# M-Bus Network Installation Notes

Save this PDF as:

Size: px
Start display at page:

## Transcription

1 M-Bus Network Installation Notes 1 M-Bus Network Installation Notes This manual explains how to calculate the maximum M-Bus cable length depends on technical parameters of used cable and number of M-Bus slave devices. It can be used for calculation if one or more M-Bus-LC-10 or M-Bus-LC-60 master M-Bus level converter is used. On slave side any M-Bus slave device can be used like: energy meters, PLC,..., etc. 1.1 Topology The topology of the M-Bus network is (almost) arbitrary. Only the ring topology as shown beneath should be avoided. In general the length of the cables should be minimized. Usually a mixture between star and bus topology should be used. 1.2 M-Bus Cable The M-Bus uses two wire cables which are going from the M-Bus Master / Repeater to each M-Bus device (bus structure). The M-Bus is polarity independent and needs no line termination resistors at the end of the cables. Page 1/5

2 Any cable type may be used as long as the cable is suitable for 42 V / 500 ma. Shielding is not necessary and not recommended since the capacity of the cable should be minimized. In most cases a standard telephone cable is used which is a twisted pair wire with a diameter of 0.8 mm each (2 x 0.8 mm). This type of cable should be used for the main wiring. For the wiring to the meters from the main wiring (last m to the meter) a cable with smaller diameter may be used. 1.3 Maximum Cable Length in M-Bus Networks The question for the maximum possible cable length in M-Bus networks is not easy to answer since several parameters are critical. However, an example calculation is shown here to give an estimation. Cable Type: 2 x 0.8 mm (JYStY N*2*0.8 mm) The limiting parameters in M-Bus networks are mainly the cable resistance and the cable capacity plus the capacity of the devices (= bus capacity). The cable resistance causes, depending on the bus current, a bus voltage drop. The maximum bus voltage drop may not be more than 16 V.. 18 V since the minimum bus voltage at any device must not be lower than 24 V (40 V 24 V = 16 V). R = U / I R: Cable Resistance U: Voltage Drop over Cable Length I: Bus Current N: connected M-Bus Umax = 16 V I = N * R= 16 / (1.5 * N) Ohm The cable resistance, therefore, limits the maximum possible cable length from the M-Bus Master / Repeater to the device with the largest distance away from it (largest cable segment). The table beneath shows an estimation of the maximum cable segment length: Page 2/5

3 Number M-Bus Resistance Length () kohm 142 km kohm 14.7 km Ohm 2.8 km Ohm 1.4 km Ohm 0.95 km Ohm 0.71 km Ohm 0.57 km The cable segment length is the distance from the M-Bus Master to the M-Bus device furthest away. NOTE: The given maximum cable segment length takes into account only the bus resistance and not the bus capacity. Therefore, some of the cable lengths in the table may not be possible in reality. At the end of the chapter is a table with real example configurations. The cable capacity plus the capacity of the M-Bus devices (= bus capacity) is responsible for sloppy signal edges. Therefore, the bus capacity limits the maximum data transfer rate of the M-Bus. The M-Bus Master is able to drive approx. 1 µf at a baudrate of 300 baud. The table beneath gives an estimation of the bus capacity / baudrate relationship: Baudrate Max. Bus Capacity Example Configuration 300 Baud 1000 nf 1 Device + 20 km Cable (1 * + 20 * 50 nf) km Cable (50 * + 19 * 50 nf) km Cable (250 * + 14 * 50 nf) 2400 Baud 300 nf 1 Device + 6 km Cable (1 * + 6 * 50 nf) km Cable (50 * + 5 * 50 nf) km Cable (250 * + 1 * 50 nf) 9600 Baud 100 nf 1 Device + 2 km Cable (1 * + 2 * 50 nf) km Cable (50 * + 1 * 50 nf) The given cable length is the sum over all cables attached to one M-Bus Master / Repeater. NOTE: The mentioned example configurations are taking into account only the bus capacity but not the bus resistance. Therefore, some of the cable lengths in the table may not be possible in reality. At the end of the chapter is a table with real example configurations. The tables beneath are showing some example configurations depending on bus resistance and capacity. In general the following topology is taken: Page 3/5

4 NOTE: The table values are theoretical maximum values. Usually the M-Bus devices are connected to the cable with varying distances from the M-Bus Master / Repeater. Therefore, larger cable length can be achieved in reality. However, for very large cable length additional parameters must be taken into account (e.g noise) and, therefore, cable length larger than approx. 10 km should not be used without amplification. 300 Baud 1 20 km 142 km 20 km km 14.7 km 14.7 km km 0.57 km 0.57 km Page 4/5

5 2400 Baud 1 6 km 142 km 6 km 50 5 km 14.7 km 5 km km 0.57 km 0.57 km 9600 Baud 1 2 km 142 km 2 km 50 1 km 14.7 km 1 km Page 5/5

### Documentation. M-Bus 130-mbx

Documentation M-Bus 130-mbx Introduction The mx M-Bus module is part of the mx Smart Slot communications family. With the integrated SmartSlot technology, mx systems ag offers automatic consumer data read-out

### MDM192 MULTI-DROPS DIGITAL MODEM FOR PRIVATE LINE. USER GUIDE Document reference : 9010709-03

MDM192 MULTI-DROPS DIGITAL MODEM FOR PRIVATE LINE USER GUIDE Document reference : 9010709-03 If you have questions about the MDM192 or desire assistance, contact ETIC TELECOMMUNICATIONS at the following

### Connection Instructions for Communication with SATEC Instruments

Connection Instructions for Communication with SATC Instruments All SATC Powermeter models today are equipped with one or two optically isolated serial communication ports. This allows work in various

### SYSTEM PRODUCTS OVERVIEW HYDRO-CENTER. System Products. Overview Application Offering Texts

HYDRO-CENTER System Products Overview Application Offering Texts 2006-01-01 1 HYDROMETER GmbH Ansbach / Germany / 2000-2006 The names HYDRO-CENTER, HYDRO-PORT, HYDRO-NET, HYDRO-FUNK, Flypper, Scampy, Bonyto

### s!nus-elektrotechnikai bt. Industrial IT & Automation

USER MANUAL s!nus-elektrotechnikai bt. USB/PPIM+ Siemens S7-200 USB/PPI Multi-Master Cable USB/RS485 Isolated For all PPI-Bus System Summary: USB / PPIM + is the PPI Multi-Master programming Cable which

### RS485 & RS422 Basics

RUA ALVARO CHAVES, 155 PORTO ALEGRE RS BRASIL 90220-040 TEL: +55 (51) 3323 3600 FAX: +55 (51) 3323 3644 info@novus.com.br RS485 & RS422 Basics INTRODUCTION The 422 and 485 standards, as they are known

### Electronics. Discrete assembly of an operational amplifier as a transistor circuit. LD Physics Leaflets P4.2.1.1

Electronics Operational Amplifier Internal design of an operational amplifier LD Physics Leaflets Discrete assembly of an operational amplifier as a transistor circuit P4.2.1.1 Objects of the experiment

### PHY 101 Lab 7 on Electric circuits: Direct current circuits Your name: Other team members:

PHY 101 Lab 7 on Electric circuits: Direct current circuits Your name: Other team members: Goals: To explore the basic principles of electric circuits, and how to measure them. Materials: Electrical resistors

### Meter Communication. Twisted Pair Baseband (M-Bus) Physical and Link Layer CEN TC 294. Date: 2000-02-15 TC 294 WI 006 CEN TC 294. Secretariat: AFNOR

CEN TC 294 Date: 2000-02-15 TC 294 WI 006 CEN TC 294 Secretariat: AFNOR Meter Communication Twisted Pair Baseband (M-Bus) Physical and Link Layer ICS: Descriptors: Document type: European Standard Document

### s!nus-elektrotechnikai bt. Industrial IT & Automation

USB/PPI+ Optoelectronic isolated USB/PPI adapter Optoelectronic isolated USB/PPI adapter, can replace Siemens 6ES7 901-3DB30-0XA0, the largest communication distance of up to 2 kilometers. Not support

### GE Industrial Solutions. EntelliGuard* Manager Gateway Installation Instructions

GE Industrial Solutions EntelliGuard* Manager Gateway Installation Instructions Contents Overview... 2 Wiring Guidelines... 3 Hardware Dimensions and Appearance... 4 RS-485 Connection to the EntelliGuard

### M-bus level converter

Metering M-bus level converter WTV531-GA5060 The level converter is an interface between M-bus meters and readout systems. PC software ACT531 reads the data locally or via the Internet using an optional

### Contents. Document information

User Manual Contents Document information... 2 Introduction... 3 Warnings... 3 Manufacturer... 3 Description... Installation... Configuration... Troubleshooting...11 Technical data...12 Device Scope: PCB

### Installation Manual (English) Adjustable Active DP Terminator T1-Pepper Active RS485 segment termination for non-compliant cable

Installation Manual (English) Adjustable Active DP Terminator T1-Pepper Active RS485 segment termination for non-compliant cable Designed for use with the COMbricks SALT repeater All baudrates Redundant

### Designing 4 to 20 ma Current Loops

This document describes how to manage the voltage drops in a 4 to 20 ma current loop, and how to determine the proper power supply voltage for the loop. 4 to 20 ma Current Loop Overview The 4 to 20 ma

### Elettronica dei Sistemi Digitali Costantino Giaconia SERIAL I/O COMMON PROTOCOLS

SERIAL I/O COMMON PROTOCOLS RS-232 Fundamentals What is RS-232 RS-232 is a popular communications interface for connecting modems and data acquisition devices (i.e. GPS receivers, electronic balances,

### PicoLog 1000 Small Terminal Board

PicoLog 1000 Small Terminal Board User s Guide DO161-3 Pico Technology Small Terminal Board User Guide CONTENTS 1 Overview 1 1.1 Introduction 1 1.2 Specifications 1 1.3 Connecting the Terminal Board to

### ELCOMPONENT LTD. User Manual

ELCOMPONENT LTD R-DCU - Remote Data a Collection Unit User Manual al CONTENTS Page 1. GENERAL... 1 2. SPECIFICATION... 4 3. INSTALLATION AND INSTRUCTIONS... 6 4. INSTRUMENT SET-UP AND RESET... 11 All rights

### Serial Port Connections

Serial Port Connections PORT 5 RS PORT RS45 Providing Power to an External Device from Port If either port is set up for communications with a serial device that requires 00mA or less at 5VDC, the device

### Network Design. Yiannos Mylonas

Network Design Yiannos Mylonas Physical Topologies There are two parts to the topology definition: the physical topology, which is the actual layout of the wire (media), and the logical topology, which

### What are the Requirements for an Accurate DSL Line Simulator? Paradyne International, France

Title: Source: Author: Contact: What are the Requirements for an Accurate DSL Line Simulator? Paradyne International, France Jack Douglass Jack Douglass Paradyne Networks, Inc. Voice: 949-233-3558 Email:

### Technical Data Sheet. 3DLevelScanner

Changing the market from level to volume Technical Data Sheet APM`s 3DLevelScanner incorporates advanced technology for accurately measuring bulk solids and powder stored in silos and open bins of all

### UNIVERSAL RS-232/422/485 CONVERTER FA-UNICON

UNIVERSAL RS-// CONVERTER FA-UNICON Universal RS-// Converter The FA-UNICON converter may be used to convert RS- signal levels to RS-/ signal levels or RS-/ signal levels to RS- signal levels. The FA-UNICON

### 1) 10. V 2) 20. V 3) 110 V 4) 220 V

1. The diagram below represents an electric circuit consisting of a 12-volt battery, a 3.0-ohm resistor, R 1, and a variable resistor, R 2. 3. What is the total resistance of the circuit 1) 6.6 Ω 2) 10

### HSG Engineering Tech Bulletin

Specifications subject to change OCT 2013; Rev. 1.3 HSG Engineering Tech Bulletin Recommended RS-485 Wiring for NetAXS-4/NetAXS-123 Loops Overview This document provides the recommended RS-485 wiring for

### M-Bus-Logger Data Logger

Data Logger User Manual Doc.-No.: E102312514074 Bär Industrie-Elektronik GmbH Rathsbergstr. 23 D-90411 Nürnberg Phone: +49 (0)911 970590 Fax: +49 (0)911 9705950 Internet: www.baer-gmbh.com COPYRIGHT Copyright

### Communication interface UT-4DR

Roger Access Control System Communication interface UT-4DR Firmware version : 1.0.0.58 Document version: Rev. A Contents 1. Description and specification... 3 1.1 Characteristics... 3 1.2. Using the interface

### Figure 1 120Ω 120Ω. Page 1 of 8 32# Transceiver. Transceiver. Transceiver. Transceiver

I. RS Bus Basics 1 RS Basic Characteristics of the Bus According to RS Industrial Bus Standards, RS industrial buses use differential method to transmit signal. This half-duplex communication bus has a

### ATS Communication Overview

ATS Communication Overview Viewpoint ATS 485 Communication link IBM Compatible Slide 1 of 23 Contents 1. Introduction 2. LonWork 3. Modbus Cards 4. Modbus Factory Configuration 5. Modbus Test Software

### Universal Converter PRODUCT INFORMATION B&B ELECTRONICS. Covers All the Bases:

4WSD9TB-0712 - p1/5 Model: 4WSD9TB Universal Converter Covers All the Bases: RS-232 to 4-wire RS-422, 2-wire or 4-wire RS-485 Highlights Selectable RS-485 2-wire half-duplex, or RS-485 4-wire full-duplex

### We hope that every customer sets up CC-Link system easily by reading this documentation.

This documentation describes items to consider in advance, how to select devices, points to keep in mind and procedure in order to set up cable wiring. Abstract of contents Chapter 1: Procedure for cable

### 1.Eastron SDM220Modbus Smart Meter Modbus Protocol Implementation V1.0

1.Eastron SDM220Modbus Smart Meter Modbus Protocol Implementation V1.0 1.1 Modbus Protocol Overview This section provides basic information for interfacing the Eastron Smart meter to a Modbus Protocol

### HARTING econ 3000 Introduction and features

HARTING Introduction and features HARTING es, unmanaged, for installation in control cabinets General Description Features The Fast es of the product family HARTING are suitable for industrial applications

### Data Sheet SIMATIC S7-200 CPU 226 DC/DC/DC and CPU 226 AC/DC/Relay

SIMATIC S7-200 and Table 1 Specifications for and Physical Size Dimensions (W x H x D) Weight Power loss (dissipation) CPU Features On-board digital inputs On-board digital outputs High speed counters

### INTERFACE CONVERTER TraxBus TO EIA-RS232 / EIA-RS422 / EIA-RS485 SAFETY INFORMATION RECEIVING

INTERFACE CONVERTER TraxBus TO EIA-RS232 / EIA-RS422 / EIA-RS485 TraxBus is a dedicated fieldbus specifically designed to operate in very harsh environments where electrical noise generated by ignition

### Standard Wiring Guide

MICRO THERMO TECHNOLOGIES Standard Wiring Guide Document No.70-PWH-1003-R0.8 MTA V4.1 No part of this publication may be reproduced, stored in a retrieval system, or transmitted, in any form or by any

### Blue ID Network module SN1/SN2/SN3/SN3t

Blue ID SN/SN/SN3/SN3t The system supports both bus and star topologies. Power over Ethernet An operating unit (TouchPoint) can be connected to the port for PoE, for instance. A major advantage of PoE

### MAKING MODERN LIVING POSSIBLE. AK-SC255 On-Site Installation Guide DANFOSS ELECTRONIC CONTROLS & SENSORS

MAKING MODERN LIVING POSSIBLE AK-SC255 On-Site Installation Guide DANFOSS ELECTRONIC CONTROLS & SENSORS How to Use This Guide Read this Guide completely as you install and start up your new AK-SC 255 controller.

### ENV909 kwh Meter Modbus Metering System

ENV909 kwh Meter Modbus Metering System 1 Programming Meters fitted with the Modbus option have two additional stages in the front panel programming menu. Baud Rate Unique Modbus Address A V In programming

Overview Analog inputs For connection of voltage and current sensors, thermocouples, resistors and resistance s Application Analog input modules can be used to connect the PLC to analog process signals.

### Whale 3. User Manual and Installation Guide. DC Servo drive. Contents. 1. Safety, policy and warranty. 1.1. Safety notes. 1.2. Policy. 1.3. Warranty.

Whale 3 DC Servo drive User Manual and Installation Guide Contents 1. Safety, policy and warranty. 1.1. Safety notes. 1.2. Policy. 1.3. Warranty. 2. Electric specifications. 2.1.Operation ranges. 3. Connections

### Electrical data Nominal voltage AC/DC 24 V Nominal voltage frequency

echnical data sheet NV24A--RE Communicative globe valve actuator for 2-way and 3-way globe valves Actuating force 1000 N Nominal voltage AC/DC 24 V Control Modulating DC (0)2...10 V Variable Nominal stroke

### MEASUREMENT OF RESISTORS

MEASUREMENT OF RESISTORS Richard G. Lupa Benjamin M. Cadieux 9/17/2007 Objectives: Learn how to utilize and code with the resistor color code system Learn how to use a digital multimeter (DMM) and an analog

### Customer Interface Publication: KCH CIP002. Public Switched Telephone Network (PSTN)

Customer Interface Publication: KCH CIP002 Public Switched Telephone Network (PSTN) Technical Characteristics of the Private Branch Exchange (PBX) Analogue Multi-Line Interface Issue: 1.1 August 2007 The

### Distributed I/O networks reduce installation and wiring cost.

Distributed I/O The new RSTi I/O system is PROFINET enabled and ideal for distributed control applications. The compact, granular build as you go design of the RSTi enables the user to optimize the design

### RS232C < - > RS485 CONVERTER S MANUAL. Model: LD15U. Phone: 91-79-4002 4896 / 97 / 98 (M) 0-98253-50221 www.interfaceproducts.info

RS232C < - > RS485 CONVERTER S MANUAL Model: LD15U INTRODUCTION Milestone s model LD-15U is a RS232 to RS 485 converter is designed for highspeed data transmission between computer system and or peripherals

### 1.Find the Thévenin equivalent with respect to the 7k ohm resistor.

Tutorial questions 1.Find the Thévenin equivalent with respect to the 7k ohm resistor. Remove the 7k ohm, since it is not part of the circuit we wish to simplify. Keep the terminals open since we are finding

### Practical steps for a successful. PROFIBUS Project. Presented by Dr. Xiu Ji Manchester Metropolitan University

Practical steps for a successful PROFIBUS Project Presented by Dr. Xiu Ji Manchester Metropolitan University Basics of PROFIBUS Content Practical steps in the design and installation stages Segmentation:

### ProfiBus overview. Fig.1 Overview of PROFIBUS versions

ProfiBus overview 1. Introduction ProfiBus (PROcess FIeld BUS) is a widely accepted international networking standard, commonly found in process control and in large assembly and material handling machines.

Data Bulletin 1210DB0002R3/05 03/2005 LaVergne, TN, USA Communications Wiring for POWERLINK G3 Systems Class 1210 Retain for future use. ABOUT THIS BULLETIN This data bulletin describes the proper wiring

### Series and Parallel Circuits

Series and Parallel Circuits Ver. 1.2 In this experiment we will investigate the properties of several resistors connected in series and parallel. Our purpose is to verify the simple equations for the

### Crosstalk effects of shielded twisted pairs

This article deals with the modeling and simulation of shielded twisted pairs with CST CABLE STUDIO. The quality of braided shields is investigated with respect to perfect solid shields. Crosstalk effects

### DATA LINK CONVERTER RS 232 / RS 485

Via M.E. Lepido, 182-40132 BOLOGNA - P.O.BOX 4052 BorgoPanigale Tel.: +39 051 404140 - Fax: +39 051 402040 - WEB: www.ducatienergia.com DATA LINK CONVERTER RS 232 / RS 485 USER S MANUAL 0798 Table of contents

### FAST TUTORIALS FOR TIME-CHALLENGED TECHNICIANS

Tech Notes from a Telephone Engineer FAST TUTORIALS FOR TIME-CHALLENGED TECHNICIANS POTS Dialtone Description: POTS Plain Old Telephone Service Long held industry acronym for standard dialtone service

### RS232/RS485 CONVERTER USER'S GUIDE

RS/RS CONVERTER USER'S GUIDE DISCLAIMER: RMV ELECTRONICS INC. does not assume any liability arising from the application and/or use of the products described herein, nor does it convey any license under

### Electric Circuits II

Electric Circuits II Experiment 4: Resistances in Circuits Equipment needed: - AC/DC Electronic Lab Board: Resistors - Multimeter Purpose The purpose of this lab is to begin experimenting with the variables

### H Unit Input/Output Manual

H Unit Input/Output Manual 4 INPUTS 4 OUTPUTS RS485 Table of Contents Safety Rules...Inside Front Cover. Introduction...IFC 2. Communications...IFC 2.2 Baud Rate...IFC 2.3 Modbus Address... 2.4 Speed of

### Network Installation Guide

Maretron NMEA 2000 Network Installation Guide Installing an NMEA 2000 Network Installing an NMEA 2000 network consists of interconnecting NMEA 2000 electronic devices using plug-and-play cables and connectors.

### OPERATING MANUAL. Table of contents. 2 Phase Stepping Motor Driver 2M542. Rev. A. Introduction page 2. Specifications page 2 Timing chart page 3

2 Phase Stepping Motor Driver 2M542 OPEATING MANUAL Table of contents Introduction page 2 Specifications page 2 Timing chart page 3 Setting page 4 Current set page 4 educe current function page 4 Micro

### RSC232 Communication Converter

RSC232 Communication Converter Installation and Operation Manual LIMITED WARRANTY The manufacturer offers the customer a 24-month functional warranty on the instrument for faulty workmanship or parts from

### ALL ABOUT BALUNS WHAT IS A BALUN? 2 WHAT DO TWINAX BALUNS DO? 2 WHAT IS IMPORTANT ABOUT CHOOSING & CONNECTING BALUNS? 3

ALL ABOUT BALUNS WHAT IS A BALUN? 2 WHAT DO TWINAX BALUNS DO? 2 WHAT IS IMPORTANT ABOUT CHOOSING & CONNECTING BALUNS? 3 REQUIREMENTS: 3 RECOMMENDATIONS: 4 RECOMMENDED MAXIMUM TRANSMISSION DISTANCES: 5

### Application/Connection Examples

This Quick Start Guide is designed to familiarize the user with the connection and configuration of the DTS-305 DIN rail mounted single / 3 phase power & energy meter with RS-485 or TCP communications.

### Digital/Analogue Signal Converters/Multiplexers Section F

Section F The conversion of Analogue signals to digital is an important part of many control systems. So is the conversion of serial data between various standards (RS, RS485 and RS4 for example). www.weidmüller.com.au

### M90-19-R5. RS232 to RS422/RS485 Isolated Universal Converter. 1. Introduction. 2. Function diagram

to RS422/RS485 Isolated Universal Converter 1. Introduction The converts serial data from the standard to either RS422 or RS485. Features: Universal converter can be used with both and other manufacturer

### MULTICAL 601 & ULTRAFLOW 14

Installation and User s Guide MULTICAL 601 & ULTRAFLOW 14 Cooling meter www.kamstrup.com Operation conditions Operation conditions/measuring ranges: Calculator θ: 2 C 180 C Θ: 3K 170K Temperature sensor

### SLATE. Analog I/O Module INSTALLATION INSTRUCTIONS R8001U3001

SLATE Analog I/O Module R8001U3001 INSTALLATION INSTRUCTIONS Scan for more information Application SLATE brings configurable safety and programmable logic together into one single platform. The platform

### Lab 1: DC Circuits. Student 1, student1@ufl.edu Partner : Student 2, student2@ufl.edu

Lab Date Lab 1: DC Circuits Student 1, student1@ufl.edu Partner : Student 2, student2@ufl.edu I. Introduction The purpose of this lab is to allow the students to become comfortable with the use of lab

### Proper Wiring for RS-485

Proper Wiring for RS-485 This application note is intended to provide basic guidelines for wiring an RS-485 network. The RS-485 specification (officially called TIA/EIA-485-A) does not specifically spell

### If you want to get an official version of this User Network Interface Specification, please order it by sending your request to:

This specification describes the situation of the Proximus network and services. It will be subject to modifications for corrections or when the network or the services will be modified. Please take into

### 350500 Dynamic Pressure Charge Amplifier

350500 Dynamic Pressure Charge Amplifier Bently Nevada* Asset Condition Moniting Description The 350500 Dynamic Pressure Charge Amplifier (DPCA) is a component in a dynamic pressure sensing system. This

### ImproX IXP20 Controller INSTALLATION MANUAL

MODEL NUMBER: ISC910-1-0-GB-XX ISC911-5-0-GB-XX IXP20 CONTROLLER SPECIFICATIONS Working Environment Plastic Housing... Power ImproX IXP20 Controller INSTALLATION MANUAL Designed to work in an indoor (dry)

### Modular I/O System Analog and Digital Interface Modules

OPERATING INSTRUCTIONS Modular I/O System Analog and Digital Interface Modules Installation Operation Maintenance Document Information Document ID Title: Operating Instructions Modular I/O System Part

ADACSNET USB Control Module Installation Guide Termination Switch 2-Pin SensorNet Connection Features and Hookup The USB Control Module contains the following: - USB port: Connects to the host computer.

### Technical Description U00980 Revision 2

Technical Description U00980 Revision 2 TLON Author: Mikael Rivarola Date of issue: 2000-01-07 Date of rev: 2009-01-30 Table of contents 1 Introduction 2 2 Definitions / Explanations 3 3 General description

### A.4 Specifications for the CPU 224

A.4 Specifications for the CPU 224 Specifications for and Physical Size Dimensions (W x H x D) Weight Power loss (dissipation) CPU Features On-Board digital inputs On-Board digital outputs High speed counters

### CB Svendsen A/S PS 2015.08.02/ rev. 1.5

CB Svendsen A/S PS 0.0.0/ rev... Description Installation guide for. The is designed for copying of signals from electricity-, heat- or water meters to s. This way, it is possible to connect a data logger

### WEB log. Device connection plans

WEB log LIGHT+ 20 BASIC 100 PRO unlimited Device connection plans Version 20151210* Copyright Copyright for this manual remains with the manufacturer. No part of this manual may be reproduced or edited,

### Process modules Digital input PMI for 24 V DC inputs for 120 V AC inputs

E031026 000823 Process modules Digital input PMI for inputs for 120 V AC inputs PMI Input E4, E5, GND L- PMI 120 V AC Input E4, E5, Common C E6, E7, GND L- E6, E7, Common C LEDs for the inputs operation

### TO-PASS. TO-PASS -FAQ- Remote Monitoring. What is TO-PASS used for? What are the special functions of TO-PASS?

TO-PASS -FAQ- Remote Monitoring What is TO-PASS used for? TO-PASS modules are used as/for: Permanent online connection Fault detectors Remote data polling Data storage Telecontrol module What are the special

### KNX. Siemens Building Technologies HVAC Products. Synco Konnex bus. For devices of the Synco 700 / RXB ranges

7 7Z0 Synco Konnex bus For devices of the Synco 700 / RXB ranges KNX The Konnex bus (short KNX) unites the three existing bus technologies EIB (European Installation Bus also called Instabus), BatiBUS,

### Poseidon RS-485 wiring examples. Poseidon 2250. Variants of RS-485 industrial bus wiring for Poseidon sensors connection.

Poseidon wiring examples Variants of industrial bus wiring for Poseidon sensors connection. STAR topology Daisy chain topology (2) Poseidon bus types (), 4 pairs () (), 3 pairs (4pin) Industrial Bus ()

Unitronics Devices and RS485 Table Of Contents RS485 Options... 1 About RS485... 1 Network Topology & Wiring... 1 RS485 Network Wiring... 1 RS485 wiring considerations... 2 RS485, by controller type...

### EasyIO FG Series User Reference v1.3. EasyIO FG Series DDC User Reference

EasyIO FG Series DDC User Reference Document Change Log 1 st April 2013 Document created. 7 th July 2013 Correct mistakes and typo error. 4 th August 2013 Restore Factory settings 10 th Sept 2013 Added

### PROFIBUS. Design and. Good Practices

Design and Good Practices Webpage www.profibus.com.sg 3 ERP DCS MES Ethernet backbone 4 3 5 6 2 1 PA coupler PA link PA 7 8 31 Author / Title of the presentation 4 3 5 6 2 1 PA 7 8 31 DP - Principle 4

### HARTING mcon 3000 Introduction and features

Introduction and features HARTING mcon 3000 es, managed, for mounting onto top-hat mounting rail in control cabinets General Description Features The fully managed es of the product family HARTING mcon

### Model CFA-24 Transparent Cable Farm Automation Switch

Model CFA-24 Transparent Cable Farm Automation Switch Ideal for Broadband Forum s ID-337 G.fast Certification and TR-249 VDSL2 Vectoring Testing High performance transparent solution designed to automate

### M-Bus Master MultiPort 250D Installation and User Guide

M-Bus Master MultiPort 250D Installation and User Guide Kamstrup A/S Industrivej 28, Stilling, DK-8660 Skanderborg Tel: +45 89 93 10 00 Fax: +45 89 93 10 01 info@kamstrup.com www.kamstrup.com Contents

### DeviceNet Troubleshooting FIELD GUIDE

DeviceNet Troubleshooting FIELD GUIDE G1001 Publised 11/11/2013 SCOPE T he purpose of this troubleshooting guide is to direct qualified service personnel to the causes of network problems and provide remedies.

### IQ SENSOR NET MIQ/JBR

Operating Manual IQ SENSOR NET Power! OK IQ SENSOR NET signal amplifier module ba76077e01 01/2012 Note For the most recent version of the manual, please visit www.ysi.com. Contact Copyright YSI 1725 Brannum

### RS485 Troubleshooting

Application Note 005 a Visual Plus Corporation Company RS485 Troubleshooting ver.1.0 This document describes how to detect errors and make right setup of RS485 network with EWS controllers www.visual-plus.com

### Application Note: XPort-AR Power over Ethernet

Application Note: XPort-AR Power over Ethernet Lantronix, Inc. 15353 Barranca Parkway Irvine, CA 92618 Tel: +1 (949) 453-3990 Part Number 920-??? Revision A May 2005 Overview Power over Ethernet (PoE)

### Current Loop Application Note 1495

Current Loop Application Note Document No. CLAN1495 International Headquarter B&B Electronics Mfg. Co. Inc. 707 Dayton Road -- P.O. Box 1040 -- Ottawa, IL 61350 USA Phone (815) 433-5100 -- General Fax

### Experiment 8 Series-Parallel Circuits

Experiment 8 Series-Parallel Circuits EL 111 - DC Fundamentals By: Walter Banzhaf, E.K. Smith, and Winfield Young University of Hartford Ward College of Technology Objectives: 1. For the student to measure

### Dynamic Pressure Charge Amplifier

350500 Dynamic Pressure Charge Amplifier Description The 350500 Dynamic Pressure Charge Amplifier (DPCA) is a component in a dynamic pressure sensing system. This sensing system, which monitors pressure

### Linear encoders without bearings incremental System for linear motion feedback

Features Robust magnetic sensing method Output signals A 90 B with index signal Output circuits: HTL/push-pull and TTL/RS422 Resolution up to 5 µm (4-times evaluation) Non-contact, wear-free sensing system

### Experiment NO.3 Series and parallel connection

Experiment NO.3 Series and parallel connection Object To study the properties of series and parallel connection. Apparatus 1. DC circuit training system 2. Set of wires. 3. DC Power supply 4. Digital A.V.O.

### DVM990BL MULTÍMETRO DÍGITAL MANUAL DEL USUARIO

DIGITAL MULTIMETER OPERATING MANUAL DIGITALE MULTIMETER BEDIENINGSHANDLEIDING MULTIMETRE DIGITAL MANUEL D UTILISATION DIGITALES MULTIMETER BEDIENUNGSANLEITUNG MULTÍMETRO DÍGITAL MANUAL DEL USUARIO 1. SAFETY