1 Kokii BatteryDAQ BMS Battery Analyzer Battery DAS Updated: October 2008
2 Caution: High Voltage Exists on Battery Power and Sampling Connectors! Please refer to device installation and operation manual for safety cautions. Kokii BatteryDAQ Company Check Your Battery Health Online Technical Support Baltimore, Maryland, USA
3 TRADEMARKS All brand and product names are the trademarks of their respective owners. BatteryDAQ is the registered trademark of Kokii BatteryDAQ Company USA. COPYRIGHT All rights reserved. NO part of this manual shall be stored in a retrieval system, or transmitted by any means without the written permission of BATTERYDAQ. LIABILITY Neither BATTERYDAQ nor any of its employees shall be liable for any direct, indirect, incidental or consequential damages arising from the failure of the battery monitoring system due to the failure of a proprietary part of the battery monitoring system, even if BATTERYDAQ had been advised in advance except for as provided by law. SPECIFICATION BatteryDAQ makes every effort to ensure that the specifications and details in this manual are accurate and complete. BATTERYDAQ reserves the right to alter or improve the specification, design or manufacturing process at any time, without notice. WARRANTY BatteryDAQ warrants this system free from defects in material and workmanship in operation for one year from the date of commissioning or sale by BATTERYDAQ or its authorized dealer. Limitation of Warranty This warranty does not apply to defects arising from system modification performed without BATTERYDAQ s written approval, or misuse of the system or any part of the system. The warranty excludes defects or malfunctions resulting from failure by the customer, or his designated personnel, to maintain and upkeep the batteries to which the system is fitted.
4 Table of Contents 1 Overview of technologies Software Installation Pre-installation Update service Pack Install.NET framework Install SqlExpress Trouble shooting BMS Software Installation Vista Installation Troubleshooting BMS configuration DAS Configuration Analyzer Configuration Map View Real-time data view History data query Menu and tool bar Important Operations Troubleshooting... 35
5 1 Overview of technologies Kokii BatteryDAQ provides advanced technologies and products for a variety of battery applications. We advance our competitors on many aspects: Measurement Data Analysis Communication and networking Operator Interface Informatics Established in 1993, our products have been used worldwide for battery test and monitoring through ZEEMOO brand, Kokii brand, BatteryDAQ brand and many ODM/OEM partners. Battery Analyzer V3.0 is the powerful monitoring software based on Kokii experience and focus. It provides users rich information about their batteries by data, tables and charts. The real-time string voltage, current, temperature and the cell voltage and Internal Resistance will be collected and stored in database. The trend of battery condition can be easily visualized and analyzed. Based on Microsoft.Net Framework 2.0, the software has powerful connectivity to network and database. It runs on both Windows XP and Vista. Client and server communicate through standard Modbus TCP protocol. One server can work for multiple clients. It is easy to integrate to the enterprise central management informatics platform and building security system. Features Real-time data display, store, analysis and report generation Easy to locate battery with position, number and date/time Trend charts for voltage and internal resistance Display of bus voltage, current, cell voltage, cell internal resistance, connection resistance, pilot battery or ambient temperature Record the discharge event, lasting time and draw discharge curve for each battery Receive and display the alarm setting and events
6 2 Software Installation BMS software has 3 major components: 1) DAS - data acquisition. This module links physical devices through various communication methods including serial ports and TCP/IP connections. 2) Database for standard user, the free Microsoft SqlExpress is the optimize option. For large scale application, it is user s responsibility to purchase the license for Microsoft Sql Server standard version. 3) Battery Analyzer it retreat data from database and provides powerful user interface and management functions. Analyzer can be installed on other PC alone which has Sql Server installed locally. The software is based on NET framework. It works on Windows XP (with service pack 2) and Vista Systems. If the environment needs update, user can download components from Microsoft website or use the patches in the installation CD. Contents in the patch folder: Depending on PC software environment, only the necessary components need to be installed.
7 2.1 Pre-installation Major steps: 1. Verify computer has Microsoft Windows XP and Service Pack 2 or above. If not, install the service pack 2. Control Panel System 2. Verify computer has Microsoft.NET framework 2.0 or later version. If not, install it. 3. Verify computer has Microsoft SqlExpress database installed. If not, install it.
8 2.1.1 Update service Pack2 Go to Control Panel System to check the operation system. If it needs update, go to the link as below: Click Download and install it.
9 SP2 is a big piece, after download, it will extract files to a temp folder. The inspection will take few minutes depends on the computer speed. This step will take longer time. Be patient. If you encounter this type of error, you may have to switch to another computer or reinstall a valid Windows XP.
10 2.1.2 Install.NET framework 2.0 If your PC doesn t have.net Framework installed, the message will guide you to Microsoft download. If the network is not connected, it will show the blank page.
11 Or it will link to the download page in Microsoft website. Select.NET Framework 2.0 Service Pack 1 (x86).
12 Download.NET Framework 2.0
13 Open the file You need Windows XP service pack 2 in order to install.net Framework. Otherwise, it will show error as below.
14 2.1.3 Install SqlExpress Install Microsoft SqlExpress from...\sqlexpress\sqlexpr32.exe
16 Keep the default, BMS does not need for client components.
17 No selection needed.
19 Now start BMS installation again. If in any case, you have installed incomplete BMS or early version, you need to uninstall it first Trouble shooting
20 2.2 BMS Software Installation
21 Select both DAS and Battery Analyzer if your computer will link to monitoring devices.
22 Select Everyone or Just me. If you encounter this error message, the database is not in place. You need to install the SqlExpress as instructed in previous chapter.
23 2.3 Vista Installation For Vista system (32-bit or 64-bit), it is often to encount error code 2869 with the installer. Follow the steps: 1) Switch user to administrator login. 2) Install Microsoft SqlExpress if you don't have. No need to install NET framework for Vista. 3) Install BMS by click setup.exe(not BMSSetup.msi), select both BatteryAnalyzer and DAS. 4) Configure DAS 5) Run Battery Analyzer, do a discharge record, in View->History Query Panel, search for record data to make sure database is working properly. 6) Switch user 7) Run SQL server 2005 Configuration Tool --> Sql Server Surface Area Configuration to add new administrator 8) Run Battery Analyzer, link to DAS for real time data 9) Do a discharge record, in View -> History Query Panel, search for discharge record data. If there is a problem, you need to check database permission.
24 2.4 Troubleshooting In Windows Vista, you do not have immediate access to the Admin Account. When logging into Windows Vista, you do not have the option of using this account. From the Start menu, simply right-click on Computer and choose Manage. Next, expand Local Users and Groups and select the Users folder. The final step is to right-click on the Administrator login and choose properties. Clear the Account is Disabled checkbox and you have now enabled your Administrator account.
25 3 BMS configuration Battery Monitoring System Software includes 3 major components: Battery DAS, Battery Analyzer and Database. Battery DAS links to devices through serial port or TCP/IP Modbus devices. It reads the real-time data from monitoring devices and register data to database. Battery Analyzer provides human operation interface to database. It does the analysis routine in the real-time mode. It receives real-time data from DAS software by Modbus TCP protocol. Database stores data and alarm information. It stores analysis or alarm result from Battery Analyzer on the same PC or through networking. 3.1 DAS Configuration Battery DAS communicates to monitoring devices through serial port or TCP/IP devices. The standard Modbus protocol provides reliable data transmission. Non-standard COMM protocol is also available for some devices.
26 The above figure shows the main scheme of DAS software. Battery DAS interfaces provide equipment configuration and communication port management. The equipment configuration window allows user to add, delete devices or modify parameters. In some cases, the configuration of monitoring device may be different from physical devices. The Logic Device concept has been used in software. The data from Logic Device come from physical devices, but from one or more devices. Click Apply, the relationship between physical devices and Logic Devices will show up as in the figure. Serial port management window allows user to set the parameters for communication. They can be different for each device. Only the ports link to battery monitoring devices have been listed. (There are possibly more ports in the computer.) Each time, after restart DAS software, you have to open each port to initiate the communication. For each device, you only need to do the configuration one time. The parameters will be saved for the later use until any change happens. * The software does not automatically open the ports. You have to do it manually each time the DAS software starts. Do not shut off DAS software if you wish to continuously monitor the batteries.
27 3.2 Analyzer Configuration Battery Analyzer software receives the real-time data from DAS and performs display, analysis, store and historical data query. Analyzer has 3 functional windows: 1) Map view. It shows registered sites on map. When any site has alarm, that site will change color and flashes. 2) Real-time data view 3) History data query Map View The map can be customized to reflect the real situation. Setting System settings. After load new map, you will need to locate the devices. Operation Map Edit Move the dots to correct locations. *The current version does not support zoom in/out.
28 3.2.2 Real-time data view
29 (Real-time data view) The real-time data view also provides both table and chart. It generates alarm list and update the status History data query The history data query provides the interface to search data in database. The left/up zone of history data query window accepts input criteria for query. String Data Cell Data Alarm Data Discharge Data By select the result, the data of voltage/current/temperature will show in table and chart. The internal resistance trend provides valuable information of battery condition.
30 3.2.4 Menu and tool bar Server settings: IP address and port. The server can be the same PC which runs the Analyzer or any other port which provides data through Modbus TCP. The default port is 502. devices. Device management: for device configuration corresponding to physical System setting:for system parameters, such as data recording interval and customized map. Map view:switch to map view. Real-time data view (main window) History query: to perform query for history data and trends. Run: to link to DAS software and database. After successful connection, the status will show at the low line and data will be refreshed timely. Stop: disconnect to server, the query will be interrupted as well. Discharge data: To start record of discharge data manually. Add first record: After the new installation and capacity verification, the initial internal resistance will be recorded to database for future comparison. Monthly report: To generate monthly report. Map Edit: To locate the monitoring devices on map. Save and exit edit: Exit map edit. You have to quit and restart Analyzer in order to update the map. Help: To open help file.
31 3.2.5 Important Operations Server setting the server is the computer which runs DAS software. If the DAS and Analyzer are installed in the same computer, the address will be , Default Port: 502. Device Configuration function to device management. the device list provides add, delete and modify
32 * When the device list changes, all data and alarm information will be reset. System setting it needs to set the basic parameters for system running.
33 The string number of each device will start from 1 when the string No independence has been selected. Otherwise, it will continue from last equipment. Auto record discharge data: (This function will need current sensor. Not available in standard version.) Software Language: English and Chinese. Other language can be ordered. Data record interval (days): The interval to write data to database for future history query. Discharge record interval (Seconds): The interval to record discharge curve. Depends on the discharge rate, the shortest interval is 1 second. Output alarm from serial port: if this option has been chosen, the alarm message will be generated continuously when there is any alarm. On the other hand, when there is no alarm, the message for no alarm will also be sending continuously. Use Map: use real picture or facility drawings to locate the battery sites. The Google Map is under development for large scale application. Click OK to save the changes. Discharge Record This function provides a manual operation for discharge recording. In this window, the left side list out the strings not for discharge. The right side lists all the strings which will discharge. Before any record takes effect, the correct string has to be selected. More than 1 string can be recorded simultaneously. Record time needs to set to cover the intended discharge time. The interval also needs to set for reasonable resolution.
34 After setting, click Start Record to record data to database. The software does not control the discharge. Click Background will hide the window and you can do other operation with Analyzer. During the recording, you can stop it at any time. The record can only work with the successful link between DAS and Analyzer. Monthly Report Analyzer provides simple report function. The left panel provides preview of the report. The right panel accepts the inputs to select data.
COMPLIANT MANAGER Model name: BMS-CM1280FTLE Prohibited Never connect the Compliant Manager to the Internet. We assume no responsibility for any problems resulting from connection to the Internet. Only
AXIS Camera Station Quick Installation Guide Copyright Axis Communications AB April 2005 Rev. 3.5 Part Number 23997 1 Table of Contents Regulatory Information.................................. 3 AXIS Camera
CDR-100 iphone Spy Recovery (for Win) iphone Data Recovery Software for Windows OS User Guide Rev. 1.0 Contents Introduction 1 System Requirements 2 Features 3 Getting Ready for Data Recovery 4 Installation
SQL Server Installation Guide 1. From the Visor 360 installation CD\USB Key, open the Access folder and install the Access Database Engine. 2. Open Visor 360 V2.0 folder and double click on Setup. Visor
Dell Statistica 13.0 2015 Dell Inc. ALL RIGHTS RESERVED. This guide contains proprietary information protected by copyright. The software described in this guide is furnished under a software license or
CONFIGURING MICROSOFT SQL SERVER REPORTING SERVICES TECHNICAL ARTICLE November/2011. Legal Notice The information in this publication is furnished for information use only, and does not constitute a commitment
Blackbaud Sphere & The Raiser s Edge Integration Guide 101311 Blackbaud Sphere 2011 Blackbaud, Inc. This publication, or any part thereof, may not be reproduced or transmitted in any form or by any means,
Introduction EASYLABEL 6 has several new features for saving the history of label formats. This history can include information about when label formats were edited and printed. In order to save this history,
Upgrading from Call Center Reporting to Reporting for Contact Center BCM Contact Center Document Number: NN40010-400 Document Status: Standard Document Version: 02.00 Date: June 2006 Copyright Nortel Networks
User Manual Onsight Management Suite Version 5.1 Another Innovation by Librestream Doc #: 400075-06 May 2012 Information in this document is subject to change without notice. Reproduction in any manner
Mobility Services Platform 3.1.1 Software Installation Guide Mobility Services Platform 3.1.1 Software Installation Guide 72E-100159-04 Revision D January 2008 2007 by Motorola, Inc. All rights reserved.
EPSON Scan Server & EPSON TWAIN Pro Network EPSON Scan Server & EPSON TWAIN Pro Network SCANNER UTILITY PROGRAMS All rights reserved. No part of this publication may be reproduced, stored in a retrieval
Desktop Surveillance Help Table of Contents About... 9 What s New... 10 System Requirements... 11 Updating from Desktop Surveillance 2.6 to Desktop Surveillance 3.2... 13 Program Structure... 14 Getting
Features Reference About Unified Communication System Before Using This Machine Starting a Meeting What You Can Do During the Meeting Leaving a Meeting Managing Address Book Changing Network Configuration
HP LaserJet MFP Analog Fax Accessory 300 Send Fax Driver Guide Copyright and License 2008 Copyright Hewlett-Packard Development Company, L.P. Reproduction, adaptation, or translation without prior written
Ash Capture Control User Guide Revision 1.4 Table of Contents Software Installation... 3 Hardware Installation... 6 System Block Diagram... 7 Using Ash Capture Control... 8 Launching the Application...
Scan to SMB(PC) Set up Guide Regarding Trade Names Windows is a registered trademark of Microsoft Corporation in the U.S.A. and/or other countries. Windows XP and Windows Vista are trademarks of Microsoft
formerly Help Desk Authority 9.1.3 Upgrade Guide 2 Contacting Quest Software Email: Mail: Web site: email@example.com Quest Software, Inc. World Headquarters 5 Polaris Way Aliso Viejo, CA 92656 USA www.quest.com
PowerShield SNMP Adaptor This manual describes the setup and operation of the PowerShield SNMP adaptor for the Sentinel battery monitoring system 6300-079A SNMP User Manual Page 1 of 9 1. Connecting the
Installation Instructions Windows USB driver for Installation If a Diagnostic Interface with USB is connected to a PC with a Windows operating system 98, ME, XP or Vista for the first time, it is necessary
Allworx OfficeSafe Operations Guide Release 6.0 No part of this publication may be reproduced, stored in a retrieval system, or transmitted, in any form or by any means, electronic, mechanical, photocopy,
ViewPower User s Manual Management Software for Uninterruptible Power Supply Systems Table of Contents 1. ViewPower Overview... 2 1.1. Introduction...2 1.2. Structure...2 1.3. Applications...2 1.4. Features...2
DigiFox Professional Instruction Manual Ver1.0 Copyright Our company owns all rights of this unpublished work and intends to maintain it as a confidential work. We may also seek to maintain this work as
WatchPower User s Manual Management Software for Inverter Table of Contents 1. WatchPower Overview... 2 1.1. Introduction... 2 1.2. Features... 2 2. WatchPower Install and Uninstall... 2 2.1. System Requirement...
SplendidCRM Deployment Guide Version 5.x Last Updated: December 14, 2010 Category: Deployment This guide is for informational purposes only. SPLENDIDCRM SOFTWARE MAKES NO WARRANTIES, EXPRESS OR IMPLIED,
Modular Messaging Release 4.0 Service Pack 4 Whitepaper: Support for Active Directory and Exchange 2007 running on Windows Server 2008 platforms. April 2009 2006-2009 Avaya Inc. All Rights Reserved. Notice
About This Guide 3 About This Guide This user guide is intended for Photovoltaic (PV) system owners, installers, technicians, maintainers, administrators and integrators who are authorized to configure
CONSOLEWORKS WINDOWS EVENT FORWARDER START-UP GUIDE BEFORE YOU BEGIN This document assumes some things: You are using ConsoleWorks 4.6 or later (required), it s currently running, and a browser displaying
Diamond II v2.3 Service Pack 4 Installation Manual P/N 460987001B ISS 26APR11 Copyright Disclaimer Trademarks and patents Intended use Software license agreement FCC compliance Certification and compliance
ArcGIS 9 Installation Guide: Workgroup for Microsoft SQL Server Express Copyright 2006 ESRI All Rights Reserved. Printed in the United States of America. The information contained in this document is the
User s Guide NPD4747-01 EN Contents Contents Copyright and Trademarks Safety Instructions Important Safety Instructions... 4 Cautions and Notes... 4 Getting to Know Your Network Interface Panel Package
Nexio Connectus with Nexio G-Scribe 2.1.2 3/20/2014 Edition: A 2.1.2 Publication Information 2014 Imagine Communications. Proprietary and Confidential. Imagine Communications considers this document and
NortechCommander Software Operating Manual MAN-00004 R6 If the equipment described herein bears the symbol, the said equipment complies with the applicable European Union Directive and Standards mentioned
User s Manual Third Edition, March 2011 www.moxa.com/product 2011 Moxa Inc. All rights reserved. User s Manual The software described in this manual is furnished under a license agreement and may be used
Docufide Client Installation Guide for Windows This document describes the installation and operation of the Docufide Client application at the sending school installation site. The intended audience is
NETWORK PRINT MONITOR User Guide Legal Notes Unauthorized reproduction of all or part of this guide is prohibited. The information in this guide is subject to change without notice. We cannot be held liable
SMS Database System Quick Start [Version 1.0.3] Warning ICP DAS Inc., LTD. assumes no liability for damages consequent to the use of this product. ICP DAS Inc., LTD. reserves the right to change this manual
SAFETICA INSIGHT INSTALLATION MANUAL SAFETICA INSIGHT INSTALLATION MANUAL for Safetica Insight version 6.1.2 Author: Safetica Technologies s.r.o. Safetica Insight was developed by Safetica Technologies
ivms-5200 Professional Web Manager User Manual UD.6L0202D1651A01 Hikvision ivms-5200 Professional Web Manager User Manual This manual, as well as the software described in it, is furnished under license
File Management Utility User Guide Legal Notes Unauthorized reproduction of all or part of this guide is prohibited. The information in this guide is subject to change without notice. We cannot be held
PN-T321 LCD MONITOR USB Flash Drive Media Tool OPERATION MANUAL Contents Introduction...2 Installing/Uninstalling the Software...3 System Requirements...3 Installing the Software...3 Uninstalling...3 Using
Legal Notes Unauthorized reproduction of all or part of this guide is prohibited. The information in this guide is subject to change without notice. We cannot be held liable for any problems arising from
Installation Guide Manuals for This Product Manuals for this product have the following structure. Read the manual according to your purpose for using this product. Disc Guides with this symbol are PDF
Omgeo OASYS Workstation Installation Guide Version 6.4 December 13, 2011 Copyright 2011 Omgeo LLC. All rights reserved. This publication (including, without limitation, any text, image, logo, compilation,
DME-N Network Driver Installation Guide for LS9 ATTENTION SOFTWARE LICENSE AGREEMENT PLEASE READ THIS SOFTWARE LICENSE AGREEMENT ( AGREEMENT ) CAREFULLY BEFORE USING THIS SOFTWARE. YOU ARE ONLY PERMITTED
SPC-1 Single Point Controller Operation Manual NOTICE: PPM Technology Limited shall not be liable for errors that may appear herein or for incidental or consequential damages in connection with or arising
Windows Peer-to-Peer Network Configuration Guide Windows Peer-to-Peer Network Configuration Guide for CCC Pathways Copyright 2008 by CCC Information Services Inc. All rights reserved. No part of this publication
TSM Studio Server User Guide 22.214.171.124 1 Table of Contents Disclaimer... 4 What is TSM Studio Server?... 5 System Requirements... 6 Database Requirements... 6 Installing TSM Studio Server... 7 TSM Studio
Intel Unite Solution Standalone User Guide Legal Disclaimers & Copyrights All information provided here is subject to change without notice. Contact your Intel representative to obtain the latest Intel
TA Instruments TRIOS Software Installation Instructions Installation Requirements Your TRIOS Instrument Control software includes all the components necessary to install or update the TRIOS software, as
Server Application ACTi NVR v2.2 Quick Installation Guide ACTi APP-2000 This document is copyrighted, 2003-2008 by ACTi Corporation. All rights are reserved. ACTi Corporation reserves the right to make
CA VPN Client User Guide for Windows 126.96.36.199 This Documentation, which includes embedded help systems and electronically distributed materials, (hereinafter referred to as the Documentation ) is for your
Dell Statistica Document Management System (SDMS) Installation Instructions 2015 Dell Inc. ALL RIGHTS RESERVED. This guide contains proprietary information protected by copyright. The software described
ebus Player Quick Start Guide This guide provides you with the information you need to efficiently set up and start using the ebus Player software application to control your GigE Vision or USB3 Vision
Crow Limited Warranty (Crow) warrants this product to be free from defects in materials and workmanship under normal use and service for a period of one year from the last day of the week and year whose
Imaging Computing Server User Guide PerkinElmer, Viscount Centre II, University of Warwick Science Park, Millburn Hill Road, Coventry, CV4 7HS T +44 (0) 24 7669 2229 F +44 (0) 24 7669 0091 E firstname.lastname@example.org
RPM Utility Software User s Manual Table of Contents 1. Introduction...1 2. Installation...2 3. RPM Utility Interface...4 1. Introduction General RPM Utility program is an RPM monitoring, and management
SA-9600 Surface Area Software Manual Version 4.0 Introduction The operation and data Presentation of the SA-9600 Surface Area analyzer is performed using a Microsoft Windows based software package. The
This is a publication of Abila, Inc. Version 2015.x Copyright 2014 Abila, Inc. All rights reserved. Abila, the Abila logos, and the Abila product and service names mentioned herein are registered trademarks
PN-L702B LCD MONITOR TOUCH PANEL DRIVER OPERATION MANUAL Version 2.1 Contents Setting up the PC...3 Installing the touch panel driver...3 Touch Panel Settings...4 How to configure settings...4 Calibration...5
Alarm Client Installation and User Guide NEC NEC Infrontia Corporation July 2008 NDA-30364, Revision 8 Liability Disclaimer NEC Infrontia Corporation reserves the right to change the specifications, functions,
MAPILab Reports for Hardware and Software Inventory Installation Guide Document version 1.0 MAPILab Ltd., January 2010 Table of Contents Introduction... 3 1. Product architecture and general explanations...
Enterprise Self Service Quick start Guide Software version 188.8.131.52 December 2013 General Information: email@example.com Online Support: firstname.lastname@example.org 1 2013 CionSystems Inc. ALL RIGHTS RESERVED.
SNMP Web Management User s Manual For SNMP Web Card/Box Management Software for Off-Grid Inverter Version: 1.2 Table of Contents 1. Overview... 1 1.1 Introduction... 1 1.2 Features... 1 1.3 Overlook...
Federated Identity Service Certificate Download Requirements Version 3.2 Exostar, LLC February 14, 2013 Table of Contents Introduction... 1 Purpose... 1 FIS System Requirements... 2 Adding Exostar as a
Telelogic DASHBOARD Installation Guide Release 3.6 1 This edition applies to 3.6.0, Telelogic Dashboard and to all subsequent releases and modifications until otherwise indicated in new editions. Copyright
MaxMobile 10.5 for Windows Mobile Smartphone Welcome to MaxMobile Introduction MaxMobile 10.5 for Windows Mobile Smartphone provides you with a way to take your customer information on the road. You can
Accounting Manager User Guide A31003-P1030-U114-2-7619 Our Quality and Environmental Management Systems are implemented according to the requirements of the ISO9001 and ISO14001 standards and are certified
January 9, 2014 Xerox Global Print Driver Installation Guide 2010-2014 Xerox Corporation. All Rights Reserved. Xerox, Xerox and Design, WorkCentre, Global Print Driver, and Mobile Express Driver are trademarks
Release Version 15.0 January 30 th, 2011 ARGUS Software: ARGUS Valuation - DCF The contents of this document are considered proprietary by ARGUS Software, the information enclosed and any portion thereof