1 7 Years Operation of BWRO Plant with Raw Water from Coastal Aquifer for Agriculture Irrigation Authors: Carlos García, Francisco Molina and Domingo Zarzo Valoriza Agua, C/Molina de Segura, nº8, 30004, MURCIA, SPAIN. Tel: , Fax: TOPIC: Brackish Water Desalination Abstract In this paper it will be shown the most relevant aspects in the 7 years operation period in the management of the O&M (Operation & Maintenance) at BWRO (Brackish Water Reverse Osmosis) plant at Cuevas de Almanzora, Almeria, Spain. This plant has a current capacity of 25,000 m 3 /day and it was built to supplying agricultural consumers in the proximities of the plant. Cuevas de Almanzora BWRO plant is an exceptional plant in many aspects; - is a plant working with brackish water, but it was designed to be able to working with seawater from the point of view of materials, qualities and pressures (except the high pressure pump), and even it could be converted easily into a seawater plant. - extensive hydrogeological studies have been done, allowing the control of aquifer exploitation and water extraction in the seawater-brackish water interface - Water is distributed to different agricultural users with different water quality requirements (it produces a la carte water) - RO trains include interstage energy recovery device to improving the hydraulic equilibrium between stages and to reducing the energy consumption In the current paper the following aspects will be presented: - BWRO plant description - Results of the aquifer hydrogeological studies for the determination of saline intrusion. Conclusions and operation guidelines. - Operation of the plant. Results. Operational problems arising from increasing salinity and specifically from sulphates - Description of the planned changes at the plant to allowing its future possible conversion into a SWRO plant - O&M Costs
2 I. INTRODUCTION 1.1. Desalination for agriculture in the area Spain suffers an important lack of water resources that is aggravated with time and includes cyclical drought periods. In the environment of this worrying situation, in general water uses are prioritized for human supply, leaving in second place other uses as agriculture irrigation or recreational uses as golf courses, irrigation of parks and gardens and urban services. For this reason, the use of potable water is restricted for other uses being necessary to looking for other non conventional resources (reuse, brackish and seawater desalination). For example, in Spain the use of potable water for irrigation of golf courses irrigation is totally forbidden. Then, in the case of Spain, farmers and other users of this water have assumed in their production costs the price of this new water coming from desalination or reuse installations. From the scarcity period around 1995, many farmers and agriculture businessmen decided to install desalination plants in the South East of Spain (mainly Mediterranean coastal areas) to solve the problem of available resources. In Spain, these technologies were very used previously in Canary Island but it was this moment the beginning in the mainland. We estimate that between 1995 and 2000 were installed more than 200 desalination plants for this application in this area, with typical sizes rating between 100 and 5,000 m 3 /day, with some plants treating more than 10,000 m 3 /day. Two examples of it are the Mazarron and Cuevas de Almanzora plants, with sizes of 13,500 and 25,000 m 3 /day, respectively. Mazarron plant was built following a project from the owner and, although it incorporated some technical innovations as energy recovery devices (turbocharger) it was not successful due that the increase of salinity in less than a year from 9,000 ppm of TDS to more than 20,000 ppm of TDS, being finally re-turn into a seawater desalination plant with larger capacity. The case of Cuevas de Almanzora plant will be described in this paper. The implementation of AGUA program from the Spanish Environment Ministry could change this situation because the large plants installed all over the Mediterranean coast could supply water for human consumption and for agriculture and services (although there is a discussion with the farmers about the final price of water) leaving abandoned or stopped the small facilities built in recent years some of which were even illegal.
3 1.2. Description of the customer and their needs Figure 1. Cuevas de Almanzora BWRO The Comunidad de Regantes de Cuevas de Almanzora is an association of agricultural producers which supplies water for different clients and end users in the area of Cuevas de Almanzora, Palomares, Villaricos and Vera, in the Almeria province, Spain. Until recent years, water resources of this community came from the dam of Cuevas, which recorded minimum levels in the last years, and the contributions of water transfers from other regions (too restricted). These allocations were insufficient as enabling many farmers to reduce land for their crops. Other additional problem was the increasing salinity of aquifers doing groundwater useless for agriculture purposes. In 2002 the works of a new desalination plant began to solve the water problems of this community. The BWRO plant was designed for a total flow of 30,000 m 3 /day, with the building, intake and other installations ready to treat 60,000 m 3 /day. Given the increasing salinity forecasts and even the possibility of exclusive use of seawater, the plant was built with components prepared to treat seawater, including 1,200 psi pressure vessels, high pressure piping 904 L stainless steel, etc. This makes it possible to convert existing facilities to treat seawater at a reduced cost. The installation of RO trains (5,000 m 3 /day each) was train by train observing the salinity increasing in the raw water. The construction was stopped with 4 trains which it was enough for the community needs and maintaining stable the aquifer. In recent years another 5,000 m 3 /day were added with the incorporation of another small plant disused from a farm. II. DESCRIPTION OF THE PROJECT 2.1. Basic Data Location: Road between Villaricos and Palomares (Almería, Spain) Owner: Irrigation Community Cuevas de Almanzora. Design, construction and operation: Consortium between SADYT and Talleres y Gruas Gonzalez (local civil works contractor) Project Type: Private installation partially subsidized by local government (Junta de Andalucia) including European Community funds and with an O&M contract for 15 years.
4 Technology: Reverse Osmosis Desalination Plant. Purpose of Installation: To obtain quality water for agricultural irrigation. Flow: 30,000 m 3 /day in different stages (currently in operation 25,000 m 3 /day) Recovery: 65-70% Water Quality: Brackish water underground from coastal aquifer. Conductivity between 9,000-20,000 µs/cm (with increasing salinity) Treated water: Contract: < 500 µs/cm The plant was executed in a record time; Beginning of the works: September 2002 Term of execution: 8 months (6 months to start-up the first RO train) 2.2. Plant Description Treatment Process 1) Water Intake By wells (6 currently), with an average depth of m. Depth of 50 m while maintaining the water level between 8 and 11 m. 2) Raw water tank 1,500 m 3 3) Physical pretreatment (sand filtration and cartridge filter): - 4 low pressure pumps 350 m 3 /h - 1 backwash filter pump 450 m 3 /h - 4 units sand filters 3,000 mm diameter and 11,000 mm length - 1 blower for filter backwash - 4 units of GRP cartrigde filters, with 150 cartridges of 40 length and 5 microns selectivity 4) Chemical pretreatment: Hydrochloric acid, Sodium hypochlorite, Sodium Bisulphite and antiscalant. Really only antiscalant is added currently. 5) REVERSE OSMOSIS TRAINS - 4 high pressure pumps 350 m 3 /h, 27.5 bar, with frequency variation, with 400 kw electric motor. Nº de trains: 4 Unitary flow: 5,000 m 3 /day Total flow: 20,000 m 3 /day Figure 2. Cuevas de Almanzora BWRO plant
5 Additionally in the last years a small 5,000 m 3 /day plant was transported and installed into the RO building increasing the total flow to 25,000 m 3 /day. This small plant (in 2 trains) was installed with all the required pre-treatment (sand filters, cartridge filters, chemical dosing ) Design Recovery: % Array: (34:17) x 6 Membrane: TORAY SU-720 F (1ª stage)/su-820 FA (2ª stage) Energy recovery system There are installed energy recovery devices (Turbocharger) to recover some of the residual energy from brine, increasing the pressure between the first and second RO stages. 6) CIP system With cleaning and flushing pumps 270 m3/h, cartrigde filter and 2 tanks with de 20 and 50 m 3, respectively, equipped with agitation and heat resistance. 7) Electrical installation Plant has 3 transformers with 750 KVA each one, CCM, and SCADA system for control. 8) Product water pond Works included an open pond with 23,000 m 3 capacity to store product water 9) Product water pumps Plant includes 2 pumping stations: 1) pumping station to Cuevas de Almanzora, with 4 pumps with 290 m 3 /h at 18.5 bar, which it sends product water to the water pipes net for distribution of community varying the flow and pressure depending on the needs of end users. 2) a second group of pumps to send water to Palomares village, with 3 additional pumps 10) Brine discharge The facilities include a submerged pipe for discharge of brine that comes to join to other brine pipe from Pulpi (another desalination plant) and ends at 350 m of shoreline and 6.5 m deep at the mouth of the Almanzora River. The outfall pipe is 650 mm in diameter with horizontal injection diffuser nozzles at the point of discharge. The point of discharge, derived from the environmental impact study, it was decided due to the characteristics of the river Almanzora with flooding periods and without sensitive species, without forgetting that this is a discharge of water with lower salinity than seawater made at the mouth of a river, which is an area degraded by sediment transport. For optimization of operation management, plant is fed from different wells with different flows and salinities, depending on behaviour of each well (those are medium values); - Well 1 : between ms/cm and ms/cm (practically not used) - Well 2 : between 9.00 ms/cm and ms/cm - Well 3 : between 9.00 ms/cm and ms/cm - Well 4 : between 7.00 ms/cm and 8.60 ms/cm - Well 5 : between 7.00 ms/cm and 8.80 ms/cm - Well 6 : between 8.00 ms/cm and ms/cm
6 2.2. Innovations Plant ready to treat different water qualities The plant was designed knowing the problem of increasing salinity in raw water, and then the concept of it was in 2 stages: 1 st stage: recovery of water from the river mouth (although the intake is from wells) avoiding the seawater. Designed to treat water with conductivity between 7,600 30,000 µs/cm 2 nd stage: Progressive incorporation of seawater treatment In the lasts years the equilibrium of the system has been maintained with growing salinity although stable, and then is not still necessary the transformation into a seawater RO plant Solutions to operate with growing salinity RO Plant designed to work with salinity 25,000-30,000 µs/cm High pressure pumps designed in a very conservative way and with frequency variation For correct hydraulic balance between stages it was included an energy recovery turbine (Turbocharger) and membranes are different on each stage: Membrane 1st stage: SU 720 F (brackish water) Membrane 2st stage: SU 820 FA (seawater) But it every fails, we will go to the B-plan. The plant is easy to transform into a seawater plant due that the following facts; - 1,200 psi pressure vessels SS pipes, Sch 80 in high pressure - GRP and materials resistant to seawater corrosion in pre-treatment - Carbon steel filters with rubber lining - High pressure pump has a longer shaft that would attach a Pelton turbine. Another option would be changing the pumps, and incorporating other energy recovery devices - Other materials (valves, pipes, fitting, instruments, etc.) were designed too for seawater treatment Production of a la carte water Quality of water supplied is different depending on the requirements of each end-user. The quality requirements are different depending of the crops irrigated (tomatoes, lettuce, potatoes, melon, etc.), or type of user (agriculture irrigation, golf course, sometimes even drinking water for surrounding municipalities). Quality of water supplied in controlled by means of an automatic blending of permeate and raw water with the control of conductivity of each flow. The price is different too and is calculated as function of registered quality or demand R&D Center In recent times the plant has become into a research centre for Sadyt, having installed some pilot plants to research about brine dilution, ZLD of brine by means of evaporation-crystallization, etc., operating on the plant.
7 Trasar 3-D Due that past problems with increasing concentration of salinity in raw water (and especially of sulphates) and the need to control the adequate dosage of antiscalant, it was agreed with Nalco the installation of a Trasar 3-D system, to control accurately this dosage Hydrogeological studies Figure 3. Nalco Trasar 3-D device In order to predict the behaviour of the aquifer with time and with the extraction of well water for the plant, a series of hydrogeologic studies were conducted Studies: Infiltration and flows calculation (rainfall studies) Geologic and hydraulic environment Piezometric levels of groundwater, water quality and evolution with time List of water intakes Evaluation of resources Crops maps and water uses Pumping tests These studies were completed with a campaign of geophysical exploration by means of Electrical tomography (technology based in the analysis of electrical resistance of ground materials). 16 profiles of electrical tomography grouped in 5 lines with direction NW-SE, perpendicular to the coast line. Each profile with 355 m lenght
8 Figure 4. Electrical tomography profiles Figure 5. Example of profile. (red=water with low salinity, green=brackish water, blue=seawater) There were observed 3 different stripes in direction NE-SW parallel to the coast; High conductivity (close to the sea). Conductive Materials. Very salty water High conductivity. Materials predominantly conductive. salty water Moderated salinity. Thick materials with brackish water in the pores. brackish water. This study allowed determine; - most adequate area for well water intake and possible evolution of aquifer - most adequate area for future seawater intake -possibility to inject brine in the salty water area (this solution was discarded finally with the construction of the brine pipe) Costs Investment cost The investment of the works was as follows; Investment for the 1st stage of the plant: 12,182,727 Subsidy of Junta de Andalucía (local Government): 6,091,363
9 O&M costs Water costs are different depending on raw water quality and product water quality required for each user. In next table a typical distribution of costs is shown. Normally the costs are below 0.3 /m3. Concept /year /m 3 Variable costs Chemicals Membrane replacement Cartrigde filters 0,.004 and others Energy Maintenance 0.01 Total variable cost Fixed costs Personnel 148, Fixed 16, maintenance Other fixed costs 19, Total Fixed costs 184, TOTAL COST Table 1. O&M costs for 17,000 µs/cm conductivity in raw water Personnel costs are very reduced in this case (as usual in desalination plants for agriculture irrigation) because the plant is managed only with 4 persons and partially from distance by means of the sending of alarms to the cell phones of O&M personnel, avoiding in this way the presence of personnel by night or in weekends. III. RESULTS 3.1. General Data In the next graphs are shown some characteristics of raw water (conductivity, chlorides and sulphates) in the last 4 years.
10 CONDUCTIVITY Figure 6.Conductivity of raw water Sulphates Figure 7. Sulphates in raw water Chlorides Figure 8. Chlorides in raw water As it can be seen, the conductivity and chlorides in the last 4 years seem quite stable, but sulphates are showing a different tendency. This is important due that the peak of sulphates obtained in the first years of operation that forced the temporarily reduction of recovery and the change of antiscalant.
11 3.2. Problems at startup and first years The plant started up in late May 2003 with salinity values in raw water of 9,200-9,400 µs/cm and a sulphate concentration of 2,800 ppm. Recovery was fixed at 63% using the antiscalant PermaTreat 191. But soon it was found a progressive increase in conductivity in the raw water, reaching values of 10,000-10,200 µs/cm, in only one month, with a period of maximum conductivity of 12,000 in July 2003, although it was stabilizing this trend. At this time, the concentration of sulphate was at values between 3,000-3,300 ppm, which forced to reduce recovery between 55-56%. Given the low economic viability of this recovery, it was decided to change the dosage of antiscalant PermaTreat 191 by a more specific product such as PermaTreat 504, which allowed the system to raise the conversion to values of 70% mg/l SULPHATES IN RAW WATER 29/04/ /07/ /10/ /01/ /04/ /06/ /09/ /12/2004 Data RAW WATER Figure 9. Sulphates in raw water It also shows the evolution of sulfate with time, which reflects the rapid increase between the months of May and August of 2003, which later was moderating over time to remain stable in the last few months setting to 2,600 ppm. Curiously, the level of sulphates it was sometimes over the level of sulphates in seawater, and the Chloride concentration was relatively stable. The interpretation of this problem was that perhaps it was due to aquifer material solution. It must be said that the graphics shown are for the purpose of showing the trend of parameters, but it can not be interpreted rigorously, because it represents blended water values from individual wells (which it have different characteristics and location), and the operation has not always worked with all the wells and sometimes even in alternation.
12 3.3. O&M data About the main process parameters it must be pointed that; - Temperature is very stable all over the year with values around 20ºC - no membranes have been replaced from the startup (7 years) - cartridge filters has been usually changed 1 time per year - only antiscalant is added as chemical treatment (Permatreat 191 and Permatreat 504 in the peak periods with high sulphate concentration) - 1 chemical membrane cleaning is done per year ph raw water ph prod. Temp (ºC) Minimum value Maximum value Average value Table 2. Some water parameters in 2009 (values obtained from 2 data per day) Cond. Raw water Cond product Cond. Reject 1st stage Cond 1st stage Cond 2nd stage Cond brine (µs/cm) (µs/cm) (µs/cm) (µs/cm) (µs/cm) (µs/cm) Minimum value 14, , ,265 Maximum value 20, , ,020 Average value 17, , ,135 Table 3. Some water parameters in 2009 (values obtained from 2 data per day) P 1 st stage (bar) P oulet 1 st stage (bar) P inlet 2 nd stage Pressures P outlet 2 nd stage P outlet 2 nd stage P backpressure Table 4.Typical operating values in year Energy consumption and energy tariffs Energy recovery due to the Turbochargers is over 30%, with a specific electrical consumption in high pressure pumping of 0.9 kwh/m 3, and 1.9 kwh/m 3 in the whole plant including permeate pumping.
13 In the next table it is shown a typical table of results for the energy recovery for a raw water conductivity of 15,000 µs/cm; Pressure (bar) Raw water Conductivity (ms/cm) Product water conductivity (µs/cm) Recovered pressure (bar) TRAIN TRAIN TRAIN TRAIN Table 5. Energy recovery Another very important issue in this plant is the use of special energy tariffs playing too with discontinuous operation. Plant stops automatically in peak and high-peak hours reducing in this way the energy costs. Unfortunately, sometimes the peak water demand is in months with more energy peak hours and then is more difficult to manage this situation. Since the beginning of free market in the electricity sector in Spain the cost of energy have changed both in terms of power and energy increasing a 59% in terms of power and 35% in consumption terms. The type of rate that corresponds to our facility (rate 6.1), the costs set out in the regulated part of the electricity tariff for access to the free market are listed in table 6. Over these energy fixed as part of regulated tariff we must to increase the marketing and distribution costs with a formula such that: Final Cost = Fixed cost + (Market Cost) x Passage Coefficient Fixed cost = cost of the regulated rate indicated in table 6 Market cost = in the energy cost published daily with a day in advance Passage Coefficient = is a variable rate set by the trader and It includes the benefit and cost of toll distribution With this formula, there are two contract possibilities - First option it is through a flat rate for each period and is renewed annually, in which the trading company after their market forecasts set a price that is unchangeable during the contract period - A second is the type of Pool. This is our case and it consists in that the price varies by the monthly average for each period to which using the above formula. Thus we are not subject to a fixed price with the advantages and disadvantages that it implies. Advantages: due that the situation that currently is suffering the market, due that lower consumer demand for the fall of national productivity it makes energy more affordable now and below average prices that companies offer. Disadvantages: it could be possible that changes in market prices rising sharply and there is no possibility of changing the form of contract until after the lifetime of this.
14 Power Term /kw year P1 P2 P3 P4 P5 P6 INCREASES , , , , , , January 10, , , , , , ,00% 2009-July 13, , , , , , ,00% 2010 January 16, , , , , , ,00% (proposed) 2010 July 17, , , , , , ,00% Consumption Term /kwh P1 P2 P3 P4 P5 P6 INCREASES , , , , , , January 3, , , , , , ,00% 2009-July 4, , , , , , ,00% 2010 January 6, , , , , , ,00% (proposed) 2010 July 7, , , , , , ,00% Table 6.Tariff 6.1. Since it came into force the free market in Spain we had the two forms of contract. At first our method was tied to a fixed rate contract with an average cost of per Kw- hr. After analyzing the market trends it was decided to change the type of contract to the second option provided with a commitment to venture with our client that obliges us to share the benefit. Since then the cost per kwhr is below IV. CONCLUSIONS The main conclusions obtained during this experience are indicated next. - Desalination plants treating underground brackish water require rigorous studies of the aquifer to test their possible temporal evolution and the impact on water extraction and exploitation - Aquifer studies can also determine the most appropriate for deposits, the optimal operating system and the location of the discharge - The design of a facility of this type, and more so, in coastal aquifers, must be flexible and able to respond to different situations of water quality an expected worsening - The desalination plant in Almeria Cuevas de Almanzora is a unique facility in many ways - is a plant that is currently working with brackish water, but is ready to work with sea water, in terms of materials, qualities and pressures (except pumps) - there were made rigorous hydrogeological studies, which control the exploitation of the aquifer and the extraction of water to be desalinated brackish water interface of sea-water - water distributed to different users with different requirements (produced water "on demand")
Technical Paper Optimizing Water Recovery and Energy Consumption for Seawater RO Systems Authors: Antonia von Gottberg, Ark Pang and Jose Luis Talavera Introduction The costs of seawater desalination have
The most complete solutions in GRP PIPES AND FITTINGS CURAÇAO DEGREMONT (Netherland Antilles) 2008 / D-2 C A S E S T O R Y SWDP desalination PROTESA MANUFACTURES, SUPPLIES AND INSTALLS THE PROCESS PIPING
IWC-00-15 INTERSTAGE ENERGY RECOVERY TURBINE APPLICATION MARCO ISLAND, FLORIDA JULIA NEMETH, PE Harn R/O Systems, Incorporated Venice, Florida STEVEN DURANCEAU, PHD, PE Boyle Engineering Corporation Orlando,
Tech Fact FILMTEC Membranes Strategies for Using FILMTEC Elements to Lower Your Total Cost of Seawater Desalination As demand for drinking water continues to increase particularly in regions of the world
Conventional vs MF/UF Pretreatment for SWRO Desalination PNWS AWWA Annual Conference 8 May, 2009 Co-Authors Acknowledgements Val Frenkel, Kennedy/Jenks Consultants Jim Lozier, CH2M HILL Marin Municipal
Prof. Maria Loizidou National Technical University of Athens (NTUA) email@example.com 1 BRAWA Project Development and implementation of an innovative, brackish water treatment pilot plant for the production
La dessalinització The Tordera desalination plant 2002 Tordera ITAM Installation of Treatment of Marine Water of the Tordera Antecedents: description of the Tordera delta and aquifer exploitation The river
TU Berlin Campus El Gouna Department Water Engineering Water and wastewater management in El Gouna, Red Sea, Egypt In the frame of: Sustainable Use of Resources: Water and Energy for Egypt IWaTec winter
Tampa Bay Seawater Desalination Plant Project History How The Plant Works Desal Fun Facts 2575 Enterprise Road, Clearwater, FL 33763-1102 Phone: 727.796.2355 / Fax: 727.791.2388 www.tampabaywater.org Tampa
Case History High Turbidity and Temperature Fluctuation No Obstacle for Site Information Location: HeBei, China Capacity: 12 m 3 /h (5283 gpm) Purpose: Pretreat sea water prior to RO system Time in Operation:
The Grand Miramare Hotel Santa Margherita (Portofino) Italy March 19 22, 2013 Inspiring Innovation and Excellence About the IDA Desalination Academy The IDA Desalination Academy aspires to increase knowledge
Water Development Department Ministry of Agriculture, Natural Resources and Environment Artificial Recharge of Tertiary Treated Sewage to the Ezousas Aquifer in Cyprus Antonis Antoniou Executive Engineer
Aquatech Seawater Reverse Osmosis System at Ghalilah, Ras Al Khaimah, United Arab Emirates In 2014, the Federal Electricity and Water Authority of the United Arab Emirates, in EPC partnership with Aquatech
CENTRAL ARIZONA SALINITY STUDY ---- Phase I Technical Appendix O Municipal TDS Research Introduction Water availability and quality are among the world s most important environmental issues. Demand for
ing Solutions for Desalination and Water Reuse 2 Experience and Proven Technology As a global leader in pump design and manufacture, Sulzer is recognized for delivering the excellent product quality and
Guidance Leaflet Reducing water use softeners and reverse osmosis Most water supplies contain dissolved solids (e.g. salts and other minerals, particularly calcium and magnesium). The type and level of
Ionics Technical Paper New Sea Water Reverse Osmosis Plants for the Caribbean Energy Recovery, Brine Recovery & Cost Reduction by Shawn Meyer-Steele and Antonia von Gottberg, Ionics, Incorporated, U.S.A.,
Desalination of Seawater by Reverse Osmosis The Malta Experience Introduction Malta, an archipelago of three islands situated 50 miles south of Sicily in the middle of the clear blue Mediterranean Sea,
CONSTRUCTION AND START-UP OF THE CLEWISTON REVERSE OSMOSIS PLANT Curtis Kurt A. Kiefer, P.E., BCEE, Vice President, CDM, Fort Lauderdale, FL Kevin McCarthy, Utilities Director, City of Clewiston, Clewiston,
Flow Configuration There are several flow configurations for RO that allow the user to get the most out of the system. This paper will cover a few of the techniques used in RO design to optimize system
Innovative Designs of the UF& SWRO Limassol Desalination Plant in Cyprus N. Nadav, Mekorot Water Co., The Projects' Design and Commissioning Engineer, Lincoln str. 9 Tel-Aviv Israel, firstname.lastname@example.org
Desalination Efficiency: Energy, Water and Other Resources Technical Paper Author: William Harvey Desalination Commercial Development Leader GE Water and Process Technologies Enviro 2008 Conference, May
Technical Paper Seawater Reverse Osmosis Plants in the Caribbean Recover Energy and Brine and Reduce Costs Authors: Shawn Meyer-Steele, Antonia von Gottberg and Jose Luis Talavera Introduction With continued
Appendix A Cost Evaluation TABLE OF CONTENTS Appendix A. Cost Evaluation... A-1 A.1 Purpose and Scope... A-1 A.2 Method and Assumptions... A-1 A.2.1 Raw and Product Water Qualities... A-2 A.2.2 Recovery...
Differentiation Summary Revolutionizing Water Clean-Up Opportunities NanoClear is a water clean-up process that affordably and efficiently converts salt, brackish or waste water into pure, usable water.
Comparative Cost of UF vs. Conventional Pretreatment for SWRO Systems Abstract P. Glueckstern and M. Priel, Mekorot Water Co., Tel-Aviv Surface seawater intended for desalination by RO need extensive pretreatment
The Economics of Desalination for Various Uses Carlos Campos Index 1. Introduction 2. Available desalination technologies 1. Desalination by MSF 2. Desalination by RO 3. Comparison of large scale desalination
Tap Water Reverse Osmosis system LPRO series LPRO-B series (Basic design) LPRO-P series (Premier design) LPRO-B16 series reverse osmosis systems are designed and manufactured for commercial and light industrial
Economic and technical assessment of desalination technologies Fawzi Banat Jordan University of Science and Technology Jordan Geneva 6-8 June, 2007 John F. Kennedy had said If we could ever competitively,
RO SYSTEMS RO Reverse Osmosis equipments A range of Reverse Osmosis equipment designed to provide the highest performances with flow rates demand from 50 to 1000 l/h. Every component of the equipment is
W e w o r k i n p a r t n e r s h i p w i t h a l l c i t i z e n s t o a c h i e v e a q u a l i t y a n d r e l i a b l e w a t e r s o u r c e. Design Team n Jcsa Owner/Operator n Buchart Horn Prime
Low Energy Desalination Demonstration Unit Results SIWW 2011 07 July By: R. Knauf, T. LeTourneau, K. H. Ng, R. Fu, L. S. Liang, M. Shaw The Desalination Challenge In August, 2007, the Singapore Environment
Reuse of Alternative Water Sources for Cooling Tower Systems Two Case Studies Using Non-Traditional Water Sources Matthew L. Haikalis Veolia Water Solutions & Technologies April 24, 2013 Operational Priorities
Highly Colored Water Removal Using Nanofiltration Membranes at the Colored Water Treatment Facility Adam Zacheis, Project Manager Carollo Engineers Topics 1. Background - Mesa Water District (Mesa) Water
Reverse Osmosis Mobile Units Aquamove Aquamove : Pure water anytime anywhere An ideal water solution for customers facing short or mid-term temporary purified water needs. Based on Reverse Osmosis (RO)
The most complete solutions in GRP PIPES AND FITTINGS 1 ABRERA WATER TREATMENT PLANT (Barcelona) 2010 / D - 7 PROJECT REPORT DWTP ABRERA DRINKING WATER TREATMENT PLANT Project Managers Plant Owner: Aigües
INNOVA-MED CONFERENCE Water Reclamation and Reuse 8-9 October 2009, Girona, Spain WATER REUSE IN SPAIN: DATA OVERVIEW AND COSTS ESTIMATION OF SUITABLE TREATMENT TRAINS Raquel Iglesias Esteban (Hydrology
Desalination 221 (2008) 202 206 Comparison of multiple port and end port connections for pressure vessels Nadav Shachaf*, Tobias Haarburger BEL Group Ltd. email: email@example.com Received 24 January 2007;
Water Equipment Technologies Advanced Membrane Technologies for Solving Worldwide Water Problems ITT Flowtronex production facility located in Dallas, Texas. Our Company Our Company ITT WATER EQUIPMENT
FORWARD OSMOSIS DESALINATION: A COMMERCIAL REALITY Authors: Neil A. Thompson, Peter G. Nicoll Presenter: Neil Thompson, Technical Development Manager Modern Water United Kingdom Abstract Modern Water is
KEMIRA MEMBRANE PROGRAM EFFICIENT WATER TREATMENT WITH MEMBRANE PROTECTION TRANSFORMING RAW WATER INTO DRINKING WATER SEAWATER DESALINATION Drinking water is a scarce resource in many parts of the world.
Energy Use at Water and Wastewater Treatment Plants Larry W. Moore, Ph.D., P.E. University of Memphis Civil Engineering Department March 13, 2012 Energy Use at WTPs Energy Energy is the ability or capacity
Tech Fact Lenntech firstname.lastname@example.org Tel. +31-152-610-900 www.lenntech.com Fax. +31-152-616-289 FILMTEC Membranes How FilmTec s New High-Rejection, Low-Energy Seawater Element Can Reduce Your Desalination
Well Water Iron Removal Using Quantum DMI-65 Granular Filter Media ASME Research Committee Power Plant and Environmental Chemistry Overland Park, Kansas April 2-4, 2007 Prepared by: W. H. Stroman Primary
Reverse Osmosis Water Treatment Plant Providing a safe and reliable supply of drinking water has always been a goal of the City of Beverly Hills. Today s growing municipal water needs require the treatment
Proceedings of the 14 th International Conference on Environmental Science and Technology Rhodes, Greece, 3-5 September 2015 CARBON DIOXIDE INJECTION TRIALS AT NELSON WATER TREATMENT PLANT, NEW ZEALAND
SUBMERSIBLE ELECTRIC PUMPS SUBMERSIBLE PUMPS Gruppo Aturia started developing the Submersible Pump for pumping water in agriculture and for distribution of water in the municipalities. For these applications
Technical Service Bulletin October 2013 TSB340.02 Procedure for Chemically Cleaning HYDRAcap MAX Module(s) This Technical Service Bulletin provides information for chemically cleaning HYDRAcap MAX module(s).
FUJAIRAH 1 INDEPENDENT WATER & POWER PLANT (F1 IWPP), UNITED ARAB EMIRATES Fujairah 1 Seawater Reverse Osmosis Expansion Innovative Energy and Water Resources Management Presentation by William Chang Executive
7. TECHNICAL ASPECTS OF DESALINATION PLANT 7.1 DESALINATION TECHNOLOGIES Desalination technologies can be classified according to the process involved, for example: Those involving phase change in water,
Mobile units for your water supply Reliable water supply Rapidly deployable Hatenboer-Water Fresh in water since 1906. Water treatment & services With specialist expertise, in-house engineering, design
Mark Wilf Ph. D. and Kenneth Klinko EFFECT OF NEW PRETREATMENT METHODS AND IMPROVED MEMBRANE PERFORMANCE ON DESIGN OF RO SEAWATER SYSTEMS. ABSTRACT RO seawater systems that operate on a surface feed water
Water Recycling in action in South Australia: a review of agricultural and municipal reuse schemes and innovation. S. Rinck-Pfeiffer * Veolia Water/United Water, Parkside, GPO Box 1875, Adelaide, South
Desalination Technologies (II) Eftihia Tzen Wind Energy Sector Email: email@example.com Membrane Processes Major desalination processes Source: Dow/FilmTec Membrane Processes In nature, membranes play an important
Pall Aria Integrated MF/RO Systems for Cost-Effective Treatment of Sea and Brackish Waters Pall Aria Integrated MF/RO Systems for Cost-Effective Treatment of Sea and Brackish Waters Water scarcity resulting
CO2 applications for drinking water production, process water treatment and waste water treatment Dr. Dr. Hermans Hermans 03.2013 11.2009 Carbon dioxide in water is -a natural food additive, non poisonous
EASTERN IRRIGATION SCHEME, VICTORIA: OPERATION OF AN ULTRA-FILTRATION PLANT FOR A CLASS A RECYCLED WATER SCHEME Paper Presented by : David Aitken Authors: David Aitken, Plant Operator, Liz Roder, Operations
TAMIL NADU GENERATION AND DISTRIBUTION CORPORATION LIMITED 10 MLD 10 MLD Desalination Desalination plant plant at at TTPS Tuticorin Thermal Power Station Prefeasibility Report September 2014 TTPS Desalination
35 th Discussion Forum «Assessment of Water Use within LCA» ETH Zürich, 05/06/08 LCA-based tool on potable water supply and further inputs for the LCA of water use François Vince Veolia Environnement R&D
Economic Siting Factors for Seawater Desalination Projects along the Texas Gulf-Coast Mark Graves and Ken Choffel 1 Abstract Technological advances in desalination, shifting market conditions, and increasingly
Sometimes hot water will have a sour smell, similar to that of an old damp rag. This smell often develops when the thermostat has been lowered to save energy or reduce the potential for scalding. Odor-causing
CHEMICAL CLEANING EXPERIMENTS FOR PERFORMANCE RESTORATION OF NF MEMBRANES OPERATED ON SEAWATER FEED 1 A. Mohammed Farooque, Ahamed S. Al-Amoudi and Ata M. Hassan Saline Water Conversion Corporation P.O.Box
_ENNTEC WATER TREATMENT SOlUTioNS Industrial Water Supply Water is widely used in industry, whether it is encountered as raw water, process water or waste water. Very often make-up water must be treated
Industrial automatic self-cleaning filters made in plastic material FilBlue Introduction The FILBLUE automatic industrial selfcleaning filters are designed to remove all suspended solids from surface water
AQUIFER STORAGE RECOVERY This continuing education unit has been created to acquaint the reader with the topic of Aquifer Storage Recovery. The International School of Well Drilling gratefully acknowledges
TEMPLATE ASSISTED CRYSTALLIZATION Presented By Ryan Lessing 11/13/2014 Different Forms of Hardness in Water Calcium and Magnesium Bicarbonate- This is what is referred to as temporary hardness. Once it
Proposed Construction of Basement Flood Risk Assessment 35 Edwardes Square London W8 6HH 1 Introduction This FRA has been carried out in accordance with the National Planning Policy Statement (NPPF), the
Cleaning guideline This paragraph provides general information about common contaminants which affect the reverse osmosis composite polyamide membrane elements operational characteristics and methods of
Technical Paper Nitrate and Nitrite Removal from Municipal Drinking Water Supplies with Electrodialysis Reversal Authors: Ted Prato and Richard G. Parent, Ionics Reprinted from Proceedings of 1993 AWWA
Bulk or On-Site Generation: What s Your Hypochlorite Solution Kyle Novak, P.E. Hazen and Sawyer Alana Loughlin, P.E. Hazen and Sawyer Melanie Mann, P.E. Hazen and Sawyer 2011 OWEA Conference June 22, 2011
MANY ASPECTS OF DEALING WITH HIGH NITRATE CONCENTRATION WATER By: Rebhy El-Sheikh M.Sc. Mechanical Engineering Palestinian Water Authority Nahed Ghbn Ph.D. Environmental and Sanitary Engineering Palestinian
Managing Water from CCS Programs Christopher Harto Argonne National Laboratory John A. Veil - Argonne National Laboratory Andrea McNemar - DOE/NETL GWPC Energy and Water Sustainability Symposium Pittsburgh,
Reverse Osmosis Desalination as an Alternative Water Resource Project for Drinking Water Production a Case Study 1 Avin J. Kajekar, 2 B. M. Dodamani Department of Applied Mechanics and Hydraulics National
Drinking Water / Wastewater Treatment / Watershed Protection Advanced Technologies in Water Filtration for Municipal Systems Bringing a half century of global experience to work for local sustainability
Wastewater Reuse Most metal finishing industries have in-house wastewater treatment to economically dispose of the acids, alkali, oils, and dissolved metals in the rinse water and occasional tank solution
This country profile was compiled by the OECD Secretariat and reflects information available as of March 2015. Further information and analysis can be found in the publication: OECD (2015) Water Resources
Reverse Osmosis User s Manual Model LT-200, LT-300 LT-300 Pictured This Page Left Blank 2 Table of Contents INTRODUCTION... 4 SAFETY... 4 FEED WATER AND OPERATION SPECIFICATIONS... 5 REJECTION, RECOVERY
Auxiliary Equipment 1. Compressor Coolers Approximately 80% of the electrical energy used by the compressor is converted to heat during the air compression process. Removal of the heat thus released from