# SIZING THE PRIMARY POWER SYSTEM FOR RESISTANCE WELDERS

 To view this video please enable JavaScript, and consider upgrading to a web browser that supports HTML5 video
Save this PDF as:

Size: px
Start display at page:

Download "SIZING THE PRIMARY POWER SYSTEM FOR RESISTANCE WELDERS"

## Transcription

1 SIZING THE PRIMARY POWER SYSTEM FOR RESISTANCE S By Jack Farrow, May, 2004 WELDING TECHNOLOGY CORPORATION ABSTRACT Information on how to select the correct size of substation transformer and 480V bus to power one to one thousand resistance welding machines is presented. Powerline voltage drop, light flicker, power factor correction and harmonic currents are discussed. Strategies to allow more welders to operate on a given power system are explained. Techniques to improve the efficiency of the power system and reliability of the welding process are identified. Consideration is given to selecting the correct sizes and types of fuses. Useful reference material will be available to attendees. INTRODUCTION Because resistance welders draw large currents on an intermittent basis, they present special problems to the primary power system in a manufacturing plant. This paper answers the following questions related to these problems. 1. What size does the three-phase power system need to be to support the number of welders I have? 2. How is a welder power bus different from other power buses? 3. What can be done to improve power system efficiency and capacity utilization? 4. What is the proper size and type of fuse to use? For the purposes of discussion in this paper, spotwelding of steel sheet of thickness between 0.5 and 3 mm. is assumed. The power system supplying the welders is 480VAC, 60 HZ, three-phase. In general, the discussion is centered around standards and practices most commonly used in the North American automobile industry. I. What size does the three-phase power system need to be to support the number of welders I have? A typical resistance spotwelder draws between 100,000 and 200,000 watts when welding! To avoid problems of cold welds due to insufficient power, the 480 VAC power system must be capable of supplying this power with less than 10% voltage drop. Now, 10% voltage drop doesn t sound like much, but consider this: The amount of power available in a circuit is proportional to the voltage squared divided by the resistance. If the voltage drops by 10% (to 0.9 times the original value) the available power drops by 19% (0.9 times 0.9 equals 0.81). A 19% drop in energy to the weld has some serious effects on weld quality! Most modern resistance welding controls have systems to compensate for powerline voltage drop, but when the powerline voltage drops by more than 10% and the available energy drops by more than 19%, there may not be enough energy left to make the weld, even after the welding control has done all the compensation it can do. For this reason, powerline voltage drops should be limited to 10% or less. 1

2 In order to calculate powerline voltage drop, the current draw of the welders and the impedance of the power system must be known. In the absence of actual measurements of powerline draw and voltage drop during weld, the following assumptions can be used: 1. Where there are several single-phase AC spotwelders connected to the same three-phase power bus, the connection of the welders to the power bus is distributed as equally as possible between the three phases so as to make the average power draw equal on all three phases. 2. For a hanging gun welder (single-phase transformer suspended from the ceiling with a kickless cable going to the welding gun), the equivalent three-phase current draw during welding is 400 amperes. 3. For a single-phase AC fixture welding gun or a robotic hip-mounted transformer welder, the equivalent three-phase current draw during welding is 270 amperes. 4. For a single-phase AC integral transformer welding gun, the equivalent threephase AC current draw during welding is 170 amperes. 5. For a three-phase MFDC welding gun, the equivalent three-phase current draw during weld is 150 amperes. 6. The duty cycle of the welders is 5%. 7. The impedance of the three-phase power system is 7%. That is, When the power system is loaded to its full continuous duty current rating, the voltage will drop by 7%. In other words, if you draw 400 amperes on a 480 V 400 amp bus with a 7% impedance factor, the voltage will drop from 480V (unloaded) to 446V (Fully loaded). The above assumptions are valid for spotwelders welding sheet steel (galvanized or bare) over the thickness range of 0.5 to 3 mm. For small numbers of welders (4 or fewer) actuated manually, there is a very high probability that all will be welding simultaneously at least several times a day. Where 4 or fewer welders are involved, the power system should be sized so the voltage doesn t drop by more than 10% when all welders weld simultaneously. If the power system cannot be sized to handle all the welders welding simultaneously, some sort of interlock can be used to assure that only one welder at a time is allowed to weld. A simple interlock circuit, consisting of only two relays per welder, is shown in Figure 1. For small shop and/or low production requirements, this simple relay circuit works well up to 5 welders. With the use of this interlock circuit, the power system only needs to be sized to handle the current of one welder with no more than 10% voltage drop. So long as the duty cycle of the welders is 5% or less, this interlock circuit slows the production rate by much less than 1%. 2

3 FIRST WELDING CONTROL MIDDLE WELDING CONTROL(S) LAST WELDING CONTROL RY2C RY2C RY2 TO NEXT WELDING CONTROL FROM PREVIOUS WELDING CONTROL RY2 TO NEXT WELDING CONTROL FROM PREVIOUS WELDING CONTROL RY2 RY1A RY1A RY1A SEPARATE 120/24VAC SOURCE RY2A RY2A TO STAGE 2 OR PRESSURE SWITCH INPUT RY2B TO STAGE 2 OR PRESSURE SWITCH INPUT RY2B TO STAGE 2 OR PRESSURE SWITCH INPUT RY2B RY1 RY1 RY1 TO WELD VALVE OUTPUT TO WELD VALVE OUTPUT TO WELD VALVE OUTPUT FIGURE 1: Simple interlock circuit for 5 or fewer welders For 5 or more welders, running at duty cycles of 5%, it becomes very unlikely that all of the welders will weld at the same time, assuming random initiation times by human operators. For 5 or more welders, statistical techniques may be used to estimate the number of welders welding at any instant of time and size the power bus accordingly. The spreadsheet associated with this paper implements a statistical method to estimate, give a certain number of welders, how often the powerline voltage will dip by more than 10% and how many welds per 1000 will be affected by the voltage drops of greater than 10%. The data values are entered in column E. These values can be changed as desired for what if calculations. For example, with the values already entered, if the average duty cycle is increased from 5% to 10% (a very high value for spotwelding), it will show that the number of welds likely to have one or more cycles of low line voltage will increase from 2 per 1000 (acceptable for most applications) to 247 per 1000 (good only for making scrap). The what if calculations can also be used to make estimates of the lowest line voltage that will occur with a given number of welders. The value for the minimum allowable 3

4 line voltage (Cell E9) can be decreased until the number of welds per million with one or more cycles of low line voltage reaches 1 per million. This allows the worst case voltage drop to be found. General case estimates for the current draw for different types of resistance spotwelding machines are in cells G2 through G5. These current draw estimates are for the welding of steel (bare or coated) only. If you know the exact value of current draw for the welding machines in your plant, then the known values should be entered here. In general, however, these estimated values should suffice for welding steel in all but the most unusual cases. The current draws for welding aluminum are about 3 times the assumed values for steel shown in cells G2 through G5. For weld time, use 5 cycles. For duty cycle, use 3%. The estimates of this spreadsheet are not accurate for a mixture of some machines welding steel and some welding aluminum. If your situation involves a mix of this sort, another analysis method should be used. Please notice that the calculations are based on the number of welding machines (welding guns), not necessarily the number of welding controls or the number of welding transformers. For example if multiple welding transformers are connected to one welding control or multiple welding guns are connected to a single welding transformer, the number entered in cell E5 should reflect the total number of welding guns or pairs of welding electrodes. The estimates in this spreadsheet are slightly biased toward worst case. If you size a welding power bus so that the number of welds with low voltage is about 1 or 2 per thousand, then it is very unlikely you will get cold welds due to low powerline voltage. The statistical assumptions and approximations in this spreadsheet are accurate with 5 or more welders. With more than 250 welders and/or if the welders have a very high duty cycle, you may find that the Average Bus current (Cell D29) is larger than the 3- phase power system continuous duty rating (Cell E11). If this happens, use the higher value in cell D29 to size the power system. Once the required supply current is calculated by any of the previous methods, the necessary substation transformer KVA is calculated with the following equation: SUBKVA = CURR*LV* where: SUBKVA is the required substation transformer KVA CURR is the required supply current LV is the powerline nominal voltage (480VAC, 390VAC, etc.) For example, with a required current of 600 amperes and a 480V bus, the necessary size substation transformer would be KVA. 4

5 II. How is a welder power bus different from other power buses? Resistance welders are probably the worst loads that can be placed on a three-phase power bus. They draw large amounts of current for short periods on a very intermittent basis. The waveform of the current they draw is almost never a smooth sine wave and it is almost never balanced between the three phases. Harmonic currents, powerline waveform distortion and rapidly changing powerline voltage are the result. For the above reasons and more, it is not a good idea to put resistance welders on the same power bus as other equipment. A power bus separate from any other in the plant, fed by a separate substation transformer is recommended for powering resistance welding machines. If a large proportion of the resistance welders in your plant are single-phase, a DELTA connected substation made with three single-phase transformers, rather than a single three-phase transformer is recommended. There are several reasons for this: 1. In a DELTA connected system, the effective impedance presented to a singlephase load is lower. 2. In a DELTA power system, which has no neutral conductor, the imbalance and harmonic currents are forced to flow through the bus, which is sized to handle the current, rather than the neutral conductor which may not be big enough to handle the current. 3. In a DELTA power bus, the three separate single-phase substation transformers rather than a single three-phase transformer reduce the coupling between phases which results in an unloaded phase increasing in voltage when another is loaded down. This reduces voltage fluctuations. This becomes particularly important in a resistance welding power bus where occasional voltage drops reach 15%. Single-phase AC welders usually have a power factor below 70%; power factors of 50% or less are not unusual. Part of this poor power factor is due to inductance in the secondary loop of the welding machines and part is due to the current waveform distortion caused by the phase control action of the welding control. Three-phase MFDC welders have a power factor in the 85-95% range. All of the poor power factor is caused by current waveform distortion and none is caused by inductance in the secondary loop of the welding machine. The usual methods of adding power factor correction capacitors to the bus simply don t work for resistance welders for several reasons: 1. The current draw of resistance welders is extremely intermittent and changes from second to second. Any constant value of power factor correction capacitor will be wrong for the load current almost all the time. 2. Due to the phase control action of the welding controls, there are a lot of harmonic currents generated, primarily 3 rd, 5 th and 7 th order. Due to the intermittent action of resistance welding, the inductance present on the power bus is constantly changing, as some welders start welding and others stop. For any reasonable value of power factor correction capacitors, there will be times when the capacitors and the inductance on the power bus form a tuned circuit, resonant at the 3 rd, 5 th, or 7 th harmonic of the powerline. The resonant action will cause severe waveform distortion on the powerline voltage and 5

6 eventually destroy the power factor correction capacitors by exceeding their current rating. 3. A large part of the poor power factor on a resistance welder bus is due to the chopping of the AC waveform which is done as part of phase control or by flat-topping of the powerline waveform caused by the rectifier input circuits of MFDC welders. Power factor correction capacitors cannot correct poor power factor due nonlinear (switched) current draw. For the above reasons, DO NOT put power factor correction capacitors on a welder power bus! DO NOT connect anything with power factor capacitors built-in (such as equipment containing motors or lighting circuits) to a welding bus. Except for one special case noted below, power factor correction capacitors on a welder bus are worse than useless. If power factor correction on a welder bus is necessary it can be done with harmonic filters (tuned to the 3 rd and 5 th harmonics) and/or active waveform correction devices. However these devices are far more expensive than simple power factor correction capacitors and are often not cost-effective. For smaller installations (50 welders or less) it is usually cheaper to pay the power factor penalty to the utility company. Only in larger installations (100 welders or more) are these devices cost-effective. There will be cases where installing a separate power bus for the resistance welding equipment simply cannot be done. This often occurs in small manufacturing plants where there are only two or three resistance welders. In this situation, there are several things that can be done to at least mitigate the negative consequences. 1. Use MFDC welding whenever possible. MFDC is much kinder to the threephase power bus and draws current from all three phases approximately equally. 2. Size the power bus so that even if all the welders weld at the same time, the voltage drop is only 5%. This will reduce light flicker and other undesirable effects on the other devices powered from the same power bus as the resistance welders. 3. Install some sort of system (such as the simple relay circuit mentioned previously) to make sure only one welder can weld at a time. 4. Install one set of very small power factor correction capacitors (1 KVAR maximum) on the power bus as close as possible to the welding machine(s) to help absorb any voltage spikes generated by the switching action of the resistance welders. 5. Put any computers or other electrically sensitive devices (such as telephone equipment) on a UPS (Uninterruptible Power Supply). 6. Get used to light flicker; it WILL happen! 6

7 III What can be done to improve power system efficiency and capacity utilization? Although resistance welders are possibly the worst load that can be placed on a threephase powerline, there are some things that can be done to make the situation better. When connecting single-phase welding machines to a three-phase powerline, DO NOT connect all the machines to the same phase of the powerline! Instead, distribute the connections approximately equally between all three phases. For example, if there are 10 welders to be installed, connect three to phase 1, three to phase 2 and four to phase 3. This distributes the average current draw more-or-less equally across all three phases. If multiple single-phase welders are welding simultaneously, try to run them in groups of three with each welder in the group of three on a different phase. This will present a more balanced load to the three-phase powerline. In general, try to run the welding transformers on the lowest tap that still gives a satisfactory weld without causing the weld control to give current regulation or voltage regulation faults. This reduces the current draw of the welder and improves its power factor, which results in lower electricity bills. A load scheduling system that limits the maximum number of welders that can weld at any instant of time can make a big difference in the maximum current draw and can allow more welders to operate on the same size power bus. The Excel spreadsheet associated with this paper allows a load scheduling system to be simulated and its effect on the production rate estimated. After entering the proper values for your system in cells E2 through E13, the maximum number of welders allowed to weld simultaneously by a load scheduling system is entered in cell E32. When this number is entered, the numbers reflecting the required bus size and the effect on production rate are calculated and displayed in cells C33 and C35. The mathematical approximation used to obtain these values is most accurate in the range of 5-60 seconds per hour of production time lost. Below 5 seconds, the lost production time tends to be overstated (bigger number than it really is) and above 60 seconds per hour, the lost production time tends to be understated (smaller than it really is). 7

8 IV. What is the proper size and type of fuse to use? For an individual welder, the general rule is that the fuse size in the bus disconnect and the wiring from the bus disconnect to the resistance welding control should match the ampere rating of the circuit breaker in the welding control. For example, if there is a 250 ampere circuit breaker in the weld control, then a 250 ampere fuse should be used in the bus disconnect and 250 MCM wire should be used between the bus disconnect and the weld control. The fuse should always be a weld limiter type of fuse which has a very slow-blow characteristic. Use of this rule assures compliance with the National Electrical Code in the USA. If the KVA of the welding transformer(s) is known for a particular installation, then all of the 480V wiring, from the bus disconnect to the welding control and from the welding control to the welding transformer can be sized according to the transformer KVA. The basic rule for single-phase welding transformers is that the minimum cable size is 1.7 amps ampacity per transformer KVA. For cable ampacity, the NFPA standard values should be used. For example, a 100KVA transformer requires a wire with an ampacity of 170 amperes, or AWG 2/0 wire. At the bus disconnect, a fuse appropriate to the wire size (200 amperes) is required. If the transformer KVA is such that the calculated ampacity is more than the rating of the circuit breaker in the resistance welding control, then the wire size and the bus disconnect fuses should be selected according to the circuit breaker rating. Two or three single-phase AC resistance welding controls can be powered from a single three-phase bus disconnect. When this is done, the following recommendations apply: 1. All three welding controls should be of the same type and have the same size circuit breakers. For example, it is not advisable to connect a multi-contactor cascade firing control with 6 welding transformers onto the same disconnect as two other single-contactor controls with one welding transformer each. 2. Each of the welding controls is connected to a different phase. 3. The transformers connected to the welding controls should all be the same total KVA. When two or three welding controls are powered from one three-phase bus disconnect, the disconnect and the fuses in it should be sized 1.5 times bigger than what would be required for a single control. For example, it is acceptable to connect three resistance welding controls with 250 ampere circuit breakers to a single 400 amp three-phase disconnect. For three-phase MFDC resistance welding controls, the bus disconnect fuses and the wiring between the bus disconnect and control should always be sized according to the circuit breaker size in the welding control. The wire used to connect the welding control to the welding transformer should have an ampacity equal to 1/3 rd of the rated current of the inverter at 10% duty cycle. For example, a 600 amp MFDC welding control equipped with a 150 amp circuit breaker should be installed with 150 amp bus fuses, AWG 0 wire between the bus disconnect and the circuit breaker and with AWG 3/0 wire (200 amps) between the welding control and the welding transformer. The bus disconnect fuses should be weld limiter (slow blow) type fuses. 8

9 The main power bus fuses feeding the welder bus should be sized according to the rated capacity of the power bus or the substation transformers, whichever is less. If the layout of the plant permits, it is advantageous to install the welder bus in a loop configuration with the beginning and end of the loop near the substation transformers. Power is fed from the substation transformers into both ends of the power bus. This both lowers the effective bus impedance by providing dual current paths to any load and it doubles the capacity of the bus. For example, if a 1200 amp welder bus is required, the requirement can be met with a looped 600 amp bus. A looped bus is particularly effective where there are a large number of welders, distributed more-or-less equally along the bus. Depending on the installation, this may save considerable amounts of money. Other bus configurations, such as the ladder configuration shown in Figure 2 can also be used. In Figure 2, the need for a 1200 amp welder bus is met with interconnected 400 amp buses. 9

10 1200 AMP SUBSTATION TRANSFORMERS 400 AMP FUSES 400 AMP BUSES = BUSES CONNECTED TOGETHER AT THESE POINTS FIGURE 2: Bus H configuration to obtain higher currents In order to meet local electrical code requirements, it may be necessary to add auxiliary fuses at the points where the power buses are interconnected. It is always good practice to have a proposed bus design reviewed by the local electrical code enforcement agency. 10

11 SUMMARY AND CONCLUSIONS The guidelines presented in this paper are directed toward resistance spotwelding equipment in an environment like an automobile body assembly line. The guidelines in this paper are not designed for resistance seam welders, very large welders (such as used to weld automobile rims or aircraft landing struts), three-phase DC welders, or to any welders with a 500 KVA or larger welding power supply. The guidelines of this paper assume that either steel or aluminum, but not a mix of the two, is being welded. For all but the most unusual installations of resistance welding equipment, the information presented in this paper should be sufficient to properly size the three-phase power bus so the welders can operate reliably. In addition to the information given in this paper, a number of articles and other material about powerlines for resistance welders are included in the appendix. This material was the basis of this paper. Because of size (over 100 pages with the appendix) this paper was distributed in electronic form (on a CDROM). If you are reading a paper copy of this paper, the electronic form, with all the appendices can be downloaded from the Welding Technology Corp. web site (www.weldtechcorp.com) or can be obtained by contacting Jack Farrow at or 11

### Product Data Bulletin

Product Data Bulletin Power System Harmonics Causes and Effects of Variable Frequency Drives Relative to the IEEE 519-1992 Standard Raleigh, NC, U.S.A. INTRODUCTION This document describes power system

### Ground Fault Protection

GE Energy Industrial Solutions Ground Fault Protection Digital Specification Program Latin America Ground Fault. I. Introduction In the electrical systems always exists the possibility of having shutdowns

### Typical Data Requirements Data Required for Power System Evaluation

Summary 66 Carey Road Queensbury, NY 12804 Ph: (518) 792-4776 Fax: (518) 792-5767 www.nepsi.com sales@nepsi.com Harmonic Filter & Power Capacitor Bank Application Studies This document describes NEPSI

### Three phase circuits

Three phase circuits THREE PHASE CIRCUITS THREE-PHASE ADVANTAGES 1. The horsepower rating of three-phase motors and the kva rating of three-phase transformers are 150% greater than single-phase motors

### Power Quality of Commercial Buildings

Hartford Steam Boiler One State Street P.O. Box 5024 Hartford, CT 06102-5024 Tel: (800) 472-1866 www.munichre.com/hsb June 2015 Background Power quality is a general term used to describe the quality of

### Harmonics Made Simple

Harmonics Made Simple Just because harmonics is becoming a more prevalent problem, that doesn t mean the subject is getting any easier to understand Welding equipment is one of several sources of harmonics

### POWER SYSTEM HARMONICS. A Reference Guide to Causes, Effects and Corrective Measures AN ALLEN-BRADLEY SERIES OF ISSUES AND ANSWERS

A Reference Guide to Causes, Effects and Corrective Measures AN ALLEN-BRADLEY SERIES OF ISSUES AND ANSWERS By: Robert G. Ellis, P. Eng., Rockwell Automation Medium Voltage Business CONTENTS INTRODUCTION...

### Line Reactors and AC Drives

Line Reactors and AC Drives Rockwell Automation Mequon Wisconsin Quite often, line and load reactors are installed on AC drives without a solid understanding of why or what the positive and negative consequences

### What is a transformer and how does it work?

Why is a transformer needed? A control transformer is required to supply voltage to a load which requires significantly more current when initially energized than under normal steady state operating conditions.

### DYNACOMP. The top-class reactive power compensator

DYNACOMP The top-class reactive power compensator Dynacomp vs Electromechanical switching of capacitors Electromechanical switching of capacitors Transients at switching Conventional banks with contactors

### EET272 Worksheet Week 9

EET272 Worksheet Week 9 answer questions 1-5 in preparation for discussion for the quiz on Monday. Finish the rest of the questions for discussion in class on Wednesday. Question 1 Questions AC s are becoming

### September, Rectifier Duty Transformers

September, 2013 Rectifier Duty Transformers Transformers play an important role in industrial applications, especially in metallurgical plants and processes. Very high currents need to be supplied for

### VOLTAGE REGULATOR AND PARALLEL OPERATION

VOLTAGE REGULATOR AND PARALLEL OPERATION Generator sets are operated in parallel to improve fuel economy and reliability of the power supply. Economy is improved with multiple paralleled generators by

### Transformerless UPS systems and the 9900 By: John Steele, EIT Engineering Manager

Transformerless UPS systems and the 9900 By: John Steele, EIT Engineering Manager Introduction There is a growing trend in the UPS industry to create a highly efficient, more lightweight and smaller UPS

### Transformer Basics Information Guide

Property of Motion Laboratories, Inc. Transformer Basics Information Guide 2014 Motion Laboratories, Inc. Created By: Jim Herrick / Michael Shaw Approved By: Peter Herrmann Page: 1 Transformer Definition

### Product Data Bulletin

Product Data Bulletin Bulletin No. 7460PD9501R8/95 August, 1995 Oshkosh, WI, USA (Replaces 7460PD9501 dated March 1995) DRIVE ISOLATION TRANSFORMERS SOLUTIONS TO POWER QUALITY Introduction The increased

### ELECTRICAL ACCEPTANCE TESTS

Scope This guideline defines the standard tests that all electrical systems and equipment must pass prior to final acceptance by the University. These tests are in addition to acceptance tests specified

### FREQUENCY CONTROLLED AC MOTOR DRIVE

FREQUENCY CONTROLLED AC MOTOR DRIVE 1.0 Features of Standard AC Motors The squirrel cage induction motor is the electrical motor motor type most widely used in industry. This leading position results mainly

### Harmonic Design Considerations

Harmonic Design Considerations Michael Leporace Specification Engineer, GE Consumer & Industrial ABSTRACT Power quality can be defined as the comparison of voltage and current waveforms to their fundamental

### Rule 5.500 Fast Track Analysis for National Life Insurance Co.

Rule 5.500 Fast Track Analysis for National Life Insurance Co. For a 500 kw Solar array to be located at 155 Northfield Street in Montpelier, Vermont Green Mountain Power Pam Allen Date: 5/31/13 SECTION

### Application guide for power factor testing of power & distribution transformers

Application guide for power factor testing of power & distribution transformers Introduction The transformer is probably one of the most useful electrical devices ever invented. It can raise or lower the

### Introduction. Harmonics and IEEE 519 Page 1 of 19

Introduction In an ideal power system, the voltage supplied to customer equipment, and the resulting load current are perfect sine waves. In practice, however, conditions are never ideal, so these waveforms

### Functions, variations and application areas of magnetic components

Westring 18 3314 Büren Germany T +49 951 60 01 0 F +49 951 60 01 3 www.schaffner.com energy efficiency and reliability 1.1 Transformers The transformer is one of the traditional components of electrical

### POWER QUALITY ANALYZER POWER METER SERIES KEW 6310 TO CONTROL COMPLETELY POWER QUALITY AND POWER CONSUMPTION (ENERGY)! NEW ARRIVAL!!

POWER METER SERIES KEW 6310 NEW ARRIVAL!! POWER QUALITY ANALYZER TO CONTROL COMPLETELY POWER QUALITY AND POWER CONSUMPTION (ENERGY)! 12 kinds of Power Measurements for Power Control and Applicable to Power

### Technical Reference. Introduction. Capstone MicroTurbine Electrical Installation

Capstone Capstone Turbine Corporation 21211 ordhoff Street Chatsworth CA 91311 USA Telephone: (818) 734-5300 Facsimile: (818) 734-5320 Website: www.microturbine.com Technical Reference Capstone MicroTurbine

### VFDs: Do s and Don ts What can t be controlled?

VFDs: Do s and Don ts What can t be controlled? Kriss Schneider President Schneider Water Services St. Paul, OR Richland, WA www.schneiderwater.com PNWS-AWWA Conference Spokane Washington Why We Are Here?

### Radial Distribution Test Feeders

Radial Distribution Test Feeders Distribution System Analysis Subcommittee Report Abstract: Many computer programs are available for the analysis of radial distribution feeders. In 1992 a paper was published

### Harmonic Distortion of the AC Power Line

Introduction Adjustable frequency drives have become the standard method of control for heating, ventilating and air conditioning (HVAC) systems due to precise control and very significant energy savings.

### Title: Australian Guidelines for grid connection of energy systems via inverters.

Title: Australian Guidelines for grid connection of energy systems via inverters. Foreword 28 April, 1998 The guidelines have been developed by a group of utility, photovoltaic and inverter industry experts

### CHAPTER 2 EXAMPLES AND TABLES

CHAPTER 2 EXAMPLES AND TABLES COMMENTARY AT 210.20(A) EXCEPTION An overcurrent device that supplies continuous and noncontinuous loads must have a rating that is not less than the sum of 100 percent of

### Power Supplies. 1.0 Power Supply Basics. www.learnabout-electronics.org. Module

Module 1 www.learnabout-electronics.org Power Supplies 1.0 Power Supply Basics What you ll learn in Module 1 Section 1.0 Power Supply Basics. Basic functions of a power supply. Safety aspects of working

### ELECTRONIC POWER SYSTEMS

ELECTRONIC POWER SYSTEMS TRADEOFFS BETWEEN SINGLE-PHASE & THREE-PHASE POWER WHITE PAPER: TW0057 1 Executive Summary Modern Electronic Systems are quite often powered from a three-phase power source. While

### SECTION 23 TRANSIENT VOLTAGE SURGE SUPPRESSORS

23.01 DESCRIPTION A. This section describes the materials and installation requirements for transient voltage surge suppressors (TVSS) for the protection of all AC and DC electrical circuits from the effects

### Table Temperature Correction Factors for Voltage Drop. Conductor Percent Correction Power Factors %

.-0 January 003 Ref. No. 0054 Tables Note: Busway voltage drop tables are shown in Section 3 of this catalog. Tables for calculating voltage drop for copper and aluminum conductors, in either magnetic

### Power Quality. Uninterruptible Power Supply

Quality Uninterruptible Supply In the electrical system environment, power disturbances will occur. These can be caused by faults on the distribution system, the operation of nearby equipment, lightning

### CHAPTER 5 PHOTOVOLTAIC SYSTEM DESIGN

CHAPTER 5 PHOTOVOLTAIC SYSTEM DESIGN 5.1 Introduction So far in the development of this research, the focus has been to estimate the available insolation at a particular location on the earth s surface

### Diode Applications. by Kenneth A. Kuhn Sept. 1, 2008. This note illustrates some common applications of diodes.

by Kenneth A. Kuhn Sept. 1, 2008 This note illustrates some common applications of diodes. Power supply applications A common application for diodes is converting AC to DC. Although half-wave rectification

### Power factor correction and harmonic filtering. Catalogue. Propivar capacitors and MV banks

and harmonic filtering Catalogue 2007 Propivar capacitors and MV banks Contents Overview 2 MV capacitor bank selection guide 2 Propivar capacitors 4 Insulation level 7.2 kv (20/60)50/60 Hz 6 Insulation

### Wave Shaping Of Current Using PWM Rectifiers

International Journal of Engineering and Technical Research (IJETR) Wave Shaping Of Current Using PWM Rectifiers Mahasweta Bhattacharya, Ashish Srivastava Abstract The paper presents the modeling and analysis

### > Executive summary. The Role of Isolation Transformers in Data Center UPS Systems. White Paper 98 Revision 0. Contents.

The Role of Isolation Transformers in Data Center UPS Systems White Paper 98 Revision 0 by Neil Rasmussen > Executive summary Most modern UPS systems do not include the internal s that were present in

### Considering the effects of UPS operation with leading power factor loads

Considering the effects of UPS operation with leading power factor loads Over the past five years, a new generation of data processing and communications equipment has become prevalent in modern data centers

### HARMONICS ISSUES THAT LIMIT SOLAR PHOTOVOLTAIC GENERATION ON DISTRIBUTION CIRCUITS

HARMONICS ISSUES THAT LIMIT SOLAR PHOTOVOLTAIC GENERATION ON DISTRIBUTION CIRCUITS Ketut Dartawan Pterra Consulting, LLC 4 Automation Lane, Ste 250 Albany, NY 12205 USA Email: ketutdartawan@pterra.us Le

### Rectiverter Wiki. Loss of mains AC voltage source seamless switch over to DC source

Rectiverter Wiki The RECTIVERTER is a technology created by Eltek. The Rectiverter is a three port module with an AC input port, an AC output port, and a bidirectional DC port. It is intended for the use

### Endicott Research Group, Inc.

Endicott Research Group, Inc. 2601 Wayne St., Endicott, NY 13760 607-754-9187 Fax 607-754-9255 DESIGN ISSUES IN THE SELECTION OF BACKLIGHT INVERTERS By: John Peterson and Scott Barney of Endicott Research

### OVERCURRENT COORDINATION GUIDELINES FOR INDUSTRIAL POWER SYSTEMS

The Electrical Power Engineers Qual-Tech Engineers, Inc. 201 Johnson Road Building #1 Suite 203 Houston, PA 15342-1300 Phone 724-873-9275 Fax 724-873-8910 www.qualtecheng.com OVERCURRENT COORDINATION GUIDELINES

### ELECTRICAL TRAINING 7 DAYS D.C. 1.0 Electron Theory, Voltaic Cells. And Electromagnetism. Materials 3.0 Resistances In Series And Parallel.

Num TITLE TABLE OF CONTENT OBJECTIVES DURATION UNIT E-01 FUNDAMENTALS OF 1.0 Electron Theory, Voltaic Cells Describe The Atomic D.C. And Electromagnetism. Structure And Its Influence 2.0 D.C. Circuits

### Tamura Closed Loop Hall Effect Current Sensors

Tamura Closed Loop Hall Effect Current Sensors AC, DC, & Complex Currents Galvanic Isolation Fast Response Wide Frequency Bandwidth Quality & Reliability RoHs Compliance Closed Loop Hall Effect Sensors

### WAVEFORM FACTS. Page 1. Manufacturer of UL Listed Products

Manufacturer of UL Listed Products 7317 Jack Newell Blvd North Fort Worth, Texas 76118-7100 817-595-4969 voice, 817-595-1290 fax 800-886-4683 toll free website wwwexeltechcom Document subject to change

### HARMONICS - Understanding the Facts - Part 3 Richard P. Bingham

HARMONICS - Understanding the Facts - Part 3 Richard P. Bingham Abstract Understanding what is important to know about harmonics can be challenging for those without extensive electrical engineering backgrounds.

### Power Quality Standards for Electric Service

Power Quality Standards for Electric Service Effective June 1, 2008 A transition period will exist from June 1 through December 31, 2008 in which installations may be approved and connected as long as

### Harmonic Mitigation, Power Factor Correction & Energy Saving with Proper Transformer & Phase Shifting Techniques

Harmonic Mitigation, Power Factor Correction & Energy Saving with Proper Transformer & Phase Shifting Techniques Abstract Harmonics in electrical distribution systems are created from a number of sources

### UPS Applications and VRLA Battery Sizing

TECHNICAL BULLETIN 41-7334 UPS Applications and VRLA Battery Sizing 41-7334/0213/CD www.cdtechno.com The uninterruptable power system (UPS) is used to protect critical equipment and processes from the

### SECTION DVD01: VOLTAGE DROP/VOLTAGE FLICKER AND TRANSFORMER SIZING GUIDELINES

Issued 06-01-07 DESIGN Section DVD00 INFORMATION SECTION Page 1 of 1 INDEX SECTION DVD01: VOLTAGE DROP/VOLTAGE FLICKER AND TRANSFORMER INTRODUCTION... Page 2 LOAD ESTIMATING AND TRANSFORMER SIZING GUIDELINES...Page

### Power Line Harmonics. and Installation Considerations. For AC and DC Drives

Power Line Harmonics and Installation Considerations For AC and DC Drives Doc # October 10, 2004 Page 1 of 14 Contents POWER LINE HARMONICS AND INSTALLATION CONSIDERATIONS FOR AC AND DC DRIVES... 3 DC

### Electrical Construction Technology

Job Ready Assessment Blueprint Electrical Construction Technology Test Code: 4130 / Version: 01 Copyright 2011. All Rights Reserved. General Assessment Information Electrical Construction Technology Blueprint

### POWER SYSTEMS STUDY SPECIFICATION

POWER SYSTEMS STUDY SPECIFICATION Load Flow Study Fault Study Protective Device Coordination Arc Flash Analysis THIS STUDY SPECIFICATION DOCUMENT CONTAINS METHODS AND PROCEDURES FOR CONDUCTING LOAD FLOW

### 615xx, 616xx, 617xxx, 646x, 64xx, 65xx Series Programmable AC source

Chroma Systems Solutions, Inc. AC Power Definitions 615xx, 616xx, 617xxx, 646x, 64xx, 65xx Series Programmable AC source Keywords: Peak, RMS, Phase, Inrush Current, Power Factor, Crest Factor, Apparent

### Specifying a Variable Frequency Drive s

Specifying a Variable Frequency Drive s Put on by Bruce Reeves and Jeremy Gonzales Dykman Electrical Covering the Western US For all of your VFD and Soft Start and Motor Needs How To Specify a Variable

### Short Circuit Current Calculations

Introduction Several sections of the National Electrical Code relate to proper overcurrent protection. Safe and reliable application of overcurrent protective devices based on these sections mandate that

### Generator Loading, Harmonics Monitoring and Mitigating Analysis in a Water Treatment Plant

Generator Loading, Harmonics Monitoring and Mitigating Analysis in a Water Treatment Plant Eddie Jones, PE; Larry Ray, PE; Tim Shuter, PE; Square D Engineering Services Abstract Water treatment plants

### Improvements of Reliability of Micro Hydro Power Plants in Sri Lanka

Improvements of Reliability of Micro Hydro Power Plants in Sri Lanka S S B Udugampala, V Vijayarajah, N T L W Vithanawasam, W M S C Weerasinghe, Supervised by: Eng J Karunanayake, Dr. K T M U Hemapala

### Power System Harmonics

Pacific Gas and Electric Company Power System Harmonics What are power system harmonics? Ideally, voltage and current waveforms are perfect sinusoids. However, because of the increased popularity of electronic

### DIVISION 26 ELECTRICAL SECTION SHORT-CIRCUIT/COORDINATION/ARC FLASH STUDY

DIVISION 26 ELECTRICAL PART 1 GENERAL 1.01 SUMMARY A. Section Includes 1. Short-Circuit, Protective Device Coordination and Arc Flash Studies 2. Labels 1.02 REFERENCES A. Institute of Electrical and Electronics

### EUROPEAN pr ETS TELECOMMUNICATION May 1996 STANDARD

FINAL DRAFT EUROPEAN pr ETS 300 132-1 TELECOMMUNICATION May 1996 STANDARD Source: ETSI TC-EE Reference: DE/EE-02001.1 ICS: 33.020 Key words: interface, power supply Equipment Engineering (EE); Power supply

### Power Electronics. Prof. K. Gopakumar. Centre for Electronics Design and Technology. Indian Institute of Science, Bangalore.

Power Electronics Prof. K. Gopakumar Centre for Electronics Design and Technology Indian Institute of Science, Bangalore Lecture - 1 Electric Drive Today, we will start with the topic on industrial drive

### Point-To-Point Method Of Short-Circuit Calculation

Point-To-Point Method Of Short-Circuit Calculation Calculation Of Short-Circuit Currents Point-To-Point Method. Adequate interrupting rating and protection of electrical components are two essential aspects

### RC NETWORKS SALES GUIDE

SALES GUIDE INTRODUCTION TO Recent developments in electronic equipment have shown the following trends: Increasing demands for numerical control machines, robotics and technically advanced appliances

### Specification Requirements DBL 700MX and 1000MX Series UPS

Specification Requirements DBL 700MX and 1000MX Series UPS Theory of Operation Upon loss of utility power, the UPS inverter shall continue to provide seamless pure sine-wave AC from the batteries without

### Figure. 1 - Split Phase 240/120V circuit (180 phase shift)

This technical note describes the option of connecting the 60Hz XW Inverter/Charger to a three-phase source by using a transformer to convert the AC source to split-phase 240/120V. INTRODUCTION: Split-phase

### T1000 Series Single Phase Uninterruptible Power Systems Product Specifications Rev 1.0 May VA (5400W) 1.0 Scope

1.0 Scope This specification document describes the Toshiba T1000 Series. The T1000 is continuous duty, singlephase, on-line, solid-state uninterruptible power supply system hereafter referred to as the

### VFD 101 Lesson 3. Parts of a Variable Frequency Drive (VFD)

VFD 101 Lesson 3 Parts of a Variable Frequency Drive (VFD) This lesson covers the parts that make up the Variable Frequency Drive (VFD) and describes the basic operation of each part. Here is the basics

### GROUND DETECTION CIRCUITS FOR STATIONARY APPLICATIONS (IN PLAIN DOWN TO EARTH LANGUAGE)

GROUND DETECTION CIRCUITS FOR STATIONARY APPLICATIONS (IN PLAIN DOWN TO EARTH LANGUAGE) Matthew Theriault Designer Hindle Power Inc. Easton, PA SCOPE AND PURPOSE OF THE PAPER Why do we bother to monitor

### R. W. Erickson. Department of Electrical, Computer, and Energy Engineering University of Colorado, Boulder

R. W. Erickson Department of Electrical, Computer, and Energy Engineering University of Colorado, Boulder Introduction to Inverters Robert W. Erickson Department of Electrical, Computer, and Energy Engineering

### The Impact of Mains Impedance on Power Quality

The Impact of Mains Impedance on Power Quality By Michael J. Russell, Consulting Electrical Engineer PowerLines, P.O. Box 1164, Waterbury, CT 06721-1164 Abstract Mains impedance is a critical parameter

### Why Your Capacitor Bank Should be Left Ungrounded

Why Your Capacitor Bank Should be Left Ungrounded Introduction Should medium voltage capacitor banks on industrial and commercial power systems be grounded? This question often arises, and the answer is

### Generator Stator Protection, under/over voltage, under /over frequency and unbalanced loading. Ramandeep Kaur Aujla S.NO 250447392

1 Generator Stator Protection, under/over voltage, under /over frequency and unbalanced loading By Ramandeep Kaur Aujla S.NO 250447392 ES 586b: Theory and applications of protective relays Department of

### No Harmony in Harmonics

No Harmony in Harmonics Common causes, implications and resolutions for problematic harmonic distortion in your electrical system Abstract Harmonic currents generated by non-linear electronic loads increase

### ARC Flash Hazard Analysis and Mitigation. IEEE Press Series on Power Engineering

Brochure More information from http://www.researchandmarkets.com/reports/2330613/ ARC Flash Hazard Analysis and Mitigation. IEEE Press Series on Power Engineering Description: Up to date analysis methodologies

### PROGRAM CRITERIA FOR ELECTRICAL ENGINEERING TECHNOLOGY

PROGRAM CRITERIA FOR ELECTRICAL ENGINEERING TECHNOLOGY Scope These program criteria apply to programs having titles involving Electrical Engineering Technology including: electrical engineering, electrical

### Voltage Distortion at the 480 VAC Bus Feeding PowerPlus Units

Transforming The Future Of Power Technology 312 Rising Sun Rd. Bordentown, NJ 08505 phone: 800-742-5695 fax: 609-298-1982 e-mail: sales.caps@nwl.com www.nwl.com Consult factory with detail requirements

### FUNDAMENTALS OF CATHODIC PROTECTION

FUNDAMENTALS OF CATHODIC PROTECTION Corrosion is the deterioration of a metal because of a reaction with its environment. For the purpose of this report, corrosion is the result of an electrochemical reaction

### 3. TYPES OF SERVICE AVAILABLE. 3.1 Scope

3. TYPES OF SERVICE AVAILABLE 3.1 Scope UI supplies 60 hertz, alternating current with different voltage and ampere ratings. Not all voltage and ampere ratings are available throughout the entire service

### insulate and isolate

Introduction to Power Systems Expensive! Influential!Intrusive! Source: Riadh W. Y. Habash, Electromagnetic Fields and Radiation, Marcel Dekker, New York, 2001. In North America, power systems operate

### ELECTRICAL PLAN EXAMINATION CHECKLIST

Electrical Plan Requirements / Diagrams of Feeders 18-27-215.5 Diagrams of Feeders Electrical Plan Requirements / Diagrams of Feeders / Required Plans In new or remodeled buildings, complete and detailed

### Quantec Wiring Instructions

Approved Document No. DNUQ777 Rev Quantec Wiring Instructions GENERAL Quantec can be compared to a very sophisticated analogue addressable fire alarm system where the integrity of the wiring is of paramount

### The George Washington University School of Engineering and Applied Science Department of Electrical and Computer Engineering

The George Washington University School of Engineering and Applied Science Department of Electrical and Computer Engineering Final Design Report Dual Channel Stereo Amplifier By: Kristen Gunia Prepared

### APPLICATION NOTE - 017

APPLICATION NOTE - 017 PWM Motor Drives Theory and Measurement Considerations Pulse Width Modulated (PWM) power electronic techniques represent a large and increasing proportion of modern power electronics.

### SAFETY PRECAUTIONS AND INSTRUCTIONS FOR USE OF TECHNICAL INFORMATION

SAFETY PRECAUTIONS AND INSTRUCTIONS FOR USE OF TECHNICAL INFORMATION Please read and understand the product instruction manual before installing, servicing or operating Yaskawa products. Technical content

### Power System Analysis Prof. A. K. Sinha Department of Electrical Engineering Indian Institute of Technology, Kharagpur. Lecture 2

Power System Analysis Prof. A. K. Sinha Department of Electrical Engineering Indian Institute of Technology, Kharagpur Lecture 2 (Refer Slide Time: 01:01) Welcome to lesson 2 on Power System Analysis.

### Electrical Principles Section 5

5 Electrical Principles Section 5 www.hubbellpowersystems.com E-mail: hpsliterature@hps.hubbell.com Phone: 573-682-5521 Fax: 573-682-8714 210 North Allen Centralia, MO 65240, USA Copyright 2015 Hubbell

### Fundamentals of Modern Electrical Substations Part 1: Mission of Electrical Substations and their Main Components

Fundamentals of Modern Electrical Substations Part 1: Mission of Electrical Substations and their Main Components Course No: E02-010 Credit: 2 PDH Boris Shvartsberg, Ph.D., P.E., P.M.P. Continuing Education

### The Importance of the X/R Ratio in Low-Voltage Short Circuit Studies

The Importance of the X/R Ratio in Low-Voltage Short Circuit Studies DATE: November 17, 1999 REVISION: AUTHOR: John Merrell Introduction In some short circuit studies, the X/R ratio is ignored when comparing

### HARMONIC DISTORTION IN THE ELECTRIC SUPPLY SYSTEM

Technical Note No.3 March 2000 HARMONIC DISTORTION IN THE ELECTRIC SUPPLY SYSTEM This Technical Note discusses harmonic distortion, its causes and adverse effects, what levels are unacceptable and how

### The full wave rectifier consists of two diodes and a resister as shown in Figure

The Full-Wave Rectifier The full wave rectifier consists of two diodes and a resister as shown in Figure The transformer has a centre-tapped secondary winding. This secondary winding has a lead attached

### Transient Overvoltages on Ungrounded Systems from Intermittent Ground Faults

Transient Overvoltages on Ungrounded Systems from Intermittent Ground Faults Introduction Many papers and standards [1][2][3][4][5][6] have discussed grounding of an electrical distribution system. Of

### Harmonics in your electrical system

Harmonics in your electrical system What they are, how they can be harmful, and what to do about them Abstract Harmonic currents, generated by non-linear electronic loads, increase power system heat losses

### The Facts About Harmonics and Power Factor. Power Quality: Harmonics & Power Factor Correction

The Facts About Harmonics and Power Factor Power Quality: Harmonics & Power Factor Correction 1 Agenda I. Harmonic Basics II. Harmonic Mitigation Methods III. Active Harmonic Filters IV. Applications V.

### Harmonics mitigation and solutions

Harmonics mitigation and solutions Summary I. Introduction II. Harmonics mitigation solution III. Case study lv.conclusion Schneider Electric 2 I. Introduction II. Harmonic mitigation solution III. Case