1 User manual EIBWeiche Serial/USB The fast local buscoupler for the EIB Order codes: EIBWeiche Visualization serial: E001-B EIBWeiche Visualization USB: E001-B EIBWeiche Visualisierung USB REG: E001-B902104
2 07/2007 V1.0.7 User manual EIBWeiche 2/15 IMPORTANT-READ CAREFULLY: This b+b End-User License Agreement ("EULA") is a legal agreement between you (either an individual or a single entity) and b+b Automations- und Steuerungstechnik GmbH, for the software product identified above, which includes computer software and may include associated media, printed materials, and "online" or electronic documentation ("SOFTWARE PRODUCT"). By installing, copying, or otherwise using the SOFTWARE PRODUCT, you agree to be bound by the terms of this EULA. SOFTWARE PRODUCT LICENSE 1. COPYRIGHT TREATIES The SOFTWARE PRODUCT is protected by copyright laws and international copyright treaties, as well as other intellectual property laws and treaties. The SOFTWARE PRODUCT is licensed, not sold. 2. GRANT OF LICENSE. This EULA grants you the following rights: a. Software Product. b+b grants to you as an individual, a personal, nonexclusive license to make and use copies of the SOFTWARE for the sole purposes of using the SOFTWARE s functionality. b. Storage/Network Use. You may also store or install a copy of the SOFTWARE PRODUCT on a storage device, such as a network server, used only to install or run the SOFTWARE PRODUCT on your other computers over an internal network; however, you must acquire and dedicate a license for each separate computer on which the SOFTWARE PRODUCT is installed or run from the storage device. A license for the SOFTWARE PRODUCT may not be shared or used concurrently on different computers. c. Electronic Documents. Solely with respect to electronic documents included with the SOFTWARE PRODUCT, you may make an unlimited number of copies (either in hardcopy or electronic form), provided that such copies shall be used only for internal purposes and are not republished or distributed to any third party. 3. DESCRIPTION OF OTHER RIGHTS AND LIMITATIONS. a. Limitations on Reverse Engineering, Decompilation, and Disassembly. You may not reverse engineer, decompile, or disassemble the SOFTWARE PRODUCT. b. Separation of Components. The SOFTWARE PRODUCT is licensed as a single product. Its component parts may not be separated for use on more than one computer. c. Changing documentations. You may not make changes to the documentation of the SOFTWARE PRODUCT. d. Termination. Without prejudice to any other rights, b+b may terminate this EULA if you fail to comply with the terms and conditions of this EULA. In such event, you must destroy all copies of the SOFTWARE PRODUCT and all of its component parts.
3 07/2007 V1.0.7 User manual EIBWeiche 3/15 4. COPYRIGHT. All title and copyrights in and to the SOFTWARE PRODUCT (including but not limited to any images, photographs, animations, video, audio, music, text, and "applets" incorporated into the SOFTWARE PRODUCT), the accompanying printed materials, and any copies of the SOFTWARE PRODUCT are owned by b+b or its suppliers. The SOFTWARE PRODUCT is protected by copyright laws and international treaty provisions. Therefore, you must treat the SOFTWARE PRODUCT like any other copyrighted material except that you may install the SOFTWARE PRODUCT on a single computer provided you keep the original solely for backup or archival purposes. You may not copy the printed materials accompanying the SOFTWARE PRODUCT. 5. LIMITED WARRANTY Except with respect to the REDISTRIBUTABLES, which are provided "as is," without warranty of any kind, b+b warrants that (a) the SOFTWARE PRODUCT will perform substantially in accordance with the accompanying written materials for a period of ninety (90) days from the date of receipt, and (b) any hardware accompanying the SOFTWARE PRODUCT will be free from defects in materials and workmanship under normal use and service for a period of one (1) year from the date of receipt. 6. CUSTOMER REMEDIES. b+b s entire liability and your exclusive remedy shall be, either (a) return of the price paid, or (b) repair or replacement of the SOFTWARE PRODUCT or hardware that does not meet b+b Limited Warranty. This Limited Warranty is void if failure of the SOFTWARE PRODUCT or hardware has resulted from accident, abuse, or misapplication. NO OTHER WARRANTIES: TO THE MAXIMUM EXTENT PERMITTED BY APPLICABLE LAW, b+b DISCLAIMS ALL OTHER WARRANTIES NO LIABILITY FOR CONSEQUENTIAL DAMAGES: TO THE MAXIMUM EXTENT PERMITTED BY APPLICABLE LAW, IN NO EVENT SHALL b+b OR ITS SUPPLIERS BE LIABLE FOR ANY SPECIAL, INCIDENTAL, INDIRECT, OR CONSEQUENTIAL DAMAGES WHATSOEVER (INCLUDING, WITHOUT LIMITATION, DAMAGES FOR LOSS OF BUSINESS PROFITS, BUSINESS INTERRUPTION, LOSS OF BUSINESS INFORMATION, OR ANY OTHER PECUNIARY LOSS) ARISING OUT OF THE USE OF OR INABILITY TO USE THE SOFTWARE OR HARDWARE PRODUCT, EVEN IF b+b HAS BEEN ADVISED OF THE POSSIBILITY OF SUCH DAMAGES. Life support: These products are not designed for use in life support appliances, devices or systems where malfunction of these products can reasonably be expected to result in personal injury. b+b customers using or selling these products for use in such applications do so at their own risk and agree to fully indemnify b+b for any damages resulting from such application. Copyright b+b Automations- und Steuerungstechnik GmbH. All rights reserved. Microsoft and Windows are trademarks of Microsoft Corporation. This handbook describes also functions, which are options. Only qualified persons are allowed to install our units.
4 07/2007 V1.0.7 User manual EIBWeiche 4/15 Softwaredesign und Coding: Documentation: Editor: Volker Knapp, Hartmut Zander, Peter Bernert Frank Schlaps, Peter Bernert Frank Schlaps Klingenweg Reichelsheim Tel: / internet:
5 07/2007 V1.0.7 User manual EIBWeiche 5/15 Contents Highlights EIBWeiche... 6 Fields of application for the EIBWeiche... 6 Package contents of the EIBWeiche... 6 Introduction... 7 Connecting the EIBWeiche... 8 Description of the EIB-Weiche LEDs... 9 Installation Windows-USB driver (EIBWeiche USB) Setting the physical address of the EIBWeiche EIBWeiche quickstart Step for step... 15
6 07/2007 V1.0.7 User manual EIBWeiche 6/15 Highlights EIBWeiche Direct coupling to EIB (two-wire) Coupling to the PC over serial interface or USB (Windows 2000 and Windows XP) Small dimensions for the mobile application Programming of the EIB over ETS and Standard-Protocol or direct over USB Direct coupling to FIAVis (FIAVis Commander, OPCServer, FIAVis.VB) Direct coupling with the virtual Control-Panel EIB Control Platform (optional) Separate OPC-Server available (optional) Contained in the EIBDoktor-package as powerful EIB-Analysing-Tool Open protocol (OpenEIB) between PC and EIBWeiche for creating own applications with EIBcoupling Fields of application for the EIBWeiche Programming the EIB-world via ETS Buscoupler for FIAVis data pool Server for the EIB-Control-Panel (simple local visualization) Buscoupler for external visualizations (serial or USB with direct driver-implementation / OPC ) Error analysis with the EIBDoktor-package Package contents of the EIBWeiche EIBWeiche-buscoupler Depending on the selected type of connection/version: - serial cable incl. PS2-connection-adapter - serial cable incl. wall power supply - USB connection cable Software (FIAVis and optional: EIBDoktor, OPC-Server, ASCII) Documentation
7 07/2007 V1.0.7 User manual EIBWeiche 7/15 Introduction The FIAVis Manager is the central to for creating EIBWeiche-FIAVis projects: with the FIAVis Manager the projection information is generated for the FIAVis data pool (and so FIAVis Visualizations, OPC- Server, etc). The FIAVis Manager manages projects for: - CCEIBGW : the universal network-eib Gateway - CCEIBSPS : the intelligent processing unit in the EIB incl. network-gateway functionality - EIBWeiche : the fast serial/usb buscoupler with simple protocol - EIBNet/IP-Router : connection over network to the EIB - OPC : connections using external OPC Servers. The configuration of a FIAVis data pool as well as the parameterization of the process items and logic programs via FIAVis Manager is described in detail in the FIAVis user manual. EIBWeiche-device connections and additional software-tools/drivers (i.e. USB driver) are described in this manual.
8 07/2007 V1.0.7 User manual EIBWeiche 8/15 Connecting the EIBWeiche EIB-Weiche (serial) 25 SUB-D connector 9 SUB-D - serial PC port PS/2-connector (power supply) EIB connection PS/2 Y-cable PC Mouse or EIB-Weiche Keyboard or EIB-Weiche
9 07/2007 V1.0.7 User manual EIBWeiche 9/15 EIBWeiche (USB) USB port PC USB-connection EIB- connection Description of the EIB-Weiche LEDs EIBWeiche USB LEDs +5V Versorgung (english: +5V power) This LED is active as soon as the EIBWeiche is correctly connected to the PC. Busspannung (english: bus voltage) If the EIBWeiche is connected to the EIB, this LED has to be active constantly. If the LED is flashing, the EIB is not correctly connected to the EIBWeiche (f.e. not connected at all, or lines are swapped, or no voltage is on the EIB) Bustelegramm (english: bus telegram) This LED is flashing when an EIB telegram gets detected. Nack As soon as a bus telegram is received with a NACK(=NOT ACKKNOWLEDGE) state, this LED gets activated. To reset the LED display, push the button "Fehler Rücksetzen" (= reset error ).
10 07/2007 V1.0.7 User manual EIBWeiche 10/15 The EIBWeiche will of course work properly, even if this LED is active. The LED is just a simple error diagnosis for the connected EIB. Busy As soon as a bus telegram is received with a BUSY state, this LED gets activated. You can turn off the LED again by pressing the button "Fehler Rücksetzen" (= reset error ). If you have an high bus load (>50%), the busy LED will be flashing. The EIBWeiche will of course work properly, even if this LED is active. The LED is just a simple error diagnosis for the connected EIB. Kollision (english: collision) As soons as a telegram collision or bus disturbances are detected, this LED gets activated. Please note that also the (dis-)connection of other bus devices can cause short bus disturbances! To reset the LED display, push the button "Fehler Rücksetzen" (= reset error ). The EIBWeiche will of course work properly, even if this LED is active. The LED is just a simple error diagnosis for the connected EIB. USB This LED can have three different states: - LED off: the EIBWeiche is not connected to a PC, ort he USB drivers for the EIB- Weiche are not installed on the PC yet. - LED on: the EIBWeiche is connected to the PC, and the USB drivers are correctly installed. Currently no PC software is communicating with the EIBWeiche - LED flashing: the EIBWeiche is in usage by a PC software right now. Sicherheit (english: security) If you have activated this mode by pressing the button "Betriebs-Art wählen" (= select mode ), nobody will be able to program EIB devices with the ETS. Therefore this mode acts like a version of an EIBWächter device. Auto-Ack If you have activated this mode by pressing the button "Betriebs-Art wählen" (= select mode ), the EIBWeiche will acknowledge every not acknowledged bus telegram, reducing bus load. Therefore this mode acts like a EIB-Ack device. EIBWeiche RS232
11 07/2007 V1.0.7 User manual EIBWeiche 11/15 +5V Versorgung (english: +5V power) This LED is active as soon as the EIBWeiche is correctly connected to the PC and the power supply/ps2 port. Busspannung (english: bus voltage) If the EIBWeiche is connected to the EIB, this LED has to be active constantly. If the LED is flashing, the EIB is not correctly connected to the EIBWeiche (f.e. not connected at all, or lines are swapped, or no voltage is on the EIB) Bustelegramm (english: bus telegram) This LED is flashing when an EIB telegram gets detected. Nack As soon as a bus telegram is received with a NACK(=NOT ACKKNOWLEDGE) state, this LED gets activated. To reset the LED display, push the button "Fehler Rücksetzen" (= reset error ). The EIBWeiche will of course work properly, even if this LED is active. The LED is just a simple error diagnosis for the connected EIB. Busy As soon as a bus telegram is received with a BUSY state, this LED gets activated. You can turn off the LED again by pressing the button "Fehler Rücksetzen" (= reset error ). If you have an high bus load (>50%), the busy LED will be flashing. The EIBWeiche will of course work properly, even if this LED is active. The LED is just a simple error diagnosis for the connected EIB. Kollision (english: collision) As soons as a telegram collision or bus disturbances are detected, this LED gets activated. Please note that also the (dis-)connection of other bus devices can cause short bus disturbances! To reset the LED display, push the button "Fehler Rücksetzen" (= reset error ). The EIBWeiche will of course work properly, even if this LED is active. The LED is just a simple error diagnosis for the connected EIB. Standard (PC-protocol) - LED on: the EIBWeiche is communicating with the PC using the standard PEI16 protocol and a 9600 baud rate. - LED flashing: the EIBWeiche is communicating with the PC using the standard
12 07/2007 V1.0.7 User manual EIBWeiche 12/15 PEI16 protocol and a baud rate. Please note: to use the EIBWeiche with the ETS software, you have to set the standard protocol. You can select this protocol by pressing the button "Betriebs-Art wählen" (= select mode ). OpenEIB - LED on: the EIBWeiche is communicating with the PC using the OpenEIB protocol. Please note: to use the EIBWeiche with the EIBDoctor, you have to set the OpenEIB protocol. You can select this protocol by pressing the button "Betriebs-Art wählen" (= select mode ). FT1.2 This mode is not supported.
13 07/2007 V1.0.7 User manual EIBWeiche 13/15 Installation Windows-USB driver (EIBWeiche USB) On the delivered b+b-eibtools-cd you find the USB-driver for Windows 2000 and Windows XP. Older Windows operating systems are not supported! If the EIBWeiche is connected the first time to an USB-port of the PC, the Windows-Hardware-Installationassistent is opened. This assistant might ask for the installations folder of the USB driver. Here you have to specify the CD, folder USB. After successful installation of the driver, in the Windows device manager you can see the entry EIB- Weiche USB Geräte -> EIBWeiche USB if the EIBWeiche USB is connected. If you want to use the EIBWeiche USB with the ETS3 or ETS2 (from Version 1.2) as programming device, so you have to install some more drivers. For the application as visualization-coupling (i.e. for FIAVis) these ETS-drivers are not required. The ETS-USB-drivers can be installed over the b+b-eibtools-cd installationsprogram. Here a short description how to install the ETS-drivers manually: 1. Install the Windows-USB-driver as described above (connect EIBWeiche USB to the PC) 2. Copy the folder Setup\bin\USB and all subfolders from the CD to the local computer 3. In the local..\usb\ets3 -folder start the file EIBWeicheUSB.exe one time (double click in the explorer) Now the usage per ETS3 is already possible, in the Windows device manager you will now also see the entry KNX Netzwerk Geräte -> EIB-USB Datenschnittstelle. For using an ETS2 over USB the following steps have to be performed, too: 4. Copy the files ETS2DriverSwitch.exe, PEI_USB32.dll and PEI_USB.dll from the..\usb\ets2 folder direct into the folder of the installed ETS2. 5. Start the file ETS2DriverSwitch.exe in the ETS2-folder (double-click) and select as interface USB. Now the ETS2-USB-driver is active, no matter if you have selected COM1 or COM2 in the ETS2, the communication will be handled over the USB interface. If you want to use a serial interface again, you can change the settings again with the ETS2DriverSwitch.exe. Setting the physical address of the EIBWeiche The EIBWeiche has, like all EIB-devices, an own programming button (in the compact case labeled with Phys. Adresse setzen ). With this button and an ETS-software you can change the physical address as usual. On the b+b-eibtools-software-cd (is delivered with every EIBWeiche) you can also find a simple test application for EIBWeiche-devices, with which you can also change the physical address very easy. For this go with the Windows-Explorer to the CD-folder SDKs and more\openeib\openeib SDK\BIN. In this folder there is the file OpenEibDemo.exe, which you can start directly from the CD (without installation) with a double-click. The following window appears:
14 07/2007 V1.0.7 User manual EIBWeiche 14/15 Now just select the interface (USB, COM1/2), and click on the button Verbinden. So the area beneath is filled with the device infos (firmwareversion, serial number) and the actual phys. address: In the example the EIBWeiche has the physical address If you want to change this address, you have to enter the new address and click on the button Setzen. With the help of the OpenEIBDemo-program you can also test, if reading and writing of group addresses over the EIBWeiche works: In Wertevorwahl enter the group address of a switch (EIS-type 0x10 = binary) and per >> -button activate the address. Now you can request/read per Lesen or Schreiben the value on the bus.
15 07/2007 V1.0.7 User manual EIBWeiche 15/15 EIBWeiche quickstart Step for step To make the access to the FIAVis-EIBWeiche world as easy as possible, here is a guidance that shows the most important steps of using an EIBWeiche and creating a project. 1. You need a PC with NT/2000/XP. Connect the EIBWeiche to the PC. If you have an USB- EIBWeiche, the Win2000/XP driver is automatically installed from the b+b-eibtools-cd, if you connect the EIBWeiche the first time. 2. Test the communication between PC and EIBWeiche, while starting the tool OpenEIBDemo direct from CD (it is located in the folder SDKs and more\openeib\openeib SDK\BIN ). With this tool you can establish a connection to the EIBWeiche and also directly configure the physical EIBaddress. 3. Creating a project: Start the FIAVis Manager. At the first start an additional window appears, that remembers you to enter the license-number and to activate the FIAVis Base data pool. Follow these instructions! In the Manager-main window, where all available projects are listed, an EIB- Weiche test project is already accessible. To create a new project, click with the right mouse button in the project tree and select in the following menu New project 4. A new project is created, you can choose the project name like you want (you can also change the name at any time, while you do a slow left click). The connection parameters of the EIBWeiche (USB/COMx) must be configured in the project settings (in the right Manager-window double click the settings, in the following window the settings then can be changed). 5. Now i.e. the EIB addresses to use must be defined. To do so you have to open the EIB addresses configuration -window of the project. For the definition of the EIB-process items you should use an existing ETS-project. All important address-data will be fetched by importing the ETS-project. From all available group addresses/objects from the list above select the data to use in your FIAVis project (list beneath). At some data items you have to reparametrize the EIS-types, the ETS contains no information about the type. Hint: you can also define group addresses manually without an ETS-project (button Define Addr. ). 6. The process item definition must now be transferred to the FIAVis data pool. For this select the project in the left tree and in the menu click on Transfer data or click on the Transfer button. In the following window you only have to press the start-button, the transfer begins. The projection data is saved in the Data -folder of the des FIAVis Base service and the connection to the EIBWeiche is opened. 7. You have created your first FIAVis project! You can now view and write the actual values of the process items, while pressing on the button "Values" in the Transfer -window. Please consider: many process items will first have no value ( bad ), as long as the according address has been sent over the EIB one time. With the flag Startup read for EIB-addresses you can tell FIAVis to request the values automatically at the beginning (but also this action will take some time depending on the number of addresses). 8. Of course now also the FIAVis OPCServer is ready for use, or can create own visualizations with the FIAVis Designer, which base on the process items, or you can access process items over FIA- Vis.VB. The necessary steps are explained in the according user manual.
Product description CCEIB-SPS The graphically programmable EIB-SPS with network interface standard DIN rail mounting device incl. engineering software und visualization (unlimited copy licence), OPC-Server,
KEPServerEX Client Connectivity Guide For Rockwell Software s RSView Studio KTSM-00002 v. 1.04 Kepware Technologies i KEPWARE END USER LICENSE AGREEMENT AND LIMITED WARRANTY The software accompanying this
Mayfair EULA for Journal Office 9-April-2014 Page 1 of 9 Mayfair EULA for Journal Office Mayfair Software End User License Agreement Software programs which you received either installed on on the device
Crestron VMK-WIN TouchPoint Virtual Mouse & Keyboard Software for Windows Installation Guide This document was prepared and written by the Technical Documentation department at: Crestron Electronics, Inc.
Acunetix Web Vulnerability Scanner Licensed Copies: 1 END USER LICENSE AGREEMENT IMPORTANT READ CAREFULLY: This End User License Agreement ("EULA") is a legal agreement between you (either an individual
END-USER LICENSE AGREEMENT FOR FORMDOCS SOFTWARE IMPORTANT-READ CAREFULLY: This End-User License Agreement ("EULA") is a legal agreement between you (either an individual or a single entity) and Formdocs
Nexinto Business Cloud Terms Microsoft Volume Licensing End user Inhalt 1. Definitions... 2 2. Ownership of products... 2 3. Use of Client Software... 3 4. Use of Redistribution Software... 3 5. Copies...
TOOLS for CC121 Installation Guide ATTENTION SOFTWARE LICENSE AGREEMENT PLEASE READ THIS SOFTWARE LICENSE AGREEMENT ( AGREEMENT ) CAREFULLY BEFORE USING THIS SOFTWARE. YOU ARE ONLY PERMITTED TO USE THIS
KEPServerEX Client Connectivity Guide For Clear Controls ClearView KTSM-00023 v. 1.04 KEPWARE END USER LICENSE AGREEMENT AND LIMITED WARRANTY The software accompanying this license agreement (the Software)
Testo USB driver Windows XP, Vista and Windows 7 Information for use en 2 General information General information Please take the time to read the Installation Instructions through carefully and make sure
USER GUIDE Programming Adapter Cable for Fujitsu Flash Microcontroller- F²MC-16LX/FR Family Fujitsu Microelectronics America, Inc. 1 Revision History Revision # Date Comment 1.0 03.25.2001 New Document
SOLARWINDS, INC ipmonitor 8.0 MANAGER END USER LICENSE AGREEMENT REDISTRIBUTION NOT PERMITTED IMPORTANT -- READ CAREFULLY BEFORE USING THIS SOFTWARE: THIS IS A LEGAL AGREEMENT BETWEEN YOU (EITHER AN INDIVIDUAL
KEPServerEX Client Connectivity Guide For Intellution s ifix KTSM-00017 v. 1.03 Kepware Technologies KEPWARE END USER LICENSE AGREEMENT AND LIMITED WARRANTY The software accompanying this license agreement
MDM Zinc 3.0 End User License Agreement (EULA) THIS AGREEMENT (or "EULA") IS A LEGAL AGREEMENT BETWEEN THE PERSON, COMPANY, OR ORGANIZATION THAT HAS LICENSED THIS SOFTWARE ("YOU" OR "CUSTOMER") AND MULTIDMEDIA
CompanionLink User's Guide COPYRIGHT 2001 BY COMPANIONLINK SOFTWARE, INC. ALL RIGHTS RESERVED. CompanionLink is a Trademark of CompanionLink Software, Inc. Other brands are trademarks of their respective
Contents Software License Agreement... 2 Conventions used in this manual... 3 Operating environment... 3 Installing the software (Windows)... 3 Installing the software (Mac)... 4 Connecting the DR-22WL/DR-44WL
TelDial Quick Start TelDial/VoIP/Skype For TelDial revision 2.00 or higher Document revision last update 8/9/2007 Warrantee Compliance and Liability Information Except as permitted under the United States
RDC-7 Windows XP Installation Guide CONTENTS 1. End User License Agreement...3 2. Important notes...4 3. Customer support...4 4. Installing the USB driver...4 I. Prior to installation...4 II. Installation
Acknowledgements Trademark Information COREflex Software Microsoft, Windows, Windows NT/ 2000/ XP, and Access are registered trademarks of Microsoft Corporation. Quickbooks is a registered trademark of
END- USER LICENSE AGREEMENT FOR Helpdesk Pilot Last Updated: 01st May 2014 IMPORTANT: PLEASE READ THE TERMS AND CONDITIONS OF THIS LICENSE AGREEMENT CAREFULLY BEFORE CONTINUING WITH THIS PROGRAM INSTALL.
FN:PCMCSET-M1.DOC PCMCSET SOFTWARE for ATS Master Clocks System Clocks and Displays ATS FREE SOFTWARE AGREEMENT Applied Technical Systems (ATS) grants you the right to use this software according to the
Price list: Rev. 04/2008 Contents: EIB Products (diagnostic bundles local and IP)... 2 EIBDoktor professional IP serial complete bundle... 2 EIBDoktor professional IP USB complete bundle... 3 Upgrade EIBDoktor
OBD2 PCM Programmer Quick Start Guide Table of Contents Introduction... 1 Minimum PC Requirements... 1 Program Installation... 1 Program Registration... 2 Program Setup... 3 Reading the PCM... 3 Programming
isnmp Installation Guide installing / licensing / unlocking New!! License Registration & Unlock (online) get yours at...www.kepware.com/mykepware Kepware is the world leader in communication software for
SOFTWARE INSTALLATION AND USB CONNECTION GUIDE ENGLISH LYT1086-001A COPYRIGHT 2003 VICTOR COMPANY OF JAPAN, LTD. M3D3/D1 DSC Printed in Japan 1202-HO-ID-VP JVC SOFTWARE LICENSE AGREEMENT IMPORTANT TO CUSTOMERS:
USER MANUAL MOBILE HARD DRIVES DESKTOP HARD DRIVES Rev. 034/Mac Dear user! Thank you for selecting the Freecom Mobile Hard Drive / Desktop Hard Drive as your external data storage device. For optimal use
ALM Works End-User License Agreement for Structure Plugin IMPORTANT - READ CAREFULLY: This End-User License Agreement (EULA) is a legal agreement between you (either an individual or a single legal entity)
RedFin SideBar for QuickBooks - Version 1.0 USER GUIDE Release 1.65 Document 1.1 Copyright 2010 RedFin Network, Inc. All Rights Reserved Introduction Visit us at: http://www.redfinnet.com. Copyright 2010
CITRIX SYSTEMS, INC. SOFTWARE LICENSE AGREEMENT PLEASE READ THIS SOFTWARE LICENSE AGREEMENT CAREFULLY BEFORE DOWNLOADING, INSTALLING OR USING CITRIX OR CITRIX-SUPPLIED SOFTWARE. BY DOWNLOADING OR INSTALLING
Welcome to Maritime Information Systems Merchant Vessel Database (MVDB) MVDB for Windows 95* and Windows 98 offers a complete U.S. Vessel Documentation database capable of searching, saving, exporting,
EULA - Page 1 of 5 END-USER LICENSE AGREEMENT FOR ESI-TECNALIA SOFTWARE IMPORTANT READ CAREFULLY: This End-User License Agreement ("EULA") is a legal agreement between you (either an individual or a single
APPLICATION Note TELECOM SOLUTIONS FOR THE 21ST CENTURY Using the PB-100 for All-Call Dialing March 22, 2002 Features Compatible with Windows 95, 98, ME, NT 4.0, 2000 Male sub-d 9 pin cable provided 20
Bachmann PrintBoy SDK HTML Edition API Reference for CodeWarrior C/C++ Developers version 7.0 Essential Printing and File Management Software for Palm OS and Pocket PC Handhelds Bachmann PrintBoy SDK copyright
END USER LICENSE AGREEMENT 1. SCOPE OF THIS AGREEMENT. This END USER LICENSE AGREEMENT ("EULA") is a legal agreement between you (either an individual or a single entity) and TradeStation ("TS") governing
Scanner Wedge for Windows Mobile v2.0 Software User Guide Contents INSTALLING SCANNER WEDGE SOFTWARE 2 ACTIVATING THE SCANNER CONNECTION 3 TRACING SCANNER OUTPUT 6 FORMATTING OUTPUT 8 SELECTING START UP
DME-N Network Driver Installation Guide for LS9 ATTENTION SOFTWARE LICENSE AGREEMENT PLEASE READ THIS SOFTWARE LICENSE AGREEMENT ( AGREEMENT ) CAREFULLY BEFORE USING THIS SOFTWARE. YOU ARE ONLY PERMITTED
COM Port Stress Test COM Port Stress Test All rights reserved. No parts of this work may be reproduced in any form or by any means - graphic, electronic, or mechanical, including photocopying, recording,
Microsoft Hosting IT Services Terms and Conditions 1. How these Terms and Conditions work 1.1 These Terms and Conditions incorporate the Master Services Terms and Conditions (the "MSTC") which are available
Installation Guide Version 126.96.36.199 CEA-grower Installation Guide Before using this product, read the End User License Agreement. You must agree to this License Agreement before using this product. AgrowSoft
PRODUCT SCHEDULE Hosted Exchange This Product Schedule (the Schedule ), between BIMASS and ( You ) is effective immediately and is issued pursuant to and incorporates by reference the terms and conditions
Ash Capture Control User Guide Revision 1.4 Table of Contents Software Installation... 3 Hardware Installation... 6 System Block Diagram... 7 Using Ash Capture Control... 8 Launching the Application...
VIVAX TECHNOLOGY Reliable Data Storage for Small Businesses Vivax Storage Server Administration Guide VSS Administration Guide REVISION ONE Vivax Technology LLC 2466 S. Bascom Ave, Suite 11 Campbell, CA
Employee Time Clock User Manual PURPOSE: This software package was created to maintain accurate account of the employees working hours. Employees new and old - can easily be added/deleted and viewed at
CompleteView Pop Up Monitor User s Manual Version 3.8 Table of Contents Introduction... 3 End User License Agreement... 4 System Requirements... 5 Installation... 6 Operating the Pop Up Monitor... 11 Normal
END-USER LICENSE AGREEMENT FOR F-PROT ANTIVIRUS This is a binding, legal agreement between the end user (the "licensee") and Frisk Software International ("FSI") for the F-Prot Antivirus software product,
CONTENTS 1 ABOUT THIS PART... 2 2 TERMS AND CONDITIONS REGARDING USE OF MICROSOFT SOFTWARE... 2 Definitions... 2 Ownership of Software Products... 2 Use of Client Software... 3 Use of Redistribution Software...
Part IV Database Client/Server Database Server 1. Run srvadmin.exe (you can add to the Windows Startup folder). Figure IV.1 DBISAM Database Server Icon Figure IV.2 DBISAM Database Server Status E-Mon Energy
FLoader User's Manual Version 1.0.07 Build February 12, 2002 Copyright Topcon Positioning Systems, Inc. 2002 All rights reserved Last Revised February 14, 2002 INTRODUCTION / TERMS AND CONDITIONS Thank
CompleteView Admin Console User s Manual Version 3.8 Table Of Contents Introduction... 1 End User License Agreement... 1 Overview... 2 Configuration... 3 Starting the Admin Console... 3 Adding a Server...
Power Log PC Application Software Users Manual May 2007 Rev. 1, 5/08 2007-2008 Fluke Corporation. All rights reserved. Specifications are subject to change without notice. All product names are trademarks
CRM Setup Factory: Extractor Version 4.0 User s Guide 2009 CRM Systems Inc. All Rights Reserved. Publisher: CRM Systems Inc, Winnipeg MB Canada No part of this documentation may be copied, photocopied,
Manual MOTOMAN robotec GmbH End User License Agreement. NOTICE TO USER: THIS IS A CONTRACT BETWEEN YOU AND MOTOMAN robotec GmbH, Allershausen, Germany. BY IN- DICATING YOUR ACCEPTANCE BELOW, YOU ACCEPT
Keep it Simple Timing Support... 1 Introduction... 2 Turn On and Go... 3 Start Clock for Orienteering... 3 Pre Start Clock for Orienteering... 3 Real Time / Finish Clock... 3 Timer Clock... 4 Configuring
ENTERPRISE EDITION INSTALLER END USER LICENCE AGREEMENT THIS AGREEMENT CONSISTS OF THREE PARTS: A. VNC SERVER ENTERPRISE EDITION END USER LICENCE AGREEMENT B. VNC VIEWER ENTERPRISE EDITION END USER LICENCE
Banyon Data Systems BDS BACKUP VAULT 2 BDS BACKUP VAULT INSTALLATION / SETUP Thank you for your purchase of the BDS Backup Vault program. This program is designed to protect each of your entities installed
Installation Guide Installing / Licensing / Unlocking Kepware Products License Registration & Unlock online at https://my.kepware.com/mykepware Kepware Technologies is a private software development company
Crow Limited Warranty (Crow) warrants this product to be free from defects in materials and workmanship under normal use and service for a period of one year from the last day of the week and year whose
XANGATI END USER SOFTWARE LICENSE TERMS AND CONDITIONS IMPORTANT: PLEASE READ BEFORE DOWNLOADING, INSTALLING OR USING THE XANGATI, INC. ("LICENSOR") SOFTWARE YOU HAVE LICENSED ("SOFTWARE"). BY EXECUTING
IMPORTANT - READ BEFORE COPYING, INSTALLING OR USING. Do not copy, install, or use the Materials provided under this license agreement ("Agreement"), until you have carefully read the following terms and
Dr.Backup - Service and Software License Agreements STANDARD SERVICE AGREEMENT This is an Agreement between Doctor Backup, LLC (a limited liability company formed in Maryland), which in the rest of this
END USER LICENSE AGREEMENT FOR SLICKEDIT(R) CORE SOFTWARE IMPORTANT THIS IS A LEGAL AGREEMENT BETWEEN YOU ("You" or "Your") AND SLICKEDIT INC. ("SlickEdit"). SLICKEDIT IS WILLING TO (1) LICENSE THE SLICKEDIT
Interface for connecting a PC to the Digital plus by Lenz system. All system functions can be controlled via the PC (with suitable software). Operating system requirements: Windows XP, Windows 7 USB interface,
High Definition Spy Pen zpen-hd User Manual The HD Video Spy Pen Is a simple, multifunctional recording device built into a working ballpoint pen. Take photos, record audio, or capture HD video with the
NOTICE TO USER: BY INSTALLING THIS SOFTWARE YOU ACCEPT ALL OF THE FOLLOWING TERMS AND CONDITIONS AND THOSE CONTAINED IN THE ATTACHED LICENSE AGREEMENT. PLEASE READ IT CAREFULLY. THE ATTACHED SOFTWARE LICENSE
C6 Easy Imaging Total Computer Backup User Guide Clickfree and the Clickfree logo are trademarks or registered trademarks of Storage Appliance Corporation. Other product names used in this guide are recognized
Kokii BatteryDAQ BMS Battery Analyzer Battery DAS Updated: October 2008 Caution: High Voltage Exists on Battery Power and Sampling Connectors! Please refer to device installation and operation manual for
C-DAC Medical Informatics Software Development Kit End User License Agreement BY DOWNLOADING AND INSTALLING, COPYING OR OTHERWISE USING THE CENTRE FOR DEVELOPMENT OF ADVANCED COMPUTING ( C-DAC ) MEDICAL
IPSec VPN Client Installation Guide Version 4 Document version - 1.0-410003-25/10/2007 IMPORTANT NOTICE Elitecore has supplied this Information believing it to be accurate and reliable at the time of printing,
Diablo EZReporter EZ Result Monitor Copyright 2013, Diablo Analytical, Inc. Diablo Analytical EZReporter Software EZ Result Monitor Reference Manual Copyright 2013, Diablo Analytical, Inc. All rights reserved.
DME-N Network Driver Installation Guide for M7CL/LS9/DSP5D ATTENTION SOFTWARE LICENSE AGREEMENT PLEASE READ THIS SOFTWARE LICENSE AGREEMENT ( AGREEMENT ) CAREFULLY BEFORE USING THIS SOFTWARE. YOU ARE ONLY
All references to the manufacturer in these Terms and Conditions should be read as Contractor (immixtechnology, Inc.), acting by and through its supplier, Attachmate. TERMS AND CONDITIONS FOR ATTACHMATE
USB Data Card Programmer user s manual and installation guide 2000 GARMIN Corporation GARMIN International, Inc. 1200 E 151 st Street, Olathe, Kansas 66062 U.S.A. Tel. 913/397.8200 or 800/800.1020 Fax.
Welcome to InFixi MSG to EML Converter Help Guide MSG to EML Converter Software Program Ver: 1.0 Introduction about InFixi MSG to EML Converter Software InFixi MSG to EML Converter Software is one of the
Database Binary Backup PC Utility Reference Manual (Version 3.xx) DRAFT 2 The flexible way to communicate The information contained in this document is proprietary and is subject to all relevant copyright,
NOTICE SOFTWARE END USER LICENSE AGREEMENT THIS SOFTWARE END USER LICENSE AGREEMENT ( THIS AGREEMENT ) IS A LEGAL AND BINDING AGREEMENT BETWEEN YOU (EITHER AN INDIVIDUAL OR ENTITY) AND TP VISION NETHERLANDS