2 Quick start ASI or STS U-Talk ASI ASI or STS RS232 Download ETHERNET RS Reset status IP= MAC=00E0D8FF855E Card Settings RS232 Download ETHERNET RS Reset status ETHERNET Card Settings Hub 1. Insert and screw the communication card NMC inside the or STS slot. It is unecessary to shut off the or STS. 2. Configure the network parameters: If you have a BOOTP/DHCP server on your network, no manual settings are required. However, ask your network administrator to set the server parameters so that the IP address assigned to the card is in a range of fixed addresses. If you do not have a BOOTP/DHCP server, the network parameters must be set manually via the Card Settings serial port. Contact your network administrator to obtain the setting values (sections 3.2 and 3.3). 3. Connect the Ethernet port to the network. Check 10 or 100 LED flashing. 4. Read IP address via the Card Settings serial port if you have a BOOTP/DHCP server on your network (sections 3.2 and 3.3). 5. To access the supervision and administration functions via your browser, enter 6. To access the supervision functions via your Network Management System (NMS), install, set up and run the selected application on the NMS station. 7. To access the other advanced configuration parameters, see the user manual available on our Web-site at (Download area section). Page EN/AG
3 Introduction Thank you for selecting a Schneider Electric product to protect your electrical equipment. The Network Management Card has been designed with the utmost care. We recommend that you take the time to read this manual to take full advantage of the many features of your new equipment. Environment Schneider Electric pays great attention to the environmental impact of its products during the design and manufacture stages, through to the end of its life cycle. This product complies with the most strict regulations. It does not contain CFCs or HCFCs. Recycling of packing materials Packing materials were selected to facilitate recycling. Please make sure they are correctly recycled in compliance with all applicable regulations. Recycling of the product at the end of its life cycle Schneider Electric undertakes to recycle all recovered products in installations, complying with applicable regulations. Please contact our sales office. Special precautions If the card must be stored prior to installation, storage must be in a dry place. The admissible storage temperature range is -10 C to +70 C EN/AG - Page 3
4 Foreword EMC compatibility When correctly installed and used in accordance with the manufacturer s instructions, Network Management Card comply with the following standards: ATI safety: EN 60950/A11 (2005). EMC: EN (2005), EN (2006). Conformity with European directives: Low voltage: 2006/95/EEC. EMC: 2004/108/EEC. Federal Communication Commission (FCC) statement This equipment has been tested and found to comply with the limits for a Class A digital device, pursuant to part 15 of the FCC Rules. These limits are designed to provide reasonable protection against harmful interference when the equipment is operated in a commercial environment. This equipment generates, uses, and can radiate radio frequency energy and, if not installed and used in accordance with the instruction manual, may cause harmful interference to radio communications. Operation of this equipment in a residential area is likely to cause harmful interference in which case the user will be required to correct the interference at his own expense. Pictograms used in this manual Important operations. Information, advice, help. Visual indication. Action. Software screen accessed via the Network Management Card. Properties : Text in bold italics has been taken from the software. Page EN/AG
5 Contents 1. Presentation 1.1 Unpacking and check on contents Overview Functions Technical characteristics List of parameters and default values Installation 2.1 Installation DIP-switch settings Installation in a or STS equipped with slots Installation in a MultiSlot module ( only) Environment Sensor installation Connection of the Ethernet link Connection to a hub Connection to a computer Indications Configuration 3.1 Default IP address Parameter setting Via the serial link Via the network EN/AG - Page 5
6 Contents 3.3 Setting the network parameters Restarting the card Restoring the default parameters Restoring the default password Operation 4.1 Operating test following installation and configuration Maintenance 5.1 Troubleshooting Loss of password Firmware upgrade Troubleshooting Appendix 6.1 Glossary Page EN/AG
7 The indispensable companion sofware for your L'indispensable complément logiciel de votre onduleur IP= MAC=00E0D8FF855E 1 2 Reset ETHERNET Card Settings Reset status 1 2 RS232 Download ETHERNET RS IP= MAC=00E0D8FF855E Reset data data Card Settings RS232 Card Settings Installation manual RS232 Download ETHERNET RS Presentation 1.1 Unpacking and check on contents Solution-Pac 00E0D8FF861F III II I I II II IIII I I Network Management Card An NMC communication card, with a standard front plate already installed. A front plate specially designed for MGE Galaxy PW s. A serial communication cable used for configuration and maintenance. Installation and user manual. The Solution-Pac 2 CD-ROM. RS232 Download EN/AG - Page 7
8 1. Presentation 1.2 Overview 4 Labels for Ethernet and IP addresses DIP switches for configuration (RS232 Download). Reset button. Green 100 M Ethernet LED (100). Orange 10 M Ethernet LED (10). Data LED signalling data transfers ( Data). IP= MAC=00E0D8FF855E 1 2 Reset data Card Settings RS232 Download ETHERNET RS RS232 serial port for Environment Sensor, configuration and maintenance (Card settings / RS232). Card part number. 10/100BT Ethernet port (ETHERNET). 10 Jumper for return to the default password. The address label 4 is made up of two areas: The upper line may be used to manually note the IP address assigned to the card. The lower line indicates the card Ethernet address (MAC address). Page EN/AG
10 1. Presentation The Network Management Card is used to directly connect the or STS to a computer network, while simultaneously operating as a Web server and SNMP agent. Remote connections are made using an ordinary internet browser or an NMS station. All the functions offered by the Network Management Card are accessible via a number of Schneider Electric software applications, depending on the user s needs. Functions Supervision or STS properties or STS log System log Alarm subscription Direct notification Environement parameters Mupgrade or Download Web browser Console Direct Telnet Supervision EPM Network Shutdown Module ( only) Configuration - Administration Network parameters Community name Shutdown parameters ( only) Scheduled shutdown ( only) Management table Time Maintenance Network cards discovery Firmware upgrade Reset agent Factory reset (Mupgrade) Servers/Workstations protection Page EN/AG
11 1. Presentation 1.4 Technical characteristics Functions Supervision Alarms Protection of client stations Network Browsers International NMS MIB Configuration Downloads Characteristics Simultaneous connection of up to 15 browsers. Up to 500 events stored in memory with battery backup. Automatic refresh of the Properties page. Alarm notification via Browser (applet), and SNMP (trap). Up to 50 protected stations. Fast ETHERNET 10/100 Mbits, auto-negotiation. HTTP 1.1, SNMP V1, TELNET, TFTP, NTP, BOOTP, DHCP. Simultaneous management of protocols. Microsoft Internet Explorer 5.x or higher. Netscape Navigator 6.x or higher. Web pages in English, French, German, Italian and Spanish. Automatic detection of browser language. Enterprise Power Manager (EPM). Standard MIB II. MGE V2.2 MIB. IETF MIB. Access via a password. Setting of parameters: IP, System, Date/time, Community name, etc. Single card or Multicard via the network using Mupgrade. Single card via TFTP or an RS232 serial link EN/AG - Page 11
12 1. Presentation 1.5 List of parameters and default values Functions Parameters Default values Possible values Network IP Address Subnet Mask Gateway Address Host Domain name Telnet Connection BOOTP/DHCP Network Upgrade Primary DNS Server Secondary DNS Server SMTP Server NTP Server xx.yy (see section 3.1) xxxx ups.domain.com Enable Enable Enable smtpserver.domain.com Network IP address Network IP address Network IP address Host name Domain name Enable/Disable Enable/Disable Enable/Disable Network IP address Network IP address IP address or DNS name Network IP address System Contact Location History Log Interval (sec) Refresh Rate (sec) Default Language Outputs name System stop duration (sec) Working time on battery (min) before stop Computer Room Manager Computer Room Auto Master/Group1/Group characters max. 32 characters max. 20 to to Auto/English/French/ German/Italian/Spanish 30 characters max. 0 to to 1092 Manager table (Empty list) 50 max. Remarks. Same password must be used to modify those parameters via internet browser, serial link or Telnet. Page EN/AG
13 1. Presentation Functions Parameters Default values Possible values Access control Manager Login Password Current community read-only Current community read/write Trap Port Number MGE MGE public public characters max. 10 characters max. 31 characters max. 31 characters max. (free) notification Recipients Logs attached files Sender Subject Text Evenement table None Schneider Electric None fault / Off sequence in progress 4 recipients max. Measures / Events / System / Environment logs 60 characters max. see configuration page 136 characters max. see configuration page Environment Temperature unit Temperature threshold Humidity threshold Celsius 40 C max. / 5 C min. 90% max. / 5% min. Celsius / Fahrenheit 0 to 70 C 0 to 100% Time Setting time Time zone Daylight Saving Time Set manually GMT-05 Eastern Time OFF NTP Server / Computer (see list) / OFF Serial link Speed Data bits Stop bit Parity 9600 bauds 8 1 None (not authorized) (not authorized) (not authorized) (not authorized) Remarks. Same password must be used to modify those parameters via internet browser, serial link or Telnet EN/AG - Page 13
14 2. Installation 2.1 Installation DIP-switch settings 7 IP= MAC=00E0D8FF855E 1 2 Reset data Card Settings RS232 Download ETHERNET RS Switch 1 Switch 2 OFF Function Reserved Serial link downloads enabled OFF Reserved 1 2 OFF OFF OFF Operational mode (default) To get more information about downloading, see section 5.3. Page EN/AG
15 IP= MAC=00E0D8FF855E 1 2 RS232 Download Reset ETHERNET data 1 2 data Card Settings RS Installation Installation in a or STS equipped with slots ASI or STS U-Talk RS232 Download ETHERNET RS Reset Card Settings It is not necessary to turn the or STS off. 1 - Using a screwdriver, remove the cover from a free slot in the or STS. 2 - Insert and secure the communication card in the or STS. Installation in a MultiSlot module ( only) MultiSlot ASI U-Talk 1 - Using a screwdriver, remove the cover from a free slot in the MultiSlot module. 2 - Insert and secure the communication card in the MultiSlot module. Us/Out/Ausg 10A/250V EN/AG - Page 15
16 2. Installation 2.2 Environment Sensor installation Refer to the EN installation manual included in the Environment Sensor kit (66846). 2.3 Connection of the Ethernet link To make use of the full potential of your installation, we recommend using shielded cables with shielded RJ45 connectors. Connection to a hub Connection to a computer Straight-through 10/100 Base-T cable RJ Crossover 10/100 Base-T cable RJ RJ45 RJ45 If the Network Management Card is connected to a hub, use a straight-through cable. If the Network Management Card is connected to a computer, use a crossover cable. Page EN/AG
17 2. Installation 2.4 Indications Green LED 6 Data Slowly flashing (1 s) Rapidly flashing Random flashing Off Function Start phase Dialogue with the / STS / MultiSlot Data exchange with the / STS / MultiSlot Card fault IP= MAC=00E0D8FF855E 1 2 Reset Data Card Settings RS232 Download ETHERNET RS Green 100 LED 2 Orange 10 LED 3 Function 2 3 Slowly flashing (1 s) Off Off Slowly flashing (1 s) 100M Ethernet traffic 10M Ethernet traffic IP= MAC=00E0D8FF855E 1 2 Reset Data Card Settings Off Off Ethernet not connected RS232 Download ETHERNET RS The card is operational approximately 30 seconds after insertion EN/AG - Page 17
18 3. Configuration 3.1 Default IP address The Network Management Card comes with a default IP address. This address is derived from the MAC address on the label on the front of the card. The format of the MAC address is 00 E0 D8 LL MM NN, where: 00 E0 D8 is the manufacturer code in hexadecimal format, LL MM NN is the serial number of the card in hexadecimal format. The default IP address of the card is made up of four bytes of which the last two are derived from the MAC address. The format of the IP address is xxx.yyy, where: is a fixed value, xxx is the decimal value of the MM byte, yyy is the decimal value of the NN byte. For example, for a MAC address 00 E0 D8 04 0A 15, the corresponding default IP address is Parameter settings Via the serial link Run Hyper Terminal on a PC running Windows (9x, Me, NT4.0, 2000 or higher). Connect the card to the PC using the cable supplied. Set up the terminal with the following communication parameters: 9600 bauds. 8 data bits. 1 stop bit. no parity. no flow control. ASCII: "echo typed characters locally" option disabled. Press the Carriage return key. The configuration menu is displayed. Enter the password (MGE by default). The main menu is displayed. Select one of the items in the configuration menu. Page EN/AG
19 3. Configuration Via the network Via Telnet Check that the card is connected to the ETHERNET network. Launch the "Run" command under Windows on a PC. Enter Connection is made. A screen is displayed. Enter the password (MGE by default). The main menu is displayed. Select one of the items in the configuration menu. Via a browser Check that the card is connected to the ETHERNET network. Run the browser on a PC. Enter the URL The main page is displayed. Select one of the items in the settings menu. 3.3 Setting the network parameters The Network Management Card requires the following network parameters: The IP address used for identification on the network. The Subnet mask which defines the group of users to which it is connected. The address of the Gateway to which it connects to communicate with another subnet. The network parameters are set up each time the system is started: Automatically if the network is equipped with a BOOTP or DHCP server; With the fixed parameters set manually if an IP address server is not available. If the BOOTP/DHCP server is not ready, saved parameters are used EN/AG - Page 19
20 3. Configuration The table below presents the initialisation mode for the network parameters: Network configuration BOOTP/DHCP server installed Mode sélectionné BOOTP/DHCP enabled BOOTP/DHCP disabled Fonctionnement Reception and use of the network parameters sent by the server (10s max.). Use of manual settings. No server available BOOTP/DHCP enabled BOOTP/DHCP disabled Attempt to connect to a BOOTP/DHCP server for ten seconds, then use settings saved during previous connection or default IP address. Use of manual settings. Important. As long as the card is not connected to the network, it continuously attempts to make connection. Once the connection has been established, the operational mode presented in the table above becomes effective. Via the serial link or Telnet Select the "Agent configuration" command by entering 1. Select the item numbers and modify all the IP parameters (address, mask, gateway). Once all the modifications have been made, exit following the instructions on the screen. Via a browser Select the "IP network" command in the configuration menu. Modify all the IP parameters (address, mask, gateway). Click the "Save changes" button. Enter the user name (MGE by default) and the password (MGE by default). Important. The modifications of the network parameters are taken into account when the card is restarted. Page EN/AG
21 3. Configuration 3.4 Restarting the card Manually Press the Reset 8 button. Via the serial link or Telnet Select the "Restart agent" command by entering 6. Then follow the instructions on the screen. Via a browser Select the "System" command in the configuration menu. Click the "Reset communication" button. Enter the user name (MGE by default) and the password (MGE by default). Remarks: The card is operational approximately 30 seconds after it is started. User customized parameters are not modified after a restart. Pressing the Reset 8 button does not modify any parameters EN/AG - Page 21
22 3. Configuration 3.5 Restoring the default parameters If problems occur during the configuration procedure or if the password is lost, it is possible to return to the default parameters (factory settings), listed in section 1.5. Via Telnet or Hyper Terminal Select the "Agent configuration" command by entering 1. Select the "Reset configuration to default" command by entering 5. Then follow the instructions on the screen. Via a browser Select the "System" command in the configuration menu. Click the "Factory Reset" button. The IP parameters are kept if the option is selected. Enter the user name (MGE by default) and the password (MGE by default) if necessary. Remark. Date and time are not modified after restoring default parameters. Page EN/AG
23 3. Configuration 3.6 Restoring the default password If you loose your password, to restore the default one MGE, you must perform following steps: Pull out the card from the or STS slot. Move jumper as shown below. Insert the card inside the or STS slot and wait for 30 seconds. Pull out the card from the or STS slot again. Move jumper to the original position shown below. Insert the card inside the or STS slot, secure it, and wait for 30 seconds Password is now reset to MGE. You can customise it again Original position Remark. When the jumper is not returned to its original position, MGE password is restored every time the card is restarted. JP EN/AG - Page 23
24 4. Operation 4.1 Operating test following installation and configuration Launch the "Run" command in Windows on a station connected to the same subnet. Enter (example: ping ). If no answer is sent by the card, check the network parameters. Use the browser to go to the URL address and check the page for the " Properties" or "STS Properties". Page EN/AG
25 5. Maintenance 5.1 Troubleshooting Problem All the LEDs are off. The "10" or "100" LED remains off following connection of the cable. The " data" LED is off. Connection using the browser is not possible. The configuration menu does not work. Cause The card is not supplied with power. The Ethernet link is not running. The card has faulted. The network parameters are incorrect. The RS232 serial link is not operational. The IP address entered by the user is incorrect. Solution Check that the is on. Check that the card is correctly inserted and secured in its slot. Remove the card and insert it again. Check the cable. If connection is made using a hub, check that the hub is supplied with power. Contact the after-sales technical support. Check that the "10" or "100" LED is on. Check that the URL corresponds to the current address of the card. Check that the computer can access the address (check the "Subnet-mask" and the "Default gateway" for the computer) Check the position of the jumper. Use the "Ping" command to test the connection. Make sure the cable used is that supplied with the card. Check the terminal parameters. Test the link using the default parameters. Note: if the problem cannot be solved, contact the after-sales technical support at the address indicated on the site. 5.2 Loss of password To return to the default password, see section EN/AG - Page 25
26 5. Maintenance 5.3 Firmware upgrade The Network Management Card firmware can be upgraded easily through two different download procedures: Via ETHERNET with Mupgrade software tool (Windows only). Via serial link with Download software tool. Schneider Electric Web site is periodically upgraded with new firmware releases. To get more information about those software tools, refer to the NMC user manual on Loss of serial cable DB9/DB9 cable (1,8 m max) male DB9 connector female DB9 connector frame male DB9 connector shielded cable frame female DB9 connector Page EN/AG
27 6. Appendix 6.1 Glossary BOOTP DHCP DST Ethernet EPM HTTP Internet Intranet IP address MAC address MultiSlot NMC NMS NSM NTP SNMP Bootstrap Protocol. A protocol for restart of products connected to the network. Dynamic Host Configuration Protocol. A protocol for the dynamic assignment of network parameters. Daylight Saving Time. Technology used in local networks. Enterprise Power Manager. HyperText Transfer Protocol. A protocol based on TCP (port 80) used to transfer requests and data between a server and a browser. Network established worldwide for interconnections between computers, based on the TCP/IP protocol. Local network offering the same services as the internet. Logic address of an element connected to a network. It is a unique address in the given network. Physical address assigned to a card. It is unique for each card. An expansion module for communication cards. Network Management Card. Network Management System. Network Shutdown Module. Network Time Protocol. System Network Management Protocol. Uninterruptible Power Supply. URL Uniform Resource Locator: the unique address for a page on the internet EN/AG - Page 27
SNMP Web card User s Manual Management Software for Uninterruptible Power Supply Systems Table of Contents 1. Overview... 3 1.1 Introduction... 3 1.2 Features... 3 1.3 Overlook... 3 1.4 Installation and
WebPower UPS SNMP HTTP AGENT User Guide WebPowerPro_man_E420 AT, IBM are registered trademarks of International Business Machines Corporation. NetWare are registered trademarks of Novell, Incorporated.
Network Management Card AP9617 AP9618 AP9619 Installation and Quick-Start Manual How to Avoid Equipment Damage Disconnect UPS power You do not need to turn off a Symmetra or a Silcon model UPS to install
User s Manual Network Management Card RMCARD202 Intelligent Network Management Card allows a UPS system to be managed, monitored, and configured Version 1.0 E-K01-SNMP005-0 TABLE OF CONTENTS Introduction
Dell Network Management Card User's Guide w w w. d e l l. c o m s u p p o r t. d e l l. c o m Notes and Warnings NOTE: A NOTE indicates important information that helps you make better use of your software.
Powerware Environmental Rack Monitor User s Guide FCC Part 15 Class B EMC Statements NOTE This equipment has been tested and found to comply with the limits for a Class B digital device, pursuant to part
User s Manual UPS SERIES Network Interface Card UPS-IPCARD I-00453 Rev B TABLE OF CONTENTS INTRODUCTION............................................................. 3-4 INSTALLATION GUIDE.......................................................
NetProbe Lite Web Based 8 Channel Sensor Collector User Manual Version 1.2 Copyright Information Copyright 2004-2005, Mega System Technologies, Inc. All rights reserved. Reproduction without permission
SNMP Web Management User s Manual For SNMP Web Card/Box Management Software for Off-Grid Inverter Version: 1.2 Table of Contents 1. Overview... 1 1.1 Introduction... 1 1.2 Features... 1 1.3 Overlook...
IP Sensor and Watchdog IPSW2210 Manual Relay Output Power input 12VDC adapter LED Indicators 1 wire 2 Dry Output Green : Power Yellow: Link temperature & humidity contact inputs LED indicator sensor input
34003991XT_EN/EG Page 1/129 Contents 1 EATON NETWORK SOLUTION 6 1.1 GENERAL PRESENTATION 6 1.1.1 Connecting the UPS to the Ethernet network 7 1.1.2 Protection of the computers/servers 7 1.1.3 Supervision
Environmental Monitoring Unit AP9312TH AP9312THi User s Guide Contents Environmental Monitoring Unit Managing the Unit............................ 1 Introduction.................................. 1 Available
Title Page Web/SNMP Management SmartSlot Card AP9606 User s Guide Thank You! Thank you for selecting the APC Web/SNMP Management SmartSlot Card. It has been designed for many years of reliable, maintenance-free
Chapter 3 Management This chapter describes how to use the management features of your ProSafe 802.11a/g Dual Band Wireless Access Point WAG102. To access these features, connect to the WAG102 as described
MODEL ATC-2004 TCP/IP TO RS-232/422/485 CONVERTER User s Manual 1.1 Introduction The ATC-2004 is a 4 Port RS232/RS485 to TCP/IP converter integrated with a robust system and network management features
RemotEye II User Manual Document Number: 50024-008 November, 2005 About This Manual This manual was written by the TOSHIBA Engineering and Marketing Groups. These groups are tasked with providing technical
Network Scan Server English EPSON Network Image Express Card User s Guide All rights reserved. No part of this publication may be reproduced, stored in a retrieval system, or transmitted in any form or
UPS SNMP Card User s Manual Table of Contents Chapter 1 Introduction 3 Features 3 System Application 3 Chapter 2 First Installation 5 Trouble Shooting 5 Chapter 3 Configuration 8 Configuring the InsightPower
UPS NETWORK INTEGRATOR User Guide IOMNETVIXX00-GB_08.doc At and IBM are registered trademarks of International Business Machines Corporation. NetWare is a registered trademark of Novell Incorporated. DOS,
Innovative Electronics for a Changing World INDEX 1. SYSTEM DESCRIPTION 2. BOARD CONNECTIONS terminals and indicators 3. CONNECTION DIAGRAM 4. START UP GUIDE and passwords 5. HOME PAGE 6. STATUS PAGE 7.
Power Switch-8 Power Management Master Slave User's Guide V.02/2004 Power Switch-8 Power Switch-8 is a couple of power control units made of a Master named Power Switch Master and a slave named Power Switch
Panduit Corp. 2010 TDP43ME NetPS PA26306A01 Rev. 01 11-2010 Network Printer Server Control Center for Ethernet Module NOTE: In the interest of higher quality and value, Panduit products are continually
Contents Introduction--1 Product Description.................................. 1 Access Procedures.................................... 3 How to Recover From a Lost Password..................... 6 Upgrading
MODEL ATC-2000 TCP/IP TO RS-232/422/485 CONVERTER User s Manual 1.1 Introduction The ATC-2000 is a RS232/RS485 to TCP/IP converter integrated with a robust system and network management features designed
USHA UPS SNMP HTTP AGENT User Guide USHAman-e504 AT, IBM are registered trademarks of International Business Machines Corporation. NetWare are registered trademarks of Novell, Incorporated. DOS, Windows
Save This Manual This manual contains important instructions and warnings that you should follow during the installation, operation, storage and maintenance of this product. Failure to heed these instructions
Chapter 4 Management This chapter describes how to use the management features of your NETGEAR WG102 ProSafe 802.11g Wireless Access Point. To get to these features, connect to the WG102 as described in
PURPOSE Verify that communication is established for the following products programming option (488.2 compliant, SCPI only): DCS - M9C & DCS M130, DLM M9E & DLM-M9G & DLM M130, DHP - M9D, P series, SG,
Broadband Router ESG-103 User s Guide FCC Warning This equipment has been tested and found to comply with the limits for Class A & Class B digital device, pursuant to Part 15 of the FCC rules. These limits
IP Power Stone 4000 User Manual Two Outlet Remote AC Power Controller Multi Link, Inc. 122 Dewey Drive Nicholasville, KY 40356 USA Sales and Tech Support 800.535.4651 FAX 859.885.6619 techsupport@multi
HPE DirectFlow UPS Management Module User Guide Abstract This document includes installation, configuration, and operation information for the HPE DirectFlow UPS Management Module software. This document
GV-Data Capture V3 Series User's Manual Before attempting to connect or operate this product, please read these instructions carefully and save this manual for future use. 2006 GeoVision, Inc. All rights
Medical Vacuum Systems-PXMI Please read and save these instructions. Read carefully before attempting to assemble, install, operate or maintain the product described. Protect yourself and others by observing
Contents of Package: DG-102S VoIP Station Gateway Power adapter CD-ROM, including User s Manual Quick Install Guide Requirements: RS-232 Console Cable Two RJ-45 CAT-5 Straight-Through Cables For more information
Olson Electronics Remote Power Monitoring Meter Operation Guide Key Features Amps: 00.00 to 32.00A True RMS (rated short period to 40A) Volts: 200.0 to 250.0V True RMS Watts: 0000 to 9999W KWh: 000000.0
Installing the RDSP-3000A-NIST Master Clock. Ethernet Connect the RJ-45 connector to a TCP/IP network. Equipment The following equipment comes with the clock system: RDSP-3000A-NIST Master Clock Module.
(VoIP) Configuration ENGINEERING REPORT No: 02-003 Introduction This report describes interfacing the IPCS VoIP Gateway Model EGW-902 to an ESTeem Model 192E Wireless Ethernet radio modem in a demonstration
Setup Manual and Programming Reference Stanford Research Systems Revision 1.05 (11/2010) Certification Stanford Research Systems certifies that this product met its published specifications at the time
NMS300 Network Management System User Manual June 2013 202-11289-01 350 East Plumeria Drive San Jose, CA 95134 USA Support Thank you for purchasing this NETGEAR product. After installing your device, locate
BIT COMMANDER Serial RS232 / RS485 to Ethernet Converter (Part US2000A) Copyrights U.S. Converters 1 Contents Overview and Features... 3 Functions..5 TCP Server Mode... 5 Httpd Client Mode.5 TCP Auto mode....6
USER MANUAL GUIMGR Graphical User Interface Manager for FRM301/FRM401 Media Racks CTC Union Technologies Co., Ltd. Far Eastern Vienna Technology Center (Neihu Technology Park) 8F, No. 60 Zhouzi St. Neihu,
Contents Introduction--1 Product Description....................................... 1 Access Procedures....................................... 3 Recover From a Lost Password..............................
Chapter 7 Troubleshooting This chapter provides troubleshooting tips and information for your ProSafe VPN Firewall 200. After each problem description, instructions are provided to help you diagnose and
CS 326e F2002 Lab 1. Basic Network Setup & Ethereal Time: 2 hrs Tasks: 1 (10 min) Verify that TCP/IP is installed on each of the computers 2 (10 min) Connect the computers together via a switch 3 (10 min)
Ethernet controller TCW181B-CM Users manual 1. Short description TCW181B-CM is 8-channel Ethernet relay board, which is designed to work in IP-based networks and managed by WEB interface or SNMP programs.
SNMP-1 Configuration Guide You must configure the Net Logic Card before it can operate properly. You have two methods to configure the Net Logic Card: Using telnet or terminal. Using Telnet 1. Make sure
Prestige 314 Read Me First Console WAN 10M PORT Prestige Rear Panel Connections CONNECTION Use an RS-232 console cable. Use the cable that came with your broadband modem. LAN 10/100M Port Number COMPUTER
KRAMER ELECTRONICS LTD. USER GUIDE Ethernet Configuration Guide (Lantronix) P/N: 2900-300321 Rev 6 Contents 1 Connecting to the Kramer Device via the Ethernet Port 1 1.1 Connecting the Ethernet Port Directly
Guide eprism 2505 eprism Email Security Suite 800-782-3762 www.edgewave.com 2001 2012 EdgeWave. All rights reserved. The EdgeWave logo is a trademark of EdgeWave Inc. All other trademarks and registered
Wireless Router Setup Manual NETGEAR, Inc. 4500 Great America Parkway Santa Clara, CA 95054 USA 208-10082-02 2006-04 2006 by NETGEAR, Inc. All rights reserved. Trademarks NETGEAR is a trademark of Netgear,
Debugging Network Communications Situation: you have a computer and your NetBurner device on a network, but you cannot communicate between the two. This application note provides a set of debugging steps
Prestige 324 Intelligent Broadband Sharing Gateway Version 3.60 January 2003 Quick Start Guide 1 Introducing the Prestige The Prestige is a broadband sharing gateway with a built-in four-port 10/100 Mbps
ZyWALL 5 Internet Security Appliance Quick Start Guide Version 3.62 (XD.0) May 2004 Introducing the ZyWALL The ZyWALL 5 is the ideal secure gateway for all data passing between the Internet and the LAN.
GW400 VoIP Gateway User s Guide P/N: 956YD30001 Copyright 2006. All Rights Reserved. Document Version: 1.0 All trademarks and trade names are the properties of their respective owners. i Table of Contents
User s Manual Remote Management Card RMCARD202/RMCARD203 RMCARD302/RMCARD303 Intelligent Remote Management Card allows a UPS system/environment sensor to be managed, monitored, and configured Version 1.6
Contents Introduction--1 Product Description.................................. 1 Access Procedures................................... 3 How to Recover from a Lost Password..................... 6 Upgrading
T3 Mux M13 Multiplexer User Manual [Type the abstract of the document here. The abstract is typically a short summary of the contents of the document. Type the abstract of the document here. The abstract
RS-232/422/485 to 10/100Base-TX Device Server / Managed Media Converter (IRF-633) User s Manual COPYRIGHT All rights reserved. No part of this publication may be reproduced, stored in a retrieval system,
Powerware Series Eaton ConnectUPS Web/SNMP Card User's Guide X, BD, and E Models FCC Part 15 Class B EMC Statements NOTE This equipment has been tested and found to comply with the limits for a Class B
Network Management Card AP9617 AP9618 AP9619 Installation and Quick-Start Manual This manual is available in English on the enclosed CD. Dieses Handbuch ist in Deutsch auf der beiliegenden CD-ROM verfügbar.
Altenergy Power System Energy Communication Unit (ECU) Installation and User Manual (For ECU-3 V3.8) ALTENERGY POWER SYSTEM INC. All rights reserved TABLE OF CONTENTS 1.0 Introduction... 2 2.0 Installation...
Prestige 202H Plus ISDN Internet Access Router Quick Start Guide Version 3.40 12/2004 Table of Contents 1 Introducing the Prestige...3 2 Hardware Installation...4 2.1 Rear Panel...4 2.2 The Front Panel
Chapter 1 Configuring Internet Connectivity This chapter describes the settings for your Internet connection and your wireless local area network (LAN) connection. When you perform the initial configuration
SOHO 6 Wireless Installation Procedure Windows 95/98/ME with Internet Explorer 5.x & 6.0 Before You Begin Before you install the SOHO 6 Wireless, you must have: A computer with a 10/100BaseT Ethernet card
Contents Introduction--1 Product Description.................................. 1 Access Procedures................................... 3 How to Recover from a Lost Password..................... 6 Upgrading
mysensors Information to Users mysensors Wireless Sensors and Ethernet Gateway Quick Start Guide This equipment has been tested and found to comply with the limits for a Class B digital devices, pursuant
Remote Management Card RMCARD202 / RMCARD203 RMCARD302 / RMCARD303 User s Manual Version 2.0 The Remote Management Card allows a UPS system and environmental sensor to be managed, monitored, and configured.
Prestige 324 Intelligent Broadband Sharing Gateway Version V3.61(JF.0) May 2004 Quick Start Guide 1 1 Introducing the Prestige The Prestige is a broadband sharing gateway with a built-in four-port 10/100
LevelOne WAP - 0005 108 Mbps Wireless Access Point User s Manual TABLE OF CONTENTS CHAPTER 1 INTRODUCTION... 1 Features of your Wireless Access Point... 1 Package Contents... 3 Physical Details... 3 CHAPTER
Management Software AT-S84 User s Guide For the AT-9000/24 Layer 2 Gigabit Ethernet Switch Version 1.1 613-000368 Rev. B Copyright 2006 Allied Telesyn, Inc. All rights reserved. No part of this publication
FWS WiTDM Series KWA-O8800-I User Manual Date: 2009 / 04 / 23 Version: 1.0 1 Copyright This user s manual and the software described in it are copyrighted with all rights reserved. No part of this publication
MasterSwitch Power Distribution Unit AP9211 AP9212 AP9217 AP9218 User s Guide Contents MasterSwitch Power Distribution Unit Introduction................................. 1 Product Description.............................