1 CENTRIFUGAL PUMP SELECTION, SIZING, AND INTERPRETATION OF PERFORMANCE CURVES 4.0 PUMP CLASSES Pumps may be classified in two general types, dynamic and positive displacement. Positive displacement pumps are those in which energy is imparted to the liquid in a fixed displacement volume, such as a casing or a cylinder, by the rotary motion of gears, screws, or vanes, or by reciprocating pistons or plungers. Centrifugal pumps are dynamic pumps. Energy is imparted to the liquid by means of a disk with curved vanes rotating on a shaft called the impeller. The impeller imparts kinetic energy to the fluid by means of its shape and high rotational velocity. This energy is transformed to pressure energy when the fluid reaches the pump casing (see Figure -). The pressure head difference between the inlet and the outlet, or Total Head produced by the pump, is proportional to the impeller speed and diameter. Therefore, to obtain a higher head, the rotational speed or the impeller diameter can be increased. To learn more about how a centrifugal pump increases a fluid's pressure, see reference 5. How a pump produces pressure is beyond the scope of this book, but an interesting experiment you can try at home will illustrate a similar process. A small plastic bottle is required to which a string is attached. Twist a rubber band around the bottle s neck a few times and attach two -foot long strings, one on each side of the glass. Tie the other ends of the string together, fill the glass half full with water and hold it suspended from the strings. Start spinning. As you may have guessed, the fluid inside the glass will become pressurized. How do you know that the fluid is pressurized? To prove it to yourself, make a very small hole in the glass bottom. Make the hole just large enough for water to dribble through. Now spin the glass again. The water will spray out of the glass bottom no matter what its position, up or down. Figure 4- Using a spinning bottle to demonstrate centrifugal force.
2 4 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES 4. COVERAGE CHART FOR CENTRIFUGAL PUMPS A coverage chart (see Figure 4-) makes it possible to do a preliminary pump selection by looking at a wide range of pump casing sizes for a specific impeller speed. This chart helps narrow down the choice of pumps that will satisfy the system requirements. Figure 4- Typical pump capacity coverage chart. 4. PERFORMANCE CURVE CHART The following figure shows a typical pump performance chart for a given model, casing size, and impeller rotational speed. A great deal of information is crammed into one chart and this can be confusing at first. The performance chart covers a range of impeller sizes, which are shown in even increments of /" from 7 /" to 9 /". Impellers are manufactured to Figure 4- Typical pump performance curve. the largest size for a given pump casing and machined or "trimmed" to the required diameter when the pump is sold.
3 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES 4 Performance Curve At some point in the pump selection process, the impeller diameter is selected. For an existing pump, the diameter of the impeller is known. For a new pump, our calculations of Total Head for a given flow rate will have determined the impeller diameter to select according to the performance curve. Figure 4-4 shows only the information relevant to the 8 /" impeller performance curve. Figure 4-4 Typical performance curve for a specific impeller diameter. A performance curve is a plot of Total Head vs. flow rate for a specific impeller diameter and speed. The plot starts at zero flow. The head at this point corresponds to the shut-off head of the pump, point A in Figure 4-4 (more about this later). Starting at this point, the head decreases until it reaches its minimum at point B. This point is sometimes called the run-out point and represents the maximum flow of the pump. Beyond this, the pump cannot operate. The pump's range of operation is from point A to B. Efficiency Curves The pump's efficiency varies throughout its operating range. This information is essential for calculating the motor power (see section 4.9). The B.E.P. (best efficiency point) is the point of highest efficiency of the pump. All points to the right or left of the B.E.P have a lower efficiency (see Figure 4-4). The impeller is subject to axial and radial forces, which get greater the further away the operating point is from the B.E.P. These forces manifest themselves as vibration depending on the speed and construction of the pump. The point where the forces and vibration levels are minimal is at the B.E.P. In selecting a pump, one of the concerns is to optimize pumping efficiency. It is good practice to examine several performance charts at different speeds to see if one model satisfies the requirements more efficiently than another. Whenever possible the lowest pump speed should be selected, as this will save wear and tear on the rotating parts.
4 4 4 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES Note: The pump performance curves are based on data generated in a test rig using water as the fluid. These curves are sometimes referred to as water performance curves. The use of these curves for fluids with a different viscosity than water can lead to error if the proper correction factors are not applied. These correction factors are applied to the Total Head, the flow and the efficiency of the pump, and are published in form of curves by the Hydraulic Institute (see Standards book published by the Hydraulic Institute, web site: and for the correction factor charts see the web site Horsepower Curves The horsepower curves are shown on the chart and give the power required to operate the pump within a certain range. For example (see Figure 4-5), all points on the performance curve to the left of the hp curve will be attainable with a hp motor. All points to the left of hp curve and to the right of the hp curve will be attainable with a hp motor. The horsepower can be calculated with the Total Head, flow and efficiency at the operating point. (More on horsepower calculations and operating point later). Note that the horsepower curves shown on the performance curves are valid for water only. Figure 4-5 Coverage area of horsepower curves. N.P.S.H. Requirement Curves The pump manufacturer specifies a minimum requirement on the N.P.S.H. in order for the pump to operate at its design capacity. These are the vertical dashed lines in Figure 4-6. The N.P.S.H. required becomes higher as flow increases, and lower as flow decreases. This essentially means that more pressure head is required at the pump suction for high flows than low flows. Keep in mind that N.P.S.H. is a head term and therefore independent of the fluid density and is in absolute fluid column height. The N.P.S.H. required for the maximum flow in Figure 4-4 is approximately 4 feet absolute. This is not very restrictive; most industrial pumping systems will have much more N.P.S.H. available.
5 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES 4 5 Figure 4-6 N.P.S.H required curves. 4. IMPELLER DIAMETER SELECTION Quite often, the operating point is located between two curves on the performance chart. We can calculate the impeller size required by linear interpolation. For example, if the operating point falls between the 9" and 9 /" impeller curve (see Figure 4-7), the following equation will give the correct size: DOP = 9 + ( H OP H 9) H 9/ H 9 where D OP : impeller diameter required; H OP : pump total head at the operating point; H 9 : pump total head at the intersection of the 9 impeller curve and flow rate; H 9/ : pump total head at the intersection of the 9 / impeller curve and the flow rate. Figure 4-7 Interpolating impeller diameter.
6 4 6 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES It is good practice to select (when possible) a pump with an impeller that can be increased in size, permitting a future increase in head and capacity. Or alternatively, an impeller which can be reduced in size. As a guide, select a pump with an impeller size no greater than between / and / of the impeller range for that casing with an operating point in the high efficiency area (see Figure 4-8). It is also important not to go too far right or left from the B.E.P.. A guideline is to locate the operating point between 0% and 80% (see reference 6) of the B.E.P. flow rate with an operating point in the desirable impeller selection area (see Figure 4-8). Figure 4-8 Desirable pump selection area. 4.4 SYSTEM CURVE The system curve is a plot of the Total Head vs. the flow for a given system. The higher the flow, the greater the head required (see Figure 4-9). The shape of the system curve depends on the type of system being considered. The system curve equation for a typical single outlet system such as in Figure -0 is: H ( q) = H ( q) + H ( q) + H ( q) + H P F EQ v TS The system curve is superimposed on the pump performance chart. The Total Static head is constant and the friction head, equipment head and velocity head are flow dependent. The calculation of Total Head at different flow rates produces a plot of Total Head vs. flow that is called the system curve. The operating point is the point on the system curve corresponding to the flow and head required. It is also the point where the system curve intersects the performance curve. The design system curve is usually calculated with extra flow capacity in mind. It is good
7 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES 4 7 practice to plot the system curve for higher flow rates than the design flow rate, since flow demand may change and extra capacity may be required. Figure 4-9 Superposition of system curve and pump performance curve. 4.5 OPERATING POINT The question in example. has remained unanswered until now. That is: How can we guarantee that the pump will deliver 500 USGPM at 70 feet of head? First, determine the right pump size by using the coverage chart (see Figure 4-). Locate the head and flow coordinate (operating point) on the chart. This will identify the casing size and pump speed. Locate the correct performance curve chart for this pump casing size and again identify the operating point. Figure 4-0 Location of operating point in example..
8 4 8 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES Determine the impeller size. The impeller size will be approximately 8.75". The dashed line represents the performance curve of the pump. The pump can only operate on its performance curve. The system can only be run somewhere on the system curve. The intersection of these two defines the operating point which is the only point that the pump and system can operate. As is often the case, one question leads to another: How does the pump get to the operating point from the moment it is switched on? There are two methods which can be used to start a pump. With method the discharge valve is closed, whereas with method the discharge valve is open. The term discharge valve refers to the manual valve located close to the pump outlet flange. Method (discharge valve closed) Pumps are often started with the discharge valve closed. Immediately after the pump is started, the head rises to point D (see Figure 4-). The system curve at this moment is vertical. By gradually opening the discharge valve to its full open position, point D will move down the performance curve to point C, where the discharge valve should be fully open. The system curve's shape is progressively modified as the operating point is moved towards point C. This is a typical way of starting large pumps and should be the preferred method for any pump operating at more than 500 USGPM. Figure 4- Starting the pump with discharge valve closed.
9 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES 4 9 Method (discharge valve open) The alternate method is to start with the discharge valve open. When the pump is just starting the initial RPM is low; the pump produces little head and flow. As the pump accelerates, it will intersect the system curve at point A at 00 RPM, point B at 500 RPM and finally point C at the normal rotational speed of the pump and motor. This happens very quickly since the motor will reach its full operating speed in a few seconds. The disadvantage of starting with this method is that high initial velocity can produce a severe water hammer, shaking pipes and equipment. Figure 4- Starting the pump with discharge valve open. Method is the preferred method of starting a pump. To minimize personnel requirements, it is the practice in many plants to equip their pumps with remote operated on-off discharge valves for large pumps (larger than 500 USGPM). The valves are opened automatically by a control system, thereby providing a smooth start-up. 4.6 SAFETY FACTOR ON TOTAL HEAD OR CAPACITY Before finalizing the choice of impeller size, consider whether you should apply an extra capacity factor or not (capacity = flow). There are no rules; however, since we normally size pumps for someone else, it is a good idea to agree on a safety margin with your client. Point on impeller curve A (see Figure 4-) is the operating point (on system curve a) before a capacity factor is applied. Safety margin on total head If we apply a head factor of 0%, we will have to select impeller C. The operating point will now be at point. This means that there must be a different system curve than curve a, which is curve c. The only explanation for this is that we have underestimated the pressure drops throughout the system. If it turns out that the pressure drop calculations were right after all, and that we really are operating with curve a, then the operating point will shift from point to on impeller curve C (assuming there is sufficient horsepower to operate at point ). If we need to get back to the flow corresponding to point for process reasons, then throttling a valve at the pump discharge will change the operating curve to match curve c and bring the operating point back to point.
10 4 0 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES Figure 4- Location of capacity factor. Safety margin on flow If we apply a capacity factor of say 0%, we will have to select impeller curve B. This means that the system curve is in reality curve d. If in actuality our original flow estimate was correct, then the operating point will shift from point 4 to 5. To get back to the original flow, we have to throttle back so that we shift to point 6, and we will operate on a new system curve b. Safety margin on total head and flow If we decide to put on suspenders and a belt (i.e. a head and capacity factor), and assuming that we are operating on system curve a, then we would select impeller curve C and operate at point. If we needed to get back to our original flow at point, then we would throttle back until we reached point. This is a similar situation to applying solely a head factor because of the shape of the performance and system curves. Therefore, applying a head factor only also provides reserve capacity on flow.
11 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES PUMP OPERATION TO THE RIGHT OR LEFT OF THE BEST EFFICIENCY POINT (B.E.P.) The impeller is subjected to axial and radial forces. The level of the radial force depends on the pressure within the casing and is taken up by the drive shaft bearings. Figure 4-4 The forces on the impeller. There is also a net radial force whose level depends on the pressure level within the casing, and also on the position of the operating point with respect to the B.E.P.. This force increases rapidly the further away the operating point (see Figure 4-5) gets from the B.E.P. of the pump (for more information see reference 6).
12 4 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES Figure 4-5 Variation on the magnitude of the radial force on the impeller according to the position of the operating point with respect to the B.E.P.(reprinted with permission of McGrawHill). Figure 4-6 Variation in the level of vibration at the operating point vs. the position of the B.E.P.(reprinted with permission of the Goulds pump company).
13 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES 4 What are the consequences of operating to the right or left of the B.E.P.? To the right of the B.E.P., or at high flows Operating at the far right of the curve, near run-out point of the pump (point B, Figure 4-4) should be avoided. As flow increases, so does the N.P.S.H. required, and therefore cavitation is more likely to occur. To the left of the B.E.P. or at low flows Operation of centrifugal pumps at reduced capacity leads to a number of unfavorable results that may take place separately or simultaneously, and should be anticipated and circumvented. Some of these are: Operating at less than best efficiency On occasion, reduced flows may be required by the process. This can be accommodated by a variable speed drive, or by using several pumps. One or more pumps can then be shut down to provide the reduced flow. Higher bearing load If a pump is of a single volute design, it will be subjected to higher radial thrust, which will increase the load on the radial bearing. Therefore, the bearing life would be expected to diminish. Temperature rise As capacity is reduced, the temperature of the pumped liquid increases. To avoid exceeding permissible limits, a minimum flow by-pass is required. Internal re-circulation At certain flows below the best efficiency, all centrifugal pumps are subjected to internal re-circulation, in both the suction and the discharge area of the impeller. This can cause hydraulic surging and damage to the impeller metal, similar to that caused by classic cavitation, but taking place in a different area of the impeller. Figure 4-7 Internal recirculation at low flow (reprinted with permission of McGraw-Hill).
14 4 4 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES 4.8 PUMP-SHUT-OFF HEAD The shut-off head is the Total Head that the pump can deliver at zero flow (see Figure 4-9). The shut-off head is important for reasons.. In certain systems (admittedly unusual), the pump discharge line may have to run at a much higher elevation than the final discharge point. The fluid must first reach the higher elevation in the system. If the shut-off head is smaller than the static head corresponding to the high point, then flow will not be established in the system.. During start-up and checkout of the pump, a quick way to determine if the pump has the potential capacity to deliver the head and flow required, is to measure the shut-off head. This value can be compared to the shut-off head predicted by the performance curve of the pump. Figure 4-8 Discharge pipe coming from a higher elevation into the discharge tank.
15 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES 4 5 Figure 4-9 Location of pump shut-off head on the performance curve. 4.9 PUMP POWER A pump's power demand is directly proportional to the difference between the inlet and outlet pressure and the flow rate. P = p P where p P is the difference in pressure at the inlet and the outlet of the pump, and q the flow rate. The above equation expressed in imperial units is: q p P( hp) = P ( psi) q( USgal / min) 74. [4-] p P is converted to head. From equation [-5]: p ( psi) = SG H P ( ft of fluid ). P [4-] by substituting equation [4-] into equation [4-] we obtain: SG H P ( ft of fluid) q( USgal/ min) P( hp) = [4-] 960
16 4 6 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES Equation [4-] would be true if the pump were 00% efficient. Pump efficiency data are available from the pump manufacturer. All manufacturers test their pumps for various flows, heads and impeller sizes. The resulting efficiency data are mapped on the pump performance curve. The true power required at the pump shaft is: SG H P( ftof fluid) q( USgal/min) P( hp) = 960 η [4-4] where η is the pump efficiency. If the pump efficiency is 60%, then the value of η is 0.6. It is good practice to design the pump base in such a way that the selected motor will stand on spacer blocks, being high enough that the next largest motor frame can be installed when the blocks are removed. This will allow the installation of a larger motor without a major disturbance if it should be required. 4.9 AFFINITY LAWS The affinity laws are derived from a dimensionless analysis of three important parameters that describe pump performance: flow, total head and power (ref: The Pump Handbook by McGraw-Hill, chapter ). The analysis is based on the reduced impeller being geometrically similar and operated at dynamically similar conditions or equal specific speed. The affinity laws were developed using the law of similitudes which provide basic relationships. Flow vs. diameter and speed Q K = nd or Q = Q n n D D
17 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES 4 7 Total Head vs. diameter and speed g H n D = K or H = H n n D D Power vs. diameter and speed P = K γ 5 n D g or P = P n n D D 5 5 where subscripts and denote the value before and after the change. P is the power, n the speed, D the impeller diameter, H the total head. If the speed is fixed the affinity laws become: Q D = D Q D H D H P = D = 5 P D 5 If the diameter is fixed the affinity laws become: Q n = n Q n H n H P = n = P n The process of arriving at the affinity laws assumes that the two operating points that are being compared are at the same efficiency. The relationship between two operating points, say and, depends on the shape of the system curve (see Figure 4-0). The points that lie on system curve A will all be approximately at the same efficiency. Whereas the points that lie on system curve B are not. The affinity laws do not apply to points that belong to system curve B. System curve B describes a system with a relatively high static head vs. system curve A which has a low static head.
18 4 8 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES Figure 4-0 Limitation on the use of the affinity laws. Diameter reduction To reduce costs pump casings are designed to accommodate several different impellers. Also, a variety of operating requirements can be met by changing the outside diameter of a given radial impeller. Euler s equation shows that the head should be proportional to (nd) provided that the exit velocity triangles remain the same before and after cutting. This is the usual assumption and leads to: Q nd = n D Q nd H n D H P = n D = P n D Which apply only to a given impeller with altered D and constant efficiency but not a geometrically similar series of impellers. If that is the case then the affinity laws can be used to predict the performance of the pump at different diameters for the same speed or different speed for the same diameter. Since in practice impellers of different diameters are not geometrically identical, the author's of the section called Performance Parameters in the Pump Handbook recommend to limit the use of this technique to a change of impeller diameter no greater than 0 to 0%. In order to avoid over cutting the impeller, it is recommended that the trimming be done in steps with careful measurement of the results. At each step compare your predicted performance with the measured one and adjust as necessary.
19 PUMP SELECTION, SIZING AND INTERPRETATION OF PERFORMANCE CURVES 4 9 Sizing things up.. Head is independent of fluid density.. For fluids other than water, it should be determined if the fluid is Newtonian. Many pure fluids are Newtonian (see the table on rheological properties of fluids in Appendix A as a starting point). If the fluid is non-newtonian, depending on the severity of its departure from Newtonian behavior, a centrifugal pump may not be an appropriate pumping device. If the fluid is Newtonian but with a different viscosity than water, apply the correction factors to the performance curve suggested by the pump manufacturer (see reference and ).. Order the pump base with spacer blocks for the motor, allowing the next larger frame to be installed when the blocks are removed. 4. Select a pump size and speed in such a way that the impeller is not close to its maximum size (i.e. within / s of it s total range) in order to allow for a future increase in capacity. Locate the operating point somewhere between 0% and 80% of the B.E.P. flow. 5. During the selection process, if the operating point falls between two performance curves, by interpolation calculate the exact impeller size required to intersect the operating point. Impeller size is easily machined down to the correct diameter. 6. Determine the total static head corresponding to the highest point of the system and make sure that it is less than the pump shut-off head. 7. Finally, beware using the affinity laws for calculating a new pump diameter or speed for systems that have a high static head, the affinity laws apply only between two points that are at the same efficiency.
CENTRIFUGAL PUMP OVERVIEW Presented by Matt Prosoli Of Pumps Plus Inc. 1 Centrifugal Pump- Definition Centrifugal Pump can be defined as a mechanical device used to transfer liquid of various types. As
HYDRAULIC MACHINES Used to convert between hydraulic and mechanical energies. Pumps: Convert mechanical energy (often developed from electrical source) into hydraulic energy (position, pressure and kinetic
Pump ED 101 Positive Displacement Pumps Part I Reciprocating Pumps Joe Evans, Ph.D http://www.pumped101.com There are many pump designs that fall into the positive displacement category but, for the most
Guidelines for Processing Plant Page : 1 of 51 Rev 01 Feb 2007 Rev 02 Feb 2009 Rev 03 KLM Technology #03-12 Block Aronia, Jalan Sri Perkasa 2 Taman Tampoi Utama 81200 Johor Bahru. (ENGINEERING DESIGN GUIDELINE)
Fans and Pumps are sized to meet the maximum flow rate required by the system. System conditions frequently require reducing the flow rate. Throttling and bypass devices dampers and valves are installed
EXPERIMENT NUMBER 7 PERFORMANCE TEST OF A CENTRIFUGAL PUMP OBJECTIVE The primary objectives of this experiment is to measure the performance of a centrifugal pump and compare the results to the manufacturers
Selecting a Vertical Turbine Pump (Information required from client) 1. Liquid to be pumped: (Note: If liquid is not clear water, the following must also be ascertained). a. Foreign material present in
FRANCIS TURBINE EXPERIMENT 1. OBJECT The purpose of this experiment is to study the constructional details and performance parameters of Francis Turbine. 2. INTRODUCTION Turbines are subdivided into impulse
Principles of Fluid Mechanics Fluid: Fluid is a substance that deforms or flows continuously under the action of a shear stress (force per unit area). In fluid mechanics the term fluid can refer to any
A BRIEF INTRODUCTION TO CENTRIFUGAL PUMPS figure below is a cross section of a centrifugal pump and shows the two basic parts. Joe Evans, Ph.D IMPELLER This publication is based upon an introductory, half
KNOWLEDGE: K1.01 [3.3/3.5] P21 Which one of the following contains indications of cavitation in an operating centrifugal pump? A. Low flow rate with low discharge pressure. B. Low flow rate with high discharge
WHITE PAPER August 2015 Pump cavitation and how to avoid it Best practices in pump system design Presented by: Xylem Applied Water Systems Cavitation is not a new phenomenon that can impact a pump system,
_02 A centrifugal with a 12 in. diameter impeller requires a power input of 60 hp when the flowrate is 3200 gpm against a 60 ft head. The impeller is changed to one with a 10 in. diameter. Determine the
Variable Frequency Drives for Water/Wastewater Discussion on Pump Optimization Principles and Need to Know Drive Technology Pumps in Water Wastewater 2 WWW Challenges: Drivers/Trends Demand for WWW Age
PEERLESS PUMP COMPANY SYSTEM ANALYSIS FOR PUMPING EQUIPMENT SELECTION Peerless Pump Company 005 Dr. Martin Luther King Jr. Street P.O. Box 706 Indianapolis, Indiana 4607-706 Phone: (317) 95-9661 Fax: (317)
Chapter 2 Pump Types and Performance Data Abstract Centrifugal pumps are used for transporting liquids by raising a specified volume flow to a specified pressure level. Pump performance at a given rotor
White Paper Pumps 101: Operation, Maintenance and Monitoring Basics Daniel Kernan Manager Monitoring and Control Group, ITT Executive Summary Pumps are at the heart of most industrial processes, and the
Key Specification Points for Turbine Driven Boiler Feed Water Pumps Used in Super Critical and Ultra Super Critical Coal Fired Power Plants By Mr. Ed Simmons PE Shaw Power Division The Risks The Boiler
Pump Formulas Imperial and Pressure to Head H = head, ft P = pressure, psi H = head, m P = pressure, bar Mass Flow to Volumetric Flow ṁ = mass flow, lbm/h ρ = fluid density, lbm/ft 3 ṁ = mass flow, kg/h
Centrifugal Pump Selection and Sizing 2009 Calgary Pump Symposium Chris Gilmour, P.Eng. Pump types being Considered One and two stage centrifugal pumps - OH2, OH3/4, BB1, BB2 - most common pumps used Pumps
Interpreting Vibration Spectrum and TWF Patterns (Understanding Motion Through Pattern Recognition) Richard Burton 6/8/2012 2 Patterns When reduced to it s most basic concept, Vibration Analysis can be
Pressure drop in pipes... PRESSURE DROP CALCULATIONS Pressure drop or head loss, occurs in all piping systems because of elevation changes, turbulence caused by abrupt changes in direction, and friction
Fluid Machines PELTON TURBINE EXPERIMENT 1. OBJECT The purpose of this experiment is to study the constructional details and performance parameters of Pelton Turbine. 2. INTRODUCTION Energy may exist in
Pump Wear Avoiding Pump Wear in Centrifugal Pumps Introduction: In the moment of starting a new pump, that pump is headed for a day when it will need repair even if the design and operation is correct.
Selecting the Pump Once the GPM and pump head are known, we can proceed with the actual pump selection. Pumps may be selected either manually using pump curves, or with software such as Taconet. To use
Advanced Hydraulics Prof. Dr. Suresh. A. Kartha Department of Civil Engineering Indian Institute of Technology, Guwahati Module - 6 Turbines Lecture - 4 Turbines, Cavitation Very good afternoon to everyone,
PRINCIPLE OF OPERATION A hydraulically and dynamically balanced impeller with raised vane sections discharges liquid as a result of the centrifugal force developed in rotation. The head developed is entirely
ENGINEERING SERVICE BULLETIN Page 1 of 6 Effective: 12-16-10 Supersedes: 5-27-85 To: MASTER CATALOG HOLDERS SUBJECT: VIKING PRESSURE RELIEF VALVES This Engineering Service Bulletin deals with the terminology
Pumps SELECTION OF A PUMP A water system needs to move the water produced from the source to its customers. In almost all cases in Minnesota, the source is at a lower elevation than the user so the water
Lecture 4 Turbines, Classification, Radial flow turbines, Axial flow turbines TURBINES A hydraulic machine is a device in which mechanical energy is transferred from the liquid flowing through the machine
FOUNTAIN PUMP SYSTEM DESIGN by Jacques Chaurette p. eng. page.2 NEW FOUNTAIN PUMP SYSTEM CALCULATIONS AND PUMP SELECTION To select a centrifugal pump that is appropriate for a fountain design we need to
Vertical selfpriming Side-Channel Pumps Type WPV FIELD OF APPLICATION The side-channel pumps are selfpriming and operate more economically (better efficiency) than normal centrifugal pumps when handling
Part I: Objective type questions and answers Chapter 3.5: Fans and Blowers 1. The parameter used by ASME to define fans, blowers and compressors is a) Fan ration b) Specific ratio c) Blade ratio d) Twist
Start of pump systems Analysis and calculations Introduction Start calculation. Introduction A start calculation is performed in order to analyse the pump system starting cycle. The starting cycle stretches
EML 316L Experiment 3 Pipe Friction Laboratory Manual Mechanical and Materials Engineering Department College of Engineering FLORIDA INTERNATIONAL UNIVERSITY Nomenclature Symbol Description Unit A cross-sectional
Construction and operation 8.03.00 Instructions for installation 8.03.00 Types of stress 8.04.00 Diagrams for static deformation of the coupling ring 8.05.00 Coupling size 8.07.00 Examples of combinations
Higher Technological Institute Civil Engineering Department Lectures of Fluid Mechanics Dr. Amir M. Mobasher 1/14/2013 Fluid Mechanics Dr. Amir Mobasher Department of Civil Engineering Faculty of Engineering
6 Energy Efficiency Best Practice Guide Contents 1 Introduction 4 2 Business benefits of efficient pumping systems 5 3 What is your opportunity? 7 4 Solution 1 Improve the efficiency of your existing system
pipe_02 A homeowner plans to pump water from a stream in their backyard to water their lawn. A schematic of the pipe system is shown in the figure. 3 m 1 m inlet pipe-to-pump coupling stream re-entrant
EML 2322L MAE Design and Manufacturing Laboratory Electric Motors and Drives To calculate the peak power and torque produced by an electric motor, you will need to know the following: Motor supply voltage,
VARIABLE VANE PUMPS V3 (series 30 and 40) Nominal sizes 12; 25; 40; 63 up to p n 100 bar V g 8.5; 19; 32; 47 cm 3 /rev KE 1015 11/02 replaces 07/97 easy commissioning due to automatic bleed facility low
Like getting two pumps in one! SP-1470-C VIKING BUILT DOUBLE PUMPS Viking double pumps are ideally suited to many applications in the industrial and mobile markets. Two independent pumping units are operated
17. Pipe flow V (11.5-11.7) Pump types Pump systems Pumps in series and in parallel Exercises: D35-36, and D38 Pump types centrifugal pump VVR 120 Fluid Mechanics Pump types axial flow pumps VVR 120 Fluid
Circular 1048 Selection Of Centrifugal Pumping Equipment 1 Dorota Z. Haman, Fedro S. Zazueta, Forrest T. Izuno 2 INTRODUCTION The pump is an essential component of an irrigation system. Proper selection
Copyright 2002, 2005, 2008 Randall W. Whitesides, P.E. Introduction This course provides the student with an understanding of fluid viscosity and its effects on the performance of centrifugal pump operation.
Waste Collection Systems Lift Stations Lift Stations Training Objectives To gain an understanding of: Lift Station vocabulary Lift Station components and their function Lift Station operational requirements
BOWIE PUMPS OPERATION - MAINTENANCE PUMPING PRINCIPLE: The meshing owieeof the gears cause a slight depression, with the resulting enmeshing of the gears causing a vacuum drawing the fluid being pumped
Applied Fluid Mechanics Sixth Edition Robert L. Mott University of Dayton PEARSON Prentkv Pearson Education International CHAPTER 1 THE NATURE OF FLUIDS AND THE STUDY OF FLUID MECHANICS 1.1 The Big Picture
Energy Efficiency Considerations in Pumps and Pump Stations Jeff Foray, P.E. (JeffForay@KennedyJenks.com) WSU Extension Energy Program 14 March 2014 How Do You Save Energy? Don t design it wrong Operate
Fluid flow pump system Pump Types Fluid flow applications can be divided into two categories: low flow at high pressure and high flow at low pressure. Low flow at high pressure applications include hydraulic
VI Rules for Classification and Construction Additional Rules and Guidelines 5 Pumps 1 Guidelines for the Design, Construction and Testing of Pumps Edition 2007 The following Guidelines come into force
APPLICATION NOTE An In-Depth Examination of an Energy Efficiency Technology Agricultural Pumping Efficiency Improvements Summary...1 How This Technology Saves Energy...2 Types of Energy Efficiency Measures...4
APPENDIX A CONTROL VALVE TESTING PROCEDURES AND EQUATIONS FOR LIQUID FLOWS Section A.1. Flow Coefficients Definition The flow coefficient or pressure loss coefficient is used to relate the pressure loss
FS No. SHEET 1 OF 7 TITLE PROCEDURE CUSTOMER END USER : FLOWTECH ENGINEERS : CETHAR VESSELS LTD CUSTOMER PO No. EQUIPMENT TAG No. SERVICE PUMP MODEL FS REF. No. : FS/FT/CVL/012/10-11 : WPP13001 A/B,WPP13002
Refrigeration and Airconditioning Prof. M. Ramgopal Department of Mechanical Engineering Indian Institute of Technology, Kharagpur Lecture No. # 22 Refrigeration System Components: Compressor (Continued)
Section 000 Bulletin 00 Issued 5/87 Replaces /8 JET PUMP TECHNICAL DATA pumping liquids This technical bulletin includes general information about Penberthy Jet Pumps plus specific details for selecting
SUBMERSIBLE PUMP selection A submersible pump consists of the following basic elements: < Bowl Assembly < Motor < Cable < Drop Pipe < Surface Plate (with)(without) discharge elbow DATA REQUIRED FOR SELECTION
Variable medium speed pumps combine superior performance with reduced life cycle cost (LCC) Dr. Christian Rossegger Flowserve (Austria) GmbH ABSTRACT Flowserve s new medium speed pump, is a vertical inline
VACUUM PUMPS Section IV Equipment used to generate vacuum, as noted earlier, is similar to air compressors. It's even possible to generate compressed air or vacuum with the same machine, depending on how
AURORA 520 Series SINGLE STAGE SUMP PUMPS WWW.AURORAPUMP.COM AURORA 520 Series Single Stage Sump Pumps Capacities to 110 G.P.M. Heads to 40 Feet Temperatures to 180 F Introduction. Vertical extended shaft
SUBMERSIBLE PUMP INSTALLATION, OPERATION & MAINTENANCE MANUAL WARRANTY Unless otherwise specifically stated, guarantees are limited to the following: A. All equipment of our manufacture is guaranteed against
Livestock Watering Order No. 590.304-5 January 2006 UNDERSTANDING GRAVITY-FLOW PIPELINES Water Flow, Air Locks and Siphons This Factsheet discusses the problems and solutions of gravity flow pipe system
Power Recovery Turbines Fixed and Variable Geometry Vertical Horizontal Bulletin PS-90-1 (E) Pump Supplier To The World Flowserve is the driving force in the global industrial pump marketplace. No other
Compressor Lubrication Lubricants for air compressors There are five types of compressors in common use: Reciprocating Rotary vane Pump or drip lubricated Oil flooded Rotary screw Pump or drip lubricated
Lecture T1 Transient Mass Transfer Up to now, we have considered either processes applied to closed systems or processes involving steady-state flows. In this lecture we turn our attention to transient
BQ FIXED DISPLACEMENT HYDRAULIC VANE PUMPS BQ SERIES Versatility, power, compactness and low running costs are the main characteristics of B&C vane pumps. All the components subject to wear are contained
INTRODUCTION: Baldor Electric Company has prepared this Specifiers Guide to help you cover all the bases when you are specifying electric motors. It will cover in a generic way most of the subjects which
Vertical Pumps for the Oil & Gas Industry ITT API Expert ITT Commitment ITT is committed to the Oil and Gas market, which is the largest segment of our business. We have been investing in technology to
DEVELOPMENT OF A TWIN SCREW EXPRESSOR AS A THROTTLE VALVE REPLACEMENT FOR WATER-COOLED CHILLERS J J Brasz, Carrier Corporation, Syracuse, NY, 13221, USA email@example.com I K Smith and N Stosic
Centrifugal Pump Handbook Centrifugal Pump Handbook Third edition Sulzer Pumps Ltd Winterthur, Switzerland AMSTERDAM. BOSTON. HEIDELBERG. LONDON NEW YORK. OXFORD. PARIS. SAN DIEGO SAN FRANCISCO. SINGAPORE.
FIRE PUMP ESSENTIALS Chamco Industries THE FIRE PUMPS FOUR TYPES/STYLES OF FIRE PUMPS Horizontal, split case. (250 usgpm - 5000 usgpm) Vertical Turbine. ( 250 usgpm - 5000 usgpm ) End Suction. ( commercial
International Journal of Mechanical Engineering and Technology (IJMET) Volume 7, Issue 2, March-April 2016, pp. 66 72, Article ID: IJMET_07_02_010 Available online at http://www.iaeme.com/ijmet/issues.asp?jtype=ijmet&vtype=7&itype=2
Figure 1 Automatic Minimum Flow System SMA 63 Advantage and Utility assurance of the required pump minimum continuous safe flow no inadmissible temperature increase in the pump; avoidance of cavitations
Pump Ratio and Performance Charts Concept and Theory Training Table of Contents Introduction... 1 Overview... 1 How to use this Module... 2 Learning Objectives...2 Text...2 Charts, Illustrations...2 Progress
4" SUBMERSIBLE PUMPS 4" SUBMERSIBLE PUMPS 50/60 HZ Multi-stage centrifugal submersible pumps for clean water in 4" wells. The 4" VSP pump series is carefully designed and manufactured for maximum resistant
SECTION 23 22 23 PART 1 GENERAL 1.1 DESCRIPTION A. Steam condensate pumps for Heating, Ventilating and Air Conditioning. B. Definitions: 1. Capacity: Liters per second (L/s) (Gallons per minute GPM) of
BQ FIXED DISPLACEMENT HYDRAULIC VANE PUMPS BQ SERIES Versatility, power, compactness and low running costs are the main characteristics of B&C vane pumps. All the components subject to wear are contained
BQ FIXED DISPLACEMENT HYDRAULIC VANE PUMPS BQ SERIES Versatility, power, compactness and low running costs are the main characteristics of B&C vane pumps. All the components subject to wear are contained
Pacific Pump and Power 91-503 Nukuawa Street Kapolei, Hawaii 96707 Phone: (808) 672-8198 or (800) 975-5112 Fax: (866) 424-0953 Email: firstname.lastname@example.org Web: www.pacificpumpandpower.com Pumps
Impulse Turbine 1. A turbine is a rotary mechanical device that extracts energy from a fluid flow and converts it into useful work. 2. Early turbine examples are windmills and waterwheels. 3. Gas, steam,