power Factor Capacitors Fixed: Fused and Unfused The REACTIVAR Medium Voltage Fixed Power Factor Correction Capacitors from SQUARE D are constructed with environmentally
More informationPower Factor Correction DeltaCap MKD Capacitors for Power Quality Solutions
Product Brief 2011 Power Factor Correction DeltaCap MKD Capacitors for Power Quality Solutions Based on the wellproven MKP technology with stacked windings, DeltaCap capacitors are especially developed
More informationMV POWER CAPACITORS AND BANKS. All film dielectric MV Power Capacitors QUALITY MADE IN ITALY
2014 MV POWER CAPACITORS AND BANKS BIORIPHASO TF All film dielectric MV Power Capacitors QUALITY MADE IN ITALY Index Icar: Products and solutions 1 ICAR Quality System 3 Medium and High Voltage Solutions
More informationPower factor correction capacitors. Manufacturers and suppliers of the Eaton capacitors system.
Power factor correction capacitors Manufacturers and suppliers of the Eaton capacitors system. Automotive Powering business worldwide Aerospace Eaton delivers the power inside hundreds of products that
More informationSURGE PROTECTIVE DEVICES
SURGE PROTECTIVE DEVICES 1. INTRODUCTION In order to ensure safety of people, protection of equipment and, to a certain extent, continuity of supply, insulation coordination aims at reducing the likelihood
More informationLow Voltage Compensation and Filtering Products
Low Voltage Compensation and Filtering Products Low voltage products for better power quality and improved network efficiency. Alstom Grid compensation equipment helps customers improve performance through
More informationPower Capacitor Units for improved power quality
Power Capacitor Units for improved power quality Applications for capacitors Reactive power compensation Most of the apparatus and loads connected to the electrical power system consume both active and
More informationPower Meter Series 700
PowerLogic powermonitoring units Power Meter Series 700 Technical data sheet 2007 Functions and characteristics E90463 The PowerLogic Power Meter Series 700 offers all the measurement capabilities required
More informationMLK Low Voltage Switchboard System
MLK Low Voltage Switchboard System New Switchboard MLK Wide Range of Applications The MLK switchboard is designed mainly for electrical distribution in real estate and industrial buildings, and its nominal
More informationDYNACOMP The topclass dynamic response compensator
DYNACOMP The topclass dynamic response compensator Reactive power and Power Quality Reactive power Excessive reactive power drawn by linear and nonlinear loads deteriorates the Power Quality of the
More informationQ pole Pole Mounted Capacitor System
Q pole Pole Mounted Capacitor System Introduction The ABB Qpole pole mount capacitor system is an economical solution for shunt reactive compensation on overhead distribution networks. The Qpole is suitable
More informationHarmonics mitigation and solutions
Harmonics mitigation and solutions Summary I. Introduction II. Harmonics mitigation solution III. Case study lv.conclusion Schneider Electric 2 I. Introduction II. Harmonic mitigation solution III. Case
More informationPower Factor Correction Capacitors
Low Voltage Fixed and Automatic Power Factor Correction Systems Power Factor Correction Capacitors Product Description....................................... VT Product History..........................................
More informationSolutions for Power factor Correction at Medium Voltage
Solutions for Power factor Correction at Medium Voltage Energy efficiency technology CIRCUTOR, SA Headquarters in Viladecavalls. Leaders by experience CIRCUTOR has over 40 years experience and 6 production
More informationMTE RLW Reactors Price book
Table of Contents TABLE OF CONTENTS...1 STANDARD DELIVERY SCHEDULE...2 SELECTION & APPLICATION GUIDE...3 SPECIFICATION DATA...4 SERVICE FACTOR...4 AMBIENT TEMPERATURE...4 APPROVALS...4 ENCLOSURES:...4
More informationMedium Voltage HRC FUSES. Catalogue sheet B30/06.03e
Medium Voltage HRC FUSES Catalogue sheet B30/06.03e 1. FEATURES High rupturing capacity Short circuit current limiting Low rated minimum breaking current (I min ) Low switching overvoltages (U m ) Can
More informationMIDIMAESTRO SERVO DRIVE ELECTROMAGNETIC COMPATIBILITY DATA
MIDIMAESTRO SERVO DRIVE ELECTROMAGNETIC COMPATIBILITY DATA PRODUCT DCD 140 8/16, DCD 140 14/28 IMMUNITY The drive complies with the following international and European harmonized standards for immunity:
More informationGUIDELINES TO INSTALL, OPERATE AND MAINTAIN HT CAPACITORS & IT S ASSOCIATED EQUIPMENT
GUIDELINES TO INSTALL, OPERATE AND MAINTAIN HT CAPACITORS & IT S ASSOCIATED EQUIPMENT GENERAL: 1. The selection of switchgear for switching the capacitors should be done carefully. The circuit breaker
More informationPower Voltage Transformers for Air Insulated Switchgear
Power Voltage Transformers for Air Insulated Switchgear Introduction Trench Power Voltage Transformers (Power VTs) combine the attributes of an inductive voltage transformer with the application of a small
More informationReactive Power Compensation. ABB High Voltage Products June 19, 2013 Slide 1
José Matias High Voltage Components ABB AB Santiago  Chile, 05June2013 Reactive Power Compensation June 19, 2013 Slide 1 Reactive Power Compensation Main Topics Topics Introduction The need for capacitors
More information3.1.1 Full Type Tests & Routine Tests according to Clause 8 2 & 8 3. 4.0 Instructions For Installation, Operation & Maintenance
SPECIFICATION FOR LOW VOLTAGE SWITCHBOARD SEN I N D E X Description 10 STANDARD TECHNICAL REQUIREMENTS 11 Standards 12 General Operating Conditions 13 General Description Of Switchboard 131 Structure 132
More informationMEDIUM VOLTAGE CEBF SWITCHBOARDS. UP TO 40.5 kv. CE  BF  C  en  REV.00 2012.4
CE  BF  C  en  REV.00 2012.4 APPLICATION CEBF Switchbords up to 40.5 kv are designed for use in public and industrial distribution system up to 40,5KV for the operation and protection of lines, transformers,
More informationPower Factor Correction PhaseCap Compact for Power Quality Solutions
EPCOS Product Brief 2015 Power Factor Correction PhaseCap Compact for Power Quality Solutions The PhaseCap Compact series is based on the EPCOS MKKtechnology, which is known for many years from the successful
More informationEnergy Distribution. Applications Low Voltage Systems E8/1. Energy Distribution Panels in Hazardous Areas of Zone 1 and Zone 2
Energy Distribution Panels in Hazardous Areas of Zone 1 and Zone 2 Circuit breakers up to 800 A Load break switch / Main switch Busbar systems for internal energy distribution Miniature circuit breakers,
More informationMotor load monitoring relays
Motor load CME Range Motor load Motor load Fields of application The motor load monitor relay monitors the load states of singlephase and threephase asynchronous motors. The evaluation of the phase
More informationHow to choose a contactor for Bank capacitor application?
How to choose a contactor for Bank capacitor application? I Type of publication Typical application Best know Method (BKM) Troubleshooting guide evel 2 use Internal use Customer II Product  Product
More informationShunt Capacitor Bank Fundamentals and Protection
2003 Conference for Protective Relay Engineers  Texas A&M University April 810, 2003, College Station (TX) Shunt Capacitor Bank Fundamentals and Protection Gustavo Brunello, M.Eng, P.Eng Dr. Bogdan Kasztenny
More informationMGE TM Galaxy TM 7000
MGE TM Galaxy TM 7000 Power efficiency for business continuity 160/200/250/300/400/500 kva > Performance 3 Phase Power Protection with high adaptability to meet the unique requirements of Medium to Large
More informationNATUS NES / NESH Drawout Type Medium Voltage Switchgear Systems. Safe energy distribution that meets the highest industrial requirements
NATUS NES / NESH Drawout Type Medium Voltage Switchgear Systems Safe energy distribution that meets the highest industrial requirements NATUS switchgear systems your advantages minimal use of insulant
More informationReactiVar. Table of Contents DE11 CAPACITORS. ReactiVar Power Factor Correction Capacitors DE111. Description
ReactiVar Table of Contents Description Page ReactiVar Power Factor Correction s AV4000 & AV5000 Automatic Banks Low Voltage Fixed Unfused Banks Low Voltage Fixed Fused Banks Automatic Power Factor Banks
More informationUL506 File #E53094 (lamp through 1200 amps) UL508 File #El80243 (1 amp through 1200 amps)
Benefits of Using Line/Load Reactors GuardAC line/load reactors help keep your equipment running longer by absorbing many of the power line disturbances which otherwise damage or shut down your inverters,
More informationSubstation Design. Detail design of substation. Consider open loop MV network as an example. source 1 source 2. NC NC or NO main MV switchboard
Consider open loop MV network as an example source 1 source 2 NC NC NC or NO main MV switchboard A B Detail design of substation NC NC NC NO NC NC switchboard 1 switchboard 2 switchboard 3 MV MV MV LV
More information1ZSC AAA en, Rev. 4. Resin impregnated paper bushing, oil to SF 6., type GSBK Technical guide
1ZSC563AAA en, Rev. 4 Resin impregnated paper bushing, oil to SF 6, type GSBK Technical guide This Technical Guide has been produced to allow transformer manufacturers, and their designers and engineers,
More informationINTERNATIONAL CAPACITORS, S.A.
TECHNICAL APPLICATION NOTES TS 03000I Issue 4 POWER CAPACITORS The objective of these Technical application notes is to help our customers, distributors and representatives giving them solutions for problems
More informationTechnical Brochure. Enclosure Busbar Chamber System (BBS) Enclosed Switchdisconnectors (LSB) Enclosed Fuse Switches (FSB)
Technical Brochure Enclosure Busbar Chamber System (BBS) Enclosed Switchdisconnectors (LSB) Enclosed Fuse Switches (FSB) Busbar Chamber System (BBS) Technical Specification Busbar Chamber System (BBS)
More informationFor the electronic measurement of current: DC, AC, pulsed..., with galvanic separation between the primary circuit and the secondary circuit.
Current Transducer CTSR series I PRN = 300, 600 ma Ref: CTSR 0.3P, CTSR 0.6P For the electronic measurement of current: DC, AC, pulsed..., with galvanic separation between the primary circuit and the
More informationsolutions to reduce your electricity bill
Power Factor Correction solutions to reduce your electricity bill Reduce your electricity bill. Increase available power. Optimise your electrical installation. Solutions that optimise your investments
More informationGuide for the Design and Production of LV Power Factor Correction Cubicles
Power Factor Correction Guide for the Design and Production of LV Power Factor Correction Cubicles Panel Builder Guide 2011 Panel Builder Guide 2011 Contents CHAPTER 1: General design rules 311 Applicable
More informationOur brand POWER DYNAMIC PASSION COMMITMENT CREATIVITY. A strong brand for strong products: 8PU Premium. MV Energy
Our brand A strong brand for strong products: The ENERGOLINE brand represents our product portfolio of INDUSTRIAL SWITCHGEAR SYSTEMS. Our products are characterized by a high degree of safety, flexibility
More informationn Choice of equipment SP 58 Index of protection: IP 2X  IP 2XC  under front plate
SP fuse carriers with protected terminals SP fuse carriers with protected terminals www.klinkmann.com n Choice of equipment Maximum cartridge rating Type Rated current 400 V± 0 V± 690 V± gg am gg am gg
More informationMiniature circuit breakers
Miniature circuit breakers DinT series ka MCB Standard AS/NZS 898 ) Approval No. N78 Short circuit breaking capacity  000 Amps Current range 0.5  Amps,, and pole Sealable and lockable handle Modular
More informationProduct Data Bulletin
Product Data Bulletin Power System Harmonics Causes and Effects of Variable Frequency Drives Relative to the IEEE 5191992 Standard Raleigh, NC, U.S.A. INTRODUCTION This document describes power system
More informationSIRCOVER. Manual changeover switches from 125 to 3200 A. Changeover switches. Function. Advantages. The solution for.
The solution for Changeover switches svr_099_b_1_cat > Manufacturing industry. > Power distribution. 3200 Strong points svr_059_a_1_cat > complete range. > Easy connections. > Stable positions. > mproved
More informationAlpivar 2 & Alpican TM. CATAlOgue CAPACITOR. THe global SPeCIAlIST
Alpivar 2 & Alpican TM ReAcT ive ener gy com pensati o n CAPACITOR CATAlOgue THe global SPeCIAlIST IN electrical AND DIgITAl BuIlDINg INFRASTRuCTuReS The Legrand Edge The Legrand group is a global specialist
More informationFundamentals of Modern Electrical Substations Part 1: Mission of Electrical Substations and their Main Components
Fundamentals of Modern Electrical Substations Part 1: Mission of Electrical Substations and their Main Components Course No: E02010 Credit: 2 PDH Boris Shvartsberg, Ph.D., P.E., P.M.P. Continuing Education
More informationKnowing the Surge Protection Device
Knowing the Surge Protection Device There are so many names for protective devices such as 'lightning barriers', 'surge arresters ', 'lightning protection units', etc. In ideal condition, the surge protection
More informationMGE TM Galaxy TM 7000
MGE TM Galaxy TM 7000 Power efficiency for business continuity 160/200/250/300/400/500 kva > Performance 3 Phase Power Protection with High Adaptability to Meet the Unique Requirements of Medium to Large
More informationDry type transformers with air insulated MV windings
E N G L I S H Dry type transformers with air insulated MV windings TTR TTO OTN, OTR, OTF reactors TTH Technology Magnetic Core The core is made of grain oriented magnetic sheets characterized by high permeability
More informationACR AirCore Reactors Dry Type
AirCore Reactors Dry Type Power compensation AirCore Reactors () provide a linear response of impedance versus current which is essential for numerous applications. The dry type design is maintenance
More informationCurrent Transducer LAX SERIES I PN
Current Transducer LAX SERIES I PN = 161 A Ref: LAX 1NP For the electronic measurement of currents: DC, AC, pulsed..., with a galvanic isolation between the primary circuit (high power) and the secondary
More informationEN (IEC) /2 The new standard for lowvoltage power switchgear and controlgear assemblies
SIVACON S8 EN (IEC) 614391/2 siemens.com/sivacon Dear SIVACONPartners, with publication of the IEC 61439 we already informed you about the replacement of the IEC 60439. With the 1 st of November 2014
More informationHigh Voltage Reactive Power Compensation and Harmonic Filtering Products
High Voltage Reactive Power Compensation and Harmonic Filtering Products Our high voltage products enhance power quality of installations and improve electrical network efficiency, both resulting in considerable
More informationMotor Starting Solutions
Application Guide Motor Starting Solutions Open Type Version In Kit Form Complete ange of Products and Accessories to Create all Motor Starter Types Manual motor starter ShortCircuit Protection... Type
More informationVoltage Rated operating voltage [kv] 12 24 Rated power frequency withstand voltage [kv] 28 50 Rated lightning impulse withstand voltage [kv] 75 125
Standards and Regulations IEC 62271200 ; VDE 0671200 ; BS EN 62271200 Technical Data MC312 MC324 Voltage Rated operating voltage [kv] 12 24 Rated power frequency withstand voltage [kv] 28 50 Rated
More informationRLW Reactors Technical Reference Manual
Form: RLWTRME Rel: March 2011 Form RLWTRME March 2011 Page 1 Table of Contents STANDARD DELIVERY SCHEDULE... 3 SELECTION & APPLICATION GUIDE... 4 MODEL CODE PART NUMBER CONFIGURATION... 5 RL REACTOR
More informationIEC Series Standards for MVSwitchgear IEC Highvoltage switchgear and controlgear Part 1: Common specifications
IEC 62271 Series Standards for MVSwitchgear IEC 622711 Highvoltage switchgear and controlgear Part 1: Common specifications Olaf Bischur Siemens AG IC LMV MS R&D GIS TD 1PG Topics 1. Standards Group
More informationCircuit diagram symbols
17 Circuit diagram symbols E 18 CIRCUIT DIAGRAM SYMBOLS electrical network elements threephase line or cable singlephase line or cable short circuit earth electrode outgoing feeder supply incoming feeder
More informationMTE SERIES RLW. World REACTORS USER MANUAL PART NO. INSTR 030 REL. 090930. 2009 MTE Corporation
MTE SERIES RLW World REACTORS USER MANUAL PART NO. INSTR 030 REL. 090930 2009 MTE Corporation IMPORTANT USER INFORMATION NOTICE MTE Series RLW reactors are components designed to improve the reliability
More informationDead Tank Circuit Breaker 72PM40C Proven reliability through common platforms
Dead Tank Circuit Breaker 72PM40C Proven reliability through common platforms ABB innovations for changing demands ABB (www.abb.com) is a leader in power and automation technologies that enables utility
More informationReactive Energy Management
Power Quality Reactive Energy Management Low Voltage components Catalogue 2014 Power Quality Your requirements. Optimize energy consumption By reducing electricity bills, By reducing power losses, By reducing
More informationCatalogue Easy 9 Price list
Easy 9 Catalogue Price list Miniature circuit breakers 6 ka Miniature circuit breakers 10kA Switch disconnectors Residual current Circuitbreakers Residual current devices with overcurrent protection Surge
More informationHybrid Shunt Reactor & Shunt Capacitor Compensation Systems
66 Carey Road Queensbury, NY 12804 Ph: (518) 7924776 Fax: (518) 7925767 www.nepsi.com sales@nepsi.com Hybrid Shunt Reactor & Shunt Capacitor Compensation Systems General Northeast Power System, Inc.
More informationFor the electronic measurement of current: DC, AC, pulsed..., with galvanic separation between the primary and the secondary circuit.
Current transducer LF 21S I PN = 2 A For the electronic measurement of current: DC, AC, pulsed..., with galvanic separation between the primary and the secondary circuit. Features Bipolar and insulated
More informationElectronic timer CTVBS.17+18 OFFdelayed without auxiliary voltage, for DC contactors Data sheet
Characteristics Singlefunction OFFdelay timer for DC contactors, without auxiliary voltage Width.5 mm CDC 5 6 F3 Approvals A culus E CCC CTVBS a Circuit diagram b Marker label Marks a CE b CTick Order
More informationAC RESONANT TEST SYSTEMS
AC RESONANT TEST SYSTEMS 80101 RESONANT TEST SYSTEMS PHENIX Technologies is a leading manufacturer of high voltage test systems. We have been engineering and supplying systems throughout the world for
More informationTransformer Test System
Transformer Test System Questionnaire Quotation number: (Will be filled in by Samgor) Customer Information Name: Company: Tel: Email: Placing location/country: A. Technical Part Application Test shop Research
More informationTHREEPHASE OIL IMMERSED EARTHING TRANSFORMERS
ISO 9001:2000 ISO 14001:2004 PNN18001:2004 99320 Żychlin, ul. Narutowicza 70 www.ftz.com.pl Secretary s Office Tel.: +48 24 285 46 05, Fax: +48 24 285 46 31, zarzad@ftz.com.pl Marketing and Sales Department
More informationCurrent transformer selection guide
The selection of a current transformer is a simple task. There are four phases in the selection procedure. Current transformer selection guide KEEP IN MIND efine customer requirements based on the primary
More informationRE7TL11BU ondelay timing relay s  24 V AC DC  1OC
Characteristics ondelay timing relay  0.05..1 s  24 V AC DC  1OC Main Commercial Status Range of product Product or component type Component name Time delay type Time delay range [Us] rated supply
More informationTypeTested Power Distribution Board 8PT with Rear Busbars. sivacon
TypeTested Power Distribution Board 8PT with Rear Busbars sivacon The Obvious Solution for Global Challenges SIVACON Typetesting is one of today s important issues for lowvoltage technology and will
More informationSF 6 Gas Insulated Switchgear Type SDF for 170 kv
Three Phase Encapsulated Type SF 6 Gas Insulated Switchgear Type SDF for 170 kv 06B1E0001 With Trustworthy Technology, Structure Fuji Electric as a manufacturer of comprehensive substation equipment
More informationCurrent distribution Comb busbars for Declic and SFT residential devices
Current distribution Comb busbars for Declic and SFT residential devices Comb busbar, for connecting 26 x 9 mm modules, consisting of two insulated bars to supply 1P + N devices (Declic, SFT, etc.). Due
More informationARCO Electric Products Installation and Maintenance Manual Low Voltage Automatic Power Factor Correction Capacitor Systems 2013
ARCO Electric Products Installation and Maintenance Manual Low Voltage Automatic Power Factor Correction Capacitor Systems 2013 READ CAREFULLY These instructions are intended to cover good practices in
More informationCapacitors. for Uninterruptible Power Supply Systems (UPS) Product Brief
Product Brief 2009 Capacitors for Uninterruptible Power Supply Systems (UPS) EPCOS is known as one of the world s leading manufacturer of electronic components, especially in the field of capacitors. Hardly
More informationThyristorcontrolled power supplies and battery chargers
Thyristorcontrolled power supplies and battery chargers Input voltage: 115 / 230 VAC, single phase, 50 / 60 Hz or 208 / 400 / 480 VAC, three phases, 50 / 60 Hz Output voltage: 12 / 24 / 48 / 60 / 72 /
More information55 SERIES. General purpose relays 7 to 10 A General purpose relays For printed circuit mounting. Type Type Type 55.
55 General purpose relays 7 to 10 55 General purpose relays For printed circuit mounting 55.12 55.13 55.14 Type 55.12  2 CO 10 Type 55.13  3 CO 10 Type 55.14  4 CO 7 C & DC coils Cadmium Free contacts
More informationWhy Your Capacitor Bank Should be Left Ungrounded
Why Your Capacitor Bank Should be Left Ungrounded Introduction Should medium voltage capacitor banks on industrial and commercial power systems be grounded? This question often arises, and the answer is
More informationRM4TG20 threephase network control relay RM4T  range 200..500 V
Characteristics threephase network control relay RM4T  range 200..500 V Complementary [Us] rated supply voltage Output contacts Setting accuracy of time delay Delay at power up Measuring cycle Marking
More informationUnified requirements for systems with voltages above 1 kv up to 15 kv
(1991) (Rev.1 May 2001) (Rev.2 July 2003) (Rev.3 Feb 2015) Unified requirements for systems with voltages above 1 kv up to 15 kv 1. General 1.1 Field of application The following requirements apply to
More informationEXTENDING THE LIFE OF POWER FACTOR CAPACITORS
by John Houdek, President, Allied Industrial Marketing, Inc., and Cesar Chavez, Engineering Manager, ARTECHE / Inelap Abstract: The addition of power factor improvement capacitors to individual motors
More informationCLASS 5830 REACTIVAR Power Factor Capacitors AV4000/AV5000 STANDARD AUTOMATIC BANKS
CLASS 5830 REACTIVAR Power Factor Capacitors AV4000/AV5000 STANDARD AUTOMATIC BANKS The new Square D REACTIVAR AV4000 & AV5000 standard Automatic Power Factor Correction banks offer unsurpassed safety,
More informationRISH EM 3490 DS Dual Source Energy Meter RISH EM 3490 DS. Application : Product Features:
Application : RISH Master 3490 DS measures important electrical parameters of Utility (in normal mode) & Generators (in Power back up) in three phase and single phase Network & replaces the multiple analog
More information2a. IEM Indoor Metal Clad Medium Voltage Switchgear 15KV 163461. 2a. Section 16346 INDOOR METAL CLAD MEDIUM VOLTAGE SWTICHGEAR (Std.
2a. IEM Indoor Metal Clad Medium Voltage Switchgear 15KV 163461 2a. Section 16346 INDOOR METAL CLAD MEDIUM VOLTAGE SWTICHGEAR (Std. Relays) Part 1 General 1.1 CONDITIONS AND REQUIREMENTS: A. Refer to
More informationVentilated DryType Transformers. Secondary Substation Transformers  5 and 15kV Class
Ventilated DryType Transformers Secondary Substation Transformers  5 and 15kV Class GE ventilated drytype transformers are designed for indoor or outdoor applications in schools, hospitals, industrial
More informationLow Voltage Products. Low Voltage Capacitors Power Factor Correction Solutions
Low Voltage Products Low Voltage Capacitors Power Factor Correction Solutions Low Voltage Capacitors Reliability for Power Factor Correction Dry type design The ABB Low Voltage Capacitors, called CLMD,
More informationElectronic timer CTTGD.12
2CDC 251 098 F0t06 a Rotary switch for the preselection of the time range of the ON time b Potentiometer with direct reading scale for the fine adjustment of the ON time c Rotary switch for the preselection
More informationELEKTROTEHNI KO PODJETJE Leskoπkova cesta 12, 1000 Ljubljana, SLOVENIA
MRO Modularne Razdelilne Omare d.o.o. ELEKTROTEHNI KO PODJETJE Leskoπkova cesta 2, 000 Ljubljana, LOVENIA MC GENERAL When to use? MC  modular switchgear cabinets are typetested, factory built switchgears,
More informationLV MCC LOW VOLTAGE SWITCHGEAR MOTOR CONTROL CENTRE PRODUCT GUIDE
LV MCC LOW VOLTAGE SWITCHGEAR MOTOR CONTROL CENTRE PRODUCT GUIDE 380/415/690 Volt AC 50/65/80/100 ka 1. Product Guide Low Voltage Motor Control Centre CONTSTRUCTION Continuous "poured in place" gasket
More informationAPPLICATION OF POWER FACTOR CORRECTION CAPACITORS
Power Factor Correction APPLICATION OF POWER FACTOR CORRECTION CAPACITORS Understanding Power Factor As with any equipment, an electrical system handles its job to some degree of efficiency ranging from
More informationRM4TR32 threephase network control relay RM4T  range V
Characteristics threephase network control relay RM4T  range 300..430 V Complementary [Us] rated supply voltage Control threshold undervoltage Control threshold overvoltage Output contacts Main Range
More informationGE Ventilated Dry Type Transformers
GE Industrial Systems GE Ventilated Dry Type Transformers Secondary Substation Transformers 5 and 15kV Class Safe, Convenient and Environmentally Sound! GE Ventilated DryType Transformers GE ventilated
More information