1 Atlanta Chapter IEEE Industry Applications Society Electrical Equipment Room Design Considerations presented at the Sheraton Buckhead Hotel Atlanta, Georgia November 20, 2006
2 Outline 1. Definitions 2. Power Distribution Configurations 3. Selection of Transformer 4. Installation and Location of Transformer 5. Service Entrance Equipment 6. Selection of Circuit Breaker 7. Electrical Equipment Room Construction (New) 8. Electrical Equipment Room Construction (Existing) 9. Maximum Impedance in a Ground Return Loop to Operate an Overcurrent Protective Device NEC Requirements
3 Outline 11. Ground Fault Sensing 12. Zero Sequence Sensing vs. Residual Sequence Sensing 13. Power Distribution Systems with Multiple Sources 14. Modified Differential Ground Fault (MDGF) Protection Systems 15. Designing a MDGF Protection System 16. Reported Ground Fault Losses
4 1. Definitions System Configuration The system configuration of any Power Distribution System is based strictly on how the secondary windings of the Power Class Transformer, or generator, supplying the Service Entrance Main or loads, are configured. (This includes whether or not the windings are referenced to earth.) The system configuration is not based on how any specific load or equipment is connected to a particular power distribution system.
5 1. Definitions Ground Fault Protection System A designed, coordinated, functional, and properly installed system that provides protection from electrical faults or short circuit conditions that result from any unintentional, electrically conducting connection between an ungrounded conductor of an electrical circuit and the normally non current-carrying conductors, metallic enclosures, metallic raceways, metallic equipment, or earth.
6 1. Definitions Ground Fault Protection of Equipment (Per Article 100 in the 2005 NEC) A system intended to provide protection of equipment from damaging line-to-ground fault currents by operating to cause a disconnecting means to open all ungrounded conductors of the faulted circuit. This protection is provided at current levels less than those required to protect conductors from damage through the operation of a supply circuit overcurrent device.
7 1. Definitions Effective Ground-Fault Current Path (per Article in the 2005 NEC) An intentionally constructed, permanent, low-impedance electrically conductive path designed and intended to carry current under ground-fault conditions from the point of a ground fault on a wiring system to the electrical supply source and that facilitates the operation of the overcurrent protective device or ground fault detectors on highimpedance grounded systems.
8 1. Definitions Ground Fault (per Article in the 2005 NEC) An unintentional, electrically conducting connection between an ungrounded conductor of an electrical circuit and the normally non current-carrying conductors, metallic enclosures, metallic raceways, metallic equipment, or earth.
9 1. Definitions Ground Fault Current Path (per Article in the 2005 NEC) An electrically conductive path from the point of a ground fault on a wiring system through normally non currentcarrying conductors, equipment, or the earth to the electrical supply source.
10 2. Power Distribution Configurations
11 3. The Selection of the Power Class Transformer to Install Dry Type Air/Dry Cast Resin Liquid Filled Mineral Oil (flammable, marketed or perceived bio hazard) Silicone (non-flammable) Bio [Corn Oil] (flammable, but not a marketed or perceived bio hazard ) Gas Type
12 4. The Location and Installation of the Power Class Transformer Outdoors Enclosure Types Relative to Environment Accessibility Camouflage to Meet Local Requirements Hazardous Locations Protection for and from people Required Markings Security Indoors To Vault or Not To Vault Fire Ratings of Location Rating of NEMA Environment Environmental Considerations Cooling Ability Accessibility Security
13 5. Service Entrance Equipment Switchboards (UL 891) The UL 891 Standard applies to switchboards nominally rated at 600 V or less and intended for use in accordance with the Canadian Electrical Code, Part 1 (CE Code, Part 1), the National Electrical Code (NEC), ANSI/NFPA 70, and the Mexican Standard for Electrical Installations (Utility), NOM-001-SEDE. The term switchboard is intended to refer to a dead-front switchboards only. Not associated with the following switchboard types: Preset and dimmer control (theater) Live front, railway control, or electrification Constructions intended only for receiving motor control center units. Covers switchboards for use on circuits having available rms symmetrical short-circuit currents of not more than A.
14 5. Service Entrance Equipment Switchboards (UL 891) continued Traditionally have less bus clearances than switchgear. Bussing is rarely insulated (unless specified and paid for). The spaces between all distribution circuit breakers are not usually compartmentalized. Employs a greater use of barriers within a section versus compartments. There are barriers between sections. Circuit Breakers employed within a switchboard section can be molded case, insulated case, or a power type. Instantaneous trip functions on molded case and insulated case circuit breakers employed within a switchboard assembly are not generally ANSI rated for higher short time withstand capability Can possibly be accessible from only one side.
15 5. Service Entrance Equipment Switchgear (UL 1558) Covers metal-enclosed low-voltage power circuit breaker switchgear assemblies containing but not limited to such devices as low-voltage power circuit breakers, other interrupting devices, switches, control, instrumentation and metering, protective and regulating equipment. Covers power equipment intended for use in ordinary locations in accordance with the National Electrical Code. UL 1558 requirements are intended to supplement and be used in conjunction with the Standard for Metal-Enclosed Low Voltage Power Circuit Breaker Switchgear, ANSI C , and the Standard for Conformance Testing of Metal- Enclosed Low-Voltage AC Power Circuit Breaker Switchgear Assemblies, ANSI C Covers equipment rated 600 Vac or less nominal, 635 Vac maximum.
16 5. Service Entrance Equipment Switchgear (UL 1558) continued For use on circuits having available rms symmetrical short-circuit currents of not more than A. Switchgear is 30 cycle rated and can be installed without instantaneous overcurrent protection to assist in selectivity. Traditionally switchgear has more bus clearances Insulated bussing is commonly employed as a standard Compartmentalized between sections cubicles versus barriers Circuit breakers employed are by definition (ANSI standards) classified as power class circuit breakers having a higher short time withstand capability than switchboards. Switchgear is front and rear accessible.
17 6. Selection of MCCB Circuit Breakers as Overcurrent Protective Devices Molded Case Circuit Breakers (MCCB) Thermal Magnetic» Low Voltage Applications up to 600Vac» Typical Current Ratings are from 5A to 2000A» Originally designed for overload and phase-to-phase short circuit protection» If intended to provide ground fault protection, these type circuit breakers must be employed on a circuit with an effective low impedance, ground fault current return path» Mechanism is totally sealed» Mainly require manual operations» Not designed or intended to be serviceable» Typically bolted onto or plugged into bus» Should be installed with equipment turned off» A ground fault module can be installed on some devices» Most are only 80% rated. 100% rating is optional» Same size and ampere rating of same circuit breakers are manufactured with various short circuit ratings. (Knowing the available short circuit current available at point of connections is imperative!) MICROLOGIC or Electronic Trip Units» Offers a combination of LSIG function to the specifier or user» Provides for improved time/current or fault coordination function
18 6. Selection of ICCB Circuit Breakers as Overcurrent Protective Devices Insulated Case Circuit Breakers (ICCB) Generally are only UL Rated and not ANSI Rated Low Voltage Applications up to 600Vac Typical Current Ratings are from 400A to 4000A They provide limited internal access to replacement of specific parts Can be fixed mounted directly onto bus or manufactured as a draw-out type within a specifically designed cubicle Can be fitted at the factory with multiple auxiliary functions Multiple Auxiliary Contacts Shunt Trip and Shunt Close Coils LSIG Trip Alarms Electric Motor Operator Most are only 80% rated, 100% rating is optional Ampere rating of circuit breakers can be manufactured with various short circuit ratings. (Knowing the available short circuit current available at point of connections is imperative!) MICROLOGIC or Electronic Trip Units Offers a combination of LSIG functions to the specifier or user Provides for improved time/current or fault coordination function
19 6. Selection of PCB Circuit Breakers as Overcurrent Protective Devices Power Circuit Breakers (PCB) ANSI Rated and not UL Rated Low Voltage Applications up to 600Vac Typical Current Ratings are from 800A to 6000A They provide internal access to inspection, maintenance, and replacement specific parts Manufactured as draw-out type construction with isolated compartment or cubicle Can be fitted at the factory with multiple auxiliary functions Multiple Auxiliary Contacts Shunt Trip and Shunt Close Coils LSIG Trip Alarms Electric Motor Operator 100% rated Tested and rated to a higher level of initial or asymmetrical short circuit current More robustly constructed than ICCBs Intended for longer use life and more open and close operations MICROLOGIC or Electronic Trip Units with LSIG functions are standard Has higher initial cost.
20 7. Electrical Room Construction (New) Electrical room accessibility by at least two portals (Based on the placement and orientation of equipment, more exits may be required by local AHJs) Cooling and humidity requirements for equipment Ventilation requirement for a specific equipment room Minimal space between physical structures and other electrical equipment Accessibility of equipment for maintenance and servicing Emergency accessibility requirements Security accessibility and requirements EPO installation and their locations To sprinkle or not to sprinkle. [The on going conflicts and turf wars between local AHJs (fire marshal, electrical inspector, building inspector) concerning the routing of steam and water pipe above electrical equipment and the requirements for a sprinkler system over electrical equipment.] NEMA 1 or NEMA 3R equipment?? Are service or load conductors rated for application and environmental conditions? Are dissimilar circuit breakers being employed in multiple ended power distribution equipment (Multiple Sources)? Need for Differential Ground Fault Protection?
21 7. Electrical Room Construction (New) - continued Conflicts between the architecture and electrical engineer of record concerning available/needed space for all electrical equipment rooms. Dual use spaces (Electrical Equipment Room and Storage Area) Fire alarms Security Cameras and their location Is all electrical equipment effectively bonded and grounded? Effective lighting within electrical rooms or closets. Equipment installation requirements and guidelines provided by the electrical equipment manufacturer Operations and Maintenance Manuals provided by the electrical equipment manufacturer Startup and Testing requirements Lock Out / Tag Out Requirements Danger and Warning Labels (Inform and Warn Requirements)
22 7. Electrical Room Construction (New) - continued The need for a house keeping pad under the equipment. Locations within a specific building or facilities for the placement of service equipment, distribution equipment, power panels, motor control centers, ATS Units, battery banks, UPS Units, onsite generators, etc Requirements for any house keeping pad constructed (material composition and necessary height) Flooding concerns from either external and internal sources Structural and seismic requirements for the electrical room Structural and bracing requirements for the electrical equipment enclosures Structural and bracing requirements for overhead busways, busducts, and conduits Need for floor drains or sump pumps in electrical rooms Critter protection Internal heater and humidity controls Will any local employees have access to water hoses???
32 8. Electrical Room Construction (New to Existing Equipment Additional Considerations) Bringing existing Service Equipment into compliance to current electrical Codes Additions of multiple power sources from another transformer or generator Dissimilar power or service equipment are rarely compatible (BIG RED FLAGS) Are all power sources effectively bonded together via a low impedance path Complex technical issues to resolve because of incompatible ground fault protection systems
33 9. Maximum Impedance in a Ground Return Loop to Operate an Overcurrent Protective Device Fuse Size in Amperes Value a Circuit Breaker Ampere Rating Value b Maximum %Z in Ground Return Loop* * (480/1.732)/ 3A (or) 1.5b 5A 10A OHMS 10A 20A 9.23 OHMS 15A 30A 6.12 OHMS 20A 40A 4.62 OHMS 30A 60A 3.08 OHMS 40A 80A 2.31 OHMS 50A 100A 1.75 OHMS 75A 150A 1.23 OHMS 100A 200A OHMS
34 9. Maximum Impedance in a Ground Return Loop to Operate an Overcurrent Protective Device Fuse Size in Amperes Value a Circuit Breaker Ampere Rating Value b Maximum %Z in Ground Return Loop* * (480/1.732)/ 3A (or) 1.5b 125A 250A OHMS 150A 300A OHMS 175A 350A OHMS 200A 400A OHMS 250A 500A OHMS 300A 600A OHMS 400A 800A OHMS 500A 1000A OHMS 600A 1200A OHMS
35 9. Maximum Impedance in a Ground Return Loop to Operate an Overcurrent Protective Device Fuse Size in Amperes Value a Circuit Breaker Ampere Rating Value b Maximum %Z in Ground Return Loop* * (480/1.732)/ 3A (or) 1.5b 800A 1600A OHMS 1000A 2000A OHMS 2500A OHMS 1500A 3000A OHMS 2000A 4000A OHMS
36 NEC Requirements Ground-Fault Protection of Equipment (per Article in the 2005 NEC) Ground-fault protection of equipment shall be provided for solidly grounded wye electrical services of more than 150 volts to ground but not exceeding 600 volts phase-to-phase for each service disconnect rated 1000 amperes or more. The grounded conductor for the solidly grounded wye system shall be connected directly to ground without inserting any resistor or impedance device. The rating of the service disconnect shall be considered to be the rating of the largest fuse that can be installed or the highest continuous current trip setting for which the actual overcurrent device installed in a circuit breaker is rated or can be adjusted.
37 NEC Requirements Setting for Ground-Fault Protection (per Article (A) in the 2005 NEC) The ground-fault protection system shall operate to cause the service disconnect to open all ungrounded conductors of the faulted circuit. The maximum setting of the ground-fault protection shall be 1200 amperes, and the maximum time delay shall be one second for ground-fault currents equal to or greater than 3000 amperes.
38 NEC Requirements Ground-Fault Protection of Equipment (NECH Commentary for Article (A) in the 2005 NEC) The maximum setting for ground-fault sensors is 1200 amperes. There is no minimum, but it should be noted that settings at low levels increase the likelihood of unwanted shutdowns. The requirements of place a restriction on fault currents greater than 3000 amperes and limit the duration of the fault to not more than 1 second. This restriction minimizes the amount of damage done by an arcing fault, which is directly proportional to the time the arcing fault is allowed to burn. Care should be taken to ensure that interconnecting multiple supply systems does not negate proper sensing by the ground-fault protection equipment. A careful engineering study must be made to ensure that fault currents do not take parallel paths to the supply system, thereby bypassing the ground-fault detection device. See , , , and for further information on ground-fault protection of equipment.
39 (The requirement for ground-fault protection system performance testing is a result of numerous reports of ground-fault protection systems that were improperly wired and could not or did not perform the function for which they were intended. This Code and qualified testing laboratories require a set of performance testing instructions to be supplied with the equipment. Evaluation and listing of the instructions fall under the jurisdiction of those best qualified to make such judgments, the qualified electrical testing laboratory (see 90.7). If listed equipment is not installed in accordance with the instructions provided, the installation does not comply with 110.3(B).) NEC Requirements Testing the Ground-Fault Protection System (per Article (C) in the 2005 NEC) The ground-fault protection system shall be performance tested when first installed on site. The test shall be conducted in accordance with instructions that shall be provided with the equipment. A written record of this test shall be made and shall be available to the authority having jurisdiction.
40 NEC Requirements Effective Ground-Fault Current Path (per Article 250-4(A)(5) in the 2005 NEC) Electrical equipment and wiring and other electrically conductive material likely to become energized shall be installed in a manner that creates a permanent, low-impedance circuit facilitating the operation of the overcurrent device or ground detector for high-impedance grounded systems. It shall be capable of safely carrying the maximum ground-fault current likely to be imposed on it from any point on the wiring system where a ground fault may occur to the electrical supply source. The earth shall not be considered as an effective ground-fault current path.
41 11. Ground Fault Sensing There are three basic types of sensor arrangement used to sense abnormal current flow in a Zero Sequence Relaying Scheme. They are; A. Zero Sequence Sensing Where one sensor is employed to surround all phase conductors and neutral conductor. B. Modified Zero Sequence Sensing Where one sensor is employed to surround all phase conductors and a separate sensor surrounding the neutral sensor. C. Residual Sequence Sensing Where one sensor surrounds each phase conductor and neutral conductor.
42 12. Zero Sequence Sensing vs. Residual Sequence Sensing Zero Sequence Sensing Current sensors or current transformer are external to disconnecting device Usually associated with a separate and externally mounted Ground Fault Relay No internal relationship to disconnect to be operated. All GFP components are externally mounted. Disconnect requires a shunt trip coil Requires a separate and reliable source of control power. (Weakest Link)
43 12. Zero Sequence Sensing vs. Residual Sequence Sensing Residual Sequence Sensing Phase sensors are usually internal to protective device to be operated. Ground fault relaying is usually performed internal to protective device or circuit breaker to be operated. No external control power supply required. Protective device or circuit breaker is self-powered. Self powered residual sequence sensing GFP is referred to as Integral Ground Fault Protection.
44 13. Power Distribution Systems with Multiple Sources Two or more sources of power connected to the switchboard or switchgear. Separate Main Circuits Breakers Tie Circuit Breakers Separate Load Busses Neutral Bus associated with each power source are interconnected together. Multiple neutral-to-ground bonds via the connection of multiple System Bond Jumpers and Main Bonding Jumpers (MBJ). The interconnection of multiple grounding conductors on the line side of the main circuit breakers can function as a parallel neutral bus. Multiple current paths for imbalanced neutral currents and ground fault currents to flow.
45 13. Power Distribution Systems with Multiple Sources
46 14. Modified Differential Ground Fault (MDGF) Protection Systems The purpose of a MDGF Protection System is to sense and properly relay all of the phase and neutral currents which circulate through and within a multiple source power distribution system at all times during normal and abnormal conditions. The MDGF Protection System prevents nuisance tripping of circuit breakers from the flow of imbalanced currents from imbalanced loads. The MDGF Protection System prevents nuisance tripping of circuit breakers from the flow circulating currents in and out of the switchboard or switchgear from closed transition operations. The MDGF Protection System opens all of the appropriate circuit breakers closes to the faulted location within a switchboard or switchgear. The MDGF Protection System provides for the sectionalization of load busses.
47 15. Designing a MDGF Protection System Before a MDGF Protection Systems for a multiple sourced switchboard can be configured the following must be evaluated. A. Type of circuit breaker? 1. The internal sensors and ground fault relaying are not always configured the same. B. Frame size of the circuit breaker? 1. Different frame size breakers often have different C.T. ratios. 2. Different series circuit breakers can have the frame size and C.T. ratios, but different instantaneous C.T. polarities.
48 15. Designing a MDGF Protection System C. How are the circuit breakers supplied with power? 1. Are the circuit breakers top feed? 2. Are the circuit breakers bottom feed? D. Are the circuit breakers fixed or draw out type? The MDGF must be maintained when any circuit breaker is open or removed from its cell (drawn out). E. Is the tie circuit breaker (52T) specified to ground fault protection? 1. Non-Relayed Tie Circuit Breaker has no GF Protection 2. Relayed Tie Circuit Breaker has GF Protection
49 16. Reported Ground Fault Losses One Major Loss (Claim) Every Two Weeks
50 Special Notes for Consideration Phase-to-ground faults are the most common form of electrical faults. (95% to 98%) During any phase-to-ground fault the ground fault return path is 50% of the power circuit. Phase-to-ground faults are the most destructive type of electrical faults. Contrary to popular belief or some marketing publications, fuses do NOT provide selective coordination from most phase-to-ground faults. For a current limiting fuse to limit current as designed and intended a fault must be a bolted fault. Current limiting fuses do not coordinate well during high impedance phase-to-ground faults. Multiple levels of ground fault protection via MICROLOGIC Circuit Breakers provides the best form of selective coordination from phase-to-ground fault condition. Complex ground fault protection systems (MDGF) require a specific level of electrical engineering expertise.
51 Code NEC, NFPA 70 The NEC is a minimum construction and installation requirement document. The NEC is NOT a design or performance standard. Minimum requirements are often insufficient for the construction and installation of mission critical facilities as Data Centers, Communication Centers, Hospitals, Industrial Plants, Military Facilities, Prisons, and Transportation Centers.
52 Questions & Answers
53 Speaker Contact Information S. Frank Waterer III Staff Engineer Schneider Electric Engineering Services 2979 Pacific Drive, Suite E Norcross, Georgia Office Phone: , Ext. 102 Office Fax:
Primary and Secondary Electrical Distribution Systems Critical Facilities Round Table 12th Quarterly Membership Meeting June 2, 2006 David D. Roybal. P.E. Eaton Electrical Cutler-Hammer Products Utility
Section 16435 - SWITCHBOARDS Introduction Part 1 - General Reference The work under this section is subject to requirements of the Contract Documents including the General Conditions, Supplementary Conditions,
Section 18 Switchgear and Metal-Enclosed Bus 180. SWITCHGEAR ASSEMBLIES 180A. General Requirements for All Switchgear. This rule covers general requirements for all switchgear. Examples of switchgear found
SECTION 16425 SWITCHBOARDS PART 1 GENERAL 1.01 SUMMARY A. Section Includes: 1. Requirements for main and distribution switchboards. B. Related Sections: 1. Section 16420 - Service Entrance 2. Section 16430
Advances in Medium and Low Voltage Power Distribution ESS Metron Expo and Technical Seminars Presented By: Greg Pelster & Robert Schmid FFI Ferrie, Franzmann Industries LOW VOLTAGE SWITCHGEAR & LOW VOLTAGE
What are the basic electrical safety issues and remedies in solar photovoltaic installations? Presented by: Behzad Eghtesady City of Los Angeles Department of Building and Safety Topics Covered Photovoltaic
STANDARDS AND RATINGS FOR THE APPLICATION OF MOLDED CASE, INSULATED CASE, AND POWER CIRCUIT BREAKERS David D. Roybal, P.E. Senior Member, IEEE Cutler-Hammer, Inc. 3697 Mount Diablo Boulevard Lafayette,
Alternate Methods to Short Circuit Breaker Coordination Nguyen Perez, PE Senior Electrical Engineer 2600 Douglas Road, Suite 301 Coral Gables, Florida 305.529.1515 (p) www.brplusa.com Importance in Healthcare
PREFACE UL developed the Dead-Front Switchboard Marking Guide for code authorities, electric utilities, contractors, installers, users, designers, and other interested parties to aid in understanding deadfront
Basis of Design This section applies to the design relating to low voltage switchboards. Design Criteria UW Class N1 facilities main switchboards shall be rear accessible. The main, tie and feeder breakers
CONVENTION SESSION HANDOUT Choosing the Best Solution for Reducing Arc Energy Terry L. Schiazza, Business Development Manager Square D / Schneider Electric SESSION #11 Independent Electrical Contractors
Important New Code Requirements for SCCR Labeling of Data Center Equipment Michael P. Murphy D V L G r o u p 1 1 5 S i n c l a i r R o a d B r i s t o l, P A 1 8 9 6 3 Short Circuit Current Ratings (SCCR)
14 SWITCHGEAR Secondary Unit Substations Overview Siemens offers a wide variety of unit substation designs to meet customer requirements. A unit substation consists of one or more transformers mechanically
Integrating SPDs in Switchgear & Switchboards Causes More Problems than it Solves White Paper July 2010 Integrating surge protective devices (SPD) into distribution equipment (i.e. switchgear, switchboards,
Circuit Breakers Circuit breakers are used in panelboards and switchboards to provide circuit protection and provide a means of energizing and de-energizing a circuit. Siemens Sentron molded case circuit
Name of School: OPTIONAL INFORMATION Date of Inspection: Vocational Program/Course/Room: Signature of Inspector: ELECTRICAL - WIRING DESIGN AND PROTECTION SELF INSPECTION CHECKLIST Guidelines: This checklist
Low Voltage 480V Switchgear General Description Low Voltage metal-enclosed switchgear is used in electric power distribution systems for the control and protection of circuits and equipment. The switchgear
Power-Zone 4 Arc Resistant Low Voltage Switchgear with ArcBlok Technology Make the most of your energy SM Workplace safety 2 I Power-Zone 4 Arc Resistant Low Voltage Switchgear Five to ten arc flash explosions
PART 1 - GENERAL SECTION INCLUDES This Section includes service and distribution switchboards rated 600 V and less. RELATED SECTIONS Division 16 Section "Basic Electrical Materials and Methods" for general
CIRCUIT BREAKER INTERRUPTING CAPACITY AND SHORT-TIME CURRENT RATINGS David D. Roybal, P.E. Senior Member, IEEE Eaton Electrical 3697 Mount Diablo Boulevard Lafayette, CA 94549 Abstract Low-voltage circuit
ELECTRICAL INSPECTION BULLETIN (Effective 2000-03-01) Rule 28-900 Standby Generator Installations Due to the increasing number of standby generator installations being established to maintain continuity
COMPLETE REVISION October 2010 Electrical PIP ELSSG01 Design and Fabrication of Low-Voltage Metal-Enclosed AC Power Circuit Breaker Switchgear PURPOSE AND USE OF PROCESS INDUSTRY PRACTICES In an effort
*** Provide this document to the inspector along with ALL system installation instructions *** Project Address: Scope: Standard plan for the installation of grounded microinverter solar PV systems, not
1 General 1.1 Switchboards shall be U.L. listed and labeled. 1.2 Each switchboard shall have its own main disconnecting means unless it is located in the same room as its source of origin. In most cases
Evaluating Water-Damaged Electrical Equipment 1 USE OF THIS PUBLICATION This publication provides information on how to evaluate electrical equipment that has been exposed to water through flooding, fire
Introduction Several sections of the National Electrical Code relate to proper overcurrent protection. Safe and reliable application of overcurrent protective devices based on these sections mandate that
Section 9: Power Distribution Equipment Bill Brown, P.E., Square D Engineering Services Introduction Power Distribution Equipment is a term generally used to describe any apparatus used for the generation,
Data Bulletin 2700DB0202R03/12 09/2012 Replaces 2700DB0202R2/09 dated 02/2009 Corner-Grounded Delta (Grounded B Phase) Systems Class 2700 Retain for future use. Introduction Corner-grounded delta systems
SURGE PROTECTIVE DEVICES (SPDs) INTEGRATED UNITS LOW VOLTAGE AC SURGE PROTECTION FOR ELECTRICAL DISTRIBUTION SYSTEMS PART 1 GENERAL 01 02 03 SCOPE The Contractor shall furnish and install the Surge Protective
Evaluating Water-Damaged Electrical Equipment 1 USE OF THIS PUBLICATION This publication provides information on how to evaluate electrical equipment that has been exposed to water through flooding, fire
Prepared by: NIB/EOB PLANNING GUIDE FOR SINGLE CUSTOMER SUBSTATIONS SERVED FROM TRANSMISSION LINES 05503 Department: Electric T&D Section: T&D Engineering and Technical Support Approved by: G.O. Duru (GOD)
Evaluating Water-Damaged Electrical www.nema.org Evaluating Water-Damaged Electrical 1 USE OF THIS PUBLICATION This publication provides information on how to evaluate electrical equipment that has been
Understanding Emergency Power Off (EPO) White Paper #22 Executive Summary Emergency Power Off (EPO) is the capability to power down a piece of electronic equipment or an entire installation from a single
A Comparison of Contemporary Electrical Distribution Equipment Standards San Francisco IEEE Industry Applications Society May 26, 2009 What are Standards? Clearly defined performance characteristics Based
SURGE PROTECTIVE DEVICES (SPDs) EXTERNAL SIDEMOUNT UNITS LOW VOLTAGE AC SURGE PROTECTION FOR ELECTRICAL DISTRIBUTION PART 1 GENERAL 01 02 03 SCOPE The Contractor shall furnish and install the Surge Protective
Appendix C Electrical Grounding Low-Voltage Equipment Grounding The most frequently cited Office of Safety and Health Administration (OSHA) electrical violation is improper occupational grounding of equipment
Product Description Full Voltage Starting Electric Fire Pump Controllers FTA1000 Description Firetrol FTA1000 Full Voltage Fire Pump Controllers are intended for use with electric motor driven fi re pumps
Extend the Life of Existing Switchgear January 2011/1910DB1002 by Hal Theobald, Product Manager Schneider Electric USA, Inc. Make the most of your energy SM Summary Introduction... p 3 Maintenance Requirements...
TM 602.783.1112 baselayer.com 2015 BASELAYER TECHNOLOGY, LLC TM D400E Data Module (60Hz) The EDGE D400E is designed to meet high power density requirements for both the HPC and Web Scale environments while
SECTION 26 09 13 - POWER MONITOR FOR ELECTRICAL, STEAM CONDENSATE, AND WATER PART I - GENERAL 1.1 SUMMARY A. This section describes the requirements for the installation of Power Monitors and associated
SWITCHGEAR SOLUTIONS FOR MISSION CRITICAL APPLICATIONS POWER DISTRIBUTION RACKS IN A MISSION CRITICAL SYSTEM MODULES IN A MISSION CRITICAL SYSTEM UPS Convertor Main Inverter Load Battery BPC UPS & BATTERY
Oil and Coolant Circulating Heating System Model - OCSM Installation & Operation Manual 216280-000 REV 2 Identifying Your System The HOTSTART heating system is designed to heat fluids for use in marine
.3 Switchboards Compartmentalized Switchboards Compartmentalized Feeder Sections Front View Circuit Breakers Product Description Eaton s Pow-R-Line i switchboards are engineered in a new compartmentalized
County of Riverside Building and Safety Department Mike Lara Director Photovoltaic Permitting Guidelines The information provided in this document is general and is intended only as a guide. Each project
ELECTRICAL: TRANSFORMERS BASIS OF DESIGN This section applies to the design and installation of transformers. Design Criteria 13.8-kV equipment shall be 15-kV class. Coordinate with short-circuit studies
Frank Waterer, Fellow Engineer, Square D Engineering Services in conjunction with the Square D Critical Power Competency Center 1. Abstract In order for the electrical power distribution systems within
Department of Community Development Building Division 4800 West 92 nd Avenue Westminster, Colorado 80031 For Information call (303) 658-2075 Fax (303) 706-3922 www.westminsterpermits.com Top Commercial
PDH Course E184 Power Plant Electrical Distribution Systems Gary W Castleberry, PE 2008 PDH Center 2410 Dakota Lakes Drive Herndon, VA 20171-2995 Phone: 703-478-6833 Fax: 703-481-9535 www.pdhcenter.com
Learning Module 13: Panelboards and Switchboards 101 Basic Series What You Will Learn We ll step through each of these topics in detail: Introduction 4 Definitions 4 Similarities Between Panelboards and
12 SOLAR PHOTOVOLTAIC POWER by John Ware IT IS PLANNED for BS 7671:2008 to include a new Section 712 providing additional requirements for safety applicable to solar photovoltaic (pv) power supply systems.
OPTIMIZING POWER SYSTEM PROTECTION FOR MODERN DATA CENTERS Data center power systems are constructed with a premium on reliability at a significant cost. The return on this investment is realized if it
Arc Terminator Active Arc-Resistant Switchgear Increasing safety and productivity by extinguishing internal arcing faults within the switchgear. The Square D Arc Terminator from Schneider Electric offers
Mike Holt s Illustrated Guide to NEC Requirements for Generators and Standby Power Systems Rule 220.87, Articles 445, 700, 701, and 702 Based on the 2011 NEC Extracted from Mike Holt s Illustrated Guides
2011/2008/2005 NATIONAL ELECTRICAL CODE SOLAR PV CODE COMPLIANCE REFERENCE PAGE 1 OF 5 This Reference provides a very comprehensive list of aspects of a solar PV installation that could be reviewed, clarifying
Scopes of Work for Electrical Acceptance Testing Schneider Electric Services: life-cycle solutions for electrical distribution equipment Make the most of your energy SM Scopes of Work for Electrical Acceptance
510 N. Crosslane Rd. Monroe, Georgia 30656 (770) 266-6915 fax (678) 643-1758 Engineers Edge, LLC PDH & Professional Training Copyright, All Rights Reserved Engineers Edge, LLC An Introduction to Interior
Appendix B-2 - Electrical Safety In Design Final Report TECHNOLOGIES THAT REDUCE LIKELIHOOD OF INJURY FROM ELECTRICAL HAZARDS, INCLUDING SHOCK, ARC FLASH AND FIRE The following are technologies that reduce
E2 Series Electric Furnaces Service Manual Table of Contents Electrical Requirements... 10 Codes, Specifications Requirements... 10 Connection Supply Service Wires... 10 Furnace Sequence of Operation...
Installation Requirements Installation and inspection of Grid-connected PV systems July 2011 (no battery storage) This document has been prepared by Energy Safe Victoria to provide guidance for electrical
Siemens STEP 2000 Course Basics of Electrical Products It's easy to get in STEP! Download any course. Hint: Make sure you download all parts for each course and the test answer form. Complete each chapter
CE - BF - C - en - REV.00 2012.4 APPLICATION CE-BF Switchbords up to 40.5 kv are designed for use in public and industrial distribution system up to 40,5KV for the operation and protection of lines, transformers,
12 - ELECTRIC SERVICE HANDBOOK SECTION D METER REQUIREMENTS This chapter gives you information on Central Lincoln s metering requirements. It's divided into three sections: General requirements This section
101 BASICS SERIES LEARNING MODULE 3: FUNDAMENTALS OF ELECTRICAL DISTRIBUTION Cutler-Hammer WELCOME Welcome to Module 3, Fundamentals of Electrical Distribution. If you have successfully completed Module
White Paper SolarEdge Three Phase Inverter System Design and the National Electrical Code June 2015 Revision 1.5 Shalhevet Bar-Asher; SolarEdge Technologies, Inc. Bill Brooks, PE; Brooks Engineering LLC
1. Introduction Proper design and installation of electrical equipment minimizes the chance of electrical faults. Faults occur when the insulation system is compromised and current is allowed to flow through
Defining the Needs of Modern Data Center Power Systems, Low Voltage Circuit Breaker Application by Reza Tajali, P.E. Square D Company ABSTRACT In modern data centers, Uninterruptible Power Supplies (UPS)
543-0032-00, 943-0032-00 User s Manual 1 Comfort Alert Diagnostics Faster Service And Improved Accuracy The Comfort Alert diagnostics module is a breakthrough innovation for troubleshooting heat pump and
KNOXVILLE, TENNESSEE SECTION 16050 PAGE 1 PART 1 - GENERAL 1.01 RELATED DOCUMENTS: SECTION 16050 A. Drawings and general provisions of Contract, including General and Supplementary Conditions and Division-1
1. How do we accomplish grounding of furnaces and / or water heaters on two wire circuits? 250.134 Equipment Fastened in Place or Connected by Permanent Wiring Methods (Fixed) Grounding. Unless grounded
Specification Guide for RVAC Direct Replacement AC Medium Voltage Circuit Breakers Table of Contents 1.0 General Work Scope...3 2.0 Standards...3 3.0 Supplier Qualifications...4 4.0 Circuit Breaker Element
Grounding of Electrical Systems NEW CODE: Grounding and Bonding Presented By Scott Peele PE Grounding of Electrical Systems Outline Defining the Terms Why should I Ground? Types of Grounding Systems Separately
City of Cotati Building Division 201 W. Sierra Ave. Cotati, CA 94931 707 665-3637 Fax 792-4604 INSTALLATION GUIDELINES for SOLAR PHOTOVOLTAIC SYSTEMS 1 Any PV system on a new structures should be included
PD-100 Single Generator Utility- Paralleling Power System Models: Single Breaker 800-4000 Amps 208-600 Volts; 50/60 Hz General Description The single-breaker PD-100 provides an economical method of operating
ARTICLE 110 Requirements for Electrical Installations INTRODUCTION TO ARTICLE 110 REQUIREMENTS FOR ELECTRICAL INSTALLATIONS Article 110 sets the stage for how you ll implement the rest of the NEC. This
SUGGESTED SPECIFICATION for Series 185 Service Entrance Rated Automatic Transfer Switches PART 1 GENERAL 1.01 Scope Optional Standby Power Generator Systems A. Furnish and install automatic transfer switches
Phone System Owner Phone System Engineered by: of Record Drawings: of System Manuals: of Test Reports: System Installer 1. GENERAL INFORMATION Phone Delaware License No: Certificate Holder No. System Supplier
LOW VOLTAGE INSTANT SWITCHBOARDS PART 1 GENERAL 1.01 1.02 1.03 1.04 SCOPE The Contractor shall furnish and install, where indicated, free-standing, deadfront-type low voltage instant switchboard(s) utilizing
9229 Waterford Centre Dr. Bldg C, Suite 110 Austin, Tx 78758 Application Bulletin 103 - NEC Reference Guide for SolarBridge-Enabled AC Module Installers Current Version: 13 AC Modules are a new product
Electrical Contractors and the New Jersey Rehabilitation Code Alan Chech Electrical Seminars 609-890-7072 www.alanchech.com Information is based on the presently adopted electrical subcode NEC 2005. Current