1 GUIDELINES FOR HANDLING WATER-DAMAGED ELECTRICAL EQUIPMENT NATIONAL ELECTRICAL MANUFACTURERS ASSOCIATION 1300 NORTH 17 TH STREET, SUITE 1752 ROSSLYN, VIRGINIA FAX
2 Guidelines for Handling Water-damaged Electrical Equipment NOTICE AND DISCLAIMER Please see the last page of this document. Use of this Publication This publication provides guidelines on how to handle electrical equipment that has been exposed to water through flooding, fire fighting activities, hurricanes, etc. It is designed for use by suppliers, installers, inspectors, and users of electrical products. Electrical equipment exposed to water can be extremely dangerous if reenergized without proper reconditioning or replacement. Reductions in integrity of electrical insulation due to moisture, debris lodged in the equipment components, and other factors, can damage electrical equipment by affecting the ability of the equipment to perform its intended function. Damage to electrical equipment can also result from flood waters contaminated with chemicals, sewage, oil, and other debris that will affect the integrity and performance of the equipment. Ocean water and salt spray can be particularly damaging due to the corrosive and conductive nature of the salt water residue. Distributors of electrical equipment should not use any inventory that has been subjected to water damage. Damaged inventory should not be sold to resellers that will place the equipment back into the market. This can lead to damaged equipment still being used and creating a hazard to individuals or property. To Contact the Manufacturer Working knowledge of electrical systems and of the equipment in question is required to evaluate damage due to contact with water. The original manufacturer of the equipment should be contacted if any questions arise or specific recommendations are needed. In many cases, replacement will be necessary. After consultation with the manufacturer, some larger types of electrical equipment may be reconditioned by properly trained personnel. The ability to recondition the equipment may vary with the nature of the electrical function, the degree of flooding, the age of the equipment, and the length of time the equipment was exposed to water. Attempts to recondition equipment without consulting the manufacturer can result in additional hazards due to the use of improper cleaning agents, which can further damage the equipment (see National Electrical Code Section FPN No.2) or due to improper reconditioning techniques. NEMA member companies are committed to safety. For specific contacts within these manufacturing firms, call or write: National Electrical Manufacturers Association 1300 North 17th Street, Suite 1752 Rosslyn, Virginia Telephone: (703) Fax: (703) ATTN: Vince Baclawski
3 Electrical Distribution Equipment Electrical distribution equipment usually involves switches and low-voltage protective components such as molded case circuit breakers and fuses, within assemblies such as enclosures, panelboards, and switchboards. These assemblies can be connected to electrical distribution systems using various wiring methods. The protective components are critical to the safe operation of distribution circuits. Their ability to protect these circuits is adversely affected by exposure to water and to the minerals and particles which may be present in the water. In molded case circuit breakers and switches, such exposure can affect the overall operation of the mechanism through corrosion, through the presence of foreign particles, and through removal of lubricants. The condition of the contacts can be affected and the dielectric insulation capabilities of internal materials can be reduced. Further, some molded case circuit breakers are equipped with electronic trip units and the functioning of these trip units might be impaired. For fuses, the water may affect the filler material. A damaged filler material will degrade the insulation and interruption capabilities. Distribution assemblies contain protective components together with the necessary support structures, buswork, wiring, electromechanical or electronic relays and meters. Exposure to water can cause corrosion and insulation damage to all of these areas. In the case of exposure of distribution assemblies to water, the manufacturer should be contacted before further action is taken. Items Which May Possibly Be Reconditioned by Trained Personnel in Consultation with Enclosed switches reference NEMA Standards Publication KS , Enclosed and Miscellaneous Distribution Equipment Switches (600 Volts Maximum), para 5.1, Busway reference NEMA Standards Publication BU , General Instructions for Handling, Installation, Operation, and Maintenance of Busway Rated 600 Volts or Less, para 3.4.4, Panelboards reference Standards Publication ANSI/NEMA PB , General Instructions for Proper Installation, Operation, and Maintenance of Panelboards Rated 600 Volts or Less, para. 10.3, , Switchboards reference Standards Publication ANSI/NEMA PB , General Instructions for Proper Handling, Installation, Operation and Maintenance of Deadfront Distribution Switchboards Rated 600 Volts or Less, para , Fire Pump Controllers reference NEMA Standards Publication ICS (R2004), Instructions for the Handling, Installation, Operation, and Maintenance of Electric Fire Pump Controllers Rated Not More Than 600 V Motor Circuits Motor circuits include motor control devices such as motor starters and contactors, together with overcurrent protection components such as overload relays, circuit breakers, and fuses often assembled into motor control panels and motor control centers as well as individual enclosures. Motor control centers contain both control and protective components together with support structures, buswork, and wiring. The protective components are critical to the safe operation of motor circuits and their ability to protect these circuits is adversely affected by exposure to water, and to the minerals and particles which may be present in the water. For molded case circuit breakers, such exposure can affect the overall operation of the mechanism through corrosion, through the presence of foreign particles, and through removal of lubricants. The condition of the contacts can be affected and the dielectric insulation capabilities of internal materials can be reduced. Further, some molded case circuit breakers are equipped with electronic trip units, and the functioning of these trip units might
4 be impaired. For fuses, the water may affect the filler material. A damaged filler material will degrade the insulation and interruption capabilities. Corrosion, loss of lubrication, and insulation quality can also be expected in contactors and starters. However, solid-state motor controllers and those electromechanical contactors or starters with integral electronic circuitry will be more severely affected by water. Drives damaged by water can be remanufactured by the original manufacturer in some cases. Contact the drive manufacturer for specifics. Items Requiring Complete Replacement: Electronically controlled and solid state contactors and starters Components containing semiconductors and transistors Overload relays Molded case circuit breakers and molded case switches reference NEMA Standards Publication AB , Guidelines for Inspection and Preventive Maintenance of Molded Case Circuit Breakers Used in Commercial and Industrial Applications, para 2.2 Fuses Items Which May Possibly be Reconditioned by Trained Personnel in Consultation with Manual and magnetic motor controllers Motor control centers Power Equipment Power equipment involves low voltage or medium voltage protective devices within an overall switchgear assembly. The assembly may also contain cabling, buswork with appropriate insulators, current transformers, electromechanical or electronic relays, and metering. Reliable operation of the protective devices is vital to system safety; however, these devices can be adversely affected by water. In the case of low voltage and medium voltage circuit breakers and switches, the operation of the mechanism can be impaired by corrosion, by the presence of particles such as silt, and by the removal of lubricants. The dielectric properties of insulation materials and insulators will degrade and, for air circuit breakers, the condition of the contacts can be affected. Further, low voltage power circuit breakers usually incorporate electronic trip units; the functioning of these units will be impaired. Similarly, the functionality of electronic protective relays and meters can be impaired. In the case of fuses, water may affect the filler material. A damaged filler material will degrade the insulation and interruption capabilities of fuses. Power circuit breakers and medium voltage breakers are designed to be maintainable with the possibility, for example, of replacing contacts in air circuit breakers. It may, therefore, be possible to reuse such breakers provided the refurbishing is performed in close consultation with the manufacturer. This would include cleaning and drying techniques, lubrication advice, and thorough testing prior to the reapplication of power. However, the electronic trip units of low voltage power circuit breakers, and electronic protective relays and meters in any power equipment should be discarded and replaced, or at least returned to the manufacturer for inspection and possible refurbishment. In the case of fused equipment, the fusible units should be replaced, and the remainder of the apparatus may be suitable for refurbishing in close consultation with the manufacturer.
5 In all cases, great attention must be paid to the thorough cleaning, drying, and testing of insulators and insulation material. The power equipment can be expected to contain additional electronic units such as solid state relays. These units can also be vital to the correct functioning of the protective device, and great care is needed in the cleaning and testing of such units. A first recommendation is to return the devices to the manufacturer. If this is not possible, the manufacturer should be consulted, for example, on the correct selection of cleaning agents which remove impurities without damaging the conformal coating. The manufacturer must also be contacted relative to the exact testing required of sophisticated electronic equipment containing, for example, microprocessors. The overall power equipment assembly (switchgear) may be able to be reconditioned provided careful steps are taken in the cleaning, drying, and testing of the equipment prior to applying power. This would require input and advice from the manufacturer. An area of particular concern is the maintenance of the dielectric properties of insulation. In the field application of medium voltage equipment, for example, standoff insulators are subjected to a wide variety of high voltage surges. Such insulators might need replacement. Items Requiring Complete Replacement: Fuses Electronic trip units of low voltage power circuit breakers Items Which May Possibly be Reconditioned by Trained Personnel in Consultation with Alternating current high-voltage circuit breakers reference NEMA Standards Publication SG , Alternating-Current High Voltage Circuit Breaker, para 6.12 Low voltage power circuit breakers Protective relays, meters, and current transformers Low voltage switchgear Medium voltage switchgear Transformers Exposure of transformers to water can cause corrosion and insulation damage to the transformer core and winding. The ability of the transformer to perform its intended function in a safe manner can also be impaired by debris and chemicals which may be deposited inside the transformer during a flood. Water and contaminates also can damage transformer fluids. Items Requiring Complete Replacement: All dry-type transformers regardless of kva ratings All dry type control circuit transformers Items Which May Possibly be Reconditioned by Trained Personnel in Consultation with Liquid-filled transformers (analysis of the insulating medium is required for evaluation of this equipment) Cast-resin transformers
6 Wire, Cable, and Flexible Cords When any wire or cable product is exposed to water, any metallic component (such as the conductor, metallic shield, or armor) is subject to corrosion that can damage the component itself and/or cause termination failures. If water remains in medium voltage cable, it could accelerate insulation deterioration, causing premature failure. Wire and cable that is listed for only dry locations may become a shock hazard, when energized, after being exposed to water. The following recommended actions are based upon the concept that the water contains no high concentrations of chemicals, oils, etc. If it is suspected that the water has unusual contaminants, such as may be found in some flood water, the manufacturer should be consulted before any decision is made to continue using any wire or cable products. Items Requiring Complete Replacement: Any wire or cable that is listed for dry locations only, such as type NM-B cable, should be replaced if it has been exposed to water. Any cable that contains fillers, such as polypropylene, paper, etc., should be replaced if the ends of the product have been exposed to water. Items Which May Possibly be Reconditioned by Trained Personnel in Consultation with Any wire or cable product that is suitable for wet locations and whose ends have not been exposed to water should be suitable for use or continued use. A qualified person, such as an electrical contractor or others familiar with wire and cable terminology, should make the determination of the product's suitability for wet locations. Any wire or cable product, not containing fillers, that is suitable for wet locations and whose ends have been exposed to water, may be considered a candidate for "purging" (using an inert gas under pressure to remove water contained in the product) under engineering supervision. If this procedure is employed, the wire or cable should be tested prior to energization. As a minimum, an insulation resistance test with a megohmmeter should be conducted. Wiring Devices, Ground Fault Circuit Interrupters (GFCI), and Surge Protectors Sediments and contaminants contained in water may find their way into the internal components of installed electrical products and may remain there even after the products have been dried or washed by the user. These may adversely affect the performance of those products without being readily apparent to the user community. Also, electrical products, such as GFCIs and surge protective devices, contain electronic circuitry and other components which can be adversely affected by water resulting in the device becoming non-functional or a hazard to the user. As a result, such products subjected to or believed to be subjected to water damage are not suitable for continued use and must be replaced with new undamaged products. Air drying and washing of water damaged products of this type should not be attempted. Lighting Fixtures and Ballasts Fluorescent, high-intensity discharge, and incandescent lights are not intended for submersion in water except for those that are listed as submersible lighting fixtures. Flooded lighting fixtures and associated equipment may be damaged by corrosive materials, sediment, or other debris in the water. Corrosion of metallic parts and contamination of internal circuitry may prevent the equipment from operating properly. Lighting fixtures and associated equipment known to have been submerged should be replaced.
7 Motors Motors which have been flooded by water may be subjected to damage by debris or pollutants. This may result in damage to insulation, switches, contacts of switches, capacitors and overload protectors, corrosion of metallic parts, and contamination of the lubricating means and should be evaluated by qualified personnel. The manufacturer should be contacted for specific instructions on possible disassembly, cleaning, and drying of the motor housing and internal components by trained personnel. Also, a method for drying is described in ANSI/IEEE , A2 and A3. Electronic Products, Including Signaling, Protection, Communication Systems, and Industrial Controls Equipment used in signaling, protection, and communication systems generally contain electronic components, and the exposure of such equipment to flooding by water can adversely affect the reliability of those systems. Contamination by pollutants or debris in flood waters may cause corrosion of components of the system, shorting of printed circuits, or alteration of circuit characteristics. Since some of these types of installations are classified as life safety systems, it is important that the reliability of those systems be maintained. Where such systems are damaged by water, it is recommended that components of these systems be replaced or returned to the manufacturer for appropriate cleaning, recalibration, and testing. Manufacturers of these systems should be contacted for information on specific equipment. Cable Trays Carefully inspect the cable tray system to determine if its mechanical and/or electrical integrity has been breached. (WARNING Do not use cable tray as a walkway.) Repair or replace any damaged portions per original installation requirements. Remove all debris from the cable tray. If any labels warning against the use of the cable tray as a walkway have been obliterated, obtain new labels from the manufacturer and apply as required. National Electrical Manufacturers Association 1300 North 17th Street, Suite 1847 Rosslyn, Virginia Telephone: (703) Fax: (703) ATTN: Vince Baclawski Copyright 2005 by the National Electrical Manufacturers Association.
8 NOTICE AND DISCLAIMER The information in this publication was considered technically sound by the consensus of persons engaged in the development and approval of the document at the time it was developed. Consensus does not necessarily mean that there is unanimous agreement among every person participating in the development of this document. NEMA standards and guideline publications, of which the document contained herein is one, are developed through a voluntary consensus standards development process. This process brings together volunteers and/or seeks out the views of persons who have an interest in the topic covered by this publication. While NEMA administers the process and establishes rules to promote fairness in the development of consensus, it does not write the document and it does not independently test, evaluate, or verify the accuracy or completeness of any information or the soundness of any judgments contained in its standards and guideline publications. NEMA disclaims liability for any personal injury, property, or other damages of any nature whatsoever, whether special, indirect, consequential, or compensatory, directly or indirectly resulting from the publication, use of, application, or reliance on this document. NEMA disclaims and makes no guaranty or warranty, express or implied, as to the accuracy or completeness of any information published herein, and disclaims and makes no warranty that the information in this document will fulfill any of your particular purposes or needs. NEMA does not undertake to guarantee the performance of any individual manufacturer or seller s products or services by virtue of this standard or guide. In publishing and making this document available, NEMA is not undertaking to render professional or other services for or on behalf of any person or entity, nor is NEMA undertaking to perform any duty owed by any person or entity to someone else. Anyone using this document should rely on his or her own independent judgment or, as appropriate, seek the advice of a competent professional in determining the exercise of reasonable care in any given circumstances. Information and other standards on the topic covered by this publication may be available from other sources, which the user may wish to consult for additional views or information not covered by this publication. NEMA has no power, nor does it undertake to police or enforce compliance with the contents of this document. NEMA does not certify, test, or inspect products, designs, or installations for safety or health purposes. Any certification or other statement of compliance with any health or safety related information in this document shall not be attributable to NEMA and is solely the responsibility of the certifier or maker of the statement.
Evaluating Water-Damaged Electrical Equipment 1 USE OF THIS PUBLICATION This publication provides information on how to evaluate electrical equipment that has been exposed to water through flooding, fire
Evaluating Water-Damaged Electrical www.nema.org Evaluating Water-Damaged Electrical 1 USE OF THIS PUBLICATION This publication provides information on how to evaluate electrical equipment that has been
Evaluating Water-Damaged Electrical Equipment 1 USE OF THIS PUBLICATION This publication provides information on how to evaluate electrical equipment that has been exposed to water through flooding, fire
Evaluating Fire- and Heat-Damaged Electrical Equipment www.nema.org 1 USE OF THIS PUBLICATION This publication provides information on how to evaluate electrical equipment that has been exposed to heat
NEMA Standards Publication A Brief Comparison of NEMA 250 Enclosures for Electrical Equipment (1000 Volts Maximum) and IEC 60529 Degrees of Protection Provided by Enclosures (IP Code) Published by National
Substance abusers are: 10 times 3.6 times 5 times 33% Protect your company from becoming part of these statistics! 1-800-533-0472. * American Council for Drug Education (Printed in EHS Today 10-6-2009)
American National Standard for Lighting Equipment Voltage Surge Requirements Secretariat: National Electrical Manufacturers Association Approved: June 19, 2015 American National Standards Institute, Inc.
NEMA SSL 3 HIGH-POWER WHITE LED BINNING FOR GENERAL ILLUMINATION NEMA Standards Publication SSL 3-2011 High-Power White LED Binning for General Illumination Published by: National Electrical Manufacturers
NEMA XR 29-2013 Standard Attributes on CT Equipment Related to Dose Optimization and Management Published by: National Electrical Manufacturers Association 1300 North 17th Street Rosslyn, Virginia 22209
NEMA Standards Publication No. WC 26-2008 EEMAC Standards Publication 201-2008 Binational Wire and Cable Packaging Standard Published by National Electrical Manufacturers Association 1300 North 17th Street,
Section 9: Power Distribution Equipment Bill Brown, P.E., Square D Engineering Services Introduction Power Distribution Equipment is a term generally used to describe any apparatus used for the generation,
Revision of ANSI C84.1-2006 American National Standard For Electric Power Systems and Equipment Voltage Ratings (60 Hertz) Secretariat: National Electrical Manufacturers Association Approved December 6,
Primary and Secondary Electrical Distribution Systems Critical Facilities Round Table 12th Quarterly Membership Meeting June 2, 2006 David D. Roybal. P.E. Eaton Electrical Cutler-Hammer Products Utility
Severe Weather Safety Resources to help weather the storm Hurricanes: By the Basics What: A Hurricane is a severe weather system that brings high winds, torrential rain, storm surges, and flooding. Hurricanes
ANSI/NEMA C29.2-2012 American National Standard For Insulators Wet Process Porcelain and Toughened Glass Suspension Type Secretariat: National Electrical Manufacturers Association Approved: October 2012
University of Iowa Main Power Plant 2008 Flood Preparations, Event, & Recovery Yellow Alert for Mayflower Residence hall Peak at 31.5 feet Power Plant floods from steam tunnel and shuts down 1993 Flood
Section 16435 - SWITCHBOARDS Introduction Part 1 - General Reference The work under this section is subject to requirements of the Contract Documents including the General Conditions, Supplementary Conditions,
Circuit Breakers Circuit breakers are used in panelboards and switchboards to provide circuit protection and provide a means of energizing and de-energizing a circuit. Siemens Sentron molded case circuit
NEMA ICS 61131-1-2005 (R2013) IEC Publication 61131-1 Programmable Controllers Part 1: General Information Published by: National Electrical Manufacturers Association 1300 North 17 th Street, Suite 900
ELECTRICAL RISKS AT THE WORKPLACE Heading FACT SHEET Overview This fact sheet provides general guidance for persons conducting a business or undertaking (PCBUs) and workers on managing electrical risks
Appendix C Electrical Grounding Low-Voltage Equipment Grounding The most frequently cited Office of Safety and Health Administration (OSHA) electrical violation is improper occupational grounding of equipment
Section 18 Switchgear and Metal-Enclosed Bus 180. SWITCHGEAR ASSEMBLIES 180A. General Requirements for All Switchgear. This rule covers general requirements for all switchgear. Examples of switchgear found
ELECTRICAL SAFETY Introduction The following sections provide general safety guidelines and procedures for electrical safety. This chapter covers the following topics: TOPIC PAGE General Electrical Safety
May 2010 DEPARTMENT OF CODES AND BUILDING SAFETY FLOOD RECOVERY INFORMATION GUIDELINES FOR PERMITS ASSOCIATED WITH THE REPAIR OF FLOOD DAMAGED HOMES AND BUILDINGS The Department of Codes and Building Safety
Keithley Instruments 28775 Aurora Road Cleveland, Ohio 44139 1-888-KEITHLEY http://www.keithley.com Model 1756 Test Lead Kit Gerneral Purpose Test Lead Information Description These test leads allow you
543-0032-00, 943-0032-00 User s Manual 1 Comfort Alert Diagnostics Faster Service And Improved Accuracy The Comfort Alert diagnostics module is a breakthrough innovation for troubleshooting heat pump and
BRANDON AND CLARK INC. // SCOTT W. CLARK, P.E. ELECTRICAL CONTINUING EDUCATION ARC FLASH - NFPA 70E Training is not a substitute for following corporate safety guidelines. Always refer to the latest safety
SECTION 16425 SWITCHBOARDS PART 1 GENERAL 1.01 SUMMARY A. Section Includes: 1. Requirements for main and distribution switchboards. B. Related Sections: 1. Section 16420 - Service Entrance 2. Section 16430
Training Title MV, HV AND EHV SWITCHGEAR TESTING & COMMISSIONING Training Duration 5 days Training Date MV, HV and EHV Switchgear Testing & Commissioning 5 20 24 Apr $3,750 Dubai, UAE In any of the 5 star
Province of Alberta APPRENTICESHIP AND INDUSTRY TRAINING ACT ELECTRICIAN TRADE REGULATION Alberta Regulation 274/2000 With amendments up to and including Alberta Regulation 122/2014 Office Consolidation
NFPA 70E 2012 Rolls Out New Electrical Safety Requirements Affecting Data Centers A market position paper from the experts in Business-Critical Continuity TM Executive Summary Electrocutions are the fourth
Service Bulletin DATE: June 18, 2008 TO: All Service and Parts Managers SUBJECT: Flood Damaged Appliances SA-008 Due to the unfortunate flooding experienced by many areas in the Midwest in recent months,
usa.siemens.com/sccr Guidelines on the Short Circuit Current Rating for Industrial Control Panels Technical Paper for Practical Applications White Paper I October 2014 As per NEC Edition 2014, and UL508A
Revision of ANSI C12.10-2004 American National Standard Physical Aspects of Watthour Meters Safety Standard Secretariat: National Electrical Manufacturers Association Approved June 28, 2011 American National
1. How do we accomplish grounding of furnaces and / or water heaters on two wire circuits? 250.134 Equipment Fastened in Place or Connected by Permanent Wiring Methods (Fixed) Grounding. Unless grounded
After the Storm Floodwater safety Health Issues and Short Term Safety Floodwaters are likely to be contaminated with unknown chemicals, oils, sewage, fertilizers, bacteria, germs and silt. Any of these
Oil and Coolant Circulating Heating System Model - OCSM Installation & Operation Manual 216280-000 REV 2 Identifying Your System The HOTSTART heating system is designed to heat fluids for use in marine
Extend the Life of Existing Switchgear January 2011/1910DB1002 by Hal Theobald, Product Manager Schneider Electric USA, Inc. Make the most of your energy SM Summary Introduction... p 3 Maintenance Requirements...
ADI 9510-B Advantium 2 Plus Alarm INSTALLATION AND OPERATING INSTRUCTIONS Carefully Read These Instructions Before Operating Carefully Read These Controls Corporation of America 1501 Harpers Road Virginia
Instruction Manual ET50 ENGLISH AC / DC VOLTAGE TO 600V POSITIVE AND NEGATIVE DC POLARITY LIGHT AND VIBRATION INDICATORS CAT IV 600V SAFETY RATING MODERN SOLID-STATE DESIGN C 1 www.kleintools.com For Professionals...Since
CAUTION! Instruction manual of pumps WQ, WQF, SN, Furiatka, Furia, KRAKEN, BIG, IP, IPE, SWQ, CTR NOTE: read the manual prior to commencement of use. For safety reasons, the pump can only be operated by
Understanding Arc Flash Presented by Eddie F. Jones, PE 1 2 3 4 5 Five to 10 arc flash explosions occur in electric equipment every day in the United States. This number does not include cases in which
FACILITIES ELECTRIC SUBCONTRACTORS SAFETY MANUAL GENERAL DYNAMICS ELECTRIC BOAT CORPORATION June 28, 2011* *All changes as of this date are noted in red. 1 of 9 Table of Contents 1. Requirements 2. Tools
i800 AC Current Clamp Instruction Sheet Introduction The i800 AC Current Clamp, the Clamp, has been designed for use with multimeters, recorders, power analyzers, safety testers, etc., for accurate non-intrusive
What are the basic electrical safety issues and remedies in solar photovoltaic installations? Presented by: Behzad Eghtesady City of Los Angeles Department of Building and Safety Topics Covered Photovoltaic
Important New Code Requirements for SCCR Labeling of Data Center Equipment Michael P. Murphy D V L G r o u p 1 1 5 S i n c l a i r R o a d B r i s t o l, P A 1 8 9 6 3 Short Circuit Current Ratings (SCCR)
SURGE PROTECTIVE DEVICES (SPDs) INTEGRATED UNITS LOW VOLTAGE AC SURGE PROTECTION FOR ELECTRICAL DISTRIBUTION SYSTEMS PART 1 GENERAL 01 02 03 SCOPE The Contractor shall furnish and install the Surge Protective
Procedure No.: BMEHS-002-012 Page: 1 of 12 Preparer: Owner: Approver: EHS Team Member S/H Manager Site Manager Signed Copy on File Signed Copy on File Signed Copy on File Document Revision Change Table
Pump Specifications 250 Series Submersible Sump / Effluent Pump 2 Solids handling 250_P1 R10/7/2015 Copyright 2015 Liberty Pumps Inc. All rights reserved. Specifications subject to change without notice.
Warranties All Products Revised: 8/1/15 7 Pages GENERAL DISCLAIMER In addition to all claims listed on each of the following individual WARRANTY pages, the following GENERAL DISCLAIMERS apply. 1. The purchaser
3053 Electrical Safety Training Program Course Outline The following outline summarizes the major points of information presented in the program. The outline can be used to review the program before conducting
SECTION 26 05 53 IDENTIFICATION FOR ELECTRICAL SYSTEMS PART 1 - GENERAL 1.1 RELATED DOCUMENTS: A. The Conditions of the Contract and applicable requirements of Divisions 0 and 1 and Section 26 00 01, Electrical
Eemax Inc., 353 Christian Street, Oxford, CT 06478 1 E ema X SERIES 12-600 VOLT ELECTRIC INSTANTANEOUS WATER HEATER FOR EMERGENCY SAFTEY EQUIPMENT INSTALLATION AND OWNERS MANUAL REQUIRED MANTENANCE WARNING
Advances in Medium and Low Voltage Power Distribution ESS Metron Expo and Technical Seminars Presented By: Greg Pelster & Robert Schmid FFI Ferrie, Franzmann Industries LOW VOLTAGE SWITCHGEAR & LOW VOLTAGE
ARCO Electric Products Installation and Maintenance Manual Low Voltage Automatic Power Factor Correction Capacitor Systems 2013 READ CAREFULLY These instructions are intended to cover good practices in
Pump Specifications 405 Series Commercial Drain Pump (High-Temp) 2 Solids handling 405_P1 R1/27/2012 Copyright 2012 Liberty Pumps Inc. All rights reserved. Specifications subject to change without notice.
Managing Water Infiltration into Buildings A Systematized Approach for Remediating Water Problems in Buildings due to Floods, Roof Leaks, Potable Water Leaks, Sewage Backup, Steam Leaks and Groundwater
EB-00-00 Filed: 00 Aug Page of DISTRIBUTION OPERATIONS AND MAINTENANCE PREVENTIVE MAINTENANCE Preventive Maintenance is intended to maintain or improve customer service reliability, extend equipment life
electrical services WWW.AU.SGS.COM/INDUSTRIAL OUR PROFILE SGS offers a full range of electrical engineering services covering the commissioning test of new plant as well as the maintenance and continual
EPM3 Phase Sequence and Motor Rotation Tester Users Manual 1 L1 L2 L3 2 3 A B C CAT 600V 3-PHASE TESTER 5 TEST M1 M2 BATT M3 EPM3 MOTOR ROTATION TESTER EPM3 MOTOR ROTATION DETERMINED WHILE FACING MOTOR
Name of School: OPTIONAL INFORMATION Date of Inspection: Vocational Program/Course/Room: Signature of Inspector: ELECTRICAL - WIRING DESIGN AND PROTECTION SELF INSPECTION CHECKLIST Guidelines: This checklist
Houston Service Center Medium Voltage Service and Aftermarket Solutions Table of contents Introduction...3 Breaker refurbishment...4 Protective relay & control service and support...5 Power Service and
Construction Electrical Terminology Electricians Acknowledgments Winnipeg Technical College and the Department of Labour and Immigration of Manitoba wish to express sincere appreciation to all contributors.
Single Phase Soft Starter Installation & Operating Manual 6/02 Table of Contents Section 1 General Information................................................... 1 1 General Description................................................
misconceptions about arc-flash hazard assessments There are some common misconceptions about Arc-Flash Hazard Assessments which reduce the effectiveness of the Assessments and can increase electrical hazards.
Owner s Manual & Safety Instructions Save This Manual Keep this manual for the safety warnings and precautions, assembly, operating, inspection, maintenance and cleaning procedures. Write the product s
Simplified Guide To Understanding Short-Circuit Current Rating FIND IT, FIX IT, FORGET IT Are You Ready For The New SCCR Marking Requirements? What Is A Short-Circuit Current Rating (SCCR)? SCCRs on components
ROUSH PERFORMANCE - Limited Warranty ROUSH PARTS AND ACCESSORIES* WHO IS COVERED ROUSH's warranty obligations for ROUSH Parts and Accessories (individually and collectively Part(s) ) is limited to defects
Scopes of Work for Electrical Acceptance Testing Schneider Electric Services: life-cycle solutions for electrical distribution equipment Make the most of your energy SM Scopes of Work for Electrical Acceptance
The device type and date of manufacture (week/year) can be found on the device rating plate. In the event of any queries about the device, please quote all the details given on the rating plate. For further
FOR NEW OR REPLACEMENT SEWAGE PUMPS RECOMMENDED INSTALLATION & MAINTENANCE AB SUMP & SEWAGE PUMP MANUFACTURERS ASSOCIATION P.O. BOX 647 NORTHBROOK, IL 60065-0647 The materials contained in this document
Electrical Safety Electricity can be a friend, but it can also hurt if you do not treat it with respect. Everyday someone loses his or her home or business due to an electrical fire. These tragedies are
14 SWITCHGEAR Secondary Unit Substations Overview Siemens offers a wide variety of unit substation designs to meet customer requirements. A unit substation consists of one or more transformers mechanically
2 12 2010 PulteGroup, Inc. All Rights Reserved. circuit breakers Circuit breakers protect your home s system from power failure. The wiring in your home is protected by circuit breakers. Circuit breakers,
A guide to understanding and maintaining your home s electrical system A publication presented by the Electrical Safety Foundation International What s Inside? Everything you need to know Should You Do-It-Yourself?
..OR How To Protect your 3-Phase Equipment Investment with 3-Phase Monitors from Time Mark... TIME MARK CORPORATION 11440 EAST PINE STREET TULSA, OK 74116 USA tel 918 438-1220 fax 918 437-7584 www.time-mark.com
2013WWOA Conference Technical Conference Program Understanding Arc-Flash Hazards, Its Implications on Operations and Solutions that Mitigate Such Exposure Presented by Jerry Baskin Senior Product Manager
Installation Requirements Installation and inspection of Grid-connected PV systems July 2011 (no battery storage) This document has been prepared by Energy Safe Victoria to provide guidance for electrical
Low Voltage 480V Switchgear General Description Low Voltage metal-enclosed switchgear is used in electric power distribution systems for the control and protection of circuits and equipment. The switchgear