3 Content 3 Table of content Kapitel 1 Security Advise 5 Kapitel 2 Description 5 Kapitel 3 Hardware Content of delivery Connections Installation 7 Kapitel 4 Configuration DHCP Network settings with GBL_Conf Configuration via webinterface Configuration - Power Ports Configuration - IP address Configuration - IP ACL Configuration - HTTP Configuration - Messages Configuration - SNMP Configuration - SNMP Trap Receiver List Configuration - Syslog 17 Kapitel 5 Operation Switching at the device Switching by Webinterface Switching Batchmode Switching via serial interface Sensor 19 Kapitel 6 Features Bootloader mode Firmware update Technical information Fabrique settings 21
4 Content 4 Kapitel 7 Support 22 Kapitel 8 Declarations of conformity Gude Analog- und Digitalsysteme GmbH
5 1 Security Advise 5 Security Advise The device must be installed only by qualified personnel according to the following installation and operating instructions. The manufacturer does not accept responsibility in case of improper use of the device and particularly any use of equipment that may cause personal injury or material damage. The device contains no user-maintenable parts. All maintenance has to be performed by factorytrained service personnel. Check if the power cord, the plug and the socket are in proper condition. The device can be connected only to 230V AC (50 or 60 Hz) sockets. Always connect the device to properly grounded power sockets. The device is intended for indoor use only. Do NOT install them in an area where excessive moisture or heat is present. Because of safety and approval issues it is not allowed to modify the device without our permission. Please note the safety advises and manuals of connected devices, too. The device is NOT a toy. It has to be used or stored out or range of children. Packaging material is NOT a toy. Plastics has to be stored out of range of children. Please recycle the packaging materials. In case of further questions, about installation, operation or usage of the device, which are not clear after reading the manual, please do not hesitate to ask our support team. 2 Description The Remote Power Switch Expert Power Control NET 8x 8210 / 8211 allows the switching of electrical devices via a TCP/IP network and a serial interface. For installation just connect the power and network cables to Expert Power Control NET 8x 8210 / After the device has received an IP address every client in the same network is able to switch the four Power Ports (max. 10 A) via webinterface. Expert Power Control NET 8x 8210 / 8211 offers also features like SNMP and Syslog. Additional Expert Power Control NET 8x 8210 / 8211 can be controlled via a serial connection. A temperature sensor and a hybrid sensor (temperature and humidity) can be connected to Expert Power Control NET 8x 8210 / A watchdog function for each power port is implemented. The display on the front is able to show the IP address, the recent total load, the peak current (timeframe adjustable) and the measurements of the sensors. Furthermore the access to the device can be restricted by IP access control lists and a HTTP password.
6 3 3.1 Hardware Content of delivery Included in delivery are: Expert Power Control NET 8x 8210 / 8211 Power supply cable (IEC) CD-ROM including Software and Manual Short manual Description 6
7 3.2 Hardware 7 Connections Connections Expert Power Control NET 4x 8212 Connections Expert Power Control NET 4x ) Power Port LEDs 2) Buttons "select" and "ok" 3) Status LED 4) Aux connector for serial interface (RS232-PS2 cable) or Sensor 5) TEMP connector for Sensor 6) Ethernet connector (RJ45) 7) Display 8) 8 Power Ports (IEC C13, max. 10A) 9) Power supply (IEC C20, max. 16A) 3.3 Installation 1.) Connect the power supply cable to the power socket at the rear side (Expert Power Control NET 4x 8212) or front side ( Expert Power Control NET 4x 8213 ) of Expert Power Control NET 8x 8210 / 8211 and a socket. Expert Power Control NET 8x 8210 / 8211 now is booting and shortly after ready for usage. 2.) Plug the Ethernet cable into the connector on the front side of Expert Power Control NET 8x 8210 / 8211 and connect it to your Ethernet. 3.) Connect the clients to the Power Ports at the rear side (Expert Power Control NET 4x 8212) or front side (Expert Power Control NET 4x 8213 ) of the device.
8 4 4.1 Hardware 8 Configuration DHCP After switch-on Expert Power Control NET 8x 8210 / 8211 looks for a DHCP server and requests an available IP address. Please check the IP address allocated to Expert Power Control NET 8x 8210 / 8211 in the DHCP server settings to make sure that the same address is used at every reboot. 4.2 Network settings with GBL_Conf For changing the network properties manually, the program GBL_Conf.exe is required. This tool is available for free on our website Furthermore GBL_Conf.exe enables you to install firmware updates and to reset Expert Power Control NET 8x 8210 / 8211 to its factory settings. Activate bootloader mode of Expert Power Control NET 8x 8210 / 8211 and run GBL_Conf.exe. The program will look automatically for connected devices and will display their network configuration. If the displayed IP address accords with the factory settings ( ), there is either no DHCP server available in the network or no free IP address could be allocated. Enter a free IP address and the according netmask in the entry mask, then save these changes by clicking on Program Device SaveConfig. Restart the firmware of Expert Power Control NET 8x 8210 / 8211, so that the changes will take effect. Now click on Search in order to have the new network configuration displayed.
9 4.3 Configuration 9 Configuration via webinterface Go to the website of Expert Power Control NET 8x 8210 / Enter the IP address of Expert Power Control NET 8x 8210 / 8211 into the address line of your internet browser: IP address of Expert Power Control NET 8x 8210 / 8211 / and press LOGIN. To enter the configuration menu, click on Configuration on the upper left side of the screen Configuration - Power Ports
10 Configuration 10 Label A name with a maximum of 15 characters can be entered here for each Power Port After power-up switch The Power Port s switching state after a power-on of the device can be defined here (on, off, remember last state) If switching on after power-up, wait... A switching delay of a Power Port can be defined here that is applied after switch on of the device. The delay can last up to 8191 seconds After turning off, wait... While this function is enabled, the Power Port will reactive after the stated time, when it got switched off Watchdog While using the watchdog, electrical devices can be observed. The watchdog sends ICMP-pings or TCP-pings to the device. If these pings were not answered, during a defined delay (time or pings), the power port will reset. The watchdog function allows to restart e.g. crashed servers or NAS systems. You can check the watchdog function and other imformation inside of the switching menu. There are different colors: Green text: Watchdog is active and receives ping replies Orange text: Watchdog is activating at the moment, waiting for first ping reply Red text: Watchdog is active and does not receive ping replies any longer When watchdog is activating it waits of a first ping reply. During this time, the information is written as an orange text. After the receive of the first ping reply, it switches to active, written in green letters.
11 Configuration When a watchdog reset a power port, the watchdog again waits for a first ping reply, as stated above Enable Watchdog Here you can activate the watchdog for this power port Watchdog type Here you can switch between ICMP ping or TCP ping Host IP Here you can enter the IP address this watchdog should observe TCP Port If TCP pings are used, here you can enter the TCP port. A TCP port is not needed, when ICMP pings are choosen Ping interval Here you can enter the time between two pings Ping retry Here you can enter how often the ping should be repeated, before a power port reset will be done. 11
12 4.3.2 Configuration - IP address Hostname Configuration 12 Enter the host name of Expert Power Control NET 8x 8210 / Expert Power Control NET 8x 8210 / 8211 uses this name to connect with DHCP server. Special signs may destabilize your network. All changes need a restart of the firmware to get valid IP Address Here you can change the IP address of Expert Power Control NET 8x 8210 / All changes need a restart of the firmware to get valid Netmask Here you can change the netmask of Expert Power Control NET 8x 8210 / All changes need a restart of the firmware to get valid Gateway Here you can change the standard gateway of Expert Power Control NET 8x 8210 / All changes need a restart of the firmware to get valid Use DHCP Here you can set, if Expert Power Control NET 8x 8210 / 8211 shall get its TCP/IP settings directly from your DHCP server. If DHCP is activated, Expert Power Control NET 8x 8210 / 8211 proves if a DHCP server is active inside of your LAN. Then Expert Power Control NET 8x 8210 / 8211 requests TCP/IP settings from this server. If there is no DHCP server inside of your network, we recommend to deactivate this function. All changes need a restart of the firmware to get valid.
13 4.3.3 Configuration 13 Configuration - IP ACL IP Access Control List (IP ACL) acts as an IP filter for your Expert Power Control NET 8x 8210 / Wether it is active hosts and subnets only can contact Expert Power Control NET 8x 8210 / 8211, if their IP adresses are stated in this IP ACL. e.g.: or If you locked yourself out by mistake, please activate the bootloader mode of Expert Power Control NET 8x 8210 / 8211, start Gbl_Conf.exe and deactivate IP ACL. You can find more information about configuration of IP ACL or have a look at Reply ICMP-Ping requests Here you can set, if Expert Power Control NET 8x 8210 / 8211 shell react on pings Enable IP Filter Here you can activate the IP Access Control List (IP ACL) of Expert Power Control NET 8x 8210 / If IP ACL is active, DHCP and SNMP only work, if all necessary servers and clients are registered in this list Configuration - HTTP
14 Configuration 14 HTTP Port Here you can enter the HTTP port number, if necessary. Possible numbers are (standard: 80). To get access to Expert Power Control NET 8x 8210 / 8211, you have to enter the port number behind the IP address of Expert Power Control NET 8x 8210 / 8211, e.g.: All changes need a restart of the firmware to get valid Require HTTP Password Password protected access can be activated here. In this case, a user and an admin password have to be defined. Passwords have a maximum lengths of 15 characters. Administrators are authorized to switch all ports and to modify the settings of Expert Power Control NET 8x 8210 / 8211 and of all ports. The username of the admin is admin. Users are authorized to switch all ports but are not allowed to modify the settings of neither Expert Power Control NET 8x 8210 / 8211 nor the ports. The username of the user is user. If you have forgotten your password, activate the bootloader mode of Expert Power Control NET 8x 8210 / 8211, start GBLConf.exe and deactivate the password request. All changes need a restart of the firmware to get valid Check Password on start page If activated, the user has to enter his password, before logging in to the webinterface Configuration - Messages Generate Temperature Messages Here you can configure if and at which Min-/Max-Temperature Expert Power Control NET 8x 8210 / 8211 shell send temperature alerts via SNMP-Traps and Syslog Max Temperature Here you can define the maximum temperature, if the sensor measures this temperature the device will generate an alert via SNMP and Syslog.
15 Configuration 15 Min. Temperature Here you can define the minimum temperature, if the sensor measures this temperature the device will generate an alert via SNMP and Syslog Configuration - SNMP SNMP To get detailed status information of Expert Power Control NET 8x 8210 / 8211 SNMP can be used. SNMP communicates via UDP (port 161) with Expert Power Control NET 8x 8210 / 8211: You can use SNMP to switch the power ports as well. Supported SNMP commands: - SNMPGET: request status information - SNMPGETNEXT: request the next status information - SNMPSET: Expert Power Control NET 8x 8210 / 8211 request change of status You will need a Network Management System, e.g. HP-Open View, OpenNMS, Nagios etc., or the command line tools of NET-SNMP to request information of Expert Power Control NET 8x 8210 / 8211 via SNMP SNMP-communities SNMP authentifies requests by so called communities. The public community has to be added to SNMP-read-requests and the private community to SNMP write requests. You can see the SNMP communites like read/write passwords. SNMP v1 and v2 transmit the communities without encryption. Therefore it is simple to spy out these communities. We recommend to use a DMZ or IP ACL MIB All information, that can be requested or changed, the so called Managed Objects, are descripted in Management Information Bases (MIBs). There are three MIBs, which can be requested from Expert Power Control NET 8x 8210 / 8211: system, interface and powerports system and interface are standardised MIBs (MIB-II). powerports (GUDEADS-EPC-MIB::gadsEPC) was created especially for Expert Power Control NET 8x 8210 / At least, there are so called Object Identifiers (OID) subordinated to those three structures. An OID describes the location of an information inside a MIB SNMP-traps SNMP-Traps are system messages, sent via SNMP-protocol to different clients. On following events, Expert Power Control NET 8x 8210 / 8211 will dispatch a SNMP-Trap: Switching of the Power Ports Min/Max-Alerts from the sensors You can find more information about configuration of SNMP at
16 Configuration 16 Enable SNMP-get Here you can activate SNMP-get protocol of Expert Power Control NET 8x 8210 / Use SNMP only if your network is fitted for Community public Here you can enter the SNMP public community. Use SNMP only if your network is fitted for Enable SNMP-set Here you can activate SNMP-set protocol of Expert Power Control NET 8x 8210 / Use SNMP only if your network is fitted for Community private Here you can enter the SNMP private community. Use SNMP only if your network is fitted for Download SNMP MIB Here you can download the MIBs of Expert Power Control NET 8x 8210 / Use SNMP only if your network is fitted for Configuration - SNMP Trap Receiver List Enable Traps Here you can activate SNMP-traps. if enabled, Expert Power Control NET 8x 8210 / 8211 will dispatch SNMP-traps to all receivers listed. Receivers have to be listed as follows: IP address (and, if necessary the HTTP port), e.g.: :8000 Use SNMP only if your network is fitted for.
17 Configuration 17 Trap Version Here you can choose between SNMP-traps standard v1 and v2c. Use SNMP only if your network is fitted for. More information about the SNMP functions of Expert Power Control NET 8x 8210 / 8211, you can find in chapter SNMP, on or ask our support team Configuration - Syslog Syslog messages are simple text messages transmitted to a syslog server using UDP. Linux OS regularly have a syslog daemon installed, e.g. syslog-ng. For Windows there are some freeware tools available. On following events, Expert Power Control NET 8x 8210 / 8211 will send a syslog message: - Booting up - Activation/deactivation of syslog - Switching of Power Ports You can find more information about configuration of Syslog in chapter Configuration - Syslog or have a look at gude.info/wiki Enable Syslog Here you can activate Syslog of Expert Power Control NET 8x 8210 / Syslog Server IP If syslog is active enter here the IP address of you Syslog server Syslog Port If syslog is active enter here the port number, that your Syslog server uses to receive syslog information. More information about Syslog you can find in chapter Syslog, on or ask our support team.
18 5 5.1 Configuration 18 Operation Switching at the device Expert Power Control NET 8x 8210 / 8211 disposes of two buttons: select and ok. By pushing select, the LED of Power Port 1 starts blinking which means that it is selected. By pushing the button again, the next Power Port is selected. If you want to change the switching state of the selected Power Port, push the ok button for two seconds. You can check the status of the Power Ports by the color of the Power Port status LED (green=enabled/red=disabled). 5.2 Switching by Webinterface Go to the website of Expert Power Control NET 8x 8210 / Enter the IP address of Expert Power Control NET 8x 8210 / 8211 into the address line of your internet browser: IP address of Expert Power Control NET 8x 8210 / 8211 / and press LOGIN Switching Here you are able to switch the ports directly. You can check the status of the Power Ports by the color of the Power Port status LED (green=enabled/red=disabled) Batchmode Each Power Port of Expert Power Control NET 8x 8210 / 8211 can be switched on or switched off for a selectable delay (130 sec. or 1-30 min.). After the chosen delay the selected port will be switched off or switched on again auto-matically. Optionally the device can be accessed by using the perl script EPC_Control2.pl through the command line (e.g. for automatic or time-triggered switching). For more information please refer to our website: 5.3 Switching via serial interface Alternatively to the Ethernet interface, the Power Ports of Expert Power Control NET 8x 8210 / 8211 can be switched through its serial interface. It only requires a terminal program like HyperTerminal, a program provided under Windows for free (to be found under Programs -> Accessories -> Communication). Connect your PC with Expert Power Control NET 8x 8210 / 8211 by a 9-pole serial cable (RS232) and plug the device into a outlet. Now you can turn on Expert Power Control NET 8x 8210 / The boot process lasts a few seconds longer than by Ethernet.
19 Operation 19 You can access Expert Power Control NET 8x 8210 / 8211 through the terminal program as soon as the status LED shines green. Choose the COM port that is connected to Expert Power Control NET 8x 8210 / 8211 and enter the following values for the serial interface: Bits per seconds Data bits Parity Stop bits Flow control none 1 none If you do not use HyperTerminal, please make sure that the terminal program supports VT100 commands. After having it connected successfully, Expert Power Control NET 8x 8210 / 8211 answers as shown in figure below. Press Enter for login. Now the Power Ports can be switched on and off per number keys. By pressing c you can check the network configuration and by pressing Esc you can log out. 5.4 Sensor Connect the temperature sensor with the TEMP and AUX connector at the front of the device. If it is connected exactly, the recent temperature is displayed in the login window, in the switching window and can be requested via SNMP. The temperature sensor can be ordered as additional supplies. More information can be found at or requested at Temperature sensor 7001
20 Operation Hybrid sensor 7002 Temperature sensor 7001 Cable length 2m Connection PS2 Measurement -10 C bis +70 C bei ±2 C (maximal) und ±1 C (typisch) Cable length 2m Connection PS2 Measurement (-40 bis +80 Grad, +- 0,5Grad/ Feuchte 0-100% +-3%) Hybrid sensor
21 6 6.1 Operation 21 Features Bootloader mode To activate the bootloader mode of Expert Power Control NET 8x 8210 / 8211 the select button must be pushed while restarting the device. In bootloader mode it is possible to disable the password protection, to update the firmware and to restore the default settings by running the program GBL_Conf.exe. If the device runs already, press the buttons "select" and "ok" for three seconds. The bootloader mode of Expert Power Control NET 8x 8210 / 8211 is indicated by BOOT-LDR appended to the device name in the program window of GBL_Conf. exe. During bootloader mode an alteration of the relais is not possible. To restart the firmware, without toggle the Power Ports, press the buttons select and ok for three seconds again. 6.2 Firmware update In order to update the firmware the program GBL_Conf.exe and the latest firmware are needed. Start the device in bootloader mode and run the program GBL_Conf.exe. On the left side of the program window all Gude devices that are in the network are listed. Select the device, that should be updated, click on Program DeviceFirmware Update and determine the location of the new firmware. Please note: The up-to-date firmware and GBL_Conf.exe can be found at free to download. 6.3 Technical information Connections: Network: Protocols: Switched Power (total): Switched Power (per port): Power supply: Operating temperature: Dimensions: Total weight: x Ethernet (RJ45) 2 x PS2 Connector 4 x Power Ports (IEC C13, max. 10A) 1 x Power supply inlet (IEC C20, max. 16A) 10/100 MBit/s 10baseT Ethernet TCP/IP, HTTP, SNMP v1 und v2c, SNMP traps, Syslog 16 A (~ 3600W) 10 A (~ 2000W) IEC C20 (16A, 230V AC) 0 C-50 C 19 / 1 rack unit ca. 1,5 kg Fabrique settings In order to restore the default settings the device must be started in bootloader mode. Besides that the program GBL_Conf. exe is required. Run GBL_Conf.exe and select the device whose settings should be restored. Then click on Program Device -> Reset to Fab default. Please notice that all current settings will be deleted. The default settings will be loaded when the firmware of the device is restarted the next time.
22 7 Features 22 Support More information, current drivers and software can be found on In case of further questions, about installation or operation of Expert Power Control NET 8x 8210 / 8211, please have look at or do not hesitate to contact our support
23 8 Declarations of conformity Declarations of conformity 23
Metering PDU Manual DN-95601 DN-95602 Safety Advice The device must be installed only by qualified personnel according to the following installation and operating instructions. The manufacturer does not
Contents of Package: DG-102S VoIP Station Gateway Power adapter CD-ROM, including User s Manual Quick Install Guide Requirements: RS-232 Console Cable Two RJ-45 CAT-5 Straight-Through Cables For more information
IP Sensor and Watchdog IPSW2210 Manual Relay Output Power input 12VDC adapter LED Indicators 1 wire 2 Dry Output Green : Power Yellow: Link temperature & humidity contact inputs LED indicator sensor input
IP Power Stone 4000 User Manual Two Outlet Remote AC Power Controller Multi Link, Inc. 122 Dewey Drive Nicholasville, KY 40356 USA Sales and Tech Support 800.535.4651 FAX 859.885.6619 techsupport@multi
Power Switch-8 Power Management Master Slave User's Guide V.02/2004 Power Switch-8 Power Switch-8 is a couple of power control units made of a Master named Power Switch Master and a slave named Power Switch
PURPOSE Verify that communication is established for the following products programming option (488.2 compliant, SCPI only): DCS - M9C & DCS M130, DLM M9E & DLM-M9G & DLM M130, DHP - M9D, P series, SG,
User Manual EtherUSB USB Ethernet Access Point for PDA V 2.0 Clarinet Systems, Inc. Clarinet Systems, Inc. http://www.clarinetsys.com Page 1 Publication Revision No. Control Table Rev. No. Date Contents
MODEL ATC-2004 TCP/IP TO RS-232/422/485 CONVERTER User s Manual 1.1 Introduction The ATC-2004 is a 4 Port RS232/RS485 to TCP/IP converter integrated with a robust system and network management features
SNMP Web card User s Manual Management Software for Uninterruptible Power Supply Systems Table of Contents 1. Overview... 3 1.1 Introduction... 3 1.2 Features... 3 1.3 Overlook... 3 1.4 Installation and
Prestige 314 Read Me First Console WAN 10M PORT Prestige Rear Panel Connections CONNECTION Use an RS-232 console cable. Use the cable that came with your broadband modem. LAN 10/100M Port Number COMPUTER
Panduit Corp. 2010 TDP43ME NetPS PA26306A01 Rev. 01 11-2010 Network Printer Server Control Center for Ethernet Module NOTE: In the interest of higher quality and value, Panduit products are continually
SNMP-1 Configuration Guide You must configure the Net Logic Card before it can operate properly. You have two methods to configure the Net Logic Card: Using telnet or terminal. Using Telnet 1. Make sure
Energy Intelligence Solutions PE6108/PE6208/PE8108/PE8208 eco PDU Distribution Unit ATEN has developed a new generation of green energy power distribution units (PDUs) to effectively increase the efficiency
Wireless Router Setup Manual NETGEAR, Inc. 4500 Great America Parkway Santa Clara, CA 95054 USA 208-10082-02 2006-04 2006 by NETGEAR, Inc. All rights reserved. Trademarks NETGEAR is a trademark of Netgear,
Prestige 660R-6x Read Me First Prestige Rear Panel Connections DSL PORT CONNECTION Connect the DSL port on the Prestige to the wall jack using the included DSL cable (telephone wire). Connect the micro
Prestige 324 Intelligent Broadband Sharing Gateway Version V3.61(JF.0) May 2004 Quick Start Guide 1 1 Introducing the Prestige The Prestige is a broadband sharing gateway with a built-in four-port 10/100
Internet connection with NAT...2 Internet connection with No NAT, IP Un-number...6 Port Forwarding...12 Filtering & Firewall Setup...20 Access Control... 21 DMZ Setup... 26 Allow Incoming Ping... 27 How
Prestige 324 Intelligent Broadband Sharing Gateway Version 3.60 January 2003 Quick Start Guide 1 Introducing the Prestige The Prestige is a broadband sharing gateway with a built-in four-port 10/100 Mbps
Prestige 650R-31/33 Read Me First Prestige Rear Panel Connections PORT DSL CONSOLE LAN 10/100M POWER Connect to a telephone jack using a telephone wire. CONNECTION Connect to a serial port (COM port) on
MAX T1/E1 TM VoIP Gateway Quick Start Guide Version 1.0 Contents INTRODUCTION 1 Hardware Needed Software Needed 1 1 NET2PHONE MAX SET UP Hardware Set Up Software Set Up Set Up Internet Protocol (IP) Address
MODEL ATC-2000 TCP/IP TO RS-232/422/485 CONVERTER User s Manual 1.1 Introduction The ATC-2000 is a RS232/RS485 to TCP/IP converter integrated with a robust system and network management features designed
NetProbe Lite Web Based 8 Channel Sensor Collector User Manual Version 1.2 Copyright Information Copyright 2004-2005, Mega System Technologies, Inc. All rights reserved. Reproduction without permission
SNMP Web Management User s Manual For SNMP Web Card/Box Management Software for Off-Grid Inverter Version: 1.2 Table of Contents 1. Overview... 1 1.1 Introduction... 1 1.2 Features... 1 1.3 Overlook...
User s Manual UPS SERIES Network Interface Card UPS-IPCARD I-00453 Rev B TABLE OF CONTENTS INTRODUCTION............................................................. 3-4 INSTALLATION GUIDE.......................................................
Model: CRMWIC Web Intelligent Controller 1 This document will illustrate various ways to connect and use a CRM-WIC as well as programming examples. When connecting CRM-WIC, the installer has several interface
Olson Electronics Remote Power Monitoring Meter Operation Guide Key Features Amps: 00.00 to 32.00A True RMS (rated short period to 40A) Volts: 200.0 to 250.0V True RMS Watts: 0000 to 9999W KWh: 000000.0
Network Guide PREFACE Every effort has been made to ensure that the information in this document is complete, accurate, and up-to-date. The manufacturer assumes no responsibility for the results of errors
Contents Introduction--1 Product Description.................................. 1 Access Procedures.................................... 3 How to Recover From a Lost Password..................... 6 Upgrading
Powerware Environmental Rack Monitor User s Guide FCC Part 15 Class B EMC Statements NOTE This equipment has been tested and found to comply with the limits for a Class B digital device, pursuant to part
Chapter 6 Using Network Monitoring Tools This chapter describes how to use the maintenance features of your RangeMax Wireless-N Gigabit Router WNR3500. You can access these features by selecting the items
Prestige 202H Plus ISDN Internet Access Router Quick Start Guide Version 3.40 12/2004 Table of Contents 1 Introducing the Prestige...3 2 Hardware Installation...4 2.1 Rear Panel...4 2.2 The Front Panel
Broadband Router ESG-103 User s Guide FCC Warning This equipment has been tested and found to comply with the limits for Class A & Class B digital device, pursuant to Part 15 of the FCC rules. These limits
Copyright Statement is the registered trademark of Shenzhen Tenda Technology Co., Ltd. Other trademark or trade name mentioned herein are the trademark or registered trademark of above company. Copyright
DAP-1360 Wireless N 300 Access Point & Router BEFORE YOU BEGIN Delivery Package Access point DAP-1360 Power adapter DC 12V Ethernet cable (CAT 5E) (brochure). If any of the items are missing, please contact
Broadband Phone Gateway BPG510 Technical Users Guide (Firmware version 0.14.1 and later) Revision 1.0 2006, 8x8 Inc. Table of Contents About your Broadband Phone Gateway (BPG510)... 4 Opening the BPG510's
SecureLinx Spider Duo Quick Start Guide SecureLinx Spider Duo Quick Start Guide SecureLinx Spider Duo QUICK START GUIDE CONTENTS Overview... 2 What s In The Box... 3 Installation and Network Settings...
OvisLink OV804WVA Quick Installation Guide 1 Indicators and Interfaces 1.1 Front Panel LED Color Status Description Power Red DSL Internet Red WAN LAN4-1 Off Power off. The initialization is normal. Initiating.
CS 326e F2002 Lab 1. Basic Network Setup & Ethereal Time: 2 hrs Tasks: 1 (10 min) Verify that TCP/IP is installed on each of the computers 2 (10 min) Connect the computers together via a switch 3 (10 min)
Load Balancer LB-2 User s Guide TABLE OF CONTENTS 1: INTRODUCTION...1 Internet Features...1 Other Features...3 Package Contents...4 Physical Details...4 2: BASIC SETUP...8 Overview...8 Procedure...8 3:
User s Manual Network Management Card RMCARD202 Intelligent Network Management Card allows a UPS system to be managed, monitored, and configured Version 1.0 E-K01-SNMP005-0 TABLE OF CONTENTS Introduction
UPS Network Interface Quick InstallationGuide Version 1.1 March 1999 COPYRIGHT Copyright 1999 RINGDALE UK Limited. All rights reserved. No part of this publication may be reproduced, transmitted, transcribed,
User Manual EtherUSB USB Ethernet Access Point for PDA V 1.6 Page 1 Publication Revision No. Control Table Rev. No. Date Contents 1.6 8/22/07 Support connection of multiple WM5.0 devices 1.5 6/18/07 Support
Debugging Network Communications Situation: you have a computer and your NetBurner device on a network, but you cannot communicate between the two. This application note provides a set of debugging steps
3.5 LAN HDD Enclosure User s Manual NOTE: 1. USB and LAN can t be used at the same time. 2. HDD should be formatted as FAT32. Please check Disk utility section in this manual. 3. For internet FTP usage,
Installing the RDSP-3000A-NIST Master Clock. Ethernet Connect the RJ-45 connector to a TCP/IP network. Equipment The following equipment comes with the clock system: RDSP-3000A-NIST Master Clock Module.
Dominion PX Question General Questions What is Dominion PX (PX)? Is Raritan new to the rack power distribution unit market? Can the PX be used as a stand-alone device? Does PX work with Raritan s CommandCenter
Chapter 7 Troubleshooting This chapter provides information about troubleshooting your Wireless-G Router Model WGR614v9. After each problem description, instructions are provided to help you diagnose and
3G/EDGE Super Modem/Router User s Guide Version: 1.0 Date: October 28, 2009 3JTech Co., Ltd. 2F, No. 342, Fu-Shing N. Rd. Taipei, Taiwan Tel: +886-2-2500 6916 e-mail: firstname.lastname@example.org Revision History
Nokia Siemens Networks CPEi-lte 7212 User Manual Contents Chapter 1: CPEi-lte 7212 User Guide Overview... 1-1 Powerful Features in a Single Unit... 1-2 Front of the CPEi-lte 7212... 1-2 Back of the CPEi-lte
Chapter 4 Management This chapter describes how to use the management features of your NETGEAR WG102 ProSafe 802.11g Wireless Access Point. To get to these features, connect to the WG102 as described in
the following parts are needed to test the unit: Arduino UNO R3 Arduino Wifi shield And reciever 5V adapter Connecting wifi module on shield: Make sure the wifi unit is connected the following way on the
T3 Mux M13 Multiplexer User Manual [Type the abstract of the document here. The abstract is typically a short summary of the contents of the document. Type the abstract of the document here. The abstract
CPEi 800/825 Series User Manual * Please see the Introduction Section Contents Introduction...iii Chapter 1: CPEi 800/825 User Guide Overview... 1-1 Powerful Features in a Single Unit... 1-2 Front of the
This product can be set up using any current web browser, i.e., Internet Explorer 6 or Netscape Navigator 6.2.3. DVG-2101SP VoIP Telephone Adapter Before You Begin 1. If you purchased this VoIP Telephone
Chapter 3 Management This chapter describes how to use the management features of your ProSafe 802.11a/g Dual Band Wireless Access Point WAG102. To access these features, connect to the WAG102 as described
KRAMER ELECTRONICS LTD. USER GUIDE Ethernet Configuration Guide (Lantronix) P/N: 2900-300321 Rev 6 Contents 1 Connecting to the Kramer Device via the Ethernet Port 1 1.1 Connecting the Ethernet Port Directly
DSL-2500U ADSL/Ethernet Router BEFORE YOU BEGIN Delivery Package Router DSL-2500U Power adapter RJ-11 telephone cable Straight-through Ethernet cable (CAT 5E) Splitter CD-ROM with User Manual and (brochure)
Setup Manual and Programming Reference Stanford Research Systems Revision 1.05 (11/2010) Certification Stanford Research Systems certifies that this product met its published specifications at the time
Network Power Manager User Manual Table of Contents 1. Introduction... 1 2. PDU Package... 2 3. Function... 3 4. Installation... 4 5. Web Interface... 5 1. Introduction The PDU is an Internet ready device
Kramer Electronics, Ltd. Site-CTRL and Web Access Online User Guide (Documentation Revision 2) Software Version 1.9. 2902 To check that you have the latest version, go to the DOWNLOADS section of our Web
(VoIP) Configuration ENGINEERING REPORT No: 02-003 Introduction This report describes interfacing the IPCS VoIP Gateway Model EGW-902 to an ESTeem Model 192E Wireless Ethernet radio modem in a demonstration
User Manual Welcome Unleash Your Phone For assistance with installation or troubleshooting common problems, please refer to this User Manual or Quick Installation Guide. Please visit www.vonage.com/vta
Chapter 7 Using Network Monitoring Tools This chapter describes how to use the maintenance features of your RangeMax NEXT Wireless Router WNR854T. These features can be found by clicking on the Maintenance
Dominion KX II-101-V2 Quick Setup Guide Thank you for your purchase of the Dominion KX II-101-V2, the economical, full-featured, single-port digital KVM-over-IP device. For details on using the KX II-101-V2,
DRO-210i LOAD BALANCING ROUTER Review Package Contents Make sure that the package contains the following items. DRO-210i Load Balancing Router 2 Straight Ethernet Cables 1 Cross Over Ethernet Cable 1 Power
Contents Introduction--1 Product Description....................................... 1 Access Procedures....................................... 3 Recover From a Lost Password..............................
0 P a g e Table of contents Front LEDs... 2 Rear Ports... 3 BASIC INSTALLATION... 4 Connecting Your Router... 5 Network Configuration... 6 Gateway Configuration... 11 Accessing your gateway... 11 Displaying
NeoGate TA Series Installation Guide Version 1.2 Date: April 1, 2015 Yeastar Information Technology Co. Ltd Contents 1. Preparation before Installation... 3 2. Hardware Specifications... 5 2.1 Overview...
Setting up Digi Connect Wi-SP or Digi ConnectPort TS W Devices On a Secured Wireless Network for use with Veriteq viewlinc Contents Before You Start the Installation...2 Introduction...2 Veriteq vnet and
Innovative Electronics for a Changing World INDEX 1. SYSTEM DESCRIPTION 2. BOARD CONNECTIONS terminals and indicators 3. CONNECTION DIAGRAM 4. START UP GUIDE and passwords 5. HOME PAGE 6. STATUS PAGE 7.
Problem: Patton / 240T WAN Setup Platform: NetGuardian 240T This TKP is a guide to setting up a PPP to T1 WAN connection between a Patton Model 2603 Router and a NetGuardian 240T. The example in this guide
Chapter 7 Troubleshooting This chapter provides troubleshooting tips and information for your ProSafe VPN Firewall 200. After each problem description, instructions are provided to help you diagnose and
NMS300 Network Management System User Manual June 2013 202-11289-01 350 East Plumeria Drive San Jose, CA 95134 USA Support Thank you for purchasing this NETGEAR product. After installing your device, locate