1 User Manual Many thanks for your selection of our products and services, and also for your trust and support to us.
2 TH- -RF X P Thermostat This product has the following features: 1) Heating control 2) Programmable function of 24-hour per day and 7-day per week 3) 2 sets of permanent programs (factory setting program and self-setting program) 4) Large LCD display 5) The temperature adjustable between off and on; 6) Allowable to calibrate the temperature display; 7) Adjustable selection of comfort temperature, economic temperature, and antifreeze temperature; 8) Suitable for the control and energy saving of wall mounted boilers, condensation boilers and individual household mearsuring heating system; 9) It can realize the function of one receiver controlling many sub-devices and many rooms at the same time; 10) Display adjustable between and F. 11)Only need 2 size AA 1.5V batteries for the power supply;. 12)Three transmission modes for selection, i.e. wired, wireless or multi-channel transmission. 13)Fast and Simple installation. Applicable Standards: EN and its revisions EN EN Compliant with the following EU directives: EU B.T.73/23/EEC Directive EU E.M.C.89/336/EEC Directive and 93/68/EEC Revision
3 Display screen symbols: Fig.1 Present ambient temperature Comfort temperature Economic temperature Antifreeze temperature Present time 7 days display in a week, and the present day display is in the square frame Program conditions Runnig Symbol of the equipment COPY ADJUST Battery conditions Celsius degree or Fahrenheit degree Automatic operation mode + Customer program mode Manual operation mode Antifreeze mode Program setting mode setting mode Date/Time setting mode
4 Operation Key: Menu key/ Power ksy Set key Confirmation key Increasing key Decreasing key Alarm Display: 00.0 Flash: Actual room temperature lower than Flash: Actual room temperature higher than 45 E0.1: probe(ntc) disconnected Product Specifications: Power: two LR6 1.5V alkaline batteries Range of temperature adjustment: 5 35 /39 95 Range of temperature display: C/ test frequency: Every minute Display accuracy: 0.1 /1 Probe sensor: NTC(100K) 1% Protection level: IP20 Output: Switch relay Contact capacity: 8A/250V (WW model); 16A/250V (RF model); 5 A/250V(MRF model) Insulating condition: Normal environment Working environment temperature: /0 122 Running program: Set per 1 week as a cycle Software level: A Minimum allowable time for increase / decrease in program setting: 1 hour Frequency: 433 MHz (RF/MRF) Wireless transmission distance: Indoor 16 / 50 m; outdoor 200m (RF/MRF) Size(mm): 77H*121W*21D Installation: Wall mounted or on battery seat Scope of Control Applications: 1. Control of wall-mounted boiler 2. Control of Thermal Actuator or electromagnetic valve 3. Control of water pump; 4. Ventilation control Run Mode
5 1. Factory Preset Mode: In this case, the icon displayed on working state column is : Factory preset program: Monday to Friday: 00 : : 00 Economic temperature 06 : :00 Comfortable temperature 08 : : 00 Antifreeze temperature 18 : : 00 Comfortable temperature 22 : : 00 Economic temperature Saturday and Sunday: 00 : : 00 Economic temperature 06 : : 00 Comfortable temperature 22 : : 00 Economic temperature Display of Energy Consumption The double ring on the lower right represents energy consumption that is controlled by program in each time section. "Comfortable temperature", economic temperature antifreeze temperature are set in the temperature setting. and the 2. User Defined Mode In event of user defined program, the icon displayed on working state column will be and. In the user defined program, the temperature for each time section is set by the user. 3. Manual Mode: In this case, the icon displayed on working state column is. The thermostat controls the temperature at a constant temperature mode, and the default temperature is 20. The temperature can be adjusted with key or key. 4. Antifreeze Mode In this case, the icon displayed on working state column is The thermostat only controls the system to be operated at the state of preventing the ambient temperature from dropping below the antifreeze temperature to have been set in order to make the equipment and pipes free from freezing. This temperature is set in the mode of, and the default valve is Switch between Run Modes Press the key to turn on the thermostat.
6 After turnning on the thermostat, you may press menu key to switch the run modes between: factory preset mode, user defined mode, manual mode and antifreeze mode Setting During setting, the thermostat is temporarily under disconnected state. When finishing the setting, press the key to confirm, if no operation of any key in 60 seconds, the thermostat will turn into run mode and then activate the control switch according to the result of comparison between room temperature and preset temperature. 1. Adjustment Setting A) Press key. The screen will display. B) Press or to set the calibration temperature value. The default value is 0 0 C, the adjustment range is -3 0 C to +3 0 C. C) End of Adjustment Setting: Press key to confirm and exit adjustment setting and resume to the run mode before access 2. Date / Time Setting Set the current date, hour and minute A) When you finish the adjustment setting, don t Press key. but press key again, then it will enter into the Time setting, The screen will display. B) When the frame displaying the present date starts flashing, press key or key to adjust the present weekday, and press key to turn to next setting C) Then the number representing the hour flashes, press key or key to adjust the present hour, and press key to turn to next setting D) Then the number representing the minute flashes, press key or key to adjust the present minute, and press key to turn to next setting E) End of Time Setting: Press key to confirm and exit the time setting and resume to the run mode before access. 3. Setting
7 Set the Comfortable temperature, Economic temperature and Antifreeze temperature The setting range of the comfortable temperature is 5 35, the preliminary value is 20 The setting range of the economic temperature is 5 35, the preliminary value is 18 The setting range of the antifreeze temperature is 5 35, the preliminary value is 5 A) When you finish the Time setting, don t Press key. but press key again, then it will enter into the setting, The screen will display. B) In this case, the temperature icon will be displayed on the left side of temperature digit, while the temperature digit will blink. Press or to set the value of comfortable temperature, and press key to turn to next setting C) In this case, the economic temperature icon will be displayed on the left side of temperature digit, while the temperature digit will blink. Press or to set the value of economic temperature. and press key to turn to next setting. D) In this case, the low temperature icon will be displayed, while the temperature digit will blink. Press or to set the value of Antifreeze temperature, and press key to turn to adjustment setting setting. E) End of Setting: Press key to confirm and exit the time setting and resume to the run mode before access.. 4. User Defined Program Setting Set the control temperature in 7 days and each time section from user-defined program A) Press key for 3 seconds, The screen will display. B) In this case, the icon and number indicating the weekday will blink. Press or to adjust the date. Press key to turn to next setting. C) Then, the icon from 0:00 to 1:00 and the preset temperature state icon (i.e. the icon on the left siude of the temperature digit) will start to blink. Press or to select the temperature state and press key to turn to next one hour setting.
8 D) Repeat the above steps until completing the setting of temperature state in 24 hours. Then, return to date selection. Under the program setting state for each hour, you may long press key to back to last hour setting, or press key for long time to directly enter into date selection again. The temperature for unset part remains to be the default temperature or the preset temperature. E) The date icon will start to blink again, entering into a new setting cycle for some day. F) End of Program Setting: You may press key to confirm and exit the program setting and enter directly into user defined run mode. In the working state display area, the icon and will be displayed. Copy One-day Program After entering a day program you can copy this into another day to save time when creating a weekly program: For example, if you want to copy the program of Monday to Thursday, the methods are as follows: A)Select the program for Monday: On the state, press key or key The outer frame for Monday flashes to select Monday and press key, the icon appears on the screen B. Copy to Thursday: Press key or key to select Thursday, then press key to finish the copying and the icon disappears. C. At this time the Thursday cursor flashes, the setting of this day can be continued with or key as well as the key. D. Copying for other days, please repeat from the Step A to B. 5. Switch from Setting to Run Mode: Under the Adjustment Setting, Time Setting or Setting, just press key to enter into the Run Mode, if no operation of any key in 60 seconds, the thermostat will turn into run mode and then activate the control switch according to the result of comparison between room temperature and preset temperature. Under the Program Setting, press key to enter into the User Defined Mode,. 6. Temporary Change of Both at mode and at and mode,you can temporarily change the temperature at a program period.
9 For example: You have set the program already the comfort temperature is 20 0 C between 8:00~12:00, but you want to lower the temperature to 18 0 C at 10:40 then you set the temperature to 18 0 C. This setting will not exist forever, it will remain until 12:00 when the program period is ended. At the program running mode, set the required temperature directly through key or key, the number representing the temperature will flash, press key to confirm and stop flashing. Without any adjustment in 5 seconds, The number representing the temperature will stop flashing and continuously to display the present room temperature. The thermostat will recover to automatic mode at the following program temperature changes. 7. Code Matching (Only used for RF /MRF model) RF Model: Press the receiver key, so that the receiver indicator will blink. If the transmitter is energized, turn off the transmitter LCD and then hold down and keys simultaneously until the indicator stops blinking. In this case, the code matching is finished. (Note: If no code matching signal is received during 1 minute when the indicator keeps blinking, this indicator will turn dark and the code matching will be stopped. Pressing the key again, the thermostat will again enter into code matching state). MRF Model: Press the receiver key, so that the indicator will blink in one flash and one stop. The thermostat will enter into the 1 st channel code matching state. The code matching operation is same as RF model. After completing the code matching, press the key again to start the 2 nd channel code matching, in which case the indicator will blink in two flashes after one stop. The thermostat then enters into code matching state. After completing the code matching, press the key again to start the 3 rd channel code matching, in which case the indicator will blink in three flashes after one stop. The code matching is then started. Likewise, press the key for the fourth time to start the 4 th channel code matching, in which case the indicator will blink in four flashes and one stop. 8. Fault Display: When the room temperature is lower than 0, the LCD will blink in When the room temperature is higher than 0, the LCD will resume automatically to normal display. When the room temperature is higher than 45, the LCD will blink in When the room temperature is lower than 45.0, the LCD will resume automatically to normal display. Upon disconnection of the temperature sensor, the display will blink in E0.1, in which case you shall check and eliminate the fault. 9. Engineering Setting Hold dwon key for 5 seconds under OFF state, The place where the time is displayed will show the setting number, while the place where the temperature is displayed will show the set parameters. Press or to change the parameter setting, and press key to enter into next setting. You may press key to confirm and exit the setting of engineering parameters. If no operation of any
10 key within 60 seconds, it will save and exit, then return to OFF state. Setting Notes on Adjustable Range Three-Digit where Remarks Number Numbering temperature is displayed(the value to be set will blink ) 00.2 from stop to restart: 0.2 from stop to 00.5 restart or from stop to restart: 0.5 cycles per 01.0 hour from stop to restart: from stop to restart: 1.5 (Default Value) 02.0 from stop to restart: from stop to restart: from stop to restart: from stop to restart: from stop to restart: On/Off per hour On/Off per hour On/Off per hour On/Off per hour On/Off per hour On/Off per hour On/Off per hour On/Off per hour On/Off per hour On/Off per hour On/Off per hour On/Off per hour 112 Set the state Disconnected (Default)) No display for the 0 after turning off the Connected No display for the 1 screen Energy-saving State No display for the 2
11 Switch between and Display in (Default) Display in No display for the No display for the 0 1 Keypad Keypad not activated No display for the 0 (Default) Lock SET key No display for the 1 Lock all keys No display for the 2 Highest temperature of heating (Adjustable by 0.1 ), Default Value 35 Display of setting temperature Selection of engineering Parameters set in factory No display for the 0 parameters Parameters set by No display for the 1 customer (Default) Fault Repair Problem Possible Cause How to Repair The thermostat does not work 1. Not connected to power 1.Battery seat: Check if the battery supply. contact is in good condition. The heating system cannot be 2. If the preset temperature is 2. Adjust the preset temperature started. higher than the temperature higher. currently on display. The mode switch doe not work. 3. Check if the keypad is 3.Enter engineering setting and locked. 4. Check if the unit is stopped. change the keypad lock mode of number 4. 4.Start the unit. The Up, Down or OK key does 5. Check if the keypad is 5.Enter engineering setting and not work. locked. 6. Check if the unit is stopped. change the keypad lock mode of number 4. 6.Start the unit. The room temperature 7. If the equipment is under 7. If the equipment is running, displayed on the screen is not run state. indicating that the temperature is in the compliant with the actual 8. If set to temperature process of heating / cooling. The two temperature. calibration. temperatures will be equal when the equipment finishs operation. 8. Change the Adjustment Setting
12 Cautions on Installation and Use: 1. To prevent the thermostat display from a high fluctuation, special treatment has been made to the program. Therefore, it is normal that the thermostat cannot immediately display the sudden change of temperature. 2. The thermostat installed in standard 86 box shall be placed 1.5m above the ground. 3. For the thermostat installed in standard 86 box or wireless thermostat with battery seat, take care not to install it to the wall corner, door / window side or behind the door or in such unheated area as exterior wall. Avoid hot / cold air duct, radiator, flue or thermal pipe. 4. If the wireless thermostat with battery seat is placed at a position where the air ventilation is poor, the temperature displayed on the thermostat might be inconsistent to the indoor average temperature. 5. Only the professional technicians are permitted to open the transmitting and receiving box of the thermostat for installation. When installing the power supply, make sure that the power cable is well insulated. 6. To install the receiving box, please install the base plate firstly and then connect the power and signal wire correctly before installing the upper cover and fix it. The thermostat is unrepairable product. The user shall not open the internal circuit board. 7. Before installing the thermostat, make sure that the system is disconnected. The maximum voltage of the system shall meet the requirements specified in the Instruction Manual (Max. AC Voltage: 250V). Wring Illustration 1 Wiring Terminals Wiring Terminal N L Remarks AC Neutral AC Live 1 NO (Normally-Open point) 2 COM (Public terminal of relay) 3 NC (Normally-Closed point) 2 Symbol Illustration B:Wall Mounted Gas Boiler U:Water Pump, Thermal Actuator or electromagnetic valve 3 Control Illustration: Fig.2: Dimensional Diagram Length, Width, Thickness, Installing Size
13 Fig.3: Control of Wall-mounted Boiler for WW model Fig.4: Control of Water Pump, Thermal Actuator or electromagnetic valve for WW model Fig.5: Control of Wall-mounted Boiler for RF mode Fig.6: Control of Water Pump, Thermal Actuator or electromagnetic valve for RF model Fig.7: Control of Under Floor Heating with Wireless 4-channel for MRF model
COMPUTHERM Q7 Programmable, digital room thermostat Operating Instructions GENERAL DESCRIPTION OF THE THERMOSTAT The COMPUTHERM Q7 type switched-mode room thermostat is suitable to regulate the overwhelming
3 072 RDJ10RF RCR10/433 Wireless room temperature controller with 24-hour time switch and LCD Programmable, for heating systems RDJ10RF/SET Operating modes: Automatic, Comfort, Energy Saving, and Frost
8400 Series Thermostats Safety & Installation Instructions READ AND SAVE THESE INSTRUCTIONS 61000652D 8400 Tstat Install.indd 1 Table of contents Installation Installation location recommendations... 3
INSTALLATION MANUAL EKRTR EKRTETS 1 2 1 2 3 60 87 170 161 ±1.5 m >0.2 m 3 5 4 34 125 4 5 28 50 EKRTR EKRTETS Contents Read this manual attentively before starting up the unit. Do not throw it away. Keep
User Manual THR840DUK Digital Thermostat 50051982-001 Rev. A WARNING: This product must be correctly installed and configured to work properly (see pages 12-24). If you are not experienced in wiring electrical
MAKING MODERN LIVING POSSIBLE living connect Installation and User Guide Danfoss Heating Solutions 2 living connect Thank you for buying a Danfoss product Danfoss Heating Solutions 3 Contents 1. System
Contents: Introduction UFH-ZONE-R UFH-EXTRAZONE -R Connection of a thermostat (UFH-THERM-R) o Joining of a thermostat with UFH-ZONE-R or UFH-EXTRAZONE-R Connection of a digital thermostat (UFH-THERM -RD)
EK908FHL - Thermostat for floor heating EK908FHL is a programmable thermostat designed for floor warming application or helping to limit floor temperature. This thermostat can be used for hot water radiant
W Ith I ntelligent Control S Ave E lectricity INTELLIGENT HOT WATER CYLINDER CONTROL INSTRUCTION MANUAL Thank you for purchasing our controller Before operating and installation carefully read all instructions.
2 242 Room temperature controller for in-wall mounting with one weekly operating mode including individual 24-hour modes and three 24-hour modes, cooling function REV26 Mains-independent room temperature
DUAL SENSING DIGITAL THERMOSTAT PRODUCT INSTRUCTIONS www.rehau.com Construction Automotive Industry SCOPE This guide gives instruction regarding REHAU Programmable Digital Thermostat installation and operation.
MAKING MORN LIVING POSSIBLE Danfoss heating living connect Installation and User Guide Contents 1.0 System overview... 3 2.0 Overview of display and control buttons... 3 3.0 Installation - step by step...
3 067 RDF310.2, RDF310.21 RDF410.21 Flush-mounted Room Temperature Controllers with LCD for 2-pipe fan coil units for use with compressors in DX type equipment RDF310 RDF410 Output for on / off valve actuator
Alpha Climatic Programmable Modulating Boiler Energy Manager Part No 3.022144 (Hard Wired) Part No 3.022143 (Radio Frequency) Installation and User Instructions 1. Description The Alpha Climatic energy
QUICK INSTALLATION GUIDE Read Installer Notes before removing cover from Thermostat. 1F85RF-275 Wireless Remote Kit INSTALLER NOTES IMPORTANT Do not apply power to the thermostat or wireless sensor until
SERVICE MANUAL FOR 6535 SERIES TWO TON HIGH EFFICIENCY PACKAGED HEAT PUMPS TABLE OF CONTENTS 1. Warnings...2 2. Accessibility Of Appliance...3 3. Unit Dimensions And Specifications...3 4. Unit Specifications
Installation and User Guide TYXIA Wireless receiver TYXIA RF 642-1 channel DELTA DORE Bonnemain - 35270 COMBOURG - France E-mail : email@example.com Unit compliant with the requirements of directives:
OPERATING INSTRUCTIONS LABORATORY & PHARMACEUTICAL UNIT 100/270/300/500/660/700/900/1400 INDEX.....PAGE Before using the appliance..................................................... 3 Safeguarding the
Model: 616-146v2 Quick Setup Guide DC: 071015 Atomic Projection Alarm with Indoor and Outdoor Temperature Snooze/Backlight BUTTONS Time, Alarm with Snooze, & Calendar Projection Arm Rotates 180 Indoor/Outdoor
Installation Guide TH4210D Programmable Thermostat Product Application This thermostat provides electronic control of 24 VAC heat pump systems with auxiliary heat (2 heat/1 cool). Power Type Battery power
Specifications are subject to change without notice according to Carrier Policy of continuous development. 03501019 Rev. (0) -2009 Thank you for selecting Carrier Air Conditioner You can be justifiably
230 V~ 369813a 1 07.02.15 The 230 V~ room thermostat adds temperature control to the LutronR hotel guestroom control solution. Controls 2-pipe, 4-pipe, and 3 fan-speed fan coil units. Compatible with LutronR
Installation Guide TH3210D Non-programmable Digital Thermostat Product Application This thermostat provides electronic control of 24 VAC heat pump systems with auxiliary heat (2 heat/1 cool). Power Type
CM702 PROGRAMMABLE THERMOSTAT FEATURES Attractive slim, modern styling makes it ideal for location in any type of home. 24-hour heating program. Up to 4 daily independent time and temperature level changes
IN-OUT Thermometer with Cable Free Sensor and Clock MODEL: RAR232 USER'S MANUAL INTRODUCTION Congratulations on your purchase of the RAR232 In-Out Thermometer with 433MHz cable free sensor and calendar
3 346 Temperature Controller (Heat Pumps) RWD34 RWD44 For comfort control in HVAC & R systems Standalone electronic controller Programmable controller with preconfigured applications Two universal inputs
TP5000 Si Range Electronic 5/2 day programmable room thermostat Mains, Battery and RF versions Certification Mark GB Installation and GB Index Index Installation Instructions 3-14 Product Specification
SAT-1 Thermostat COOL FAN DRY HEAT AUTO SLEEP SWING AUTO ZONE SUN MON TUE WED THU FRI SAT HEATER ON OFF ERR UNIT USER'S OPERATING INSTRUCTIONS CONTENTS Introduction 3 Features Summary 3 Display 4 Operation
HOME APPLIANCES MAGICOOL HOME APPLIANCES HOME APPLIANCES Registered trademark/tm Trademark of Whirlpool, U.S.A. 2009 Whirlpool of India Ltd. All rights reserved. Due to advancement of technology and constant
RADIO CONTROLLED DIGITAL CLOCK MODELS 88905 / 88906 QUICK SETUP GUIDE IMPORTANT! INSTALL BATTERIES IN THE OUTDOOR TRANSMITTER BEFORE INSTALLING BATTERIES IN THE RADIO-CONTROLLED CLOCK. ALKALINE BATTERIES
LX Series Digital Thermostat Digital Thermostat Model S1-THSU21P1 S1-THSU32P7 S1-THSU32HP7 RESIDENTIAL BACKLIT DISPLAY Owner s Manual and Installation Instructions CAUTION Follow the Installation Instructions
User Guide Temperature and Humidity Datalogger Model 42280 Introduction Congratulations on your purchase of the Extech 42280 Thermometer and Relative Humidity Datalogger. The 42280 is a wall-mount, tripod
FITTING AND OPERATING INSTRUCTIONS FOR DIGISTAT OPTIMISER PROGRAMMABLE 7 DAY ROOM THERMOSTAT SYSTEM General information is given in the users instruction leaflet despatched with the appliance and/or on
A Quick Guide to Using Your NIBE F470 Exhaust Air Heat Pump. How do exhaust air heat pumps work? An exhaust air heat pump uses the heat that s in the building s ventilation air to heat up the accommodation.
Programmable indoor transmitter of temperature T0118 Programmable indoor transmitter of atmospheric pressure T2118 Programmable indoor transmitter of temperature, relative humidity and other derived humidity
ENGLISH INSTRUCTION & INSTALLATION MANUAL DUCTLESS MINI SPLIT AIR CONDITIONING SYSTEMS Céliera Corporation. All rights reserved. Unauthorized duplication, reproduction prohibited. CONTENTS SAFETY PRECAUTIONS...
evohome Wireless Radiator Zoning Kit Installation & User Guide Getting the most from your evohome system Installation & User Guide 1 Getting the most from your evohome system Thanks for choosing an evohome
Wireless 7 Day Programmable Room Thermostat Cat. No. TRT037 Transmitter Receiver Operating & Installation Instructions What is a programmable room thermostat? an explanation for householders A programmable
WIRELESS 433 MHz WEATHER STATION Instruction Manual INTRODUCTION: Congratulations on purchasing this Weather Station with wireless 433MHz transmission of outdoor temperature and humidity and display of
User Manual of WT 493 Introduction Congratulations on your purchase of this smart unit. This unit can be used as a radio to catch the latest news and enjoy the beautiful music; it can also be used as an
SERVICE INSTRUCTION SPLIT TYPE ROOM AIR CONDITIONER WALL MOUNTEDtype INVERTER Models Indoor unit Outdoor unit ASYG07LECA ASYG09LECA ASYG12LECA ASYG14LECA AOYG07LEC AOYG09LEC AOYG12LEC AOYG14LEC R410A CONTENTS
BRAVA small size, big performance www.sime.it BRAVA: small size, big performance Brava Slim and Brava One are part of a new generation wall hung boilers, particularly compact and functional. They represent
DT0 PROGRAMMER DIGITAL TWIN CHANNEL PROGRAMMER FOR GREENSTAR i and GREENSTAR Si MODELS off timed once on heating CHW ON AM OFF MON TUE WED THU FRI SAT SUN CLOCK? PROG? DATE? HDAY? off timed once on hot
T5000 T000 LCD Digital Fan Coil Thermostat T000 LCD Digital Fan Coil Thermostat T000 LCD Digital Fan Coil Thermostats are designed to control heating, cooling, or year round air conditioning unit in Commercial,
New GSM Alarm System User s Manual Profile For a better understanding of this product, please read this user manual thoroughly before using it. Chapter 1. Features Chapter 2. Alarm Host Introduction Chapter
8 716 473 216-00.3O Gas boiler WBN 6000-30-H-E-N/L-S2400 Operating instructions for the end customer en 2 Contents Contents 1 Key to symbols and safety instructions................... 2 1.1 Key to symbols..................................
LOAD BANK PART NUMBER 2004297/2004298 OPERATIONS AND MAINTENANCE MANUAL Prepared by: 5455 N River RD W Geneva, OH 44041 Phone: 1-800-969-8527 TechSupport@get-psi.com HDT 1 TM-2004297/2004298 TABLE OF CONTENTS
AQUATROL Zone Synchronizing Programmable Relay Boiler Controls AQ25A USER OPERATION AND MAINTENANCE WARNING Risk of electrical shock. Can cause severe injury, property damage or death. Only trained, experienced,
KRONOS GA11 WEEKLY-PROGRAMMING DIGITAL CHRONOTHERMOSTAT FOR THE REMOTE CONTROL OF HOT AIR GENERATORS THROUGH BRAHMA INTERFACE BOARD APPLICATION The digital chronothermostat Brahma Kronos series integrates
just a test. Air conditioning, electrical testing 01-253 Wire and component test using VAG1598 A test box Special tools and equipment VAG 1598 A test box and VAG 1598/11 adapter cable and VAG 1598/12 VAG1526
R22. K Control. Indoor Unit. Nomenclature. PL H 3 G K H B Compatibility Unit style Heat Pump Horse Power Control Boost Heaters R22. K Control. Outdoor Unit. Nomenclature. PU H 3 Y K A Compatibility Outdoor
1F89-211 Non-programmable Electronic Digital Heat Pump Thermostat INSTALLATION AND OPERATION INSTRUCTIONS Operator: Save these instructions for future use! FAILURE TO READ AND FOLLOW ALL INSTRUCTIONS CAREFULLY
Installation Guide TH3110D Non-programmable Digital Thermostat Product Application This thermostat provides electronic control of 24 VAC single-stage heating and cooling systems, or 750 mv heating systems.
VAV Office Tenant Fitout Specification SECTION 23 09 00 AUTOMATIC TEMPERATURE CONTROLS PART 1 - GENERAL 1.1 AUTOMATIC TEMPERATURE CONTROLS A. Provide an extension to an existing DDC control system. The
SERVICE INSTRUCTION SPLIT TYPE ROOM AIR CONDITIONER Universal Floor / Ceiling Duct / Cassette Wall Mounted / Floor type INVERTER MULTI R410A Models Indoor unit Outdoor unit AB*14LBAJ AB*18LBAJ AB*F14LAT
OWNERS ' MANUAL REMOTE CONTROLLER R/E-0 Warning. Be sure there are no barriers between the remote controller and the receiver of indoor unit otherwise the air conditioner will not work.. Keep the Remote
MODEL WS 585 INTERNET WEATHER STATION INSTRUCTION MANUAL (Figure 1) QUICK SETUP Step 1 Connect your computer on-line to the internet. Step 2 Insert the wireless USB into your computer (lift up the antenna
RANCO INSTALLATION INSTRUCTIONS ETC TWO STAGE ELECTRONIC TEMPERATURE CONTROL Relay Electrical Ratings PRODUCT DESCRIPTION The Ranco ETC is a microprocessor-based family of electronic temperature controls,
1.Normal Mode 2.4 Press [SELECT] button to set year in following screen, Then press [UP] or [DOWN] to set year. 2. Clock and Date Setting 2.1 Press Both [SET] and [SELECT] for 3 seconds during Normal Mode
Installation and service instructions for contractors VIESMANN Vitotrol 100 Type UTDB-RF2 Room temperature controller with digital time switch and wireless receiver For applicability, see the last page
308-805 FAQ OUTDOOR TEMPERATURE Q: What sensors are compatible with my station? A: The W186-E will work with this station. Q: Outdoor temperature shows dashes. A: Dashes means the connection is lost between
FAQs Conserve package Gateway... 2 Range Extender... 3 Smart Plug... 3 Thermostat... 4 Website... 7 App and Mobile Devices... 7 FAQs Gateway Can I have someone install my system for me? If you are concerned
Devices Clima-phone - TECHNICAL CHARACTERISTICS 01913 - Electronic GSM timer-thermostat Supply voltage: 120-230 V~, 50-60 Hz. 2 AAA NiMH 1,2 V rechargeable batteries (supplied) in order to operate during
SERVICE INSTRUCTION SPLIT TYPE ROOM AIR CONDITIONER WALL MOUNTEDtype INVERTER Models Indoor unit Outdoor unit ASU 9RLF ASURLF ASU5RLS AOU 9RLFW AOURLFW AOU5RLS R40A CONTENTS. DESCRIPTION OF EACH CONTROL