2 2 WHAT IS AN AIR SCRUBBER? In the simplest terms, an air scrubber is a portable filtration system. It draws in air from the surrounding environment and passes it through a series of filters. These filters efficiently remove particles from the air to help improve indoor air quality. Air scrubber or negative air machine? Often the terms "air scrubber" and "negative air machine" are used interchangeably. However, the two terms refer to very different applications. regular air scrubber negative air machine An air scrubber stands alone in the center of a room without any ducting attached. The air it filters is recirculated to the surrounding area. An air scrubber application helps improve the general air quality of the jobsite. A negative air machine uses ducting to remove contaminated air from a sealed containment area. The filtered air is exhausted outside of the containment. This creates negative air pressure (a slight vacuum effect) inside the containment relative to surrounding areas. A negative air machine application helps limit the spread of contaminants to other areas inside the structure. Many air scrubbers can also be used as a negative air machine, but this requires additional features: ductable in and ductable out sealed housing precise airflow adjustment a blower motor with variable speed to maintain containment
3 WHY SHOULD I USE AN AIR SCRUBBER? 3 The goal of every restoration job is to safely and efficiently return the indoor environment to pre-loss condition for the customer. Part of this responsibility is to address the quality of the air inside the structure. Any job that involves cleanup of sewage, mold, and/or fire damage will generate significant amounts of particulates and odiferous (smelly) gases. These contaminants are a direct result of the damage itself, as well as the necessary process of treating and cleaning damaged materials. This includes not only damage in the occupied space, but also contaminants in wall or ceiling cavities that may be disturbed and unknowingly introduced into the occupied space. These contaminants can settle on carpet, upholstery, furnishings, and be drawn into the HVAC system. Even clean-water losses are susceptible to compromised indoor air quality. The high-velocity airflow necessary for effective drying does more than evaporate moisture into the air it also stirs up millions of microscopic particles that have been trapped in the carpet or have settled on structural materials. Some of these particles, such as human skin cells, animal hair, and dirt, are nearly always present but are innocuous to occupant health. Chemical agents such as soot particles, hydrogen sulfide gas, and mercaptans (organic sulfur-containing chemicals generated by sewage-borne bacteria) can create unwanted visual damage and noxious odors. Potential human allergens such as cat or dog dander or dust mites may be released in large concentrations from damaged carpets and furniture. Most importantly, readily aerosolized biological agents such as sewage-born bacteria or mold spores (and spore byproducts) are likely to be introduced into the air in large amounts during the drying restoration process and these agents can cause adverse human health effects when inhaled. Ultimately, if these pre-existing or newly introduced contaminants are not removed effectively they will impact the indoor air quality (IAQ) of the worksite and compromise the quality of the entire restoration job. Some contaminants can even create a potential indoor health hazard. An air scrubber helps prevent these undesirable and potentially harmful particles and gases from remaining in the indoor environment or lodging in your equipment. By greatly reducing the types and quantity of airborne particles, an air scrubber also reduces the chances that occupants or technicians will inhale contaminants or gases. Removing contaminants safely, efficiently, and cost-effectively with an air scrubber is a great benefit to your business, your employees, and your customers. For your occupants An air scrubber helps create a cleaner, safer indoor environment for occupants both during the restoration work and after it is done. Occupants who are able to re-enter a previously damaged building without visual, odor, or health complaints are likely to be satisfied with your work. Using an air scrubber on a job is a cost-effective way to increase the quality and value of the service you offer to your customers. For your technicians Using an air scrubber on the job also reduces the risk for those working on the job. In many cases, an air scrubber may be much more effective, comfortable, and less expensive than requiring the use of respirators. An air scrubber is a short-term and long-term investment in the health and productivity of the people who do the work of restoration. Legal implications An air scrubber not only addresses indoor air quality concerns while the work is being performed, it can also help limit your legal exposure long after the job is done. This is especially true with water damage and mold contamination. Sometimes a restored structure develops a problem with IAQ due to a pre-existing condition or subsequent damage that is beyond the scope of your company's responsibility. By using an air scrubber on every job, you are taking an extra step to minimize unintended liability and complications that affect indoor air quality and occupant health. Increase safety and productivity Improving IAQ also benefits equipment performance and quality of work. For instance, in water damage restoration an air scrubber captures dirt, dust, and debris that might otherwise coat dehumidifier coils (thereby decreasing water removal efficiency) and/or clog airmover intake vents (thereby reducing airflow). An air scrubber helps keep your equipment clean so that it can perform at its best.
4 4 WHAT'S IN THE AIR? Pollutants of concern Air is composed of much more than nitrogen, oxygen, and carbon dioxide. Even the relatively "clean" air of a normal (non-smoking) household or office environment contains a variety of microscopic particles, allergens, and organic chemicals. Most of these commonly occurring agents are the result of normal human and animal activity, plants, insects, cleaning products, and personal hygiene products. The normal introduction of dirt and certain soil- and plant-borne mold spores into the indoor environment occurs through open windows, doors, and foot traffic. These particulates comprise most of what is found in normal indoor dust, both on surfaces (such as carpets) and in the air. A normal indoor environment also includes trace quantities of volatile organic chemicals (VOCs). These VOCs are the result of evaporation or off-gassing from carpeting, furniture, and certain household or other chemical products. Most of these substances are either harmless or, in a few cases, represent potential allergens to a small number of genetically susceptible individuals. These normally occurring indoor substances can be distinguished from actual indoor "contaminants" or "pollutants." The latter substances have the potential to cause adverse health effects, both short-term (acute) and long-term (chronic). The Environmental Protection Agency (EPA) 1 and American Lung Association 2 have both published articles listing pollutants of concern. These pollutants can be classified into two types: particulate and gaseous. Particulate Pollutants These very small solid or liquid particles are light enough to float around in the air. They may include organic (i.e. carbon-containing) or inorganic compounds and both dormant and living organisms. Of primary concern are: depth loading particles captured in filter WDR FILTRATION STUDY 3 1) 2) Particles found on Standard Water Damage Jobs Debris Fibers Ascospore Aspergillus ochraceus Aspergillus versicolor Bacillus sp. 1 Bacillus sp. 2 Bacillus sp. 3 Chactomium sp. Cladosporium spp. Epithelial cells Hyphae Pollen Insect parts Micrococcus sp.1 Micrococcus sp. 2 Nigrospora spp. Paecilomyces sp. Penicillium sp.1 Stachybotrys - like Taeniolella spp. Torula spp. Trichoderma sp. D. Pteronysisinus (Der p I) (dust mite) D. Farinae (Der f I) (dust mite) Cat allergen (Fel d I) non-visible respirable particles that can penetrate deep into the lungs where they may stay a long time and cause acute or chronic health effects; and larger particles such as pollen, animal dander, or dust that do not penetrate as deeply, but may cause an allergic reaction. Gaseous Pollutants These include combustion gases and organic chemicals that are not associated with particles. With the development of increasingly sophisticated measurement equipment, hundreds of different gaseous chemical pollutants have been detected in indoor air. Sources include combustion appliances, cigarette smoking, vehicle exhaust, building materials, furnishings, paints, adhesives, dyes, solvents, cleaners, deodorizers, personal hygiene products, pesticides, and even the cooking of food or the metabolic processes of humans, animals or plants. Health effects depend on the type and concentrations of gaseous pollutants, frequency and duration of exposure, and in the case of allergenic substances, individual sensitivity. Some of these chemicals are simply transient irritants, capable of causing short-lived reactions such as watering or burning of the eyes or nose, cough, or other adverse reactions related to their unpleasant odor. For all but a few specific agents, the long-term health effects (at relatively low concentrations found in typical indoor environments) are unknown and/or not studied. 1 United States Environmental Protection Agency and the United States Consumer Product Safety Commission Office of Radiation and Indoor Air, The Inside Story: A Guide to Indoor Air Quality - EPA Document #402-K , 19 June 2003 <http://www.epa.gov/iaq/pubs/insidest.html>. 2 American Lung Association, Residential Air Cleaning Devices: Types, Effectiveness, and Health Impact, 19 June 2003 <http://www.lungusa.org/pub/cleaners/air_clean_toc.html>. 3 Information presented by Dri-Eaz and 3M at the 2003 Dri-Eaz Restorative Drying Symposium
5 5 Because many of these particulate or gaseous agents are reasonably well tolerated by most individuals in otherwise "normal" indoor environments, their role as actual "pollutants" in buildings that sustain water, fire, or sewage damage is probably minimal. However, substances of concern to restoration professionals mold, bacteria and their odorcausing chemicals, and combustion products may nevertheless be difficult to identify by sight or smell from these many common background substances. For this reason, in at least some restorations for water damage, fire, mold, or sewage, sampling of the indoor air and dust for specific biological (and less often, chemical) contaminants is necessary prior to starting the restoration work. Measured in microns Most airborne particles of concern to human health are not visible to the naked eye. The size of these particles is measured in microns. A micron, short for micrometer and abbreviated µm, is one millionth (1/1,000,000) of a meter. A particle of 1 micron in diameter is far smaller than the period that ends this sentence. The following chart compares the average sizes of some common airborne particles and gas molecules. PARTICLE SIZE SPECTRUM Virus Tobacco Smoke Oil Smoke Respirable Pollens Household Allergens Paint Pigment Mold Spores Fungi Bacteria Invisible Visible Human Hair Particle Size µm
6 6 Settling of particles The smallest particles are light enough to be suspended in the air indefinitely. However, most indoor airborne particles are gravimetric. That is, they will eventually settle to the ground or onto surfaces like furnishings, counter tops, and windowsills. In the turbulent environment of water damage restoration or wherever else high-velocity airflow is employed even the heaviest particles can remain airborne where they may be inhaled. Restoration procedures often disturb particulate matter in such a way that the indoor air, if not sufficiently filtered, can become contaminated. Depending on size and other physical properties, as well as environmental conditions, some particles can take quite a long time to settle. In the case of very small mold spores arising from water-damaged building materials, they are often able to "latch on" to larger particles and remain in the settled dust for long periods of time. The following chart shows the relative time it takes for particle sizes to settle one meter under still (non-turbulent) indoor air conditions. APPROXIMATE PARTICLE SIZES AND TIME TO SETTLE 1 METER 3 Particle type Diameter (µm) Time Human hair seconds Skin flakes Visible dust > 10 Common pollens Mite allergens minutes Fungal spores 2-10 Bacteria 1-5 Cat dander hours Tobacco smoke Metal and organic fumes < Cell debris Viruses < days 3 Spengler, John D, Ph. D., Harvard School of Public Health, Boston, MA; referenced in Residential Air Cleaning Devices: Types, Effectiveness, and Health Impact (American Lung Association), 19 June 2003, Appendix 1: Table - Approximate Particle Settling Time <http://www.lungusa.org/pub/cleaners/fig2.html>.
7 HOW AN AIR SCRUBBER WORKS In order to remove airborne particles from the surrounding environment, an air scrubber draws the air through a series of filters. Each filter stage operates with progressively higher efficiency. The net effect is to produce the cleanest air possible at the highest rate of airflow through the entire filter system. Pre-filters The first stage of filtration is known as the "pre-filter" stage. Pre-filters capture the majority of "larger" particles that may range from visible down to 10 µm. This is accomplished by arranging several pre-filters in order of increasing efficiency. By capturing these larger particles, a set of relatively inexpensive pre-filters actually extend the service life of a more expensive primary filter. Without pre-filters, the high-efficiency primary filter would load with particles earlier, thereby causing the airflow rate and filtration efficiency to decrease. Removing these relatively larger particles with pre-filters helps the entire unit maintain high airflow, better filtration efficiency, and process more cubic feet per minute (CFM). Depending on the duration of the job, pre-filters may be replaced several times during the lifetime of one high-efficiency primary filter. Optional carbon filters Most air scrubbers include space in the pre-filter stage for an optional carbon filter. The carbon filter captures the gas- and vapor-phase molecules that the human nose detects as odors. This is accomplished through a process called adsorption, where the gaseous molecules are physically attracted to the surface of the carbon. The greater the surface area of the carbon, the more effective the filter is at adsorbing odor-causing molecules. Activated carbon is the preferred material for odor removal because it has a very large surface area. Just one gram of activated carbon may have as many as 2,000 square meters of surface area to adsorb gaseous odor molecules. The service life of a carbon filter depends on the type and concentration of the odor. Your sense of smell will let you know when it's time to replace the carbon filter. pre-filter primary HEPA filter Primary filter The final stage of filtration in an air scrubber is the primary filter. The primary filter completes the filtration process by removing the tiniest particles from the air. These particles may be as small as 0.3 microns in diameter. An effective primary filter should be constructed of HEPA filter media. HEPA media is laboratory-tested to capture at least 99.97% of all 0.3-micron particles that pass through the filter media at a predetermined rate of airflow. It is important to recognize that not all HEPA-media filters provide the same level of performance on the jobsite that they provide in the laboratory. We'll address this issue in the section titled, "The HEPA Facts." The primary filter should be changed during a job when it becomes loaded with particulate and performance begins to suffer. To avoid cross-contamination, the primary filter should be changed between every job. Blower No matter how effective the filter system is, an air scrubber needs a dependable and versatile blower. The blower pulls the air through the filters and exhausts the filtered air out of the unit. If the unit is to be used as a negative air machine, the blower should be powerful enough to provide sufficient static pressure for maintaining constant negative air pressure in the contained area. It is important that the blower's power complements the efficiency of the installed filter system. A blower that is too powerful (that is, it pulls too many CFM) may overwhelm a mismatched filter system and actually decrease the system's efficiency. Some air scrubbers offer the added benefit of variable speed operation. This feature allows the operator to adjust the blower speed to better filter small rooms and containment areas. 7
8 8 THE HEPA FACTS The most common buzzword surrounding air scrubbers is HEPA, which stands for High Efficiency Particulate Air in reference to filter performance. It seems that nearly every manufacturer of high-efficiency filters or air-cleaning devices claims to be HEPA or have a rating of 99.97%. But what does this HEPA rating actually mean? The history of HEPA In order to discover what sort of difference a HEPA filter actually makes in real world applications, let's look back at the origins of HEPA filtration. The first HEPA filters were developed in the 1940s by the research and development firm Arthur D. Little as part of the Manhattan Project, a classified U.S. government project that developed the atomic bomb. The researchers needed a way to control the spread of very small, radioactive particles. They identified the 0.3-micron particle as the most penetrating particle into the human lung and focused their testing of filter performance around this particle size. The initial filters were so effective that they were referred to as "absolute filters." The generic term "HEPA" came into use in the 1950s after the absolute filter was commercialized. FILTRATION PRODUCTS Many Manufacturers Offer Few Manufacturers Offer Increasing Efficiency HEPA Test Velocity Application Velocity Increasing Flow Rate
9 9 The 99.97% standard The modern day standard for HEPA performance is very similar to the original tests performed for the Manhattan Project nearly 60 years ago. Though not regulated by any government agency, HEPA filter manufacturers conform to the recommended procedures set by the Institute for Environmental Sciences and Technology (IEST). IEST-RP- CC021.1 and IEST-RP-CC001.3 are the most cited recommended practices for determining whether or not a filter meets true HEPA standards. IEST-RP-CC021.1 specifies that, in order to qualify as HEPA media, the filter media must be 99.97% efficient against 0.3-micron oily aerosol particles traveling at a specified rate of 5.3 centimeters (cm) per second. This test focuses on the material out of which a filter is constructed. IEST-RP-CC001.3 specifies that, in order to qualify as a HEPA filter, the entire filter must be 99.97% efficient against 0.3-micron oily aerosol particles at the application flow rate. This test focuses on the entire filter in its final constructed form. Though these brief descriptions do not even begin to describe the tests in complete detail, they raise issues that are important to a discussion of HEPA filtration. Note that each test addresses three separate factors: particle type, particle size, and particle flow rate, or the speed at which particles encounter the filter. These are all critical to establishing whether a filter meets HEPA standards of 99.97% efficiency. HEPA and application rates The particle flow rate at which a filter is tested has a significant effect on its efficiency rating. The slower the rate, the longer the dwell time for particles within the filter and the easier they are to capture. A slow particle flow rate results in a higher efficiency rating. In the previous section we noted that both IEST-RP- CC021.1 and IEST-RP-CC001.3 account for particle flow rates as part of the testing procedure. When testing the media alone (IEST-RP-CC021.1), this rate is defined as 5.3 cm/second. But when testing the entire filter (IEST-RP-CC001.3), this rate is left open to interpretation as the "application rate," meaning the rate at which the filter will be used when performing the intended work. In order to qualify as HEPA according to the IEST, many air scrubber filters are tested at slower application rates. The actual particle flow rate (velocity in cm/second) may vary according to the size of the filter but translates to processed volumes of air as low as 150 to 200 CFM or less. This is in sharp contrast to the stated capacity of a typical air scrubber that may process CFM (or more) in real-world operating conditions. Thus, a filter that is merely designed to pass a test for HEPA efficiency in the laboratory may be overwhelmed at normal operating airflow on the job. It might provide good filtration, but it will not necessarily be HEPA. It's important to look at more than just claims of HEPA efficiency when selecting an air scrubber for your needs. Make certain that the filtration system is designed for high volumes of airflow. You should also look for a filter system that will help to minimize the build-up of pressure on the filters (also known as "pressure drop").
10 10 Pressure drop By design, every filter system creates some resistance to airflow. As the blower pulls air through an air scrubber's filter system, any resistance to airflow will create a drop in pressure (a decrease in airflow) behind the filters. The greater this resistance to airflow, the greater the pressure drop and the fewer useable CFM for the job. Open filter media, low pressure drop Optimal filter systems minimize this resistance (i.e. they have a low pressure drop) to help maximize filtration efficiency. Lower quality filter systems create high resistance (i.e. high pressure drop) that decreases filter performance. An air scrubber with low pressure drop will be able to process higher volumes of air with less strain on the motor. The ideal filtration system combines high filtration efficiency, high volumes of airflow, and low pressure drop for the best real-world performance. Loading capacity How a HEPA filter collects particles is another important point to consider. A filter design that collects particles mostly on the surface (like a lint trap on a dryer) will load quickly, causing an increase in pressure drop, a decrease in airflow and a decrease in filtration efficiency. On the other hand, a filter design that can utilize its entire depth to capture particles, not just the surface, will maintain a lower pressure drop, higher airflow, higher filtration efficiency, and provide a longer service life. This performance feature is often called "depth loading," and is advantageous to the restorer for the reasons outlined above. High airflow throughput Tighter filter media, high pressure drop Durability of HEPA filters The durability of HEPA filter media plays a critical role in the quality of an air scrubber's performance in the real world. A filter may perform perfectly well in the laboratory, but should it be damaged through shipping or handling, it will suffer a permanent loss of filtration efficiency. Fragile media can be crushed or torn, leaving gaps and holes that allow particles to pass through unfiltered and negating the benefits of a HEPA rating. Make certain that the filter media in the air scrubber you select is designed to withstand the rigors of restoration work. It should be resilient enough to withstand the bumps and drops common to being transported as freight (before the purchase) and installed in the unit (on the jobsite). resistance Lower airflow throughput resistance
11 11 CLEAN AIR DELIVERY RATE (CADR) Clearly, airflow is a critical element in the efficiency of a filtration system. As emphasized earlier, a filter that meets the HEPA standard when tested in the laboratory at 150 CFM may not provide HEPA-quality filtration at 500 CFM. Even though a CFM rating or air changes per hour tells you little about the quality of filtration, this is the way the restoration community has compared air scrubber performance. The Association of Home Appliance Manufacturers (AHAM) has a rating system that's been used to compare performance filtration equipment for years: Clean Air Delivery Rate (CADR). CADR is a measure of the actual volume of cleaner air delivered per minute. It factors in how the filtration system and the entire machine work together, at the airflow rate you're using. The highest CADR numbers belong to air scrubbers that combine high filtration efficiency, high airflow, and low pressure drop. Selecting the proper filter media can optimize CADR. The CADR system is unique because it indicates how efficiently a machine removes particles from the air not just the number of CFM or the type of filtration. The restoration/remediation market is beginning to use the CADR system because it represents a better way of comparing performance between units. CADR is a step forward for the industry because it tells you how much cleaner the air really is, when processed by a particular machine at a particular flow rate. CADR: VOLUME OF CLEANER AIR DELIVERED PER MINUTE The highest CADR numbers belong to air scrubbers that combine high filtration efficiency, high airflow, and low pressure drop. 450 CADR airflow airflow airflow Airflow: 450 CFM Filtration Efficiency: 0% CADR: 0 CFM Airflow: 450 CFM Filtration Efficiency: 80% (low pressure drop) CADR: 360 CFM Airflow: 450 CFM Filtration Eff: 99.97% (True HEPA) (low pressure drop) CADR: 450 CFM
12 12 HOW TO USE AN AIR SCRUBBER Preparation Before using an air scrubber, be certain that you start with a clean unit with new filters. The best practice is to thoroughly clean the unit and replace both the pre-filters and the primary filter after every job. This extra step eliminates the possibility of cross-contaminating a clean space as fungal spores and other microbes can grow through any filter over time. The cost of filters should be considered part of the cost of restoration. During the job, change filters as soon as the pressure drop increases to the point where filtration efficiency begins to suffer. Higher quality air scrubbers are able to monitor pressure drop and alert you when filters need changing. Placement for water damage For water damage restoration, an air scrubber should be placed in the center of the affected area. The air scrubber will draw in the surrounding air and return the filtered air back into the same environment. To operate the air scrubber, simply turn the unit on. It will immediately begin drawing in air through the filter system and capturing airborne particles. When working in large areas or spaces that are divided by walls, doorways, or hallways, you may need to place several air scrubbers at strategic locations. For more information, see the next section "Maximizing circulation." Maximizing circulation 500 CFM or 2000 CFM? Contaminants in the air may not be evenly dispersed throughout a room or structure. It is possible for "stale" pockets of air to remain out of an air scrubber's reach. These stale pockets may be in corners, closets, hallways, through doorways, or in any area that is isolated or blocked from the air scrubber. Remember, dirty air will not move to clean air. The only way to truly filter an indoor structure is to place air scrubbers in several strategic locations. The goal is to eliminate stale pockets: several 500 CFM units will provide a better environment than one CFM unit. If conditions allow you may consider placing airmovers in a room or structure to specifically improve circulation of the indoor air for better filtration. You may also wish to duct the process air from the air scrubber to another part of the structure to increase air circulation between rooms. More likely, you may need to place more than one air scrubber throughout a structure to minimize stale pockets of air. Determining ACH ACH stands for air changes per hour. An air scrubber accomplishes one "air change" when it filters a volume of air equivalent to the size of the room (known as "equivalent volume"). For instance, a room with 500 square feet and 8-foot ceilings has 4,000 cubic feet. In this situation, an air scrubber would achieve one air change after filtering the room's equivalent volume, or 4,000 cubic feet of air. Of course this figure will vary depending on the size of the structure or area. Currently there are no standards for the minimum number of ACH on water damage restoration. All standards for ACH come from other industries such as asbestos remediation, mold remediation, or hospital sterilization. The standards vary widely depending on application and jurisdiction. For example, the IICRC's S520 mold guidelines (Sec ) recommend that "a minimum of four air changes per hour be maintained for ventilation and contaminant dilution" when using pressure differentials. As a general rule you should achieve a minimum of 6 ACH. This means that an air scrubber must complete six air changes every hour, or one every 10 minutes. If you can increase the ACH, do so. 1 2 You can determine the CFM needed to achieve 6 ACH with a simple 3-step formula: 3 Calculate the room's volume in cubic feet. To do this, multiply the square footage by the ceiling height. In the example above, the floor has an area of 500 square feet (multiple length by width) and 8-foot ceilings. 500 x 8 = 4,000 cubic feet of volume. Multiply the room's volume (in cubic feet) by 6 to find the total cubic feet of filtration needed per hour 4,000 cubic feet x 6 = 24,000 cubic feet per hour Divide the total cubic feet per hour by 60 to convert to cubic feet per minute (CFM) 24,000 cubic feet per hour / 60 minutes = 400 CFM You can see that you would need an air scrubber with 400 CFM to maintain 6 ACH in a 4,000 cubic foot space. You can apply this formula to any closed environment and determine the CFM required to achieve 6 ACH. New to the industry is CADR, or Clean Air Delivery Rate. This is a more effective way at matching an air scrubber to the volume of a space.
13 13 WHEN TO USE AN AIR SCRUBBER Water damage restoration One of the most practical and necessary places to use an air scrubber is on every water damage restoration job. The immense amount of airflow necessary for the evaporation of moisture from carpet, pad, drywall and other damaged materials also stirs up a vast amount of debris into the air from carpet, furniture, and ductwork. These airborne particles can range from allergens normally found indoors (like pet dander) to potentially hazardous contaminants that may be a result of water damage (like mold spores). Use an air scrubber on water damage to drastically reduce the number of these airborne particles and improve the quality of indoor air. Fire damage restoration Use an air scrubber on fire damage to not only reduce particle counts, but to reduce odors. Supplement the pre-filter stages with an optional carbon filter to effectively capture gas molecules that cause odors in addition to airborne debris stirred up by the restoration and reconstruction process. Dust control An air scrubber is a valuable tool in any environment where dust is undesirable for reasons of safety, comfort, or precision. Situations may include workshops, construction sites, or factory production lines. Odor Control With an optional carbon filter placed in the pre-filter stage, an air scrubber can remove odor-causing gas molecules from the air in addition to microscopic particles. Applications include cleanup for fire, sewage, mold contamination, and even standard carpet cleaning jobs. Sewage remediation Use an air scrubber with an optional carbon filter to help control odor and reduce the number of gaseous pollutants while remediating sewage damage. Negative air machine for mold remediation Certain air scrubbers can also be used as negative air machines for containment purposes. In order to function effectively as a negative air machine, an air scrubber must include these features: ductable in and ductable out capability sealed housing precise airflow adjustment For mold remediation, an air scrubber/negative air machine should be placed outside the containment. It will draw air from the contained area through ducting and exhaust filtered air outside the containment area. Use the variable speed operation to control the pressure differential of the containment area and thereby avoid collapsing the containment barrier because of too much vacuum pressure from the air scrubber/negative air machine. Achieving true HEPA filtration efficiency of 99.97% (as described earlier in this guide) is especially critical when using an air scrubber as a negative air machine, because the air scrubber (and filter) will only process the air one time, as it's ducted out. According the IICRC's S520 mold guidelines (Sec. 10.3), "If pressure differentials are used, it is highly recommended that they be created using HEPA air filtration devices set up as negative or positive air machines." An air scrubber/negative air machine helps prevent contaminants from escaping from a properly constructed containment area.
14 14 AIR SCRUBBER SAFETY What an air scrubber does not do Though an air scrubber is a powerful and versatile tool when properly applied, there are inherent limits to its abilities. The most significant limitation is implied by its name an air scrubber helps clean the air but it does not help clean surfaces. An air scrubber is effective only against airborne particles (and gaseous pollutants) that pass through the filter system. Particles that settle on furniture, countertops, or other surfaces, or which are drawn in to the HVAC system, are beyond an air scrubber's reach. The use of an air scrubber is not a guarantee that the air will be decontaminated at the conclusion of the job. The design of any building will have spaces of "dead air" that resist circulation. It is possible that an air scrubber will miss certain groups of airborne particles because that air will never pass through the filter system. An air scrubber will not capture every single particle or gas molecule that passes through the filter system. Even the most efficient air scrubber filter systems are only rated 99.97% effective against particles 0.3 microns in diameter or larger. Some particles in this size range and smaller will be able to pass through the filter without being captured. Changing filters and cleaning To help prevent cross-contamination between jobs, limit your liability, and to optimize the performance of your air scrubber, you should perform a basic maintenance routine between every use: decontaminate the entire unit inside and out, (Milgo QGC works great for this) and replace the entire filter system (both pre-filters and primary) before placing the unit on a new job. During a job, filters should be changed when they become so loaded with particles that they begin to reduce airflow and increase pressure drop. Overly loaded filters not only restrict CFM, they can result in a loss of filtration efficiency. You may need to monitor the exhaust airflow with a manometer at selected intervals to determine pressure drop. Some air scrubbers include on-board pressure sensors that automatically alert you when the filters need changing. Use appropriate PPE An air scrubber captures particles that can be hazardous to human health. During the process of changing filters, decontamination, or performing maintenance, large concentrations of captured particles can become airborne in the immediate area. For these reasons, air scrubber operators should wear appropriate personal protection equipment (PPE) when performing any type of service on an air scrubber. A NIOSH-approved respirator is always essential for these tasks. If you've used the air scrubber for mold remediation or in another environment with known contaminants, you should also consider wearing gloves, eye protection, and coveralls. Loaded filter Disposal of filters The particles captured by a filter can cause adverse human health effects should they be re-released into the air. For this reason, you should dispose of used filters with care. You should place used filters in a plastic bag and seal the top before disposing. Always follow local regulations when disposing of used filters.
15 15 Classes and education This guide to air scrubbing is a great place to begin your education in the uses, features, and advantages of air scrubbers. Now you understand more about how an air scrubber can help to improve indoor air quality for various types of restoration jobs and what features to look for when you purchase. But this publication should not be the end of your education on air scrubbing and jobsite air filtration. There are currently a number of classes available that comprehensively address building investigation, restoration methods, and indoor air quality. As the restoration and construction industries continue to learn about the importance of jobsite filtration there will be even more opportunities to learn. An investment in your education will ultimately benefit your customers and employees, and in so doing, increase the quality, reputation, and longevity of your business.
DRI-EAZ PRODUCTS, INC., 15180 JOSH WILSON RD., BURLINGTON, WA 98233 1-800-932-3030 FAX: (360) 757-7950 www.dri-eaz.com GUIDE TO air scrubbing 2 WHAT IS AN AIR SCRUBBER? In the simplest terms, an air scrubber
Please Note: EPA neither certifies nor recommends particular brands of home air cleaning devices. While some home air cleaning devices may be useful in some circumstances, EPA makes no broad endorsement
Trane CleanEffects Patented technology. Superior performance. Trane CleanEffects is unlike anything else out there. So is the air it produces. Today s air needs tomorrow s air cleaning system. There may
Indoor Air Quality FILL YOUR HOME WITH AIR THAT IS AS CLEAN AS IT IS COMFORTABLE. QUALITY AIR STARTS HERE. AccuExchange Energy Recovery Ventilator Improve your home s indoor environment by exchanging stale
AIR FILTRATION AND THE USE OF HEPA FILTERS IN BIOLOGICAL SAFETY CABINETS Suzy Whitt Introduction Air filtration is a topic affecting everyone s lives, whether it is for occupational safety requirements,
Mold and Mildew Mold and mildew can be detected by sight, smell and touch. Molds are usually black (not unlike the molds that grow in showers and between grout), green or tan in color, but can be in various
605 Satellite Blvd., Suite 300 Suwanee, GA 30024 678.889.4200 FAX 678.889.4201 SALES 800.634.9091 www.abatement.com Why Insurers Should Approve the Use of Portable Air Scrubbers on Every Water Damage Remediation
Robert McCabe Director, Health Care Solutions HTS Chicago Improved Air Quality and Energy Efficiency through Air Handler Filtration System Upgrade Biography Robert McCabe has been involved in commercial
Radford University Indoor Air Quality Management Plan Spring 2015 Introduction Concerns with Indoor Air Quality (IAQ) have increased since energy conservation measures were instituted in office buildings
Questions and Answers on Stachybotrys chartarum and other molds Questions and Answers 1. I heard about "toxic molds" that grow in homes and other buildings. Should I be concerned about a serious health
Mold Basics The key to mold control is moisture control. If mold is a problem in your home, you should clean up the mold promptly and fix the water problem. It is important to dry water-damaged areas and
Stachybotrys chartarum a mold that may be found in water-damaged homes November 2000 Environmental Health Investigations Branch California Department of Health Services Stachybotrys chartarum ecology Stachybotrys
Asbestos in the Workplace: A Guide to Removal of Friable Asbestos Containing Material Revised November 21, 2013 Application Code of Practice Where asbestos is present or believed to be present in a workplace
Mold and Indoor Air Quality in Schools University of Nebraska Lincoln Extension Indoor Air Quality (IAQ) Air quality can be affected by many compounds and organisms Molds and other indoor air pollutants
AccuClean For Air That s As clean as it is comfortable. Why is American Standard AccuClean air filtration better than the rest? Cleaner air starts with better airflow. Thanks to the patented technology
1.0 Introduction DESERT RESEARCH INSTITUTE This Desert Research Institute (DRI) Mold Assessment and Remediation Procedure was established to assure that consistent and uniform information is provided to
APPENDIX B. EPA s Investigating, Evaluating, and Remediating Moisture and Mold Problems (see EPA website for complete details) Table 1: Water Damage - Cleanup and Mold Prevention Table 1 presents strategies
West Virginia University Environmental Health and Safety STANDARD OPERATING PROCEDURES FOR MOLD REMEDIATION Origination Date August 2013. Contents Purpose:... 2 Job Scope... 2 Definitions... 2 Roles/Responsibilities:...
City of Philadelphia Mold Remediation, Water Damage and Use of s This document provides direction for remediation of building materials in City facilities with potential, visible or laboratory verified
www.epa.gov/mold/mold_remediation.html Compiled by SUNY Office for Capital Facilities, May 2014 Page 1 Compiled by SUNY Office for Capital Facilities, May 2014 Page 2 Compiled by SUNY Office for Capital
Guidelines for Mold Remediation (Removal) Indoor mold growth, water damage, or musty odors should be addressed quickly. Removing mold growth and correcting the underlying cause of water accumulation can
Oakland Unified San Jose Unified Stanford University Santa Ana Unified Newhall Unified Clovis Unified Merced Union High School Grossmont Union High School District Industry Standards Damage Assessments
1.0 Policy Statement The University of New Haven has developed a mold response and remediation plan in accordance with best practices set forth by the Environmental Protection Agency (EPA), Occupational
MOLD RESPONSE AND REMEDIATION PLAN Prepared By: Triumvirate Environmental Developed: April 2011 Last Revised: March 2015 Program Approval Associate Vice President of Public Safety & Administrative Services
IAQA Home Health Committee Draft Healthy Home Environmental Assessment Principles Scope: This document provides the essential principles and concepts to conduct a healthy home environmental assessment.
Building and Grounds Maintenance Checklist Name: School: Room or Area: Date Completed: Signature: Instructions 1. Read the IAQ Backgrounder and the Background Information for this checklist. 2. Keep the
Guidelines for Cleaning Staff on Managing Mould Growth in State Buildings Prepared by the State Claims Agency 2 Index 1. Background 2. What are moulds? 3. What are the possible health effects? 4. How do
MOLD REMEDIATION KEY STEPS The EPA has developed the following guidelines for mold remediation managers. These guidelines are generally helpful, but we believe an expert in the industry should be consulted
CETA Application Guide for the Exhaust System Requirements of Class II, Type B Biosafety Cabinets CAG-007-2010 March 24, 2010 1. Background Class II Type B Biosafety Cabinets (BSCs) are unique laboratory
Questions & Answers (Q & A) Regarding Asbestos Treatment with the Fire Suppression and Renovation Project The Watergate Community is currently in the process with the fire suppression and interior renovations
Take Action on Asthma Environmental triggers of asthma and allergies What are asthma and allergies? They are both conditions where the body reacts to substances commonly found in the air. Asthma is a very
ASBESTOS SCIENCE TECHNOLOGIES, INC. P.O. Box 505 Bangor, CA 95914 Phone (530) 518-0934 Email - firstname.lastname@example.org Report for Lincoln Elementary School 1582 Lincoln Road Yuba City, Ca. 95993 Mold Report
Camfil Technical Services Bulletin Tools for Schools Filtration for Improved Indoor Air Quality Most non-practitioners notice the HVAC system when it is too hot, or too cold, or in other ways not working
Indoor Air Quality & Mold Class Spring 2012 Building Monitors Meeting Presentation Agenda IAQ - indoor ventilation Air contaminants Molds Requirements for growth Health effects Mold prevention - moisture
MOLD FAQs 1. What is mold and where does it live? Molds are microscopic fungi that are part of the natural environment. They can grow almost anywhere (inside and out), but live especially in the soil outside.
Owner's Manual Air-Purifier MK-B1000 Air Cleaning Expert 110V Model Quick Reference Table of Contents How the Air-Purifier MK-B1000 works (pg.2) Getting to Know Your New Air-Purifier MK-B1000 (pg.2).location
OFFICE OF ENVIRONMENTAL HEALTH AND SAFETY 5255 Hampton Blvd. Spong Hall, suite 2501 Norfolk, Virginia 23529 Phone: (757) 683-4495 Fax: (757) 683-6025 Occupational Safety & Health Environmental Health Laboratory
INDOOR AIR QUALITY ASSESSMENT Massachusetts Department of Developmental Services 436 Dwight Street Springfield, Massachusetts Prepared by: Massachusetts Department of Public Health Bureau of Environmental
Testimonials Very great Company!!! Owners and workers are very polite and dependable. They go above and beyond to make sure things are taken care of in a timely manner & at an affordable price. I would
Mold Guidelines for New Jersey Residents Understanding Mold Investigations & Remediation What Services Should I Ask For? What Are Important Inspection Procedures? Is Mold Sampling Helpful? What Information
"An Office Building Occupant's Guide to Indoor Air Quality" Office of Air and Radiation (OAR) Indoor Environments Division (6609J) Washington, DC 20460 EPA-402-K-97-003, October 1997 Contents A Summary
Water Incursion Standard Operating Procedure Purpose: To provide a standardized procedure in the event of water incursion into any Penn State University facility. References: A Brief Guide to Mold, Moisture
ASTHMA REGIONAL COUNCIL WHAT S THAT SMELL? Simple Steps to Tackle School Air Problems ARC is a coalition of governmental and community agencies dedicated to addressing the environmental contributors to
Modular Ventilation and Filtration System Modular Ventilation and Filtration Systems for all Chemical Safety Cabinets. Vent-Box Shown on flammable safety cabinet; not included. Protection Against Chemical
Mould A Basic Guide Summary Mould is a fact of life. Moulds will grow practically everywhere people live and work. Mould is recognized as an occupational hazard for indoor workers as well as outdoor workers
WATER DAMAGE, MOLD* GROWTH AND IAQ *Mold and Mildew are fungi What conditions may pose a problem & why What to do My name is: Jacquelyn Brown Environmental Protection Program Specialist (Health & Safety
WATER DAMAGE INVESTIGATION Massachusetts Gaming Commission 101 Federal Street Boston, Massachusetts Prepared by: Massachusetts Department of Public Health Bureau of Environmental Health Indoor Air Quality
Carson Dorn, Inc. 712 West 12th Street Juneau, Alaska 9981 December 18, 212 Patrick Holmes Associate Manager Juneau I, LLC 645 G Street, Suite 1-64 Anchorage, AK 9951 Dear Mr. Holmes, The renovation of
Indoor Comfort You Can Rely On The Evolution of Comfort ENVIRONMENTALLY SOUND COOLING Bryant is at the forefront of a comfort revolution with its exclusive Evolution System. Starting with the sleek, dependable
EMERGENCY RESPONSE: If you are a victim of a wildfire, we're here to help. We provide complete demolition services, erosion control, smoke mitigation, restoration services and re-build in all of El Paso
March 2007 Connecticut Department of Public Health Environmental Health Section Environmental & Occupational Health Assessment Program 410 Capitol Avenue MS # 11EOH, PO Box 340308 Hartford, CT 06134-0308
Did You Know? Because natural gas is colorless, odorless, and tasteless, mercaptan (a chemical that smells like sulfur) is added before distribution, to give it a distinct unpleasant odor (it smells like
Reliable Home Inspection Inspection Document 1 Reliable Home Inspection Inspection Services Agreement 1. Binding Contract; Definitions. This Inspection Services Agreement includes the Limitations and Exclusions
Cleanroom Basics Controlling the environment What is a cleanroom? ISO 14644-1: 'A room in which the concentration of airborne particles is controlled, and which is constructed and used in a manner to minimise
Guidelines for Cleaning up Former Methamphetamine Labs Methamphetamine (meth) drug labs are not a new hazard to Iowa. In 2003, federal, state and local authorities seized more than 1,100 Iowa labs, and
Indoor air quality monitoring made easy with the Fluke 985 Particle Counter Application Note Introduction Energy savings is top of facilities owners agenda. HVAC system tends to be the largest contributor
Restoring your Property: How to be prepared for Rapid Response to Flood Damage After a flood, the restoration process can be long and complex, particularly for large commercial properties. Failure to apply
AIM OF CREDIT To encourage and recognise the design and maintenance of air distribution systems that minimise the risk of particulate and microbial contamination to the internal air supply. CREDIT CRITERIA
Electronic Air Cleaner 90-1147 Owner s Manual Model 5000 Safety, Operating and Maintenance Instructions READ AND SAVE THIS MANUAL WARNING 120 Volts may cause serious injury from electrical shock. Disconnect
INDOOR MOLD AND HEALTH A Fungus Among Us This article addresses some of the most common questions and concerns about indoor mold, how it affects human health and ways in which you can prevent or remove
University of Texas at Dallas Indoor Air Quality Policy for University Buildings Effective Date: October 1, 2005 Summary Sridhar Hanumanthaiah, Industrial Hygienist, EH&S Esequiel (Zeke) Barrera, Director,
Improving Indoor Air Quality on a Tight Budget The HVAC system serving our shelter was outdated, extremely inefficient, and constantly malfunctioning, so it was time for new equipment. I researched information
WATER DAMAGE INVESTIGATION Massachusetts Department of Public Utilities 1 South Station Boston, Massachusetts Prepared by: Massachusetts Department of Public Health Bureau of Environmental Health Indoor
w that Your Building Experienced Water Damage What Must You and Your Water Damage Restoration Contractor Agree On? By Completing a Building and Occupant Survey Hopefully Your Questions will be Answered
Webinar Questions and Answers Mold and Moisture Control in Schools: Potential Health Effects and Safe Clean-Up Practices Q: If a school wanted to set up a preventive program for mold and moisture, what
ASBESTOS MANAGEMENT PROGRAM Prepared By: Triumvirate Environmental Program Approval Developed: August 2011 Updated: June 2015 Associate Vice President of Public Safety & Administrative Services Date Associate
University of Vermont Department of Physical Plant Burlington, Vermont WATER INTRUSION GUIDELINES In accordance with: IIRC S500 IIRC S520 EPA Document 402-K-01-001 REVISED AND DISTRIBUTED BY: THE UNIVERSITY
Mold In Your Home and at Work Forsyth County Office of Environmental Assistance and Protection What is mold? Mold is a term used to describe a type of fungus that can be found all year round both indoors
Page: 1 of 5 1.0 BACKGROUND Mold is one of nature s primary decomposers of organic materials. Many different types of mold feed on grass, leaves, wood, deceased animals and other organic materials that
AVOIDING MOLD AND WATER DAMAGE LIABILITIES IN HOMES Overview Part I Why Mold? Why Now? Part II Water Intrusions Part III Mold Contamination Part I Why Mold? Why Now? Mold Has Been an Issue for a Long Time!!
Consumer Guide to Carpet Cleaning The carpet cleaning industry is one of the few industries in New Zealand that is not regulated, and also has a very low barrier to entry in that anyone can call himself
MOLD INSPECTION REPORT For the Subject Property: UCD Anschutz Medical Campus Building 402 12474 E. 19 th Ave. Aurora, CO 80045 Report Date: August 7, 2015 Inspection/Testing Date: August 1, 2015 SET Project:
HVAC Filter Maintenance Part of responsible homeownership includes, of course, regular home maintenance. And there are some tasks that, if deferred, can lead to a home system that s inefficient and overworked,
Today s topic is Asbestos Safety. This training is a part of OSHA s Asbestos Standard (29 CFR 1910.1001). You will learn the: About the dangers of asbestos. How to identify asbestos. How to protect yourself